1 Products Solutions Services High Level Alarms Industrial Safety
2 Erwin Post Product Manager Level Tankgauging Praxis mit Gamma. Only a safe plant is economical Endress+Hauser B.V. Nikkelstraat AJ Naarden The Netherlands Phone: Mobile: Fax:
3 Topics Overfill prevention Bunchfield lessons learned PGS29 translation Tank types and level detection State of the art SIL level technology Only a safe plant is economical
4 The Buncefield facility
5 Buncefield overspill incident
6 Even visible from space
7 Buncefield days after.
8 And no casualties (thank God it s was Sunday)
9 The Buncefield incident Fuel depot in Buncefield near London Sunday morning, December 11th, 2005 Failure of level measurement, no change in level indication High level alarm in override. Overspill of 300m 3 of gasoline. Heavy explosion 40 people injured No fatal casualties Depot and surroundings have been heavily damaged Took several days before the fire was under control Environmental emissions and damage.
10 Products Solutions Services High Level Alarms
11 Lessons learned Recommendation 3: Operators of Buncefield-type sites should protect against loss of containment of petrol and other highly flammable liquids by fitting a high integrity, automatic operating overfill prevention system (or a number of such systems, as appropriate) that is physically and electrically separate and independent from the tank gauging system.
12 Lessons learned Recommendation 5: All elements of an overfill prevention system should be proof tested in accordance with the validated arrangements and procedures sufficiently frequent to ensure the specified safety integrity level is maintained in practice in accordance with the requirements of Part 1 of BS EN
13 Post Buncefield effect Oops, can that happen to us too? Are the risk assessments OK? Are the HAZOP studies done? Did we cover all scenarios? Authorities start to interfere Regulations are improved or re-written (PGS 29) Proof testing becomes mandatory! What about SIL?
14 SIL Legal status Legal framework Seveso Directive [ Seveso II - Directive 96/84/EC] Workers protection regulations (social) Environmental regulations Associated permits or license system, local, regional or even national Regulations require state of the art equipment for safety assurance State of the art is defined in standards. i.e. for functional safety EN/IEC [EN August 2002] (generic standard) EN/IEC [EN August 2004] (process industry standard)
15 PGS29:2008, 84 pages.
16 PGS29:2008, 84 pages Hoogniveau-alarmering en overvulbeveiliging 87. Tanks moeten zijn uitgevoerd met: a. een hoogniveau-alarmering die ter plaatse en / of in de controlekamer, alarm geeft, voordat het hoogst toelaatbare vloeistofniveau in de tank wordt bereikt, zodat maatregelen genomen kunnen worden om de pompcapaciteit te verminderen of het verpompen te stoppen, en; b. een fysiek onafhankelijke instrumentele overvulbeveiliging die bij het bereiken van het hoogst toelaatbare vloeistofniveau in de tank de toevoer naar de tank doet stoppen.
17 PGS29:2008, 84 pages. De betrouwbaarheid van de instrumentatie en beveiligingen moet in relatie staan tot het veiligheidsrisico. Er dient een methodiek gehanteerd te worden die de samenhang tussen de risico s, vastgesteld middels veiligheidsstudies, en (de betrouwbaarheid van de) maatregelen (instrumentatie en beveiligingen) aantoont en documenteert. Voorbeelden van methodieken: SIL-systematiek waarin, afhankelijk van de gewenste risicoreductie, eisen worden gesteld aan de keuze en onderhoudsfrequentie/type van de benodigde regelingen en beveiligingen; (NEN-EN 61511/61508) safety-layerssystematiek, bijv. LOPA; bedrijfsbeleid waarmee het risico gekoppeld wordt aan de maatregel; b.v. bij een scenario met risicowaardering X moeten minimaal twee onafhankelijke LOD s (Lines Of Defense) worden ingezet om het risico te beheersen.
18 PGS29:2008, 84 pages. Toelichting: Indien bij scheepslossingen de tweede beveiliging technisch niet mogelijk is, kan in overleg met het bevoegd gezag hiervan afgezien worden of een alternatieve oplossing worden overeengekomen met een aanvaardbaar beschermingsniveau. Onder fysiek onafhankelijk wordt verstaan: Los van niveaumeting Apart stuursignaal Onder overvulbeveiliging wordt verstaan: Elk systeem dat de toevoer tot de tank automatisch doet stoppen zonder tussenkomst van een operator.
19 Simple instrument safety rules still apply A good High Level Alarm typically: is based on a different physical phenomenon (avoid systematic failures) is Fail to Safe classified for SIL services is active (needs power to operate) is proven technology has all appropriate certificates (IEC 61508/61511) is provided with internal diagnostics is preferably provided with a separate failure alarm can be checked easily. Proof testing has a long, predictable lifetime can be repaired immediately without process interference
20 Typical bulk liquid storage tanks Possibilities are determined by tank constructions Fig. a. storage tank with conical roof Fig. b. storage tank with external floating roof
21 Fixed Roof SAFE HHLA Solutions Tuning Fork Measurement of aggregation phase by density, Gas versus Liquid Radar and Guided Wave Radar. Measurement of true level using di-electric impedance jump at phase change
22 Liquid Bulk Storage, Independent High Level Alarms State of the art. Liquiphant is always the first solution. SIL2/3 Compliant - IEC61508/IEC61511 Loop approach! Suitable for all Cone Roof Tanks using existing tank fittings. Very simple and cost effective proof testing by push button only!
23 Liquiphant summary Liquiphant is an active in-situ density measurement rather than a switch! Density change of liquids is huge and the absolute density of liquid phase is irrelevant thus providing a robust physical deviation. Easy test methodology using push button activated test generator Simplicity of the concept offers extremely low failure rates. Availability joined to the highest safety level! Proven as robust. Reliable lifetime is typically long!
25 Self-Monitoring Safe alarm function Immersion depth fa -15% switch point approx. 850 Hz fa oscillation frequency in air approx. 1 khz 25 mm 0 A L A R M A L A R M fa -15% fa fa + 6,5% 1500 f [Hz] sensor alarm 0,4 s delayed normal operation corrosion alarm 60 s delayed sensor Alarm 0,4 s delayed
26 Recurring Proof Test of Overspill Protections switch relay test generator switch switching electronic pulse switch receiver fault relay
27 Push button proof test coverage (1) λ du 40 FIT Drive current Resonance frequency Only the resonance controller is not covered Frequency λ du controller: 10 FIT [FIT = h )
28 Push button proof test coverage (2) Failure rate FTL5* and 7* series connected to FTL325P 2,100E-03 1,750E-03 1,400E-03 PFD 1,050E-03 7,000E-04 PTC 75% 3,500E-04 0,000E yr
29 Overview of measures for SIS according to IEC61511 Component Level Systematic Failures & Random Failures & Certified IEC Prove in application or Proven-in use [supplier] or Prior-use demonstration [user] PFD avg Certified IEC61508 Failure Tolerance Redundancy 1oo1 1oo2 2oo2 2oo3
30 Fixed Roof SAFE HHLA Solutions Tuning Fork Measurement of aggregation phase by density, Gas versus Liquid Radar and Guided Wave Radar Measurement of true level using di-electric impedance jump at phase change
31 Liquid Bulk Storage - Fixed Roof Tanks Guided radar Suitable for all Cone Roof Tanks using existing tank fittings on tank. Continuous level Measurement. Flexible set points via 4-20mA Signal Deviation alarms possible (comparing with ATG) Provided with internal redundancy using End Of Probe algorithm SIL 2/3 Compliant - IEC61508 Safety parameters are state of the art. Proof testing by generating test signals.
32 Developed according IEC61508 Continuous automatic internal check in the device Logic program run control Check Reference pulse HF Quartz synchronization Measuring cycle time Supply voltage Temperature Check sum RAM Cable breakage Continuous self-monitoring to check the correct functionality of the device More than 80 diagnostic measures and techniques permanently running in the background
33 Proof test from control room Proof procedure via manual started self check (proof test) Check Send Developed acc. to IEC61508, also the data communication between Device-DTM and device is secured (send check).
34 HistoROM Example HistoROM functionality Electronic change during night shift The HistoROM is fixed in the housing (can not be lost or forgotten )
35 Floating Roof Safe HHLA Solutions (Tuning fork Stilling well mounted is always preferred) Free Field Radar, Time of Flight Measurement of roof level using dielectric reflection at phase change Capacitance type contact switching Measurement of dielectric impedance change by roof contact
36 Floating Roof Tanks Free Space Radar Free Space Radar Suitable for all tank types (Excluding Spheres). Continuous level Measurement. Flexible set points via 2-wire 4-20mA Signal SIL2/3 Compliant - IEC61508 Proof testing by test generator
37 Floating Roof Tanks Free Space Radar Proof Testing external External Swivel plate for functional proof testing
38 Floating Roof Tanks Radar Proof Testing integral design Complete with checker mechanism to enable safe alarm checks can be performed and ensuring Zone segregation.
39 Developed according IEC61508 Continuous automatic internal check in the device Logic program run control Check Reference pulse HF Quartz synchronization Measuring cycle time Supply voltage Temperature Check sum RAM Cable breakage Continuous self-monitoring to check the correct functionality of the device More than 80 diagnostic measures and techniques permanently running in the background
40 Floating Roof Safe HHLA Solutions (Tuning fork Stilling well mounted is always preferred) Free Field Radar, Time of Flight Measurement of roof level using dielectric reflection at phase change Capacitance type contact switching Measurement of dielectric impedance change by roof contact
41 Floating Roof Tanks (alternatively) Capacitance Capacitance Probe Suitable for all Cone Roof Tanks using existing tank fittings on tank. Suitable for Floating Decks. Flexible set points via 4-20mA Signal, or via switch point. SIL2 Compliant - IEC61508/IEC61511 Snow tolerant solution Hard to test (mechanical contact required)
42 Secure Switch Settings using Contact Plate
43 Floating roof failure scenarios Snow cover Damaged deck Lost deck Free space Radar May lead to lost echo Fails Safe Availability increased using new Advanced May lead to lost and deflected echo depending on deck position Fails Safe May lead to some switch point deviation (up to 100 mm) No failure Dynamics design Capacitance type Top of snow detected as raised level No Failure Switch level may raise depending on deck position May fail when deck gets over flooded May lead to severe switch point deviation Fails dangerous May become safe when weight is modified
44 Summary Overfill prevention Bunchfield lessons learned PGS29 translation Tank types and level detection State of the art SIL level technology Only a safe plant is economical
45 Products Solutions Services Thank you very much for your attention
Technical Information TI 64F/4/ae Liquid Level Limit Switch liquiphant T FTL 0 Level limit switch for liquids Applications The Liquiphant T FTL 0 is a level limit switch for virtually any kind of fluid
Minerva S200PLUS Ex ia Intrinsically Safe & Ex d Flameproof Solar Blind Flame Detectors Triple Waveband Infra-Red Flame Detection Key Features Unrivalled black body rejection over a wide range of source
& Inventory Management Solutions Automation solutions for oil & gas, defense and aviation applications FuelsManager, Varec s industry-leading software is available in four editions: Standard, Professional,
Selecting Sensors for Safety Instrumented Systems per IEC 61511 (ISA 84.00.01 2004) Dale Perry Worldwide Pressure Marketing Manager Emerson Process Management Rosemount Division Chanhassen, MN 55317 USA
D46 Isolating Barriers for our sensors A5S1 in Ex-areas Series KEY FEATURES ATEX / IECEx certified, also approval for UL / CSA and EAC (Russia, Kazakhstan and Belarus Customs Union) Protection grade Ex
PROCESS AUTOMATION SAFETY MANUAL SIL Switch Amplifier KCD2-SR-(Ex)*(.LB)(.SP), HiC282* ISO9001 2 With regard to the supply of products, the current issue of the following document is applicable: The General
September 2005 DVC6000 SIS Training Course 1 Basic Fundamentals Of Safety Instrumented Systems Overview Definitions of basic terms Basics of safety and layers of protection Basics of Safety Instrumented
Why SIL3? Josse Brys TUV Engineer firstname.lastname@example.org Agenda Functional Safety Good planning if specifications are not right? What is the difference between a normal safety and SIL3 loop? How do systems achieve
Instruction Manual Service Program ULTRA-PROG-IR Parameterizing Software for Ultrasonic Sensors with Infrared Interface Contents 1 Installation of the Software ULTRA-PROG-IR... 4 1.1 System Requirements...
425 CONTROLS DATA MANAGEMENT PROCESS AUTOMATION EUROCUBE General purpose single phase thyristors and solid state relays Product data abc 425 EUROCUBE A complete range of low cost solid state relays and
CLASSIFICATION NOTES Type Approval, Installation and Testing of Water Level Detectors on Bulk Carriers and Single Hold Cargo Ships other than Bulk Carriers General Information This edition of the classification
PROCESS AUTOMATION SAFETY MANUAL SIL RELAY MODULE KFD0-RSH-1.4S.PS2 ISO9001 3 With regard to the supply of products, the current issue of the following document is applicable: The General Terms of Delivery
0102 Model Number Features Comfort series 5 mm flush Usable up to SIL 2 acc. to IEC 61508 Accessories BF 18 Mounting flange, 18 mm EXG-18 Quick mounting bracket with dead stop Technical Data specifications
Meeting Spill Prevention Regulations using RF Admittance and Ultrasonic Level Measurement Technologies Martin Bahner Marketing Manager Drexelbrook Engineering Co. 205 Keith Valley Rd. Horsham, PA 19044
VIBROCONTROL 4000 Sensitive Machine Monitoring Reliable Machine Protection with VIBROCONTROL 4000 Brüel & Kjaer Vibro has for many years been one of the leading manufacturers of machine protection systems.
0102 Model Number Features 3.5 mm slot width Usable up to SIL 3 acc. to IEC 61508 Extended temperature range Application Danger! In safety-related applications the sensor must be operated with a qualified
Expert Report Dipl.-Ing. Jochen Loos Dipl.-Wirtschaftsing. (FH), Dipl.-Informationswirt (FH) Markus Tuffner, Bosch Industriekessel GmbH History of the development of water level control in steam- and hot
GAM900/GAM900S Acceleration precisely measured and safely monitored The benefits at a glance: Less sensors more safety Minimum size, maximum performance Extremely reliable and robust IP 67 protection thanks
Safety Requirements Specification Comments on this report are gratefully received by Johan Hedberg at SP Swedish National Testing and Research Institute mailto:email@example.com -1- Summary Safety Requirement
CELO5 User & Installation Manual www.audac.eu 2 Introduction 5 High-end Slim Ceiling Speaker The CELO5 is the 5 version of AUDAC s CELO High-end Slim ceiling speaker series with an RMS power of 50 Watt
THE WORLD'S FIRST WIRELESS GUIDED WAVE RADAR Level measurements where you need them, however remote "Research 80% indicates that nearly of production downtime is preventable..." Ian Nimmo, Founder of the
Labkotec SET Labkotec separator alarm system protecting our environment Designed to comply EN 858-1&2 and PPG3 norms Warns of excessive levels of oil, sludge & liquids Prevents pollution incidents Fail-safe
Hardware safety integrity Comments on this report are gratefully received by Johan Hedberg at SP Swedish National Testing and Research Institute mailto:firstname.lastname@example.org Quoting of this report is allowed
Automatic Fire Fighting Monitors Fire Protection Solutions Automatic Fire Fighting Monitors Foreword Automatic monitors are devices used to deliver large amounts of water or water/foam solution to remote
Machineontwerp volgens IEC 62061 Insert Photo Here Safety solution Architect Safety Local Business Leader Benelux. Stephen Podevyn Safety Solution Seminar Agenda deel 1 1. Richtlijnen en normen 2. Safety
Understanding Safety Integrity Levels (SIL) and its Effects for Field Instruments Introduction The Industrial process industry is experiencing a dynamic growth in Functional Process Safety applications.
0102 Model Number Features 15 mm quasi flush Usable up to SIL2 acc. to IEC 61508 Accessories BF 30 Mounting flange, 30 mm V1-G-N-2M-PUR Female cordset, M12, 2-pin, NAMUR, PUR cable V1-W-N-2M-PUR Female
Model Number Single head system Features Parameterization interface for the application-specific adjustment of the sensor setting via the service program ULTRA 000 programmable switch outputs Hysteresis
www.kem-kueppers.com Certified according to DIN EN ISO 9001 Technical Datasheet KVO Series Vortex Flow Meter Description The KVO Vortex flow meters utilize two primary sensing elements a vortex shedding
PROCESS AUTOMATION SAFETY MANUAL SIL SMART Transmitter Power Supply KFD2-STC4-(Ex)*, KFD2-STV4-(Ex)*, KFD2-CR4-(Ex)* ISO9001 2 3 With regard to the supply of products, the current issue of the following
ROBERTS Sound for Generations CR9971 2 Band Auto Set Dual Alarm Clock Radio Please read this manual before use Contents Contents... 1 Controls...2-5 Switching on... 6 Setting the time manually... 6 Setting
Products for Bulk Liquid Storage Tanks 2500 Automatic Tank Gauge The industry standard for float and tape tank gauging for over 50 years Provides a level accuracy of 0.2-1 inch (4-25 mm) Continuous level
GE Measurement & Control Solutions Sentinel LCT Panametrics Ultrasonic Flowmeter for Liquid Custody Transfer Measurement Benefits Extremely reliable and highly accurate flowmeter, designed specifically
Plena Two-zone Call Station en Installation and User Instructions PLE-2CS Plena Two-zone Call Station Installation and User Instructions Important safeguards en 2 Important safeguards Before installing
ATEX category II 1 G, Ex zone 0 ATEX category II 1 D, Ex zone 20 SIL2 as per IEC 61508 Threaded barrel, M18 x 1 Chrome-plated brass DC 2-wire, nom. 8.2 VDC Output acc. to DIN EN 60947-5-6 (NA- MUR) M12
Unit features Safety features Gertebild ][Bildunterschrift_NOT_Sch.tuer_Licht Safety relay for monitoring E-STOP pushbuttons, safety gates and light beam devices Approvals Gertemerkmale Positive-guided
California CUPA Northern Region Presents Underground Storage Tank Designated Operators Workshop Workshop Agenda Definitions Tank Construction Corrosion Protection Spill Prevention Overfill Prevention Piping
Power Supply and Indicator Unit Type 5024-1 Fig. 1 Type 5024-1 Mounting and Operating Instructions EB 9539 EN Edition October 2003 Application 1 Application The Type 5024-1 Power Supply and Indicator Unit
Management of Comments on this report are gratefully received by Johan Hedberg at SP Swedish National Testing and Research Institute mailto:email@example.com Quoting of this report is allowed but please
SIMATIC Safety Matrix The Management Tool for all Phases of the Safety Lifecycle Brochure September 2010 Safety Integrated Answers for industry. Functional safety and Safety Lifecycle Management Hazard
TMS TANK MANAGEMENT SYSTEM Page 1 of 9 Operating Instructions GENERAL The Tank Management System is a bespoke design to control, monitor and accommodate efficient storage and dispensing of TMS. FUNCTIONS
Health and Safety Executive Safety and environmental standards for fuel storage sites Process Safety Leadership Group Health and Safety Executive Safety and environmental standards for fuel storage sites
Manual for Fire Suppression & Methane Detection System Fogmaker North America Post address: 150 Gordon Dr Exton, PA 19341 Delivery address: 150 Gordon Dr Exton, PA 19341 Tel: 610-265-3610 Fax: 610-265-8327
conventional system operation detection line operation Conventional detection systems normally operate on a 24VDC line. In the standby condition, the detectors will draw a low current, typically less than
Safety Integrity Level (SIL) Assessment as key element within the plant design Tobias WALK ILF Consulting Engineers GmbH Germany Abstract Special attention has to be provide to safety instrumented functions
Laser Diode Module A HIGH SPEED MODULATABLE LASER WITH SPEEDS UP TO 50 MHZ Features Modulation speeds up to 50 MHz Visible and Infra red versions Powers from 1mW to 100 mw Flexible design accommodating
Short Form Catalogue Alarm Systems Reliable Supervision and Control Alarm Monitors and Indicators The SELCO product range includes a number of alarm monitors and indicator panels for use in numerous applications.
Integrated Fire and Gas Solution - Improves Plant Safety and Business Performance Integrated Fire and Gas Solution - Improves Plant Safety and Business Performance 1 Table of Contents Table of Figures...1
Performance Based Gas Detection System Design for Hydrocarbon Storage Tank Systems Srinivasan N. Ganesan, M.S., P.E. MENA Region Manager, Kenexis DMCC, Dubai, UAE Edward M. Marszal, PE, ISA 84 Expert ABSTRACT
Release date: 06-0- 09: Date of issue: 06-0- 009_eng.xml Model Number Single head system Features Parameterization interface for the application-specific adjustment of the sensor setting via the service
AlarmSense 2-wire detection and alarm system Product Guide Contents What is AlarmSense? 2 The purpose of AlarmSense 4 How AlarmSense works 4 Alarmsense Features 5 Detector removal monitoring 5 Priority/non-priority
L-LAS-TB-CL serie laser light curtains for inline measuring tasks Maximum distance 2.000 mm Measurement range 6 up to 98 mm Resolution up to 4 µm up to 1,5 khz scan rate 0-10 V or 4-20 ma analogue output
1. Introduction HB Series of microwave motion sensor module are X-Band Mono-static DRO Doppler transceiver front-end module. These modules are designed for movement detection, like intruder alarms, occupancy
INTEGRATED CIRCUITS DATA SHEET 24 W BTL or 2 x 12 W stereo car radio File under Integrated Circuits, IC01 January 1992 GENERAL DESCRIPTION The is a class-b integrated output amplifier encapsulated in a
T E C H N I C A L S P E C I F I C A T I O N The ATL EL-AD-151 (Resistance Output) and EL-AD-152 (Voltage Output) Fuel Level Senders are highly advanced sensors for continuously measuring the contents of
SEISMIC VELOCITY TRANSDUCER T1-40 Measurement of Omnidirectional Absolute Vibrations Certified according to ATEX 94/9/CE directive OPERATION Transducer T1-40 serves for seismic measurement of the absolute
Telephone- and leased line modem for industrial applications TD-36 Modem for industrial PSTN- and leased line applications The TD-36 is an analogue V.34 PSTN modem as well as an industrial 2-wire leased
ISpac isolators the perfect system 2 safe isolation Handling flammable and potentially explosive substances is part and parcel of everyday operations in many branches of industry. However, it is not possible
SUITABILITY OF DIFFERENT TEST VOLTAGES FOR ON-SITE TESTING OF XLPE CABLE SYSTEMS Michael Hensel HIGHVOLT Prüftechnik Dresden GmbH 2 3 Content 1 Introduction Test parameters and their significance Differences
SIL in de praktijk (Functional Safety) 23.04.2015 - Antwerpen SAMSON AG Dr. Thomas Karte 61508 Compliance of Actuators and Life Cycle Considerations 2015-04-23 SAMSON AG Dr. Karte - 61508 Compliance of
0102 Model Number Features 4 mm non-flush Usable up to SIL 3 acc. to IEC 61508 Application Danger! In safety-related applications the sensor must be operated with a qualified fail safe interface from Pepperl+Fuchs,
E0006 000824 Safety relay E-2 For emergency stop monitoring Description The safety module E-2 for emergency stop monitoring is used for safety breaking one or more circuits and is designed to be incorporated
Specifications and description HRTL 3B Laser diffuse reflection light scanner with background suppression Dimensioned drawing We reserve the right to make changes DS_HRTL3B_en.fm en 01-2010/12 50114049
Technical Article EMC filters for medical devices September 2010 EMC filters for medical devices Schaffner, the market leader in EMC filters and power quality, has supplemented its proven IEC inlet filter
ENDORSEMENT PROGRAM The CFSE endorsement program helps current holders of CFSE and CFSP certification build /demonstrate expertise and knowledge in specific focus areas of functional safety. What is CFSE?
Value Paper Author: Edgar C. Ramirez Diverse redundancy used in SIS technology to achieve higher safety integrity Diverse redundancy used in SIS technology to achieve higher safety integrity Abstract SIS
TECHNICAL SPECIFICATIONS Page 1 of 10 FIRE DETECTION AND ALARM SYSTEM Scope Furnish a complete 24V DC conventional, electrically supervised, zone annunciated, fire detection and alarm system as specified
Test report: 936/21219899/C of 30 August 2013 Initial certification: 23 July 2013 Expiry date: 22 July 2018 Publication: BAnz AT 01 April 2014 B12, chapter II, No. 1.1 Approved application The tested AMS
T5 TC-L PCA T5 BASIC lp Y II, 1 80 W BASIC T5 Product description Processor-controlled ballast with y II inside Highest possible energy class CELMA EEI = A1 BAT 1 Noise-free precise control via DSI signal,
RX-FM4SF 433,92 MHz The super-heterodyne FM receiver RX-FM4SF with High sensitivity and selectivity. It is equipped by front-end SAW filter that allows an High noise immunity. Enable pin allows to reach
INSTRUCTION MANUAL SIGNAL AMPLIFIER 4-20 ma 0305 260 IMPORTANT USER INFORMATION IMPORTANT USER INFORMATION Reading this entire manual is recommended for full understanding of the use of this product Should
Features: INSTALLATION Install in accordance with NFPA 70. DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS Up to 1.95 Amps Load Capacity Class 2 Rated Outputs Overload, Over Voltage, and Short
LAMTEC Flame Monitoring Flame monitoring device F5 Flame scanner FFS07 (Ex) Flame scanner FFS08 LAMTEC Flame monitoring Standards and Directives (under approval): DIN EN 98:0 DIN EN 30:005 DIN EN 60730--5:0