Mathematical Modelling and Design of an Advanced OnceThrough Heat Recovery Steam Generator


 Martina Taylor
 2 years ago
 Views:
Transcription
1 Mathematical Modelling and Design of an Advanced OnceThrough Heat Recovery Steam Generator Abstract MarieNoëlle Dumont, Georges Heyen LASSC, University of Liège, Sart Tilman B6A, B4000 Liège (Belgium) Tel: Fax: The oncethrough heat recovery steam generator design is ideally matched to very high temperature and pressure, well into the supercritical range. Moreover this type of boiler is structurally simpler than a conventional one, since no drum is required. A specific mathematical model has been developed. Thermodynamic model has been implemented to suit very high pressure (up to 40 bar), sub and supercritical steam properties. We illustrate the model use with a 180 bar oncethrough boiler (OTB). 1. Introduction Nowadays combined cycle (CC) power plants become a good choice to produce energy, because of their high efficiency and the use of low carbon content fuels (e.g. natural gas) that limits the greenhouse gases production to the minimum. CC plants couple a Brayton cycle with a Rankine cycle. The hot exhaust gas, available at the output of the gas turbine (Brayton cycle) is used to produce highpressure steam for the Rankine cycle. The element, where the steam heating takes place, is the heat recovery steam generator (HRSG). High efficiency in CC (up to 58%) has been reached mainly for two reasons : Improvements in the gas turbine technology (i.e. higher inlet temperature); Improvement in the HRSG design We are interested in the second point. The introduction of several pressure levels with reheat in the steam cycle in the HRSG allows recovering more energy from the exhaust gas. Exergy losses decrease, due to a better matching of the gas curve with the water/steam curve in the heat exchange diagram (Dechamps,1998). Going to supercritical pressure with the OTB technology is another way to better match those curves and thus improve the CC efficiency. New improvements are announced in near future to reach efficiency as high as 60%. In the present work we propose a mathematical model for the simulation and design of the oncethrough boiler. It is not possible to use empirical equations used for the simulation of each part of the traditional boiler. General equations have to be used for each tube of the boiler. Moreover there is a more significant evolution of the water/steam flow pattern type due to the complete water vaporization inside the tubes (in a conventional boiler, the circulation flow is adjusted to reach a vapor fraction between 0% and 40% in the tubes and the vapor is separated in the drum). Changes of flow pattern induce a modification in the evaluation of the internal heat transfer coefficient as well as in the pressure drop formulation. The right equation has to be selected dynamically according to the flow conditions prevailing in the tube.
2 The uniform distribution of water among parallel tubes of the same geometry subjected to equal heating is not ensured from the outset but depends on the pressure drop in the tubes. The disappearance of the drum introduces a different understanding of the boiler s behavior. Effect of the various twophase flow patterns have to be mathematically controlled. The stability criteria has changed.. Mathematical Model.1. Heat transfer.1.1. Water Mathematical models for traditional boilers are usually based on empirical equations corresponding to each part of the boiler : the economizer, the boiler and the superheater. Those three parts of boiler are clearly separated thus it is not difficult to choose the right equation. In a oncethrough boiler this separation is not so clear. We have first to estimate the flow pattern in the tube then to choose the equation to be used. Liquid single phase and vapor single phase are easily located with temperature and pressure data. According to Gnielinski (1993) the equation 1 applies for turbulent and hydrodynamically developed flow. ( ξ )( ) / 8 Re 1000 Pr l α * d Nu = = ; ξ = 1+ 1,7 /8 Pr 1 λ ( ξ /3 )( ) 1 ( 1,8 log Re 1, 64) During vaporization different flow patterns can be observed, for which the rate of heat transfer also differs. In stratifiedwavy flow pattern incomplete wetting has an effect on the heat transfer coefficient. A reduction could appear for this type of flow pattern. Computing conditions where a change in flow pattern occurs is useful. A method to establish a flow pattern map in horizontal tube for given pressure and flow conditions is clearly exposed by Steiner (1993). This method has been used in this study. The different flow pattern in the vaporisation zone of the OTB are given in figure 1. The heat transfer coefficient is estimated from numerous data. It is a combination of convective heat transfer coefficient and nucleate boiling heat transfer coefficient. 10 (1) 1.E+0 1.E+01 1.E+00 1.E01 1.E0 1.E03 1.E04 1.E05 Flow Pattern Diagram for Horizontal Flow (VDI (1993)) Flow in tubes with 5.08t/h and 5.166t/h Annular Mist (5) Wavy () Stratified (1) *1e XMartinelli parameter Figure 1: Flow pattern map in the boiling zone. Plug or Slug (4) Internal heat transfer coef (kcal/hr/m²/k) ECOV3 6A ECOV34A ECOV3A ECOV30A ECOV8A ECOV6A ECOV4A Oncethrough HRSG ECOVA ECOV0A ECOV18A ECOV16A ECOV14A ECOV1A ECOV10A ECOV08A ECOV06A ECOV04A ECOV0A SUPH06A SUPH04A SUPH0A Traditional HRSG Figure : Internal heat transfer coefficient.
3 0 α( z) = 3α( z) 3 + α( z) 3 () conv B () z α conv ρ ( 1 x) 1.x ( 1 x) liq α go ρ x 1 8( 1 x) liq = α ρ α ρ lo vap lo vap (3) α ( z) B = { heatflow,pressure,roughness,geometry} (4) α lo α LO is the heat transfer coefficient with total mass velocity in the form of the liquid and α GO is the heat transfer coefficient with total mass velocity in the form of the vapor. The internal coefficients computed for all the tubes of the OTB are presented in figure..1.. Fumes There is no difference between the equations used for a conventional heat recovery boiler and a once trough heat recovery boiler. The main part of the heat transfer coefficient is the convective part (low fumes temperature). The effect of the turbulence has been introduced to reduce the heat transfer coefficient in the first few rows of the tube bundle. The main difficulty to evaluate the heat transfer coefficient for the fume side comes from the fins that enhance the heat transfer, but could also produce other sources of resistance in the heat transfer, such as fouling on the surface of fins or inadequate contact between the core tube and the fin base. There are two methods to evaluate the heat transfer coefficient: The first one is based on a general equation to evaluate the Nusselt number in cross flow over pipes and the efficiency of the fins. An apparent heat transfer coefficient is then computed with equation 6. The second one is based on empirical correlations derived from experimental data. For more than four banks in staggered arrangement, equation 7 can be used. It is not obvious to find the most appropriate correlation for a given fin geometry and tube bundle arrangement. The best is to ask finned tube manufacturers to provide their correlations for heat transfer coefficient and fin efficiency corresponding to the required finned tube LOAD (kw) ECOV36A ECOV34A ECOV3A ECOV30A ECOV8A ECOV6A ECOV4A ECOVA ECOV0A ECOV18A ECOV16A ECOV14A ECOV1A ECOV10A ECOV08A ECOV06A ECOV04A ECOV0A SUPH06A SUPH04A SUPH0A LOAD FUME IN WATER OUT Figure 3: Heat exchange diagram TEMPERATURE (C) Pressure drop (mmho) ECOV36A ECOV34A ECOV3A ECOV30A ECOV8A ECOV6A ECOV4A ECOVA ECOV0A ECOV18A ECOV16A Pressure drop ECOV14A ECOV1A ECOV10A ECOV08A ECOV06A ECOV04A vapour fraction ECOV0A SUPH06A Figure 4: Pressure drop and vapor fraction evolution SUPH04A SUPH0A
4 A A po fo α = α * + η app f A f A 0.15 A 1 Nu = 0.38 Re 0.6 Pr 3 d d A b (6) (7).1.3. Overall heat transfer coefficient Finally the overall heat transfer coefficient is obtained from equation 8. The global heat transferred for each tube is computed with equation 9. We call T sl semi logarithmic temperature difference. It is the best compromise between pure logarithmic temperature difference that has no sense here (only one tube) and pure arithmetic temperature difference that does not allow to follow the evolution of water properties along the tube. The heat exchange diagram of the OTB is presented in figure e 1 = + + (8) α α A A app λ* w α * i A i A Q = α * A* T ; sl.. Pressure drop..1. Water ( T T ) T = w w1 sl T T mf w1 ln T mf T w ; T + T f 1 f T = (9) mf 64 f = f ρ V l Re P = with g d i f = 4 Re (10) The coefficient f depends on the Reynolds number for flow within the tube. In laminar flow, the HagenPoiseuille law can be applied. In turbulent flow the Blasius equation is used. The main difficulty is the evaluation of water pressure drop during transition boiling. The pressure drop consists of three components : friction ( P f ), acceleration ( P m ) and static pressure ( P g ). In oncethrough horizontal tubes boiler P g =0. The LockardMartinelli formulation is used to estimate the friction term. P P = Φ L L ftt phases liquid (11)
5 0 1 Φ = 1+ + ftt X X with X = P L liquid P L vapor (1) The acceleration term is defined with equation 13 where α is the volume fraction of vapor (void fraction). It is recommended to discretize the tube in several short sections to obtain more accurate results (figure 4). x x ( 1 x) P = G * m α * ρ + ( 1 )* vap α ρ liq x 1 (13)... Fumes The pressure drop in a tube bundle is given by equation 14. In this case the number of rows (N R ) plays an important role in the pressure drop evaluation. The coefficient f is more difficult to compute from generalized correlations. The easiest way is once more to ask the finned tubes manufacturer to obtain accurate correlation. f ρ V P = N (14) R 3. Stability Stability calculation is necessary for the control of water distribution over parallel tubes of the same form and subjected to equal heating in forced circulation HRSG and particularly in OTB. The stability can be described with the stability coefficient S. HRSG manufacturers try to keep the stability coefficient in the range (0.7). In OTB design inlet restrictions have been installed to increase singlephase friction in order to stabilize the boiler. Based on the πcriterion (Li Rizhu, Ju Huaiming, 00) defined as π P + P in liq =, the design has been realized with π about. This number has to Pboi + Pvap be reduced in near future when all various flow instabilities would be identified. relative change ( in pressure drop) relative change ( ) S = = with in flow rate S>0 stable S 0 unstable d( p) p d( M) M Pressure drop DP UNSTABLE STABLE Mass flow M Figure 5: Stability example.
6 4. An Example Results have been obtained for an OTB of pilot plant size (4 rows). WATER (10.5 t/h ;Tin=44 C ;Tout=500 C) FUMES (7.5 t/h ; Tin=59 C ;Tout= 197 C).In VALI Belsim software in which the simulation model has been implemented, the simulation of the OTB needs 4 modules, one for each row of tubes. Since VALI implements an numerical procedures to solve large sets of nonlinear equations, all model equations are solved simultaneously. The graphical user interface allows easy modification of the tube connections and the modelling of multiple pass bundles. 5. Conclusions and Future Work The mathematical model of the oncethrough boiler has been used to better understand the behaviour of the boiler. Future mathematical developments have still to be done to refine the stability criteria and improve the OTB design. Automatic generation of alternative bundle layouts in the graphical user interface is also foreseen. 6. Nomenclature A total area of outer surface (m²) A b bare tube outside surface area A fo fin outside surface area (m²) A i inside surface area (m²) A po free area of tube outer surface A w mean area of homogeneous tube wall c p specific heat capacity at constant pressure (J/kg/K) d i tube internal diameter (m) P pressure drop (bar) f pressure drop coefficient G mass flux (kg/m /s) H enthalpy flow (kw) N R number of rows in the bundle Nu Nusselt number Nu l l = α λ P pressure (bar) Pr Prandl number Pr = Q exchanged heat (kw) Re Reynolds number T temperature (K) V c p η fluid velocity (m/s) x vapor mass fraction x i component flow rate (kg/s) α heat transfer coefficient (kw/m²/k) α(z) local heat transfer coefficient λ thermal conductivity (W/m/K) ρ density (kg/m 3 ) η dynamic viscosity (Pa.s) or (kg/m/s) fin efficiency η f λ 7. References D. Steiner, 1993, VDI heat atlas, VDIVerlag, HBB, Düsseldorf, Germany V.Gnielinski, 1993, VDI heat atlas, GA,GB, VDIVerlag, Düsseldorf, Germany P.J. Dechamps, 1998, Advanced combined cycle alternatives with the latest gas turbines, ASME J. Engrg. Gas Turbines Power 10, Li Rizhu, Ju Huaiming, 00, Structural design and twophase flow stability test for the steam generator, Nuclear Engineering and Design 18, Acknowledgements This work was financially supported by CMI Utility boilers (Belgium).
Module 2 : Convection. Lecture 20a : Illustrative examples
Module 2 : Convection Lecture 20a : Illustrative examples Objectives In this class: Examples will be taken where the concepts discussed for heat transfer for tubular geometries in earlier classes will
More informationBoiler Calculations. Helsinki University of Technology Department of Mechanical Engineering. Sebastian Teir, Antto Kulla
Helsinki University of Technology Department of Mechanical Engineering Energy Engineering and Environmental Protection Publications Steam Boiler Technology ebook Espoo 2002 Boiler Calculations Sebastian
More informationCorrelations for Convective Heat Transfer
In many cases it's convenient to have simple equations for estimation of heat transfer coefficients. Below is a collection of recommended correlations for singlephase convective flow in different geometries
More informationHANDLY & FREQUENTLY USED FORMULAS FOR THERMAL ENGINEERS
HANDLY & FREQUENTLY USED FORMULAS FOR THERMAL ENGINEERS GEOMETRY & MATH GEOMETRI & MATEMATIK Cylindrical (Tube) Volume V = p / 4 d 2 L [m 3 ] Cylindrical (Tube) Surface A = p d L [m 2 ] Rectangular Triangle
More informationHeat Transfer Prof. Dr. Ale Kumar Ghosal Department of Chemical Engineering Indian Institute of Technology, Guwahati
Heat Transfer Prof. Dr. Ale Kumar Ghosal Department of Chemical Engineering Indian Institute of Technology, Guwahati Module No. # 04 Convective Heat Transfer Lecture No. # 03 Heat Transfer Correlation
More information16. Heat Pipes in Electronics Cooling (2)
16. Heat Pipes in Electronics Cooling (2) 16.1 Pulsating Heat Pipes 16.1.1Introduction Conventional heat pipe technology has been successfully applied in the last thirty years for the thermal management
More informationAPPLIED THERMODYNAMICS TUTORIAL 1 REVISION OF ISENTROPIC EFFICIENCY ADVANCED STEAM CYCLES
APPLIED THERMODYNAMICS TUTORIAL 1 REVISION OF ISENTROPIC EFFICIENCY ADVANCED STEAM CYCLES INTRODUCTION This tutorial is designed for students wishing to extend their knowledge of thermodynamics to a more
More informationFREESTUDY HEAT TRANSFER TUTORIAL 3 ADVANCED STUDIES
FREESTUDY HEAT TRANSFER TUTORIAL ADVANCED STUDIES This is the third tutorial in the series on heat transfer and covers some of the advanced theory of convection. The tutorials are designed to bring the
More informationEntrance Conditions. Chapter 8. Islamic Azad University
Chapter 8 Convection: Internal Flow Islamic Azad University Karaj Branch Entrance Conditions Must distinguish between entrance and fully developed regions. Hydrodynamic Effects: Assume laminar flow with
More informationExergy Analysis of a Water Heat Storage Tank
Exergy Analysis of a Water Heat Storage Tank F. Dammel *1, J. Winterling 1, K.J. Langeheinecke 3, and P. Stephan 1,2 1 Institute of Technical Thermodynamics, Technische Universität Darmstadt, 2 Center
More informationTheoretical and Numerical Analysis of Heat Transfer in Pipeline System
APCOM & ISCM 4 th December, 20, Singapore Theoretical and Numerical Analysis of Heat Transfer in Pipeline System Xiaowei Zhu, Hui Tang, *Hua Li, Jiahua Hong, Songyuan Yang School of Mechanical & Aerospace
More informationNatural Convection. Buoyancy force
Natural Convection In natural convection, the fluid motion occurs by natural means such as buoyancy. Since the fluid velocity associated with natural convection is relatively low, the heat transfer coefficient
More informationReview: Convection and Heat Exchangers. Reminders
CH EN 3453 Heat Transfer Review: Convection and Heat Exchangers Chapters 6, 7, 8, 9 and 11 Reminders Midterm #2 Wednesday at 8:15 AM Review tomorrow 3:30 PM in WEB L104 (I think) Project Results and Discussion
More informationFluid Mechanics: Static s Kinematics Dynamics Fluid
Fluid Mechanics: Fluid mechanics may be defined as that branch of engineering science that deals with the behavior of fluid under the condition of rest and motion Fluid mechanics may be divided into three
More informationChapter 3. Fossilfuel steam Generators
Chapter 3 Fossilfuel steam Generators Introduction Steam generators are mainly used in both fossiland nuclearfuel electric generation power plants. Main components are: a. Economizer b. Boiler c. Super
More informationInternal Convection: Fully Developed Flow
Internal Convection: Fully Developed Flow Laminar Flow in Circular Tube: Analytical local Nusselt number is constant in fully develop region depends on surface thermal condition constant heat flux Nu D
More informationPower Plants. BENSON OnceThrough Heat Recovery Steam Generator. Power Generation
Power Plants BENSON OnceThrough Heat Recovery Steam Generator Power Generation BENSON OnceThrough technology for Heat Recovery Steam Generators New application of proven technology Siemens development
More information5.2. Vaporizers  Types and Usage
5.2. Vaporizers  Types and Usage 5.2.1. General Vaporizers are constructed in numerous designs and operated in many modes. Depending upon the service application the design, construction, inspection,
More informationME 144: Heat Transfer Convection Relations for External Flows. J. M. Meyers
ME 144: Heat Transfer Convection Relations for External Flows Empirical Correlations Generally, convection correlations for external flows are determined experimentally using controlled lab conditions
More informationINTERNAL FLOW TEST PROBLEMS. Test Problem 1
INTERNAL FLOW TEST PROBLEMS The nonproprietary test problems that have been used to validate some of the capabilities provided in INSTED for the analysis of internal flow are presented in this section.
More informationInternational Journal of Latest Research in Science and Technology Volume 4, Issue 2: Page No.161166, MarchApril 2015
International Journal of Latest Research in Science and Technology Volume 4, Issue 2: Page No.161166, MarchApril 2015 http://www.mnkjournals.com/ijlrst.htm ISSN (Online):22785299 EXPERIMENTAL STUDY
More informationFluid Mechanics Prof. T. I. Eldho Department of Civil Engineering Indian Institute of Technology, Bombay. Lecture No. # 36 Pipe Flow Systems
Fluid Mechanics Prof. T. I. Eldho Department of Civil Engineering Indian Institute of Technology, Bombay Lecture No. # 36 Pipe Flow Systems Welcome back to the video course on Fluid Mechanics. In today
More informationHEAT TRANSFER ENHANCEMENT AND FRICTION FACTOR ANALYSIS IN TUBE USING CONICAL SPRING INSERT
HEAT TRANSFER ENHANCEMENT AND FRICTION FACTOR ANALYSIS IN TUBE USING CONICAL SPRING INSERT Rahul M. Gupta 1, Bhushan C. Bissa 2 1 Research Scholar, Department of Mechanical Engineering, Shri Ramdeobaba
More informationA LAMINAR FLOW ELEMENT WITH A LINEAR PRESSURE DROP VERSUS VOLUMETRIC FLOW. 1998 ASME Fluids Engineering Division Summer Meeting
TELEDYNE HASTINGS TECHNICAL PAPERS INSTRUMENTS A LAMINAR FLOW ELEMENT WITH A LINEAR PRESSURE DROP VERSUS VOLUMETRIC FLOW Proceedings of FEDSM 98: June 5, 998, Washington, DC FEDSM98 49 ABSTRACT The pressure
More informationCASLU20130193000
L3:THM.CFD.P7.06 Implementation and validation of the new RPI boiling models using STARCCM+ as CFD Platform Victor Petrov, Annalisa Manera UMICH September 30, 2013 EXECUTIVE SUMMARY This milestone is
More informationCFD Simulation of Subcooled Flow Boiling using OpenFOAM
Research Article International Journal of Current Engineering and Technology EISSN 2277 4106, PISSN 23475161 2014 INPRESSCO, All Rights Reserved Available at http://inpressco.com/category/ijcet CFD
More informationTransient Analysis of Integrated Shiraz Hybrid Solar Thermal Power Plant Iman Niknia 1, Mahmood Yaghoubi 1, 2
Transient Analysis of Integrated Shiraz Hybrid Solar Thermal Power Plant Iman Niknia 1, Mahmood Yaghoubi 1, 2 1 School of Mechanical Engineering, Shiraz University, Shiraz, Iran 1, 2 Shiraz University,
More informationHybrid Modeling and Control of a Power Plant using State Flow Technique with Application
Hybrid Modeling and Control of a Power Plant using State Flow Technique with Application Marwa M. Abdulmoneim 1, Magdy A. S. Aboelela 2, Hassen T. Dorrah 3 1 Master Degree Student, Cairo University, Faculty
More informationDynamic Process Modeling. Process Dynamics and Control
Dynamic Process Modeling Process Dynamics and Control 1 Description of process dynamics Classes of models What do we need for control? Modeling for control Mechanical Systems Modeling Electrical circuits
More informationHeat pipes and Thermosyphons. Heat pipes and Thermosyphons. Heat pipes and Thermosyphons. Heat pipes. Heat pipes. Heat pipes
Heat pipes and Thermosyphons Cold end Hot end Inside the system, there is a fluid (usually termed refrigerant) Heat pipes and Thermosyphons Cold end Hot end Heat is transferred as latent heat of evaporation
More informationDepartment of Chemical Engineering, National Institute of Technology, Tiruchirappalli 620 015, Tamil Nadu, India
Experimental Thermal and Fluid Science 32 (2007) 92 97 www.elsevier.com/locate/etfs Studies on heat transfer and friction factor characteristics of laminar flow through a circular tube fitted with right
More informationOUTCOME 4 STEAM AND GAS TURBINE POWER PLANT. TUTORIAL No. 8 STEAM CYCLES
UNIT 61: ENGINEERING THERMODYNAMICS Unit code: D/601/1410 QCF level: 5 Credit value: 15 OUTCOME 4 STEAM AND GAS TURBINE POWER PLANT TUTORIAL No. 8 STEAM CYCLES 4 Understand the operation of steam and gas
More informationFired Heater Design and Simulation
Fired Heater Design and Simulation Mahesh N. Jethva 1, C. G. Bhagchandani 2 1 M.E. Chemical Engineering Department, L.D. College of Engineering, Ahmedabad380 015 2 Associate Professor, Chemical Engineering
More informationSimulation and CFD Analysis of heat pipe heat exchanger using Fluent to increase of the thermal efficiency
Simulation and CFD Analysis of heat pipe heat exchanger using Fluent to increase of the thermal efficiency M. H. SABER, H. MAZAHER ASHTIANI CFD department Fanavar Petro Arya engineering Co. Tehran, Saharak
More informationAn introduction to thermodynamics applied to Organic Rankine Cycles
An introduction to thermodynamics applied to Organic Rankine Cycles By : Sylvain Quoilin PhD Student at the University of Liège November 2008 1 Definition of a few thermodynamic variables 1.1 Main thermodynamics
More informationQUESTIONS THERMODYNAMICS PRACTICE PROBLEMS FOR NONTECHNICAL MAJORS. Thermodynamic Properties
QUESTIONS THERMODYNAMICS PRACTICE PROBLEMS FOR NONTECHNICAL MAJORS Thermodynamic Properties 1. If an object has a weight of 10 lbf on the moon, what would the same object weigh on Jupiter? ft ft ft g
More informationENGINEERING COUNCIL CERTIFICATE LEVEL THERMODYNAMIC, FLUID AND PROCESS ENGINEERING C106 TUTORIAL 5 STEAM POWER CYCLES
ENGINEERING COUNCIL CERTIFICATE LEVEL THERMODYNAMIC, FLUID AND PROCESS ENGINEERING C106 TUTORIAL 5 STEAM POWER CYCLES When you have completed this tutorial you should be able to do the following. Explain
More information2. CHRONOLOGICAL REVIEW ABOUT THE CONVECTIVE HEAT TRANSFER COEFFICIENT
ANALYSIS OF PCM SLURRIES AND PCM EMULSIONS AS HEAT TRANSFER FLUIDS M. Delgado, J. Mazo, C. Peñalosa, J.M. Marín, B. Zalba Thermal Engineering Division. Department of Mechanical Engineering University of
More informationThe soot and scale problems
Dr. Albrecht Kaupp Page 1 The soot and scale problems Issue Soot and scale do not only increase energy consumption but are as well a major cause of tube failure. Learning Objectives Understanding the implications
More informationSizing of triple concentric pipe heat exchanger
Sizing of triple concentric pipe heat exchanger 1 Tejas M. Ghiwala, 2 Dr. V.K. Matawala 1 Post Graduate Student, 2 Head of Department 1 Thermal Engineering, SVMIT, Bharuch392001, Gujarat, INDIA, 2 Department
More informationFundamentals of Heat and Mass Transfer
2008 AGIInformation Management Consultants May be used for personal purporses only or by libraries associated to dandelon.com network. SIXTH EDITION Fundamentals of Heat and Mass Transfer FRANK P. INCROPERA
More informationNUMERICAL INVESTIGATIONS ON HEAT TRANSFER IN FALLING FILMS AROUND TURBULENCE WIRES
NUMERICAL INVESTIGATIONS ON HEAT TRANSFER IN FALLING FILMS AROUND TURBULENCE WIRES Abstract H. Raach and S. Somasundaram Thermal Process Engineering, University of Paderborn, Paderborn, Germany Turbulence
More information8. Evaporators */ A. Introduction
CHAPTER 8. EVAPORATORS 8. Evaporators */ A. Introduction 8.01 The evaporator is one of the four basic and necessary hardware components of the refrigeration system. (The refrigerant may be considered as
More informationDesign of heat exchangers
Design of heat exchangers Exchanger Design Methodology The problem of heat exchanger design is complex and multidisciplinary. The major design considerations for a new heat exchanger include: process/design
More information1. (Problem 8.23 in the Book)
1. (Problem 8.23 in the Book) SOLUTION Schematic An experimental nuclear core simulation apparatus consists of a long thinwalled metallic tube of diameter D and length L, which is electrically heated
More informationExperimental Study of Free Convection Heat Transfer From Array Of Vertical Tubes At Different Inclinations
Experimental Study of Free Convection Heat Transfer From Array Of Vertical Tubes At Different Inclinations A.Satyanarayana.Reddy 1, Suresh Akella 2, AMK. Prasad 3 1 Associate professor, Mechanical Engineering
More informationCHEPTER3 EFFECT OF OPERATING VARIABLES ON THERMAL EFFICIENCY OF COMBINED CYCLE POWER PLANT
CHEPTER3 EFFECT OF OPERATING VARIABLES ON THERMAL EFFICIENCY OF COMBINED CYCLE POWER PLANT 3.1 THERMAL EFFICIENCY OF THE COMBINED CYCLE:  In combined cycle power plants if power in gas turbine and steam
More informationExperiment 3 Pipe Friction
EML 316L Experiment 3 Pipe Friction Laboratory Manual Mechanical and Materials Engineering Department College of Engineering FLORIDA INTERNATIONAL UNIVERSITY Nomenclature Symbol Description Unit A crosssectional
More informationEnergy : ṁ (h i + ½V i 2 ) = ṁ(h e + ½V e 2 ) Due to high T take h from table A.7.1
6.33 In a jet engine a flow of air at 000 K, 00 kpa and 30 m/s enters a nozzle, as shown in Fig. P6.33, where the air exits at 850 K, 90 kpa. What is the exit velocity assuming no heat loss? C.V. nozzle.
More informationApplied Thermodynamics for Marine Systems Prof. P. K. Das Department of Mechanical Engineering Indian Institute of Technology, Kharagpur
Applied Thermodynamics for Marine Systems Prof. P. K. Das Department of Mechanical Engineering Indian Institute of Technology, Kharagpur Lecture  10 Steam Power Cycle, Steam Nozzle Good afternoon everybody.
More informationFUNDAMENTALS OF ENGINEERING THERMODYNAMICS
FUNDAMENTALS OF ENGINEERING THERMODYNAMICS System: Quantity of matter (constant mass) or region in space (constant volume) chosen for study. Closed system: Can exchange energy but not mass; mass is constant
More information4.1 Introduction. 4.2 Work. Thermodynamics
Thermodynamics 41 Chapter 4 Thermodynamics 4.1 Introduction This chapter focusses on the turbine cycle:thermodynamics and heat engines. The objective is to provide enough understanding of the turbine
More informationME19b. SOLUTIONS. Feb. 11, 2010. Due Feb. 18
ME19b. SOLTIONS. Feb. 11, 21. Due Feb. 18 PROBLEM B14 Consider the long thin racing boats used in competitive rowing events. Assume that the major component of resistance to motion is the skin friction
More informationWaste Heat Recovery through Air Conditioning System
International Journal of Engineering Research and Development eissn: 2278067X, pissn : 2278800X, www.ijerd.com Volume 5, Issue 3 (December 2012), PP. 8792 Waste Heat Recovery through Air Conditioning
More informationFeedwater and Steam System Components
Helsinki University of Technology Department of Mechanical Engineering Energy Engineering and Environmental Protection Publications Steam Boiler Technology ebook Espoo 2002 Feedwater and Steam System Components
More informationEstimation of a tube diameter in a church window condenser based on entropy generation minimization
archives of thermodynamics Vol. 36(2015), No. 3, 49 59 DOI: 10.1515/aoter20150021 Estimation of a tube diameter in a church window condenser based on entropy generation minimization RAFAŁ LASKOWSKI 1
More informationComparison of Heat Transfer between a Helical and Straight Tube Heat Exchanger
International Journal of Engineering Research and Technology. ISSN 09743154 Volume 6, Number 1 (2013), pp. 3340 International Research Publication House http://www.irphouse.com Comparison of Heat Transfer
More informationThe Effect of Mass Flow Rate on the Enhanced Heat Transfer Charactristics in A Corrugated Plate Type Heat Exchanger
Research Journal of Engineering Sciences ISSN 2278 9472 The Effect of Mass Flow Rate on the Enhanced Heat Transfer Charactristics in A Corrugated Plate Type Heat Exchanger Abstract Murugesan M.P. and Balasubramanian
More informationEnergy Efficient Process Heating: Insulation and Thermal Mass
Energy Efficient Process Heating: Insulation and Thermal Mass Kevin Carpenter and Kelly Kissock Department of Mechanical and Aerospace Engineering University of Dayton 300 College Park Dayton, OH 454690210
More informationFOSSIL FUEL FIRED BOILER PLANT CONFIGURATION R.A.
FOSSIL FUEL FIRED BOILER PLANT CONFIGURATION R.A. Chaplin Department of Chemical Engineering, University of New Brunswick, Canada Keywords: Steam, Boiler, Arrangement Contents 1. Introduction 1.1 Terminology
More informationTHERMAL ANALYSIS OF WATER COOLED CHARGE AIR COOLER IN TURBO CHARGED DIESEL ENGINE
THERMAL ANALYSIS OF WATER COOLED CHARGE AIR COOLER IN TURBO CHARGED DIESEL ENGINE J.N. Devi Sankar 1, P.S.Kishore 2 1 M.E. (Heat transfer in Energy Systems) Student, Department of Mechanical Engineering,
More informationTraining programme on Energy Efficient technologies for climate change mitigation in Southeast Asia. Cogeneration
Training programme on Energy Efficient technologies for climate change mitigation in Southeast Asia Cogeneration Session Agenda: Cogeneration Introduction Types of steam turbine cogeneration system Types
More informationHeat Exchangers. Heat Exchanger Types. Heat Exchanger Types. Applied Heat Transfer Part Two. Topics of This chapter
Applied Heat Transfer Part Two Heat Excangers Dr. Amad RAMAZANI S.A. Associate Professor Sarif University of Tecnology انتقال حرارت کاربردی احمد رمضانی سعادت ا بادی Autumn, 1385 (2006) Ramazani, Heat Excangers
More informationHeat transfer in Flow Through Conduits
Heat transfer in Flow Through Conduits R. Shankar Suramanian Department of Chemical and Biomolecular Engineering Clarkson University A common situation encountered y the chemical engineer is heat transfer
More informationMercury Flow through a Long Curved Pipe
Mercury Flow through a Long Curved Pipe Wenhai Li & Foluso Ladeinde Department of Mechanical Engineering Stony Brook University Summary The flow of mercury in a long, curved pipe is simulated in this task,
More informationThere is no general classification of thermodynamic cycle. The following types will be discussed as those are included in the course curriculum
THERMODYNAMIC CYCLES There is no general classification of thermodynamic cycle. The following types will be discussed as those are included in the course curriculum 1. Gas power cycles a) Carnot cycle
More informationTHE UNIVERSITY OF TRINIDAD & TOBAGO
THE UNIVERSITY OF TRINIDAD & TOBAGO FINAL ASSESSMENT/EXAMINATIONS JANUARY/APRIL 2013 Course Code and Title: Programme: THRM3001 Engineering Thermodynamics II Bachelor of Applied Sciences Date and Time:
More informationHEAT TRANSFER ANALYSIS IN A 3D SQUARE CHANNEL LAMINAR FLOW WITH USING BAFFLES 1 Vikram Bishnoi
HEAT TRANSFER ANALYSIS IN A 3D SQUARE CHANNEL LAMINAR FLOW WITH USING BAFFLES 1 Vikram Bishnoi 2 Rajesh Dudi 1 Scholar and 2 Assistant Professor,Department of Mechanical Engineering, OITM, Hisar (Haryana)
More informationTurbulence, Heat and Mass Transfer (THMT 09) Poiseuille flow of liquid methane in nanoscopic graphite channels by molecular dynamics simulation
Turbulence, Heat and Mass Transfer (THMT 09) Poiseuille flow of liquid methane in nanoscopic graphite channels by molecular dynamics simulation Sapienza Università di Roma, September 14, 2009 M. T. HORSCH,
More informationMATLAB AS A PROTOTYPING TOOL FOR HYDRONIC NETWORKS BALANCING
MATLAB AS A PROTOTYPING TOOL FOR HYDRONIC NETWORKS BALANCING J. Pekař, P. Trnka, V. Havlena* Abstract The objective of this note is to describe the prototyping stage of development of a system that is
More information1. Why are the back work ratios relatively high in gas turbine engines? 2. What 4 processes make up the simple ideal Brayton cycle?
1. Why are the back work ratios relatively high in gas turbine engines? 2. What 4 processes make up the simple ideal Brayton cycle? 3. For fixed maximum and minimum temperatures, what are the effect of
More information1. A belt pulley is 3 ft. in diameter and rotates at 250 rpm. The belt which is 5 ins. wide makes an angle of contact of 190 over the pulley.
Sample Questions REVISED FIRST CLASS PARTS A1, A2, AND A3 (NOTE: these questions are intended as representations of the style of questions that may appear on examinations. They are not intended as study
More informationSteam turbine power generation is a Rankine Cycle, best plotted on a temperature/entropy [T/s] diagram : Critical Point
Cogeneration Thermodynamics Revisited Dr Mike Inkson and Ben Misplon Thermal Energy Systems Abstract Whilst most engineers understand that higher HP steam conditions result in a more efficient power station,
More informationCONTENTS. ZVU Engineering a.s., Member of ZVU Group, WASTE HEAT BOILERS Page 2
WASTE HEAT BOILERS CONTENTS 1 INTRODUCTION... 3 2 CONCEPTION OF WASTE HEAT BOILERS... 4 2.1 Complex Solution...4 2.2 Kind of Heat Exchange...5 2.3 Heat Recovery Units and Their Usage...5 2.4 Materials
More informationCFD Study of the Heat Pipes with Water Nanoparticles Mixture
CFD Study of the Heat Pipes with Water Nanoparticles Mixture Gabriela HUMINIC 1, Angel HUMINIC 1 1 Department of Thermodynamics and Fluid Mechanics Transilvania University of Brasov, Romania Abstract:
More informationEffective parameters on second law analysis for semicircular ducts in laminar flow and constant wall heat flux B
International Communications in Heat and Mass Transfer 32 (2005) 266 274 www.elsevier.com/locate/ichmt Effective parameters on second law analysis for semicircular ducts in laminar flow and constant wall
More informationFundamentals of THERMALFLUID SCIENCES
Fundamentals of THERMALFLUID SCIENCES THIRD EDITION YUNUS A. CENGEL ROBERT H. TURNER Department of Mechanical JOHN M. CIMBALA Me Graw Hill Higher Education Boston Burr Ridge, IL Dubuque, IA Madison, Wl
More informationThermal Analysis of a Supercritical CFB Boiler
Thermal Analysis of a Supercritical CFB Boiler Kurapati Nageswara Rao MTech Student Kakinada Institute Of Technology & Science, Divili, Mr. Sanmala Rajasekhar Associate Professor Kakinada Institute Of
More informationA heat pipe heat recovery heat exchanger for a minidrier
A heat pipe heat recovery heat exchanger for a minidrier A Meyer Department of Mechanical Engineering, University of Stellenbosch, Stellenbosch R T Dobson Department of Mechanical Engineering, University
More informationCONDENSERS AND CONDENSER COOLING SYSTEMS
CONDENSERS AND CONDENSER COOLING SYSTEMS INTRODUCTION Conventional cooling methods of thermal power plants are extremely water intensive processes. Oncethrough cooling needs large natural bodies of water
More informationTheoretical and Experimental Investigation of Heat Transfer Characteristics through a Rectangular Microchannel Heat Sink
Theoretical and Experimental Investigation of Heat Transfer Characteristics through a Rectangular Microchannel Heat Sink Dr. B. S. Gawali 1, V. B. Swami 2, S. D. Thakre 3 Professor Dr., Department of Mechanical
More informationTHERMODYNAMICS NOTES  BOOK 2 OF 2
THERMODYNAMICS & FLUIDS (Thermodynamics level 1\Thermo & Fluids Module Thermo Book 2ContentsDecember 07.doc) UFMEQU201 THERMODYNAMICS NOTES  BOOK 2 OF 2 Students must read through these notes and
More informationNovel Application of Organic Rankine Cycle (ORC) Technology for Waste Heat Recovery from Reheat Furnace Evaporative Cooling System
Novel Application of Organic Rankine Cycle (ORC) Technology for Waste Heat Recovery from Reheat Furnace Evaporative Cooling System Ahmet DURMAZ TMEIC 2060 Cook Drive Salem, VA 24153, USA Tel: 5402832000
More information2.2. Basic Equations for Heat Exchanger Design
.. Basic Equations for Heat Exchanger Design... The Basic Design Equation and Overall Heat Transfer Coefficient The basic heat exchanger equations applicable to shell and tube exchangers were developed
More informationHEAT TRANSFER IM0245 3 LECTURE HOURS PER WEEK THERMODYNAMICS  IM0237 2014_1
COURSE CODE INTENSITY PREREQUISITE COREQUISITE CREDITS ACTUALIZATION DATE HEAT TRANSFER IM05 LECTURE HOURS PER WEEK 8 HOURS CLASSROOM ON 6 WEEKS, HOURS LABORATORY, HOURS OF INDEPENDENT WORK THERMODYNAMICS
More informationCoupling Forced Convection in Air Gaps with Heat and Moisture Transfer inside Constructions
Coupling Forced Convection in Air Gaps with Heat and Moisture Transfer inside Constructions M. Bianchi Janetti 1, F. Ochs 1 and R. Pfluger 1 1 University of Innsbruck, Unit for Energy Efficient Buildings,
More informationThe Effects of Fin Spacing and Tube Outer Diameter of Evaporator on System Performance in Heat Pump Tumble Dryers
Purdue University Purdue epubs International Refrigeration and Air Conditioning Conference School of Mechanical Engineering 2014 The Effects of Fin Spacing and Tube Outer Diameter of Evaporator on System
More informationSIZING SAFETY VALVES FOR SUPERCRITICAL STEAM BOILERS
SIZING SAFETY VALVES FOR SUPERCRITICAL STEAM BOILERS J A Hare 1,3 and G Hawkins 2 1 Health and Safety Laboratory, Process Safety Section 2 Health and Safety Executive, Hazardous Installations Directorate,
More informationSTEAM TURBINE 1 CONTENT. Chapter Description Page. V. Steam Process in Steam Turbine 6. VI. Exhaust Steam Conditions, Extraction and Admission 7
STEAM TURBINE 1 CONTENT Chapter Description Page I Purpose 2 II Steam Turbine Types 2 2.1. Impulse Turbine 2 2.2. Reaction Turbine 2 III Steam Turbine Operating Range 2 3.1. Curtis 2 3.2. Rateau 2 3.3.
More informationThe Three Way Catalyst in Hybrid Vehicles
CODEN:LUTEDX/(TEIE5242)/147/(2007) Industrial Electrical Engineering and Automation The Three Way Catalyst in Hybrid Vehicles Bobbie Frank Dept. of Industrial Electrical Engineering and Automation Lund
More informationcmn_lecture.2 CAD OF DOUBLE PIPE HEAT EXCHANGERS
cmn_lecture.2 CAD OF DOUBLE PIPE HEAT EXCHANGERS A double pipe heat exchanger, in essence, consists of two concentric pipes, one fluid flowing through the inner pipe and the outer fluid flowing countercurrently
More informationHeating In Agitated & NonAgitated Vessels
Heating In Agitated & NonAgitated Vessels IBD/BFBiMidland Section Engineering Symposium on Heat Transfer and Refrigeration BurtononTrent Jan 2014 Mark Phillips Briggs of Burton Contents Heat Energy
More informationThe RanqueHilsch Vortex Tube
The RanqueHilsch Vortex Tube Giorgio De Vera May 10, 2010 Abstract The RanqueHilsch vortex tube has been used for many decades in various engineering applications. Because of its compact design and little
More informationINTRODUCTION TO. Chapter 15
INTRODUCTION TO HEAT EXCHANGERS Chapter 15 What is a Heat Exchanger? A heat exchanger is a device that is used to transfer thermal energy (enthalpy) between two or more fluids, between a solid surface
More informationAN EXPERIMENTAL STUDY OF EXERGY IN A CORRUGATED PLATE HEAT EXCHANGER
International Journal of Mechanical Engineering and Technology (IJMET) Volume 6, Issue 11, Nov 2015, pp. 1622, Article ID: IJMET_06_11_002 Available online at http://www.iaeme.com/ijmet/issues.asp?jtype=ijmet&vtype=6&itype=11
More informationHeat exchangers are devices that facilitate the exchange of heat between
cen5426_ch23.qxd /26/04 9:42 AM Page 03 HEAT EXCHANGERS CHAPTER 23 Heat exchangers are devices that facilitate the exchange of heat between two fluids that are at different temperatures while keeping them
More informationSuperheaters: design and performance
Superheaters: design and performance Understand these factors to improve operation V Ganapathy, ABCO Industries, Abilene, Texas Steam superheaters are widely used in steam generators and heatrecovery
More informationLecture 5 Hemodynamics. Description of fluid flow. The equation of continuity
1 Lecture 5 Hemodynamics Description of fluid flow Hydrodynamics is the part of physics, which studies the motion of fluids. It is based on the laws of mechanics. Hemodynamics studies the motion of blood
More informationEXPERIMENTAL RESEARCH ON FLOW IN A 5STAGE HIGH PRESSURE ROTOR OF 1000 MW STEAM TURBINE
Proceedings of 11 th European Conference on Turbomachinery Fluid dynamics & Thermodynamics ETC11, March 2327, 2015, Madrid, Spain EXPERIMENTAL RESEARCH ON FLOW IN A 5STAGE HIGH PRESSURE ROTOR OF 1000
More informationUNITIII PROPERTIES OF PURE SUBSTANCE AND STEAM POWER CYCLE
UNITIII PROPERTIES OF PURE SUBSTANCE AND STEAM POWER CYCLE Pure Substance A Pure substance is defined as a homogeneous material, which retains its chemical composition even though there may be a change
More information