1 MULTIPOISE, CONDENSING 8MCA, 8MVP, 8MXA HEATING & COOLING USER'S INFORMATION MANUAL FOR THE OPERATION AND MAINTENANCE OF YOUR NEW GAS-FIRED FURNACE NOTE TO INSTALLER: THIS MANUAL MUST BE LEFT WITH THE EQUIPTMENT USER. U L T R A H I G H E F F I C I E N C Y G A S F U R N A N C E WARNING: If the information in this manual is not followed exactly, a fire or explosion may result causing property damage, personal in- jury or loss of life. Do not store or use gasoline or other flam- mable vapors and liquids in the vicinity of this or any other appliance. WHAT TO DO IF YOU SMELL GAS: Do not try to light any appliance. Do not touch any electrical switch; do not use any phone in your building. Immediately call your gas supplier from a neighbor's phone. Follow the gas supplier's instructions. If you cannot reach your gas supplier, call the fire department. Installation and service must be performed by a qualified installer, service agency or the gas supplier.
2 WELCOME TO A NEW GENERATION OF COMFORT Congratulations In light of rising energy costs, the Weather- Maker 9200, 8MCA, and WeatherMaker Infinity, Multipoise, Gas-Fired Condensing Furnaces are among the soundest investments today s homeowner can make. Your new furnace is truly a triumph of technology in home heating. A revolutionary design employs 2 heat exchangers to squeeze out the maximum amount of heat from the fuel consumed. In fact, your new furnace is so efficient, over 90%* of the heat generated during combustion is captured and delivered inside your home. That is more than a 33%* increase in heating efficiency over conventional furnaces. These are among the most energy-efficient furnaces you can buy today. They also are among the safest and most dependable. We are proud of the technological advances incorporated into the design of these furnaces. With only minimal care, your new furnace will deliver many years of moneysaving home comfort and enjoyment. Spend just a few minutes with this manual to learn the operation of your new furnace and the small amount of maintenance it takes to help keep it operating at peak efficiency year after year. * The output capacity and any representations of efficiency for this furnace are based on standard Department of Energy test procedures. Date Installed Dealer Name Address City INSTALLATION DATA MODELS 8MXA (SHOWN) AND 8MCA FIXED-CAPACITY FURNACES U L T R A H I G H E F F I C I E N C Y G A S F U R N A N C E 1 State Zip Telephone FURNACE Product No. Model No. Serial No. Product No. Model No. Serial No. SPLIT-SYSTEM U L T R A H I G H E F F I C I E N C Y G A S F U R N A N C E INDOOR COIL: Product No. Model No. Serial No. MODEL 8MVP VARIABLE-CAPACITY FURNACE 2 2
3 FURNACE COMPONENTS Combustion-air intake connection to ensure contaminant-free air (right or left side). Burner sight glass for viewing burner flame. Burner assembly (inside). Operates with energysaving inshot burners and hot surface ignitor for safe, dependable heating. Redundant gas valve. Safe, efficient. Features 1 gas control with 2 internal shut-off valves. Vent outlet. Uses PVC pipe to carry vent gases from the furnace s combustion system (right or left side). Inducer motor. Pulls hot flue gases through the heat exchangers, maintaining negative pressure for added safety. Blower access panel safety interlock switch. Air filter and retainer. Condensate drain connection. Collects moisture condensed from burned gases for disposal into home drain system. Heavy-duty blower. Circulates air across the heat exchangers to transfer heat into the home. Secondary condensing heat exchanger (inside). Wrings out more heat through condensation. Constructed with Polypropylene-laminated steel to ensure durability. Primary serpentine heat exchanger (inside). Stretches fuel dollars with the S-shaped heat-flow design. Solid construction of corrosion-resistant aluminized steel means reliability. Control center. 3-amp fuse provides electrical and component protection. Light emitting diode (LED) on control center. Code lights are for diagnosing furnace operation and service requirements. Pressure switch(s) ensure adequate flow of flue products through furnace and out vent system. Rollout switch (manual reset) to prevent overtemperature. Junction box for 11-v electrical power supply. Transformer (24v) behind control center provides low-voltage power to furnace control center and thermostat. Limit switch (manual reset) on 8MVP only MODELS 8MXA AND 8MCA FURNACES (UPFLOW POSITION) MODEL 8MVP FURNACE (UPFLOW POSITION)
4 IMPORTANT FACTS Your gas furnace uses air from outside the home for combustion and venting. It is not to be installed using in-house air. Therefore, both pipes must terminate outside the structure and must not be obstructed in any way. This furnace contains SAFETY DEVICES which must be MANUALLY RESET. If the furnace is left unattended for an extended period of time, have it checked periodically for proper operation. This precaution will prevent problems associated with no heat, such as frozen water pipes, etc. See section Before You Request a Service Call in this manual. To minimize the possibility of serious personal injury, fire, damage to your furnace, or improper operation, carefully follow these safety rules: Keep the area around your furnace free of combustible materials, gasoline, and other flammable liquids and vapors. Do not cover the furnace, store trash or debris near it, or in any way block the flow of fresh air to the unit. A furnace installed in an attic or other insulated space must be kept free and clear of insulating material. Examine the furnace area when installing the furnace or adding more insulation. Some materials may be combustible. NOTE: Do not use this furnace if any part has been under water. Immediately call a qualified service technician to inspect the furnace and to replace any part of the control system and any gas control which has been under water. SAFETY CONSIDERATIONS Installation and service of heating equipment can be hazardous due to gas and electrical components. Only trained and qualified personnel should install, repair, or service heating equipment. Untrained personnel can perform basic maintenance functions such as cleaning and replacing air filters. All other operations must be performed by trained service personnel. Observe safety precautions in this manual, on tags, and labels attached to the furnace and other safety precautions that may apply. Recognize safety information. This is the safety-alert symbol. When you see this symbol on the furnace and in instructions or manuals, be alert to the potential for personal injury. Understand the signal words DANGER, WARNING, and. These words are used with the safety-alert symbol. DANGER identifies the most serious hazards which will result in severe personal injury or death. WARNING signifies hazards which could result in personal injury or death. is used to identify unsafe practices which would result in minor personal injury or product and property damage. STARTING YOUR FURNACE Instead of a continuously burning pilot flame which wastes valuable energy, your furnace uses an automatic, hot surface ignition system to light the burners each time the thermostat turns on your furnace. Follow these important safeguards: NOTE: The qualified installer or agency must use only factory-authorized replacement parts, kits, and accessories when modifying this product. 6 Never attempt to light the burners manually with a match or other source of flame. Read and follow the operating instructions on the furnace, especially the item that reads as follows: Wait minutes to clear out any gas. Then smell for gas, including near the floor. If you smell gas, STOP Follow B in the safety information above on this label. If you don t smell gas, go to the next step. 7 4
5 If a suspected malfunction occurs with your gas control system, such as the burners not lighting when they should, refer to the shutdown procedures on the furnace, or in the section, Shutting Down Your Furnace and call your dealer as soon as possible. WARNING If overheating occurs or the gas valve fails to shut off the gas supply, turn off the manual gas valve to the furnace BEFORE turning off the electrical supply. (See Fig. 9.) Failure to follow this warning could result in a fire or explosion, and personal injury or death. CHECK AIR FILTER: Before attempting to start your furnace, be sure the furnace filter is clean and in place. See section Performing Routine Maintenance in this manual. Then proceed as follows: STEPS FOR STARTING YOUR FURNACE 1. Set your room thermostat to the lowest temperature setting. (See Fig. 8.) 2. Close the external manual gas valve. (See Fig. 9.) 3. Turn off electrical supply to the furnace. (See Fig. 10.) 70 CLOSE OFF 12 NOTE: If the burners fail to ignite after 4 attempts, the furnace control system will lockout. If lockout occurs, main burners fail to light, or blower does not come on, shut down the furnace and call your dealer for service SYSTEM COOL OFF HEAT FAN AUTO ON Remove the furnace access door. (See Fig. 11.). Turn control knob on the gas valve to the OFF position and wait minutes. Then smell for gas, including near the floor. If you smell gas, STOP Follow operating instructions on furnace access door. (See Fig. 12.) 6. After waiting minutes, turn control knob on the gas valve to the ON position. (See Fig. 12.) 7. Replace furnace access door. (See Fig. 13.) 8. Turn on electrical supply to the furnace and wait 1 minute. (See Fig. 14.) 9. Open the external manual gas valve. (See Fig. 1.) 10. Set room thermostat to a temperature slightly above room temperature. This will automatically signal the furnace to start. 11. When the furnace receives the start signal, the hot surface ignitor at the main burners is automatically heated for 1 to 20 sec. When the microprocessor control verifies that there is sufficient heat to ignite, the gas valve permits gas to flow to the main burners. After ignition and a time delay of about 3 sec, your blower will start at low speed until the control makes the necessary adjustments to operate the blower at either the low- or high-fire speed OPEN Set your thermostat to the temperature that satisfies your comfort requirements. SUGGESTION: Setting the thermostat back a few degrees and compensating for the difference with warmer clothing can make a big difference in your fuel consumption on extremely cold days. The few degrees at the top of your thermostat comfort level are the most costly degrees to obtain.
6 When room temperature drops below the temperature selected on the thermostat, the furnace will be switched on automatically. When room temperature reaches the degree selected on the thermostat, the furnace will be switched off automatically. Some thermostats have a FAN switch with 2 selections, AUTO and ON. When thermostat is set to AUTO, the furnace blower cycles on and off, controlled by the thermostat. In ON position, the furnace blower runs continuously. This keeps the temperature level in your home more evenly balanced. It also continuously filters the indoor air. SHUTTING DOWN YOUR FURNACE Should you need to shut down your furnace for service or maintenance, you will need to turn the furnace off. The following procedures must be followed: OFF WARNING Turn off electrical power supply to your furnace before removing the access door to service or perform maintenance. Failure to follow this warning could result in personal injury or death Although special care has been taken to minimize sharp edges, be extremely careful when handling parts or reaching into the furnace. SYSTEM COOL OFF HEAT FAN AUTO ON Set your room thermostat to the lowest temperature setting. (See Fig. 16.) 2. Close the external manual gas valve. (See Fig. 9.) 3. Turn off electrical supply to the furnace. (See Fig. 17.) 4. Remove furnace access door. (See Fig. 11.). Turn control knob on the gas valve to OFF position. (See Fig. 18.) 6. Replace furnace access door. (See Fig. 13.) 7. If the furnace is being shut down because of a malfunction, call your dealer as soon as possible. Furnace is not to be installed, operated, and then turned off and left turned off in an unoccupied structure during winter. (See winterizing procedures in maintenance section). PERFORMING ROUTINE MAINTENANCE With proper maintenance and care, your furnace will operate economically and dependably. Instructions for basic maintenance, which can easily be followed, are found on this and the following pages. However, before beginning maintenance, follow these safety precautions: 6 FILTERING OUT TROUBLE A dirty filter will cause a loss of airflow in your duct system. When excessive loss of airflow occurs, the furnace may cycle on the safety controls. If this condition is left unattended, the furnace will eventually lockout. It is recommended that the furnace filter be checked every 3 or 4 weeks and cleaned if necessary. Never operate your furnace without a filter in place. Doing so may damage the furnace blower motor. An accumulation of dust and lint on internal parts of your furnace can cause a loss of efficiency. The air filter is normally located in the blower compartment. (See Fig. 3 or 4.) If filter has been installed in another location, contact your dealer for instructions. To inspect, clean and/or replace the air filter(s), follow these steps: 1. Turn off electrical supply to the furnace. (See Fig. 17.) 2. Remove furnace access door. (See Fig. 19.) 3. Remove blower access panel. (See Fig. 20.) NOTE: It will be necessary to remove 1 screw. FILTER(S) LOCATED IN BOTTOM: 1. Slide filter retainer sideways until it is free of latch. (See Fig. 21 and 22.) FILTER LOCATED IN SIDE: 1. Remove filter retainer from latch. (See Fig. 23.) 2. Gently remove filter and carefully turn the dirty side up (if dirty) to avoid spilling dirt from the filter. (See Fig. 24.) 3. Inspect the filter. If torn, replace it.
7 FURNACE FILTER TABLE FURNACE CASING WIDTH (IN.) FILTER SIZE* (IN.) FILTER TYPE 17-1/2 (1) 16 x 2 x 1 Cleanable 21 (1) 20 x 2 x 1 Cleanable 24-1/2 (2) 16 x 2 x 1 Cleanable * Furnace with a side return-air inlet may have a different filter size. Measure the filter to obtain the correct size NOTE: If washable filter that was shipped with the furnace has been replaced with an electronic air cleaner (EAC), refer to the EAC Owner s Manual for maintenance information. 4. Wash filter (if dirty) in a sink, bathtub, or outside with a garden hose. Always use cold tap water. A mild liquid detergent may be used if necessary. Spray water through filter in the opposite direction of airflow. Allow filter to dry.. Reinstall clean filter. 6. Reinstall filter retainer. 7. Replace blower and control access panels and turn on electrical supply to the furnace. (See Fig. 2 and 26.) COMBUSTION AREA AND VENT SYSTEM Visually inspect the combustion area and vent system before each heating season. Make sure that all PVC pipes leading into the combustion area and vent are free from any cracks and sags. Also check the combustion-air intake and vent pipes on the outside of your home for blockage. When dirt, soot, scale or rust is allowed to build up, your furnace can suffer a loss of efficiency and perform improperly. Accumulations on the main burners can result in firing out of normal sequence. This delayed ignition creates an alarmingly loud sound. If your furnace makes an especially loud noise when the main burners light, shut down your furnace and call your dealer. To inspect the combustion area and vent system, you will need a flashlight. Refer to Fig. 3 or 4, and proceed as follows: 1. Turn off gas and electrical supplies to the furnace and remove the access door. (See Fig. 9, 10, and 11.) 2. Remove burner enclosure front. (See Fig. 27 or 28.) Inspect the gas burners and ignitor area for dirt, rust, or scale If your furnace filter needs to be replaced, be sure to use the same size and type of filter that was originally supplied. Use the furnace filter table and compare your furnace size with the proper filter size. If dirt, rust, soot, or scale accumulations are found, call your dealer. Do not operate your furnace. 3. Inspect the combustion-air and vent pipes for sags, holes, cracks, or disconnections. 7
8 Do not use ethylene glycol (Prestone II antifreeze coolant or equivalent). Failure of plastic components will occur. a DANGER If holes are found in the pipes or if any portion has become disconnected, toxic fumes can escape into your home. DO NOT OPERATE YOUR FUR- NACE. Call your dealer for service. 4. Reinstall burner enclosure front.. If your furnace is free of the above conditions, replace access door and turn on electrical and gas supplies to the furnace. (See Fig. 13, 14, and 1.) 6. Start the furnace and observe its operation. Watch the burner flames to see if they are clear blue, almost transparent. (See Fig. 29.) If you observe a suspected malfunction, or the burner flames are not clear blue, call your dealer Turn off electrical supply to the furnace. (See Fig. 17.) 3. Remove furnace access door. (See Fig. 19.) 4. Remove upper inducer housing drain connection cap. (See Fig. 30.). Connect field-supplied 1/2-in. ID tube to upper inducer housing drain connection. 6. Insert field-supplied funnel into tube. 7. Pour 1 quart of antifreeze into funnel/tube. Antifreeze should run through inducer housing, overfill condensate trap, and flow into open field drain. (See Fig. 31.) 8. Remove funnel and tube from inducer housing and replace drain connection cap and clamp. 9. Replace furnace access door. (See Fig. 26.) HEADING SOUTH FOR THE WINTER? DON T FORGET YOUR FURNACE If the furnace is installed in an unconditioned space where the ambient temperatures may be 32 F or lower, freeze protection measures must be taken. Since the furnace uses a condensing heat exchanger, some water will accumulate in the unit as a result of the heat transfer process. Therefore, once it has been operated, it cannot be turned off and left off for an extended period of time when temperatures will reach 32 F or lower unless winterized. Follow these procedures to winterize your furnace: 1. Obtain propylene glycol (RV/swimming pool antifreeze or equivalent) A CHECKUP CHECKLIST Your furnace represents an important investment in your family s comfort and your home s value. To keep it performing properly and as a preventative to future problems, have a trained service specialist give your furnace a professional check-up annually. The following checklist can be used as a guideline to proper service: Inspect all flue gas passages, burners, heat exchangers, coupling box(es), and inducer assembly. Inspect all combustion-air and vent piping inside structure and pipe terminations outside the structure. Check gas pipes leading to and inside of your furnace for leaks. Inspect and clean the blower motor and wheel. NOTE: The inducer and blower motors are pre-lubricated and require no additional lubrication. These motors can be identified by the absence of oil ports on each end of the motor. Inspect and change or clean air filter(s) if necessary. Inspect all supply- and return-air ducts for obstructions, air leaks, and insulation. Remedy any problem when necessary.
9 Inspect the return-air duct connection(s) at the furnace to ensure it is physically sound, sealed to the furnace casing, and terminates outside the space containing the furnace. Inspect electrical wiring, connections, and components for loose connections. Perform an operational checkout to determine whether your furnace is working properly and if it requires adjustments. Inspect all condensate drain tubes and condensate trap assembly for leaks. The condensate removal system should be cleaned annually by a qualified service agency. Refer to the Service and Maintenance Instructions for further information. Examine the physical support of the furnace. Support should be sound with no cracks, sagging, gaps, etc. around the base. Check furnace for any obvious signs of deterioration. BEFORE YOU REQUEST A SERVICE CALL If your furnace is not operating or not performing properly, you may save the expense of a service call by checking a few things yourself before calling for service. FOR INSUFFICIENT AIRFLOW: Check for dirty air filter(s). Check for blocked return-air or supply-air grilles throughout your home. Ensure they are open and unobstructed. If problem still exists, call your dealer for service. IF FURNACE FAILS TO OPERATE: Follow this checklist step by step, advancing to the next step only if furnace fails to start. Check thermostat for proper temperature. Is thermostat set above room temperature? Is thermostat switch on HEAT? Check fuses and circuit breakers. Is electrical supply on? Is manual shut-off valve in gas supply pipe in open position? (Follow start-up procedures if you open gas valve.) NOTE: Turn off electrical supply before continuing with checklist. Is control knob on gas valve in ON position? (Follow startup procedures if you must reset knob to ON.) Check manual reset flame rollout switch located on the burner box. (See Fig. 2 or 3.) If furnace has experienced high temperature conditions, this switch will shut off the furnace. Reset it by pushing the button on the switch. If it trips again, shut down the furnace and call for service. See section Shutting Down Your Furnace in this manual. Check for obstructions around the vent termination. If the furnace still fails to operate, call your service representative. For your convenience, record the furnace product and serial numbers on page 2. Should you ever require service, you will have ready access to the information needed by your service representative. This furnace has an LED operation and fault code display to aid the installer, service technician, or homeowner while installing or servicing the unit. The LED code can be seen by removing the access door and viewing the LED(s) through the view port in the blower access panel. NOTE: Removing the blower access panel or turning off the 11-v electrical power supply will terminate LED diagnostic code display. To decipher the meaning of the LED code, and suggested action, the following cross-reference can be used. MODEL 8MCA and 8MXA DIAGNOSTIC CHART (See Fig. 3.) FAULT CODE FAULT CODE DESCRIPTION CHECKLIST 13 or 33 Limit Switch Lockout Check for dirty air filter. Check for blocked return-air or supply-air grilles. 14 or 34 Ignition Lockout or Ignition Proving Fault Check to be sure manual shut-off valve in gas supply pipe is in the open position. (Follow start-up procedure if you open gas line.) NOTE: Turn off the electrical supply and remove access doors before continuing with this checklist. Check to be sure control knob on gas valve is in ON position. (Follow start-up procedures if you must reset dial to ON.) 24 Furnace Fuse Open Check for blown fuse and possible short in 24-v wiring. 31 Pressure Switch Not Closed Check to make sure that all PVC pipes leading into the combustion-air intake and vent/exhaust are free from any cracks and sags. Also check the combustion-air intake and vent/exhaust pipes on the outside of your home for blockage. 12, 21, 22, or 23 No Fault Code Signaled Any Other Fault Code Furnace Fails to Operate and No Fault is Signaled Call dealer for service. Check thermostat for proper temperature setting. Check for blown fuses and circuit breakers. Check to be sure blower access panel is properly in place. NOTES: 1. Light on continuously means control has power and working properly. 2. The status codes are a 2 digit number. The first digit is determined by the number of short flashes of the light and the second digit is determined by number of long flashes of the light. 9
10 FAULT CODE FAULT CODE DESCRIPTION CHECKLIST MODEL 8MVP DIAGNOSTIC CHART (See Fig. 4.) 12 Blower Calibration Lockout Check for dirty air filter. 13 or 33 Limit Switch Lockout Check for blocked return-air or supply-air grilles. Turn electrical supply off, then back on. Set the thermostat switch to call for heat. 14 or 34 Ignition Lockout or Ignition Proving Fault Check to be sure manual shut-off valve in gas supply pipe is in open position. (Follow start-up procedure if you open gas line.) NOTE: Turn off the electrical supply and remove access doors before continuing with this checklist. Check to be sure control knob on gas valve is in ON position. (Follow start-up procedures if you must reset dial to ON). Check for disconnected ground wire. 24 Furnace Fuse Open Check for blown fuse and possible short in 24-v wiring. 31, 32, or 43 Pressure Switch Fault 42 Inducer Outside Valid Speed Range 44 Blower Calibration Fault Check to make sure that all PVC pipes leading into the combustion-air intake and vent/exhaust are free from any cracks and sags. Also check the combustion-air intake and vent/exhaust pipes on the outside of your home for blockage. Check for dirty air filter(s). Check for blocked return- or supply-air grilles. NOTE: In zoned applications, fault 44 may flash during operation when a single zone is calling for heat. When other zones call for heat, or the unit cycles, the fault should clear itself. Call for service if fault 12 develops. 21, 22, 23, or 41 No Fault Code Signaled Any Other Fault Code or Either of the Red Lights On Continuously Furnace Fails to Operate and No Fault is Signaled Call dealer for service. Check thermostat for proper temperature setting. Be sure thermostat switch is on HEAT. Check for blown fuses and circuit breakers. Check to be sure blower access panel is properly in place. NOTES: 1. Red light 1 on continuously means furnace is operating in emergency heat. 2. Red light 2 on continuously means the microprocessor board has malfunctioned. 3. Yellow light on continuously means furnace is operating in high heat. 4. Green light on continuously means furnace is operating in low heat.. The status codes are a 2 digit number. The first digit is determined by the number of flashes of the yellow light and the second digit is determined by number of flashes of the green light. TO OBTAIN INFORMATION ON PARTS: Consult your installing dealer or classified section of your local telephone directory under the Heating Equipment or Air Conditioning Contractors & Systems headings for dealer listing by brand name. Have available the Model No., Series Letter & Serial No. of your equipment to insure correct replacement part. Carrier Corporation Syracuse, New York Manufacturer reserves the right to discontinue, or change at any time, specifications or designs without notice and without incurring obligations. Copyright 1994 Carrier Corporation Form: OM8-67 Replaces: OM8-61 Printed in the U.S.A PC 101 Catalog No
USER S INFORMATI MANUAL MODEL 40MAV, 0MAV, MAV CDENSING GAS FURNACE NOTE TO INSTALLER: This manual must be left with the equipment user. As an ENERGY STAR SM Partner, Bryant Heating & Cooling Systems has
48SS 48SX Combination Gas Heating/Electric Cooling Units A Guide To Operating and Maintaining Your Gas Heating/Electric Cooling Unit NOTE TO INSTALLER This manual should be left with the equipment owner.
USER S INFORMATI MANUAL USER S INFORMATI MANUAL MODELS 7LAV, 76CAV DOWNFLOW/HORIZTAL and 8KAV, 95CAV UPFLOW GAS FURNACE NOTE TO INSTALLER: This manual must be left with the equipment user.! WARNING: If
Single-- Package Rooftop Unit (RTU) Gas Heating /Electric Cooling Units With R-- 410A Refrigerant User s Information Manual NOTE: Read the entire instruction manual before starting the installation. ELECTRICAL
UPFLOW / HORIZONTAL / DOWNFLOW HIGH EFFICIENCY GAS FURNACE Owner s Manual NOTE TO INSTALLER: THIS MANUAL MUST BE LEFT WITH THE EQUIPMENT USER. USER: Please read all instructions in the manual and retain
CENTRAL AIR CONDITIONER A GUIDE TO OPERATING AND MAINTAINING YOUR RESIDENTIAL AIR CONDITIONING UNIT. NOTE TO INSTALLER: THIS MANUAL SHOULD BE LEFT WITH THE EQUIPMENT USER. WELCOME TO EFFICIENT HOME COOLING
Heat Pump USER S INFORMATION MANUAL FOR THE OPERATION AND MAINTENANCE OF YOUR NEW RESIDENTIAL HEAT PUMP NOTE TO INSTALLER: THIS MANUAL MUST BE LEFT WITH THE EQUIPMENT USER. WELCOME TO EFFICIENT YEAR-ROUND
USER S INFORMATION MANUAL CENTRAL AIR CONDITIONER with PURON REFRIGERANT NOTE TO INSTALLER: This manual must be left with the equipment user. WELCOME TO EFFICIENT HOME COOLING COMFORT Congratulations on
USER S INFORMATION MANUAL UPFLOW, DOWNFLOW, UPFLOW/HORIZONTAL & HORIZONTAL ONLY INDUCED DRAFT GAS FURNACES Recognize this symbol as an indication of Important Safety Information If the information in this
CASE STUDY 1 COMMISSIONING A GAS FIRED STEAM BOILER A steam boiler has been built and installed at a factory for the provision of process steam. The following lists the requirements used in the commissioning
Operator: Save these instructions for future use! FAILURE TO READ AND FOLLOW ALL INSTRUCTIONS CAREFULLY BEFORE INSTALLING OR OPERATING THIS CONTROL COULD CAUSE PERSONAL INJURY AND/OR PROPERTY DAMAGE. DESCRIPTION
TM Water Dispenser Owner s Manual 500 Series IMPORTANT: This manual includes important safety material; please read all instructions before plugging power supply cord into receptacle. STOP & READ DIRECTIONS
3 & cooling 17 heating 2010 PulteGroup, Inc. All Rights Reserved. condensation The line that drains condensed moisture away from your heating and/or cooling unit needs periodic maintenance. Air conditioning
THREE Heating and Cooling 17 Condensation Drain Line The line that drains condensed moisture away from your heating and/or cooling unit needs periodic maintenance. If your unit is located in the attic,
Owner s Information Manual Air Conditioning ystem NOTE TO EQUIPMENT OWNER: For your convenience, please record the model and serial numbers of your new equipment in the space provided. This information,
NATURAL GAS TO PROPANE CONVERSION KIT 090 INSTALLATION INSTRUCTIONS FOR ALTITUDES 0 -,00 FT. ONLY PROPANE CONVERSION KIT SAFETY... INSTALLATION REQUIREMENTS... Tools and Parts... LP Gas Requirements...
coaching Whitepaper: Home Maintenance Tips for First Time Homebuyers By: John B. Elson Technical Leader and Director of Education Inspect-It 1 st Property Inspection March, 2010 Inspect-It 1 st Property
LGB Gas fired boiler Control Supplement LGB-4-4 & LGB-5-5 Universal Control System -5 Series 2 Propane gas Contents Installation... 2 Conversion (Natural/Propane)... 2 Gas piping...3 Wiring...4 Operating
USER INSTRUCTIONS FOR GET PORTABLE 12k BTU AIR CONDITIONER MODEL No. GPACU12HR CONTENTS Introduction Safety Notes Identification of parts Installation instructions Operation instructions Maintenance Troubleshooting
2011 Lennox Industries Inc. Dallas, Texas, USA 506789 01 08/2011 MS7 Single Zone Mini Split System Air Conditioners and Heat Pumps This manual is the property of the homeowner and must be left with the
USER INSTRUCTIONS FOR 10 LITRE PORTABLE DEHUMIDIFIER MODEL NO. DHMD102 THANK YOU FOR CHOOSING YOUR NEW DEHUMIDIFIER. BEFORE USING THE UNIT READ THESE INSTRUCTIONS FULLY AND RETAIN THEM FOR FUTURE REFERENCE
For the user Instructions for use ecomax Wall hung room sealed fan assisted condensing boilers ecomax 63/ E ecomax 68/ E ecomax 6/ E ecomax 635 E ecomax 84/ E ecomax 88/ E ecomax 835 E GB Table of contents
USER S INFORMATION MANUAL HEAT PUMPS with Puron Refrigerant Single Speed, Two-Speed TWO-SPEED NOTE TO INSTALLER: This manual must be left with the equipment user. WELCOME TO EFFICIENT YEAR- ROUND COMFORT
San josé OWNER S MANUAL Assembling & operating manual San josé 30 mbar - PORTABLE GAS BARBECUE 1. 2. 3. Improper installation, adjustment, alteration, service or maintenance can injury or property damage.
Service Literature G26 SERIES UNITS G26 series units are high-efficiency upflow gas furnaces manufactured with DuralokPlust aluminized steel clamshell-type heat exchangers. G26 units are available in heating
FV-05VS3 FV-08VS3 FV-10VS3 2-3 5 (Joist Mounting) (Wall Mounting) (Cleaning) 5-6 6 7 Back cover Back cover Back cover For Your Safety To reduce the risk of injury, loss of life, electric shock, fire, malfunction,
Instruction Sheet 07-2013 Installation Instructions for Alarm Module Kit A043F059 1 Introduction The information contained within is based on information available at the time of going to print. In line
Boiler Preparation, Start-Up and Shutdown Learning Outcome When you complete this module you will be able to: Describe the basic preparation of a boiler for start-up, and the start-up and shutdown procedures.
32-5038-10 User s Information Guide Trane CleanEffects TM Whole House Air Filtration System Congratulations Your TRANE CleanEffects TM air filtration system is the most advanced, innovative and effective
Air Conditioner Water Heater - A Product of HotSpot Energy LLC PLEASE READ THIS BEFORE YOU INSTALL THE UNIT 1. This air conditioner must be installed and/or repaired by a qualified technician. If you perform
8 716 473 216-00.3O Gas boiler WBN 6000-30-H-E-N/L-S2400 Operating instructions for the end customer en 2 Contents Contents 1 Key to symbols and safety instructions................... 2 1.1 Key to symbols..................................
Evaluate, Clean, and Tune Guidance The Evaluate, Clean and Tune (ECT) process serves three essential purposes in the Weatherization Assistance Program (WAP). The first is to evaluate the existing system
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
Use and Care Manual Model CPA12KH AIR CONDITIONER Introduction Thank you for choosing this air conditioner to provide you and your family with all of the "Home Comfort" requirements for your home, cottage
15 / PROPANE GAS SYSTEM Propane gas is used to operate the range, oven, furnace, water heater, and the refrigerator (when 120-volt AC power is unavailable). The gas is stored in portable DOT cylinders.
Condensing Water Heater Operation Manual Model NPE-180A/ 210A/ 240A NPE-180S/ 210S/ 240S * Lead Free Keep this manual near this water heater for future reference whenever maintenance or service is required.
EVANS ELECTRONIC TEMPERATURE CONTROL TROUBLESHOOTING GUIDE for systems equipped with electric coolant valve and external PC board. This Troubleshooting Guide covers the electric coolant valve and control
Specifications are subject to change without notice according to Carrier Policy of continuous development. 03501019 Rev. (0) -2009 Thank you for selecting Carrier Air Conditioner You can be justifiably
SWIMMING POOL HEAT PUMP Installation & User Manual Model HP40B HP50B HP65B Hayward Pool Products Canada, Inc. T: 1-888-238-7665 www.haywardpool.ca CONTENT I. Application 4 II. Features 4 III. Technical
OTF Oil Fired Pool Heater Installation Operation Maintenance Manual Service Policy 722010 Congratulations on the purchase of your new pool heater. In order to maintain peak performance of your pool heater
Tankless Water Heater USER S INFORMATION MANUAL Models WGRTNG199 / WGRTLP199 WGRTCNG199 / WGRTCLP199 NOTICE: Westinghouse reserves the right to make product changes or updates without notice and will not
N8MXL Product Specifications 80% ECM Single Stage Heating Furnace EASIER TO SELL 80% AFUE Flame roll out sensors standard Category I venting Blocked vent switch 24 VAC humidifier terminal Electronic air
SECTION 23 81 03 - PACKAGED ROOFTOP AIR CONDITIONING UNITS NON-CUSTOM PART 1 - GENERAL 1.1 SUMMARY A. Section Includes: 1. Packaged rooftop air conditioning unit (5 tons and smaller). 2. Roof curb. 1.2
USER S INFORMATION MANUAL UPFLOW/DOWNFLOW/HORIZONTAL CONDENSING GAS FURNACES WARNING PROPOSITION 65: THIS FURNACE CONTAINS FIBERGLASS INSULATION. RESPIRABLE PARTI- CLES OF FIBERGLASS ARE KNOWN TO THE STATE
USERS GUIDE LOGIC Combi 24, 30, 35 For installation guide see reverse of book When replacing any part on this appliance, use only spare parts that you can be assured conform to the safety and performance
Portable Air Conditioner OWNER S MANUAL Read these instructions before use 8 Model: MN12CES / MN10CESWW Voltage rating: 120V~60Hz Power rating : 1100W (MN12CES) Power rating : 900W (MN10CESWW) Customer
6302 6959 02/2006 GB For the user Operating instructions Logano G215 WS Oil and gas-fired boilers Please read thoroughly before use. Overview Regulations and directives Installation: 90/396/EEC gas appliance
THC 85 INDUSTRIAL / COMMERCIAL SPACE HEATER Certified to / Certifié à CGA 2.14 M2000 Conforms to / Conforme à ANSI std Z83.7 2000 Suitable for indoor or outdoor installation / Unvented / Unattended Type
Portable Air Conditioner OWNER S MANUAL Read these instructions before use Model: MM14CCS Customer Support : 1-800-474-2147 Voltage rating: 115V~60Hz Power rating : 1400W For product inquiries or support
HEAT PUMP FREQUENTLY ASKED QUESTIONS HEAT PUMP OUTDOOR UNIT ICED-UP DURING COLD WEATHER: It is normal for a heat pump to have a build up of white frost on the outside coil during cold damp weather. The
http://waterheatertimer.org/how-to-troubleshoot-gas-water-heater.html APPLY POWER TO APPLIANCE FIELD WIRING CORRECT? DPLAY ERROR CODE 1 OR 2 Intelli-Vent TM Sequence of Operation REQUEST FOR HEAT PRESENT?
Installation instructions Ventilation Fan Model TY-110-A Model TY-110-B Read and save these instructions. Please read these instructions carefully before attempting to install, operate or service the Ventilation
NewAir AC-10000E, AC-10000H Portable Air Conditioner Owner s Manual PLEASE READ AND SAVE THESE INSTRUCTIONS BEFORE USE GENERAL SAFETY INSTRUCTIONS: ALWAYS OPERATE THE UNIT IN AN UPRIGHT POSITION AND PLACE
READ INSTRUCTIONS CAREFULLY: READ AND FOLLOW ALL INSTRUCTIONS. PLACE INSTRUCTIONS IN A SAFE PLACE FOR FUTURE REFERENCE. ONLY USE IN A WELL VENTILATED AREA USER MANUAL FOR GAS AND QUARTZ TUBE HEATER (R-7010)
AAON RM SERIES HEATING COOLING & COMBINATION ROOFTOP UNITS USERS INFORMATION MANUAL 7-2003! WARNING If the information in this manual is not followed exactly, a fire or explosion may result causing property
R-410A Duct Free Split System Air Conditioner and Heat Pump Product Family: DFS4(A/H)-System, DFC4(A/H)3-Outdoor, DFF4(A/H)H-Indoor Please read the operating instructions and safety precautions carefully
SU SERIES UPFLOW PACKAGED TERMINAL AIR CONDITIONERS Heating and Cooling Unit Cooling - Only Unit INSTALLATION & OPERATION MANUAL Effective February 1985 (Revision Date: April 2009) This manual supersedes
Elite Fire Tube Combi Floor and Wall Mount Models USER S INFORMATION MANUAL Models EFTC-140F / 199F EFTC-140W / 199W NOTICE: HTP reserves the right to make product changes or updates without notice and
Use & Care Guide X AIR CONDITIONERS ACM052 ACM062 ACM072 Contents Page Important Safety Instructions....2 Operating Your Air Conditioner....3 Starting your air conditioner......3 Changing air direction....3
Portable Evaporative Air Cooler OWNER S MANUAL Read and save these instructions before use Model: CL48PM Power rating: 130 Watts Voltage rating: 230 Volt, 50Hz Made in P.R.C. QUICK START GUIDE Fill with
GE Appliances Dehumidifiers Owner s Manual AHG20 SAFETY PRECAUTIONS When using this dehumidifier, always follow basic safety precautions, including the following: Use this appliance only for its intended
m TM Water Dispenser Owner s Manual 300m Series IMPORTANT: This manual includes important safety material; please read all instructions before plugging power supply cord into receptacle. 1 Load water bottle
Portable Air Conditioner Owner's Manual Model:3 in 1 12,000 Btu/h Series 3 Please read this owner s manual carefully before operation and retain it for future reference. CONTENTS 1. SUMMARY...1 2. PORTABLE
Propane Conversion Kit Supersedes: 145.25-IOM2 (708) Form 145.25-IOM2 (908) PROPANE CONVERSION KIT INSTALLATION MANUAL "LPKIT " - PROPANE CONVERSION KIT Kits are available for field conversion from natural
Consulting, Resource, Education, Training, and Support Services for Home Inspectors A candle loses no light when it lights another candle. Gas-Fired, Residential Storage Type Water Heaters Most inspectors
USER GUIDE VB0156 MODELS CONSTRUCTO 1.5* CONSTRUCTO 2.0 READ AND SAVE THESE INSTRUCTIONS *This product earned the ENERGY STAR by meeting strict energy efficiency guidelines set by Natural Resources Canada
Low Refrigerant Charge Low Side Reads Low High Side Reads Low 2 102 You see bubbles in the sight glass. The air from the vents in the vehicle compartment is only slightly cool. Insufficient refrigerant
Heating, Ventilation, Air Conditioning and Refrigeration (HVACR) I. Demonstrate safety skills in typical HVACR work situations to NATE Core Installer Knowledge Areas for Technician Excellence for Safety
CHAPTER 18 Boiler Safety compliance Boiler is an important utility in factories. It is used to generate steam. The generated steam is distributed through pipes to feed various equipment in the factory.
ELECTRICIANS GUIDE To ensure that the system is installed properly, provide your electrician with these instructions. ELECTRICAL INSTALLATION A qualified and licensed electrician in accordance with the
WHYNTER BUILT-IN ICE MAKER INSTRUCTION MANUAL MODEL# : UIM-155 1. ICE BUCKET 2. FOOT 3. ON/OFF SWITCH 4. DOOR PARTS OVERVIEW WARNING TO REDUCE THE RISK OF FIRE, ELECTRICAL SHOCK, OR INJURY WHEN USING YOUR
Baxi Combi 8e & 15e Please keep these instructions safe. Should you move house, please hand them over to the next occupier. Gas Fired Wall Mounted Combination Boiler User s Operating Instructions Natural
ELECTRIC FIREPLACES SAFETY INFORMATION AND INSTALLATION MANUAL INSERT-26-3825, INSERT-30-4026, INSERT-33-4230 Read these instructions completely before beginning installation. Failure to follow them could
American Fireglass Outdoor Fire pit kit information General instructions/warnings for outdoor gas pan and burner systems We strongly recommend that our burner products be installed by a licensed and certified
MODE ALARM Portable Air Conditioner OWNER S MANUAL Read these instructions before use 8 Model: MF08CESWW Voltage rating: 115V~60Hz Power rating : 800W Customer Support : 1-800-474-2147 For product inquiries
Contents GENERAL SAFETY INFORMATION 1 READ PRIOR TO STARTING THIS EQUIPMENT 1 DESCRIPTION 2 INSTALLATION 3 OPERATION 5 MAINTENANCE 6 FLOW SCHEMATIC 7 TROUBLESHOOTING 8 0 GENERAL SAFETY INFORMATION 1. This
72 Beadel Street Brooklyn, NY 11222 phone 718/ 388-5650 Outside New York State 800/ 221-5032 facsimile 718/ 388-5860 www.townfood.com SR-24M SR-24C SR-24-G SR-18-F front gas manifold SR-18-R rear gas manifold
Steam Humidifier Model 800 Residential Steam Humidifier Owner s Manual Includes Safety & Operating Instructions and Warranty Information READ AND SAVE THESE INSTRUCTIONS TABLE OF CONTENTS Safety Cautions...
Installation Sheets Manual 121 Gas Combustion Combination Controls and Systems Section G Technical Bulletin Issue Date 0300 Intermittent Pilot Ignition Controls Figure 1: Intermittent Pilot Ignition Control