1 R40A SPLIT SERIES DC INVERTER Models ECO905SINV ECO205SINV ECO805SINV Read This Manual Inside you will find many helpful hints on how to use and maintain your air conditioner properly. Just a little preventative care on your part can save you a great deal of time and money over the life of your air conditioner. You'll find many answers to common problems in the chart of troubleshooting tips. Review the chart of Troubleshooting Tips before calling your service engineer.
2 DISPOSAL When using this air conditioner in the European countries, the follow information must be followed: DISPOSAL: Do not dispose this product as unsorted waste. It is prohibited to dispose of this appliance in domestic household waste. For disposal, : A) Contact your local council for disposal. B) The manufacture will take back the old appliance for disposal when you replace with a new product. C) Old products contain valuable resources, which should be recycled as scrap metal. Wild disposal of waste in forests and landscapes endangers your health when hazardous substances leak into the ground-water and find their way into the food chain.
3 CONTENTS SAFETY PRECAUTIONS... PARTS NAMES... 4 OPERATING TEMPERATURE... 5 MANUAL OPERATION... 5 OPTIMAL OPERATION... 5 ADJUSTING AIR FLOW DIRECTION... 6 HOW THE AIR CONDITIONER WORKS... 7 MAINTENANCE... 8 OPERATION TIPS... 0 TROUBLESHOOTING TIPS... 2 Read This Manual Inside you will find many helpful hints on how to use and maintain your air conditioner properly. Just a little preventative care on your part can save you a great deal of time and money over the life of your air conditioner. You'll find many answers to common problems in the chart of troubleshooting tips. If you review the chart of Troubleshooting Tips first, you may not need to call for service. CAUTION Contact an authorised service technician for repair or maintenance of this unit. Contact the installer for installation of this unit. The air conditioner is not intended for use by young children or invalids without supervision. Young children should be supervised to ensure that they do not play with the air conditioner. If the power cord is to be replaced, replacement work shall be performed by authorised personnel only. Installation work must be performed in accordance with the national wiring standards by authorised personnel only.
4 Safety Precautions To prevent injury to the user or other people and property damage, the following instructions must be followed. Incorrect operation due to ignoring of instructions may cause harm or damage. The seriousness is classified by the following indications. WARNING This symbol indicates the possibility of death or serious injury. CAUTION This symbol indicates the possibility of injury or damage to property. Meanings of symbols used in this manual are as shown below. Never do this. Always do this. Connect with the power properly. Otherwise, it may cause electric shock or fire due to excess heat generation. Do not modify power cord length or share the outlet with other appliances It may cause electric shock or fire due to heat generation. Always ensure effective earthing. No earthing may cause electric shock. Disconnect the power if strange sounds, smell, or smoke comes from it. It may cause fire and electric shock. Keep firearms away. It may cause fire. WARNING Do not operate or stop the unit by inserting or pulling out the power plug. It may cause electric shock or fire due to heat generation. Do not operate with wet hands or in damp environment. It may cause electric shock. Do not allow water to run into electric parts. It may cause failure of machine or electric shock. Do not use the socket if it is loose or damaged. It may cause fire and electric shock. Do not use the power cord close to heating appliances. It may cause fire and electric shock. Do not damage or use an unspecified power cord. It may cause electric shock or fire. Do not direct airflow at room occupants only. This could damage your health. Always install circuit breaker and a dedicated power circuit. No installation may cause fire and electric shock. Do not open the unit during operation. It may cause electric shock. Do not use the power cord near flammable gas or combustibles, such as gasoline, benzene, thinner, etc. It may cause an explosion or fire. Ventilate room before operating air conditioner if there is a gas leakage from another appliance. It may cause explosion, fire and, burns. Do not disassemble or modify unit. It may cause failure and electric shock.
5 CAUTION When the air filter is to be removed, do not touch the metal parts of the unit. Do not clean the air conditioner with water. Ventilate the room well when used together with a stove, etc. It may cause an injury. Water may enter the unit and degrade the insulation. It may cause an electric shock. An oxygen shortage may occur. When the unit is to be cleaned, switch off, and turn off the circuit breaker. Do not put a pet or house plant where it will be exposed to direct air flow. Do not use for special purposes. Do not clean unit when power is on as it may cause fire and electric shock, it may cause an injury. This could injure the pet or plant. Do not use this air conditioner to preserve precision devices, food, pets, plants, and art objects. It may cause deterioration of quality, etc. Stop operation and close the window in storm or hurricane. Hold the plug by the head of the power plug when taking it out. Turn off the main power switch when not using the unit for a long time. Operation with windows opened may cause wetting of indoor and soaking of household furniture. Failue to do so may cause electric shock and damage. It may cause failure of product or fire. Do not place obstacles around air-inlets or inside of air-outlet. Ensure that the installation bracket of the outdoor appliance is not damaged due to prolonged exposure. It may cause failure of appliance or accident. If bracket is damaged, there is concern of damage due to falling of unit. Always insert the filters securely. Clean filter once every two weeks. Operation without filters may cause failure. Do not use strong detergent such as wax or thinner. Use a soft cloth for cleaning. Appearance may be deteriorated due to change of product color or scratching of its surface. Do not place heavy object on the power cord and take care so that the cord is not compressed. There is danger of fire or electric shock. Do not drink water drained from air conditioner. It contains contaminants and could make you sick. Use caution when unpacking and installing. Sharp edges could cause injury. If water enters the unit, turn the unit off at the power outlet and switch off the circuit breaker. Isolate supply by taking the power-plug out and contact a qualified service technician. 2
6 Prior to Operation. Contact an installation specialist for installation. 2. Make sure the unit is grounded efficiently. 3. Do not use a damaged or non-standard power cord. 4. Do not share the same outlet with other appliances. 5. Do not use an extension cord. 6. Do not start/stop operation by shutting off the power supply. Usage. Exposure to direct airflow for an extended period of time could be hazardous to your health. Do not expose occupants, pets, or plants to direct airflow for extended periods of time. 2. Due to the possibility of oxygen deficiency, ventilate the room when used together with stoves or other heating devices. 3. Do not use this air conditioner for non-specified special purposes (e.g. Preserving precision devices, food, pets, plants, and art objects). Usage in such a manner could harm such property. Cleaning and maintenance. Do not touch the metal parts of the unit when removing the filter. Injuries can occur when handling sharp metal edges. 2. Do not use water to clean inside the air conditioner. Exposure to water can destroy the insulation, leading to possible electric shock. 3. When cleaning the unit, first make sure that the power and circuit breaker are turned off. Service For repair and maintenance, contact your authorised service dealer. 3
7 AUTO COOL DRY HEAT SWING AIR DIRECTION TEMP ON/OFF SLEEP RESET LOCK ( C) FAN HIGH MED LOW TIMER ON TIMER OFF LED DISPLAY TURBO Parts names Indoor unit Outdoor unit MODE FAN SPEED SET TEMPERATURE 9 OPERATING INSTRUCTIONS Indoor unit. Front panel 2. Air inlet 3. Air filter 4. Air outlet Horizontal air flow grille Vertical air flow louver 7. Display panel 8. Remote controller Outdoor unit 9. Connecting pipe, drain hose 0. Air inlet (side and rear). Air outlet NOTE: All the pictures in this manual are for explanation purpose only. Your air conditioner may be slightly different. The actual shape shall prevail. Indicator Lights on Display panel The display panel on the indoor unit would look like one of the following: Signal receptor auto AUTO indicator: This indicator illuminates when the air conditioner is in AUTO operation. DEFROST Indicator (For cooling& heating model only): This indicator illuminates when the air conditioner starts defrosting automatically or when the warm air control feature is activated in heating operation. DIGITAL DISPLAY: Displays the current setting temperature when the air conditioner is in operation. OPERATION indicator: The indicator flashes once every second after power is on and illuminates when the air conditioner is in operation. TIMER indicator: The indicator illuminates when TIMER is set ON/OFF. 4
8 OPERATING TEMPERATURE Temperature Mode Cooling operation Room temperature 7 C~ 32 C ~ Outdoor temperature 8 C 43 C Heating operation Drying operation 0C~ 30C 7 C 32 C ~ -7 C~ 24 C C ~ 43 C. If air conditioner is used outside of the above conditions, certain safety protection features may come into operation and cause the unit to function abnormally. 2. Room relative humidity less than 80%. If the air conditioner operates in excess of this figure, the surface of the air conditioner may attract condensation. Please sets the vertical air flow louver to its maximum angle (vertically to the floor), and set HIGH fan mode. 3. Optimum performance will be achieved within these operating temperature. MANUAL OPERATION Manul operation can be used temporarily in case you can not find the remote controller or test running purpose or maintenance necessary. Panel Manual control button AUTO/COOL 2 3 Open and lift the front panel up to an angle until it remains fixed with a clicking sound. One press of the manual control button will lead to the forced AUTO operation. Close the panel firmly to its original position. CAUTION: Push the button to initiate forced AUTO mode, push again to stop. If push the button twice within five seconds, the unit will operate in forced COOL mode. This function is used for testing purposes only. Do not choose it unless it is necessary. To restore the remote controller operation, use the remote controller directly. OPTIMAL OPERATION To achieve optimal performance, please note the following: Adjust the air flow direction correctly so that it is not directed on people. Adjust the temperature to achieve the highest comfort level. Do not adjust the unit to excessive temperature levels. Close doors and windows on COOL or HEAT modes, or performance may be reduced. Use TIMER ON button on the remote controller to select a time you want to start your air conditioner. 5
9 RESET LOCK AUTO COOL DRY HEAT TEMP R FAN HIGH MED LOW CANCEL Do not put any object near air inlet or air outlet, as the efficiency of the air conditioner may be reduced and the air conditioner may stop running. Clean the air filter periodically, otherwise cooling or heating performance may be reduced. Do not operate unit with horizontal louvre in closed position. ADJUSTING AIR FLOW DIRECTION Adjust the air flow direction properly otherwise, it might cause discomfort or cause uneven room temperatures. Adjust the horizontal louver using the remote controller. Adjust the vertical louver manually. Adjusting the Vertical Air Flow Direction (up - down) The air conditioner automatically adjusts the vertical air flow direction in accordance with the operating mode. MODE ON/OFF FAN SWING ECONOMY TIMER DIGITAL DISPLAY To set the vertical air flow direction Perform this function while the unit is in operation. Keep pressing the AIR DIRECTION button on the remote controller to move the louver to the desired direction. Adjust the vertical air flow direction to the desired direction. In subsequent operations, the vertical air flow is automatically set in the direction to which you adjusted the louver by pressing the AIR DIRECTION button. Lever To set the horizontal air flow direction (left - right) Adjust the vertical louver manually using the lever on the left or right side of the vertical louver arm (Depending on model). Take care not to catch fingers on the fan, horizontal louver or to damage vertical louvers. When the air conditioner is in operation and the horizontal louver is in a specific position, move the lever at left (or right, depending on model) end of the air outlet to the desired position. To automatically swing the air flow direction (up - down) Perform this function while the air conditioner is in operation. Press the SWING button on the remote controller. To stop the function, press the SWING button again. Press AIR DIRECTION button to lock louver in desired position. 6
10 CAUTION The AIR DIRECTION and SWING buttons will be disabled when the air conditioner is not in operation (including when the TIMER ON is set). Do not operate the air conditioner for long periods with the air flow direction set downward in cooling or dry mode. Otherwise, condensation may occur on the surface of the horizontal louver causing moisture to drop on to the floor or on furnishings. Do not move the horizontal louver manually. Always use the AIR DIRECTION or SWING button. If you move this louver manually, it may malfunction during operation. If the louver malfunctions, stop the airconditioner once and restart it. When the air conditioner is started immediately after it was stopped, the horizontal louver might not move for approximately 0 seconds. Open angle of the horizontal louver should not be set too small, as COOLING or HEATING performance may be impaired due to too restricted air flow area. Do not operate unit with horizontal louver in closed position. When the air conditioner is connected to power (initial power), the horizontal louver may generate a sound for 0 seconds, this is a normal operation. HOW THE AIR CONDITIONER WORKS Set Temperature Set Temperature Press Sleep button hour Press Sleep button Cooling hour hour hour Heating AUTOMATIC OPERATION When you set the air conditioner in AUTO mode, it will automatically select cooling, heating(cooling/heating models only), or fan only operation depending on what temperature you have selected and the room temperature. The air conditioner will control room temperature automatically round the temperature point set by you. If the AUTO mode is uncomfortable, you can select desired conditions manually. ECONOMIC OPERATION When you push SLEEP button during cooling, heating (cooling only type without),or AUTO operation, the air conditioner will automatically increase (cooling) or decrease (heating) per hour. The set temperature will be steady 2 hours later. The fan speed will be automatically controlled. Room temperature Cooling Fan only Cooling set temperature Fan only Cooling Time DRYING OPERATION The dry mode will automatically select the drying operation based on the difference between the set temperature and the actual room temperature. The temperature is regulated while dehumidifying by repeating turning on and off of the cooling operation or fan only. The fan speed is LOW. DRYING operation 7
11 MAINTENANCE Household Drain Cleaner No WARNING It is necessary to stop the air conditioner and disconnect the power supply before cleaning. Cleaning the indoor unit and remote controller Thinner CAUTIONS Use a dry cloth to wipe the indoor unit and remote controller. A cloth dampened with cold water may be used on the indoor unit if it is very dirty. The front panel of the indoor unit can be removed and cleaned with water. Then wipe it with a dry cloth. Do not use a chemically treated cloth or duster to clean the unit. Do not use benzine, thinner, polishing powder, or similar solvents for cleaning. These may cause the plastic surface to crack or deform. Cleaning the air filter A clogged air filter reduces the cooling efficiency of this unit. Please clean the filter once every 2 weeks.. Lift the indoor unit panel up to an angle until it stops with a clicking sound. 2. Take hold of the handle of the air filter and lift it up slightly to take it out from the filter holder, then pull it downwards. Filter Handle 3. Remove the AIR FILTER from the indoor unit. Clean the AIR FILTER once two weeks. Clean the AIR FILTER with a vacuum cleaner or water, then dry it up in cool place. 4. Remove the air freshening filter from its support frame Clean the air freshening filter at least once a month, and replace it every 4-5 months. Clean it with vacuum cleaner, then dry it in cool place. 8
12 5. Remove the Plasma dust collector from its support frame as shown in the Figure on the left(on some models). Air freshening filter Plasma dust collector Do not touch the Plasma dust collector within 0 minutes after opening the inlet grille, it may cause an electric shock. Clean the Plasma dust collector with mild detergent or water and dry in the sunlight for two hours. Before re-install the Plasma dust collector, check whether the corona line or support frame is damaged or not. 6. Install the air freshening filter back into position. 7. Insert the upper portion of air filter back into the unit taking care that the left and right edges line up correctly and place filter into position. Maintenance If you plan to idle the unit for a long time, perform the following: () Operate the fan for about half a day to dry the inside of the unit. (2) Stop the air conditioner and disconnect power. Remove the batteries from the remote controller. (3) The outdoor unit requires periodic maintenance and cleaning. Do not attempt to do this yourself. Contact your dealer or servicer. Checks before operation Check that the wiring is not broken off or disconnected. Check that the air filter is installed. Check if the air outlet or inlet is blocked after the air conditioner has not been used for a long time. CAUTIONS Do not touch the metal parts of the unit when removing the filter. Injuries can occur when handling sharp metal edges. Do not use water to clean inside the air conditioner. Exposure to water can destroy the insulation, leading to possible electric shock. When cleaning the unit, first make sure that the power and circuit breaker are turned off. 9
13 OPERATION TIPS The following events may occur during normal operation.. Protection of the air conditioner. Compressor protection The compressor can't restart for 3 minutes after it stops. Anti-cold air (Cooling and heating models only) The unit is designed not to blow cold air on HEAT mode, when the indoor heat exchanger is in one of the following three situations and the set temperature has not been reached. A) When heating has just starting. B) Defrosting. C) Low temperature heating. The indoor or outdoor fan stop running when defrosting (Cooling and heating models only). Defrosting (Cooling and heating models only) Frost may be generated on the outdoor unit during heat cycle when outdoor temperature is low and humidity is high resulting in lower heating efficiency of the air conditioner. During this condition air conditioner will stop heating operation and start defrosting automatically. The time to defrost may vary from 4 to 0 minutes according to the outdoor temperature and the amount of frost buildup on the outdoor unit. 2. A white mist coming out from the indoor unit A white mist may generate due to a large temperature difference between air inlet and air outlet on COOL mode in an indoor environment that has a high relative humidity. A white mist may generate due to moisture generated from defrosting process when the air conditioner restarts in HEAT mode operation after defrosting. 3. Low noise of the air conditioner You may hear a low hissing sound when the compressor is running or has just stopped running. This sound is the sound of the refrigerant flowing or coming to a stop. You can also hear a low "squeak" sound when the compressor is running or has just stopped running. This is caused by heat expansion and cold contraction of the plastic parts in the unit when the temperature is changing. A noise may be heard due to louver restoring to its original position when power is first turned on. 4. Dust is blown out from the indoor unit. This is a normal condition when the air conditioner has not been used for a long time or during first use of the unit. 5. A peculiar smell comes out from the indoor unit. This is caused by the indoor unit giving off smells permeated from building material, from furniture, or smoke. 6. The air conditioner turns to FAN only mode from COOL or HEAT (For cooling and heating models only) mode. When indoor temperature reaches the temperature setting on air conditioner, the compressor will stop automatically, and the air conditioner turns to FAN only mode. The compressor will start again when the indoor temperature rises on COOL mode or falls on HEAT mode (For cooling and heating models only) to the set point. 0
14 7. Dripping water may generate on the surface of the indoor unit when cooling in a high relatively humidity (relative humidity higher than 80%). Adjust the horizontal louver to the maximum air outlet position and select HIGH fan speed. 8. Heating mode (For cooling and heating models only) The air conditioner draws in heat from the outdoor unit and releases it via the indoor unit during heating operation. When the outdoor temperature falls, heat drawn in by the air conditioner decreases accordingly. At the same time, heat loading of the air conditioner increases due to larger difference between indoor and outdoor temperature. If a comfortable temperature can't be achieved by the air conditioner, we suggest you use a supplementary heating device. 9. Auto-restart function Power failure during operation will stop the unit completely. For the unit without Auto-restart feature, when the power restores, the OPERATION indicator on the indoor unit starts flashing. To restart the operation, push the ON/OFF button on the remote controller. For the unit with Auto-restart feature, when the power restores, the unit restarts automatically with all the previous settings preserved by the memory function. 0. Lightning or a car wireless telephone operating nearby may cause the unit to malfunction. Disconnect the unit with power and then re-connect the unit with power again. Push the ON/OFF button on the remote controller to restart operation.
15 Troubleshooting tips Malfunctions and Solutions Stop the air conditioner immediately if one of the following faults occur. Disconnect the power and contact the nearest customer service center. OPERATION indicator or other indicators flash rapidly (5 times every second) and this flash can't be fixed by disconnecting the power, and then connect it in again. Trouble Fuse blows frequently or circuit breaker trips frequently. Other objects or water penetrate the air conditioner. The remote controller won't work or works abnormally. Other abnormal situations. Malfunctions Unit does not start Unit not cooling or heating (Cooling/ heating models only) room very well while air flowing out from the air conditioner Power cut Cause Unit may have become unplugged. Fuse may have blown. Battery in Remote controller may have been exhausted. The time you have set with timer is incorrect. Inappropriate temperature setting. Air filter is blocked. Doors or Windows are open. Air inlet or outlet of indoor or outdoor unit has been blocked. Compressor 3 minutes protection has been activated. Wait for power to be restored. Check that plug is securely in wall receptacle. Replace the fuse. Replace the battery. Wait or cancel timer setting. Set temperature correctly. For detailed method please refer to " Using remote control" section. Clean the air filter. Close the doors or windows. Clear obstructions away first, then restart the unit. Wait. What should be done? If the trouble has not been corrected, please contact a local dealer or the nearest customer service center. Be sure to inform them of the detailed malfunctions and unit model. Notes: Do not attempt to repair the unit yourself. Always consult an authorised service provider. 2
16 MEMO Date of installation: Purchased from (Dealer Name): Date of purchase: Model number: Serial number:
17 ONE ()YEAR LIMITED WARRANTY Save This Warranty Information EcoAir guarantees this product free from defects in materials and workmanship for a period of one () year from the date of purchase, limited to parts only. Faults arising from a faulty installation is specifically excluded. This unit must be operated under conditions as recommended, at voltages indicated on the unit. Any attempts made to service or modify the unit by unqualified technician, will render this WARRANTY VOID. The actual product may differ slightly from the illustration. This warranty is in addition to, and does not affect, your statutory rights. For further information, please contact Copyright Reserved
OWNER S MANUAL Split Type Room Air Conditioner KSWM units Please read the operating instructions and safety precautions carefully and thoroughly before installing and operating your room air conditioner.
Before using your air conditioner, please read this manual carefully and keep it for future reference. SPLIT- TYPE ROOM AIR CONDITIONER Read This Manual Inside you will find many helpful hints on how to
User Manual Room Air Conditioners R410A Split Type Y Series DC INVERTER ECO940SD ECO120SD ECO1840SD Please read this installation manual completely before installing the product. When the power cord is
WNER S MANUAL Inverter Single Zone Ductless Mini Split Heat Pump VMH 30/36 Series Version C Heat Controller, Inc. 1900 Wellworth Ave. Jackson, MI 49203 (517)787-2100 www.heatcontroller.com wner s Manual
Before using your air conditioner, please read this manual carefully and keep it for future reference. SPLIT - TYPE RM AIR CNDITINER Read This Manual Inside you will find many helpful hints on how to use
OWNER S MANUAL VMH 09/12/18/27/36 InverterFlex Version C Single, Dual, Tri or Quad Zone Ductless Mini-Split System Heat Controller, Inc. 1900 Wellworth Ave. Jackson, MI 49203 (517)787-2100 www.heatcontroller.com
ENGLISH INSTRUCTION & INSTALLATION MANUAL DUCTLESS MINI SPLIT AIR CONDITIONING SYSTEMS Céliera Corporation. All rights reserved. Unauthorized duplication, reproduction prohibited. CONTENTS SAFETY PRECAUTIONS...
Portable Air Conditioner Owner's Manual Model:3 in 1 12,000 Btu/h Series 3 Please read this owner s manual carefully before operation and retain it for future reference. CONTENTS 1. SUMMARY...1 2. PORTABLE
SPLIT WALL MOUNTED TYPE AIR CONDITIONERS OWNER'S MANUAL Thank you for choosing our Air Conditioner. Please read this OWNER'S MANUAL carefully prior to use and keep it for further reference. CONTENTS Contents
F566272 Operating Instructions Air Conditioner CS-C18FFH CS-C28FFH CU-C18FFH CU-C28FFH ENGLISH Before operating the unit, read these operating instructions thoroughly and keep them for future reference.
DAIKIN ROOM AIR CONDITIONER Operation Manual OPTIONAL SLENDER REMOTE CONTROL BRC944A2B READ BEFORE OPERATION Safety Precautions...2 Names of Functions of Parts...4 Preparation before Operation...5 OPERATION
United Technologies USER'S MANUAL Split Type Room Air Conditioner Please read the operating instructions and safety precautions carefully and thoroughly before installing and operating your room air conditioner.
USER INSTRUCTIONS FOR 10 LITRE PORTABLE DEHUMIDIFIER MODEL NO. DHMD102 THANK YOU FOR CHOOSING YOUR NEW DEHUMIDIFIER. BEFORE USING THE UNIT READ THESE INSTRUCTIONS FULLY AND RETAIN THEM FOR FUTURE REFERENCE
USER S MANUAL Duct Type Series MH MH FEEA Series FUEA Series ENGLISH ESPAÑOL PORTUGUÊS E HNIKA DEUTSCH ITALIANO FRANÇAIS Free Joint Multi Air Conditioner (Cooling and Heating) E S F I P D G DB98-29565A(1)
All about the Use &Care of your Split Type Room Air Conditioner Refer to Page 2 for table of contents. www.frigidaire.com USA 1-800-944-9044 www.frigidaire.ca Canada 1-800-265-8352 66129904886 (June 2009)
NewAir AC-10000E, AC-10000H Portable Air Conditioner Owner s Manual PLEASE READ AND SAVE THESE INSTRUCTIONS BEFORE USE GENERAL SAFETY INSTRUCTIONS: ALWAYS OPERATE THE UNIT IN AN UPRIGHT POSITION AND PLACE
R-410A Duct Free Split System Air Conditioner and Heat Pump Product Family: DFS4(A/H)-System, DFC4(A/H)3-Outdoor, DFF4(A/H)H-Indoor Please read the operating instructions and safety precautions carefully
Double-Hung Windows Room Air Conditioner Installation Instructions and Owner's Manual This manual must be left with the owner of the equipment. Before using your air conditioner, please read this manual
OWNER S MANUAL AIR CONDITIONER (SPLIT TYPE) For general public use ENGLISH EN Indoor Unit RAS-07PKVP-E RAS-10PKVP-E RAS-13PKVP-E RAS-16PKVP-E RAS-18PKVP-E RAS-07PKVP-ND RAS-10PKVP-ND RAS-13PKVP-ND RAS-16PKVP-ND
ENGLISH FRANÇAIS ESPAÑOL OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. TYPE : Room Air Conditioner P/NO : 3828A20434H www.lg.com
DAIKIN ROOM AIR CONDITIONER Operation Manual MODELS FT50GAVEA FT60GAVEA FTY50GAVA FTY60GAVA ENGLISH ESPAÑOL TURKISH CONTENTS READ BEFORE OPERATION Safety Precautions... Names of Parts Indoor unit, Opening
NewAir AC-10100E / AC-10100H Portable Air Conditioner Owner s Manual PLEASE READ AND SAVE THESE INSTRUCTIONS ELECTRICAL SAFETY This appliance is for indoor use only. Always turn off the unit and unplug
Use and Care Manual Model CPA12KH AIR CONDITIONER Introduction Thank you for choosing this air conditioner to provide you and your family with all of the "Home Comfort" requirements for your home, cottage
SAFETY PRECAUTIONS Do not install the appliance if it is connected to the power supply. The Installation and service/repair must be performed by a qualified technician, in compliance with the producer's
AIR CONDITIONER (SPLIT TYPE) Indoor Unit Not accessible to the general public Model name: 4-way Air Discharge Cassette Type RAV-SM564UT-E RAV-SM804UT-E RAV-SM1104UT-E RAV-SM1404UT-E Air conditioner (Split
RMI-1103-A SERVICE MANUAL MIDEA AIRCONDITIONER EUROPE MARKET DC INVERTER MULTI TYPE R DC INVERTER MULTI SERIES CONTENTS 1. Precaution... 1 1.1 Safety Precaution... 1 1.2 Warning... 1 2. Function... 6 3.
SPLIT TYPE AIR CONDITIONER INDOOR UNIT/OUTDOOR UNIT MODEL RAS-60YHA/RAC-60YHA OUTDOOR UNIT INDOOR UNIT RAC-60YHA RAS-60YHA Instruction manual Page 1~26 To obtain the best performance and ensure years of
DAIKIN ROOM AIR CONDITIONER Operation Manual MODELS FT50BSG FT60BSG CONTENTS READ BEFORE OPERATION Safety Precautions... 2 Names of Parts Indoor unit, Opening the front grille... 5 Remote controller, Outdoor
Table of Contents Important Safeguards...2 Product Layout...3 Preparing for Use...4 Air-conditioning without installation...4 Air-conditioning with installation...5 Control Panel...6 Operating from the
Air Conditioner Water Heater - A Product of HotSpot Energy LLC PLEASE READ THIS BEFORE YOU INSTALL THE UNIT 1. This air conditioner must be installed and/or repaired by a qualified technician. If you perform
LG Multi Type Air Conditioner OWNER'S MANUAL LG Prior to installation, this airconditioning unit must be submitted for approval by the utility service which provides electricity (EN 61000-2, EN 61000-3
AIRREX AIR CONDITIONER USER S MANUAL HSC-24A Thank you for purchasing an AIRREX AIR CONDITIONER. BEFORE operation please read this user s manual carefully. Keep this manual readily available. It is ESSENTIAL
Multi System 16 SEER, Inverter System 9,000 to 18,000 BTU/Hr Single Split 4MXW8-A 4TXM6-A March2013 42 Warnings and Cautions Warnings and Cautions. Notice that warnings and cautions appear at appropriate
USER INSTRUCTIONS FOR GET PORTABLE 12k BTU AIR CONDITIONER MODEL No. GPACU12HR CONTENTS Introduction Safety Notes Identification of parts Installation instructions Operation instructions Maintenance Troubleshooting
Portable Air Conditioner OWNER S MANUAL Read these instructions before use 8 Model: MN12CES / MN10CESWW Voltage rating: 120V~60Hz Power rating : 1100W (MN12CES) Power rating : 900W (MN10CESWW) Customer
VERY IMPORTANT! MODEL: GDC-AC9RW / GDC-AC9RCS GDC-AC9RCW / GDC-AC12RW GDC-AC12RB / GDC-AC12RCB GDC-AC12RCW INSTRUCTIONS FOR USE PORTABLE AIR CONDITIONER Do not install and use your portable air conditioner
Portable Air Conditioner OWNER S MANUAL Read these instructions before use Model: MM14CCS Customer Support : 1-800-474-2147 Voltage rating: 115V~60Hz Power rating : 1400W For product inquiries or support
OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. TYPE : WALL MOUNTED P/NO : MFL67657205 www.lg.com ITALIANO ESPAÑOL FRANÇAIS
Meaco 30L and Meaco 40L dehumidifier instruction manual Please read this instruction manual before using the dehumidifier and keep safe for future reference SAFETY INSTRUCTIONS PLEASE READ ALL INSTRUCTIONS
Operating Instructions Air Conditioner Model No. Indoor Unit CS-S9PKR CS-S12PKR CS-S18PKR CS-S24PKR CS-S28PKR Outdoor Unit CU-S9PKR CU-S12PKR CU-S18PKR CU-S24PKR CU-S28PKR Operating Instructions Air Conditioner
Window Wall (Manual) Room Air Conditioner User Manual KWH15CMC Refrigerant R410 Congratulations Contents Congratulations and thank you for choosing our Manual Window Wall room air conditioner. We are sure
EVAPORATIVE AIR COOLER INSTRUCTION MANUAL Model: SF-614P Please read this manual thoroughly before using this product. Keep in a safe place for future reference. CONTENTS A. PRODUCT INTRODUCTION 2 B. TECHNICAL
DAIKIN ROOM AIR CONDITIONER Operation Manual MODELS FTKD50BSG FTKD60BSG FTKD7BSG CONTENTS READ BEFORE OPERATION Safety Precautions... Not for multi System... 4 Names of Parts Indoor unit, Opening the front
Contents PREPARING YOUR AIR CONDITIONER Safety Precautions..................................................... 3 View of the Indoor unit................................................ 8 RECOMMENDATIONS
TEMPORARY SWITCH SPLIT TYPE AIR CONDITIONER INDOOR UNIT/OUTDOOR UNIT MODEL RAS-50FH7/RAC-50YH7 ENGLISH DEUTSCH FRANÇAIS INDOOR UNIT ITALIANO HITACHI RAS-50FH7 OUTDOOR UNIT DC INVERTER ESPAÑOL PORTUGUÊS
AIR CONDITIONER (SPLIT TYPE) Owner s Manual Indoor Unit Model name: For commercial use 4-way Cassette Type RAV-SM564UT-E RAV-SM804UT-E RAV-SM1104UT-E RAV-SM1404UT-E RAV-SM1604UT-E Owner s Manual English
Before using your air conditioner, please read this manual carefully and keep it for future reference. INVERTER SPLIT TYPE - DUCTLESS MINI SPLIT SYSTEM WYE SERIES HEAT PUMPS The design and specifications
Portable Evaporative Air Cooler OWNER S MANUAL Read and save these instructions before use Model: CL30XC Power rating: 250 Watts Voltage rating: 230 Volt, 50Hz Made in P.R.C. QUICK START GUIDE Fill with
2-SLICE COOL TOUCH TOASTER PLA0405 Instruction Manual Due to on-going product improvements, specifications and accessories may change without notice. Actual product may differ slightly to that depicted.
SPLIT-TYPE AIR CONDITIONERS OPERATING INSTRUCTIONS INDOOR UNIT MSZ-A18YV MSZ-A24YV MSZ-A26YV MSZ-A30YV For customers Thank you very much for purchasing this Mitsubishi room air conditioner. To use this
AIR CONDITIONER Duct Type OPERATING MANUAL KEEP THIS MANUAL FOR FUTURE REFERENCE P/N9374379460 CONTENTS SAFETY PRECAUTIONS... 1 FEATURES AND FUNCTIONS... 3 NAME OF PARTS... 4 PREPARATORY OPERATION... 5
MODE ALARM Portable Air Conditioner OWNER S MANUAL Read these instructions before use 8 Model: MF08CESWW Voltage rating: 115V~60Hz Power rating : 800W Customer Support : 1-800-474-2147 For product inquiries
THERMAWAVE CERAMIC HEATER Model HZ-850 Series Model HZ-860 Series IMPORTANT SAFETY INSTRUCTIONS WARNING READ AND SAVE THESE OPERATING AND SAFETY INSTRUCTIONS BEFORE USING THIS HEATER. Warning Failure to
HEAT CONTROLLER, INC. Owner s Manual WINDOW/WALL - TYPE ROOM AIR CONDITIONER Room MULTI-STEP Conditioner SPEED ELECTRONIC CONTROL with R-410A: RADS-81G RADS-101G RADS-121G Before using your air conditioner,
PORTABLE AIR CONDITIONER MAC 7500 Owner s Manual Air Conditioner Dehumidifier Oscillating Fan Please read this owner s manual carefully before operating the unit. POWERED BY 66126113.p65 17 INTRODUCTION
Before using your air conditioner, please read this manual carefully and keep it for future reference. INVERTER SPLIT-TYPE RM AIR CNDITINER The design and specifications are subject to change without prior
Installation and Operation Manual Room Air Conditioners Portable Range ECO8P Register your air conditioner Model information can be found on the CE label. Please register your product online at www.ecoair.org.
Get Me Cool Now Portable Air Conditioner User s Manual GMCN100 SERIES Questions or Concerns? Contact technical support department at 1.877.645.0299, 8 a.m. - 5 p.m., EST, Monday - Friday or www.americancomfort.com
Portable Air Conditioner OWNER S MANUAL Read these instructions before use Model: MM14CHCSCS Voltage rating: 120V~60Hz Power rating : 1400W(Cooling) Power rating : 1350W(Heating) Customer Support : 1-800-474-21477
DC Inverter Portable Air Conditioner Model VS12 12,000 BTU Introducing The World s Most Efficient Portable Air Conditioner VS12 User & Installation Manual Version 1.0 1 Read This Manual Inside you will
FRANCAIS ESPAÑOL OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. TYPE : WALL MOUNTED LSN-LSU-90-120HYV Applied Models : AS-W093MMM9
SPLIT TYPE AIR CONDITIONER INDOOR UNIT MODEL RAK-18QH8(W) RAK-25QH8(W) RAK-35QH8(W) RAK-50QH8(W) RAK-18QH8(B) RAK-25QH8(B) RAK-35QH8(B) RAK-50QH8(B) INDOOR UNIT ESPAÑOL ITALIANO FRANÇAIS DEUTSCH ENGLISH
ENGLISH FRANÇAIS ESPAÑOL OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. TYPE : WALL MOUNTED P/NO : MFL67502019 http://www.lghvac.com
Visit us at : http://www.lgservice.com LG Wireless Remote Controller Owner's & Installation Manual Models: PQWRHSF0 PQWRCSF0 LG ENGLISH ITALIANO ESPAÑOL FRANÇAIS DEUTSCH IMPORTANT Please read this installation
JH026EAV Series JH035EAV Series Air Conditioner user manual imagine the possibilities Thank you for purchasing this Samsung product. To receive more complete service, please register your product at www.samsung.com/global/register
SWIMMING POOL HEAT PUMP Installation & User Manual Model HP40B HP50B HP65B Hayward Pool Products Canada, Inc. T: 1-888-238-7665 www.haywardpool.ca CONTENT I. Application 4 II. Features 4 III. Technical
HIGH-WALL DUCTLESS AIR CONDITIONING & HEATING SYSTEM Models: GWH09MA-A3DNA3A GWH12MB-A3DNA3A GWH09MB-D3DNA3D GWH12MB- D3DNA3D GWH18MC-D3DNA3D GWH24MD-D3DNA3D GWH30LB-D3DNA3E GWH36LB-D3DNA3E Thank you for
Website: www.andico.com.au Service manual CAUTION - BEFORE SERVICING THE UNIT, READ THE SAFETY - PRECAUTIONS IN THIS MANUAL. - ONLY FOR AUTHORISED SERVICE PERSONNEL. MODELS: MPK1-09CR-QB8 MPK1-12ER-QB6
OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. Type : Floor Standing Type(Console) www.lg.com ENGLISH ITALIANO ESPAÑOL FRANÇAIS
SVENSKA NORSK SUOMI DANSK OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. TYPE : WALL MOUNTED P/NO : MFL67641301 www.lg.com
Visit us at http://www.lgservice.com LG Room Air Conditioner OWNER'S MANUAL Dear Owner Thank you for installing LG air conditioner. Your best choice guarantees you a great performance and service to make
OPERATION MANUAL Split System Ducted Air Conditioner To suit Daikin FDY "F" Series and FD "F" Series AIR CONDITIONER A hr o C (and other models incorporating BRC1B62/52 Remote Controller) Dear Owner, Thank
Cassette Type_E_26442.indd 1 2007-12-07 ソタネト 6:18:33 Contents PREPARING YOUR AIR CONDITIONER Safety Precautions..................................................... 3 View of the Indoor unit................................................