1 An ASSA ABLOY Group brand ABLOY DA6 SWING DOOR OPERATOR Installation and commissioning manual
2 APPROVALS / STANDARDS Electrical safety tested and approved FI, S, N, D (according to CB-scheme) Low Voltage directive 006/9/EC EMC directive 00/08/EC Approvals in fi re doors (Finland): EN 0- EN 6- Warning! Warning! THIS MANUAL CONTAINS IMPORTANT SAFETY INSTRUCTIONS Warning - IT IS IMPORTANT FOR SAFETY OF PERSONS TO FOLLOW THESE INSTRUCTIONS SAVE THESE INSTRUCTIONS This appliance is not intended for use by persons (including children) with reduced physical, sensory or mental capabilities, or lack of experience and knowledge, unless they have been given supervision or instruction concerning use of the appliance by a person responsible for their safety. Do not allow children to play with fi xed controls. Frequently examine the installation for imbalance and sings of wear or damage to cables, springs and mountings. Do not use if repair or adjustment is necessary. Disconnect the supply when cleaning or other maintenance is being carried out. Before installing the operator, check that the operator is in good mechanical condition and it opens and closes properly. Ensure that entrapment between door and the surroundings is avoided. Ensure that the operator is suited for installation. Check temperature, humidity, door weights, etc. restriction in line with specifi cations applicable in the manual or other Abloy Oy material. Note! Instructions, design specifi cations and illustrations which are contained in this manual are not binding. Abloy Oy reserves the right as part of ongoing product development to make changes without previous notice.
3 CONTENTS REVISION... CONTENT OF DELIVERY... GENERAL INFORMATION... 6 OPERATION... 7 MAIN SWITCH AND MODE SWITCH DOOR WEIGHT INSTALLATION Installing the mounting plate DA Assembly of the operator and standard arm DA7, DA8 to the closing side Assembly of the operator and sliding arm DA9 to the closing side Assembly of the operator and sliding arm DA9 to the opening side Removing of the position sensor Door closer adjustments... 8 INTERNAL CONNECTIONS COMMISSIONING A SAFE DOOR... 9 EXTERNAL CONNECTIONS... 0 CONNECTION EXAMPLES.... Safety sensors DA00 and DA DA06 and DA06 Microwave motion sensor.... DA06 Microwave motion sensor.... DA0 Elbow switch.... DA09 ja DA09 rotary switch....6 Electric locks EL0, EL0, EL Motor locks EL90, EL Motor locks EL0, EL Electric lock EL Fire door system... 6 SELF DIAGNOSTICS... 7 MAINTENANCE Adjusting the clearance of the electromagnetic clutch... 9 SPARE PARTS... 0
4 REVISION Following pages have been revised: Page Revision As at
5 CONTENT OF DELIVERY DA6 Swing door operator - screws 6 pcs M6x DA0 Mounting plate - screws 6 pcs,x DA7 Standard arm - screws pcs,x and pcs M8x0 + M8x0 DA8 Extended arm - screws pcs,x and pcs M8x0 + M8x0 DA9 Sliding arm - screws pcs,x0 and pcs M8x0 + M8x0 DA0/0 Extension piece 0 mm - M8x DA0/0 Extension piece 0 mm - M8x + M8x
6 GENERAL INFORMATION Technical data Measures 7 (L) x 8 (H) x 07 (W) mm Weight 9 kg Supply voltage 00/0 VAC (±0 %) Hz Rated output 0 W Enclosure class IP0 Temperature range Storage C (in dry premises) Operation C (in dry premises) The automatic swing door operator must not be installed in applications where it is subjected to water or snow Interfaces Voltage output VDC, stabilized, 00 ma (max 800 ma for seconds) Potential free relay output 0,8 0VDC resistive load 0, 0VDC inductive load Door closer according EN: Class Standard arm Sliding arm Closing torque Door mass [kg] / width [mm] Door mass [kg] / width [mm] [Nm] (0- ) 0 / / / / / / / / 00 Features Easy to install Normal door closer function when the power is switched off or templed Push&Go as a standard feature Prepull before opening Adjustable hold open time s or sequential use Fire detector connection Lock control relay with NO/NC contacts Secondary DC inlet for power back up ( VDC (± %), min. A) Maximum opening angles: With standard arm 0 With sliding arm (on the opening side) 00 With sliding arm (on the closing side) 00 6
7 OPERATION The Abloy DA6 electromechanical swing door operator is especially suited to external and fi re resisting doors. The door is opened by motor force, and closed with the on board door closer. The motor and door closer are connected via clutch mechanism, which is engaged during the opening cycle, and released for the closing cycle. If the opening cycle of the door operator is interrupted, the clutch mechanism will disengage, the Abloy DA6 will try to open the door four times, stopping for one second before each attempt. After fourth attempt the clutch will release, and the door will close via the on board door closer. The Abloy door operator is controlled with normally open devices, triggering closed. In the event of power failure the door operator reverts to manual opening, closing via the on board door closer making the product an ideal specifi cation for Fire Resisting door sets. When the Abloy DA6 is used on Fire Resisting door sets the unit must be interfaced with the Fire Detection system, ensuring that the door closes, in line with current European and local standards. [Local standards may vary due to local requirements, and the Installer must ensure that these have been adhered to]. The door operator will allow for manual escape, [and re closing] even after activation of the Fire Detection system. The Abloy DA6 has a Push&Go function. When Push&Go is in operation and door is pushed or pulled manually, operator opens the door to adjusted opening angle and closes the door after a second of hold open time. MAIN SWITCH AND MODE SWITCH Main switch AUTO MAN OPEN Mode switch When the power is switched on, the mains switch lights up. I = on 0 = off The door opens via an impulse and closes after the adjusted hold open time. Manual use. The door opens and stays open. Note! There is seconds constant delay when mode switch is changed position OPEN to AUTO or MANUAL. 7
8 6 DOOR WEIGHT Standard arm Door weight [kg] Door width [cm] Sliding arm Door weight [kg] Door width [cm] 8
9 7 INSTALLATION Tools required - Drill - Set of ball ended allen wrenches - # Phillips head screwdriver - Flat blade screwdrivers, pcs Steps of installation - Preparing installation - Installing the mounting plate - Mounting the operator and the arm - Connecting the operator to mains - Commissioning - Testing - Connecting impulse devices Preparing installation - Check the correct function of the door - Hinges - Door clearance - Check the correct function of the lock - Lock case - Striker plate - Suitability of the lock s function Removal of housing Note! Remove the protective earth wire from cover and connect it back after installation. Ensure the mains disconnected when removing or re-fi tting the cover. 9
10 7. Installing the mounting plate DA0 The operator is installed on the transom, with the main switch located towards the hinge side of the door. Use the mounting plate DA0 with the door operator ensuring the installation base is level. Securely fi x the mounting plate to the transom. Minimum requirement for wall profi le is mm (steel). Hinge line 0 0, , 0 Ø, 0
11 7. Assembly of the operator and standard arm DA7, DA8 to the closing side Mounting of the operator: M6x and washer DA0 Y Min 0* * If you need closing force according to EN class 6, use measurement 00 mm. Y Y Length of extension piece no extension piece 6 0 mm (DA0/0) 7 0 mm (DA0/0) Mounting of the arm M8x0 + washer M8x0 + washer M8x + washer Frame depth Pre-setting of the spring force - 90 Frame depth DA7 DA8 Frame depth 0-0 mm 0-0 mm - After installation, ensure that the arm and door are properly adjusted. - Mount a door stop to the door open position so that wind will not drive the door against the wall, resulting in damage. - Tighten the holding screw.
12 7. Assembly of the operator and sliding arm DA9 to the closing side Mounting of the operator: M6x and washer DA0 Y Min 8 L 8 M Frame depth Arm distance L/mm Minimum door width M/mm < Y Y Length of extension piece 8 no extension piece 8 0 mm (DA0/0) 68 0 mm (DA0/0) Mounting of the arm M8x0 + washer M8x0 + washer M8x + washer Frame depth Pre-setting of the spring force Frame depth - - After installation, ensure that the arm and door are properly adjusted. - Mount a door stop to the door open position so that wind will not drive the door against the wall, resulting in damage. - Tighten the holding screw.
13 7. Assembly of the operator and sliding arm DA9 to the opening side Mounting of the operator: M6x and washer DA0 Y Min Max 0 L 8 M Frame depth Arm distance L/mm Minimum door width M/mm < Y Y Length of extension piece no extension piece 0 mm (DA0/0) 6 0 mm (DA0/0) Mounting of the arm M8x0 + washer M8x0 + washer M8x + washer Frame depth Pre-setting of the spring force - Frame depth. Mount the arm to the operator. Teach door open position - (see page 8). Remove the arm. Turn mode switch to OPEN. Close the door and mount the arm to the operator and to the sliding rail 6. Teach door closed and open positions again - After installation, ensure that the arm and door are properly adjusted. - Mount a door stop to the door open position so that wind will not drive the door against the wall, resulting in damage. - Tighten the holding screw.
14 7. Removing of the position sensor The position sensor must be removed, if the clutch or closing force need adjustment. This prevents possible damage of the sensor during adjustment. Fixing screw for position sensor Position sensor removed 7.6 Door closer adjustments Closing speeds L C C Closing speed L Latching speed
15 Closing force adjustment Open the door fully and observe the closing function assuming that the door closes as is required, check the closing function from approximately from the door s closed position ensuring that there is suffi cient power to close the door fully. Before adjusting the force of the door closer it is sensible to try and obtain a satisfactory closing action utilising the closing and latching speed. If this can not be achieved adjust the door closer force as shown. Fastener screws Lock nut Spanner wrench Force increases in + direction Spanner wrench Before adjusting closing force, remove position sensor (see 7.). Make sure operator s cables are not damaged during adjustment. - Loosen lock nut before adjusting closing force. - Use spanner wrench for force adjustment (included in delivery). Loosen the fastener screws a little if needed. - Tighten lock nut and fastener screws after adjusting. - Factory setting for closing force is Standard arm: EN - Adjustable between EN-6 Sliding arm: EN - Adjustable between EN- - Note - Fire Resisting door set require a minimum setting of level.
16 8 INTERNAL CONNECTIONS - Electrical connections should be made by a qualifi ed electrician. - The power plug must have an easy access. - If permanent connection is made unit must be equipped with an external switch providing all pole disconnection. - Keep the mains disconnected during installation. X X 7 6 black To motor red black Clutch red 0 V To DC supply back-up red black X6 X X L N AUTO: red & black MAN: NC OPEN: blue & black Position sensor A blue black red Mode switch AUTO MAN OPEN I 0 Main switch white brown white brown DC supply back-up When not mains operated, or for back-up supply, the external VDC (± %) supply (min A) can be connected to X connectors and. Connect + from DC supply back-up to X connector and to connector. No battery charging or maintenance is provided by DA6. Local regulation vary with respect to electrical installations, and the installer must ensure that they are not in conflict with the locally applicable requirements. 6
17 9 COMMISSIONING Check the free movement of the door. Turn mode switch to MAN. The mode switch is located in the head panel. Plug in the mains and turn the switch on. The main switch is located in the head panel. Choose the type of the arm. standard sliding ARM Jumpers are located on the control board. Jumper is connected. Jumper is disconnected. Choose the size of the door. small medium large sealed custom DOOR S, M and L settings define door weight in ratio to door width. Always select at first S in to guarantee maximum safety. If there is not enough force on the operator for moving the door then shift setting from S to M. If the door behaviour is satisfactory then the chosen value is right. If not then shift to next setting point L. small medium large sealed custom DOOR Jumper in block Custom together with S, M or L gives you more power. S + Custom, force between S and M. M + Custom, force between M and L. L + Custom, force more than L. small medium large sealed custom Sealed enables motorised closing pull before opening. Select this to ensure the proper function of the lock when prepull is needed. Motorised closing will be activatd 0-0 mm before the doors closed position. DOOR 6 Check the OPTION. Select single for a stand alone door. Master and Corridor, not yet available. single master corridor fi re n.c. OPTION single master corridor fi re n.c. OPTION If the jumper is connected then operator requires N.C. output from the fire detector. If the jumper is disconnected then operator requires N.O. output from the fire detector. 7 Teach door open and closed position. TEACH CLOSED TEACH OPEN POWER ON TEACH - Push TEACH-button to enter learning mode. - Teach the door closed position: Yellow led blinks: close the door and push TEACH-button. - Teach the door open position: Green led blinks: open the door to the desired angle and push TEACHbutton. - Yellow TEACH CLOSED led blinks: close the door manually. 7
18 8 Opening speed and hold open time min SPEED max Adjust the opening speed. A slow door is a safe door. The door speed should be set to allow unhindered access but as slow as is possible. 0 HOLD OPEN seq 60 Adjust the hold open time ( s). Full right position (seq) means that every other impulse either opens or closes the door. Time (sec) Door weight (kg) ,7,,,9 000,,0,,8 00,,7,,8 00,,,8 6, Door width (mm) Minimum safe opening and closing times for door of various widths and weights are summarized in the table. 9 Push&Go In fully left position Push&Go is set to off. PUSH&GO In fully right position Push&Go function is on. Operator opens the door to adjusted opening angle and closes the door after a second of hold open time. Push&Go is functional only when the door is closed. Pushing on a door during its closing cycle will not activate the Push&Go feature. Push&Go only functions from the closed position. 0 Test the operation Note! Long hold open time increases the safety of the door. - Turn mode switch to AUTO. - Test the operation. - The door will open to the adjusted opening angle after fi ve openings. - If the function is not as desired, turn mode switch to MAN and repeat steps If doors opening speed or jumper are changed, the door will open to adjusted opening angle after fi ve openings. 8
19 0 A SAFE DOOR The safety of an Automatic door is achieved with careful basic adjustments. Low speed, higher speeds increase the force applied to any obstruction. The speed should be set so that users are able to pass through the door unhindered, with the speed set as slow is as reasonable possible. The position of the input devices are also a factor i.e. where ever possible, they should see users approaching and start to open allowing the door to open slowly. The door operator should always be set to the lowest possible force setting, ensuring that the door operates smoothly, but equally does not have excessive force for the application. In all cases the door size should be set to the smallest possible setting, S small, M Medium, L Large, remembering the half steps achievable with the custom setting we effectively have S, S+, M, M+, L, L+. We should always remember that these force setting also has an effect with the inbuilt safety settings, i.e. the more force applied, the lower the sensitivity, hence should the door make contact with an obstruction it will apply a greater force is the door weight is set higher. We recommend that safety sensors are fi tted to all applications, particularly on the driven side, opening face in the case of a DA6. Higher speeds are only achievable when full safety is specifi ed. 9
20 EXTERNAL CONNECTIONS Connector X +V out Impulse input Safety sensor Locking circuit Fire detector 0 + VDC, 00mA output 9 Ground 6,7,8 Potential free relay output for lock drive Impulse input Safety sensor Ground to stop the door movement during operation Locking circuit Inhibits the opening if the lock bolt is thrown. Grounding this input allows for opening Fire detector 0 V - Do not strip any cables for unnecessary length. Loose wires may cause unwanted contacts. Fire detector: Remove the LINK, between terminals &, and connect the detection outputs, inputs. During activation of the Fire Detection System the door will close via the on board door closer. Once the Fire Detection System, is deactivated, the door requires re-setting with a manual opening. When the Abloy DA6 is fi tted to a Fire Resisting door set, the door operator MUST be interfaced with the Fire Detection system. Local requirements will vary, but the door must close in the event of activation in line with current European regulations. The Installer must ensure that the confi guration meets the local prevailing regulations. Safety sensor: On the opening side of the door: The Safety Sensor is connected to terminals and, with the power taken from terminal 0, and grounded via terminal 9. The loop must have a K resistor in parallel across the terminals and, [supplied]. This MUST be fi tted in the safety sensor, in order that the door operator monitors the condition of the cable between the sensor and the operator. This cable is vulnerable due to the doors movement, and in the event of an open circuit it will prevent a potentially unsafe door opening. The safety sensor is active, for the fi rst 70% of the door opening, it will not stop the door opening when it has passed the 70% point, because it has been designed so that it can ignore any obstacles, like the door reveal, or walls running in parallel to the door opening angle. The resistor between terminals and must be left in position if a safety sensor is not used. On the closing side of the door: Safety sensor is connected to impulse input terminal. When safety sensor detects an obstacle, it reopens the door. Impulse input: The closing contact drive (NO) must be potential free. The impulse device must be installed within direct sight of the door. Maximum length of the impulse device cable is 0 m. The total resistance of the control switch and its wiring must not exceed 00 ohm, when switch is closed. 0
21 CONNECTION EXAMPLES. Safety sensors DA00 and DA00 On the opening side ohm 6 7 Fire detector Locking circuit Safety sensor Impulse input V out The loop must have a K resistor in parallel across the terminals and. This must be fi tted in safety sensor, in order that the door operator monitors the condition of the cable between the sensor and the operator. This cable is vulnerable due to the door s movement, and in the event of an open circuit it will prevent a potentially unsafe door opening. When sensor detects an obstacle, the operator stops the door. On the closing side ohm Fire detector Locking circuit Safety sensor Impulse input +V out When sensor detects an obstacle, the operator opens the door for duration of the hold open time. LIGHT ON LIGHT ON (LO) Jumper settings and connection block for DA00 and DA
22 . DA06 and DA06 Microwave motion sensor 000 ohm yellow white brown green Fire detector Locking circuit Safety sensor Impulse input +V out. DA06 Microwave motion sensor white pink yellow blue brown green 000 ohm Fire detector Locking circuit Safety sensor Impulse input +V out
23 . DA0 Elbow switch N.C N.O COM V out Fire detector Locking circuit Safety sensor Impulse input. DA09 ja DA09 rotary switch red X blue black
24 .6 Electric locks EL0, EL0, EL0 NOTE! black blue green Not to be installed in doors with seal force. Bolt and trigger bolt have to be lubricated when lock is installed and when necessary. red 000 ohm Fire detector Locking circuit Safety sensor Impulse input +V out.7 Motor locks EL90, EL90 grey blue green white red 000 ohm Fire detector Locking circuit Safety sensor Impulse input +V out
25 .8 Motor locks EL0, EL0 -VDC -8VAC S/N: AC /DC AC /DC NO OPEN BACKUP+ BACKUP - C DOOR NC CLOSED WHITE BLACK+VIOL. 6 NO USED GREEN 7 8 C HANDLE NC NOT USED YELLOW RED 9 NO USED BROWN 0 C CYLINDER NC NOT USED BLUE RED/GREEN NO ORANGE BOLT IN C TURQUOISE NC GREY BOLT OUT C PINK 6 OPENING DELAY SWITCH TIME s 7 RESERVED s 0 0 s 8 0 s Example s s 0 8s 0 s s CONTROLS POWER EA V Extension cable ABLOY EA8, EL9 EA8 EL0 consumes max. 600 ma current. Length 6m/0m Cable 6 x 0. mm^ 000 ohm Fire detector Locking circuit Safety sensor Impulse input +V out.9 Electric lock EL0 black blue green red 000 ohm Fire detector Locking circuit Safety sensor Impulse input +V out
26 .0 Fire door system Motor lock EL90/EL90 Adjust the lock delay to minimum grey blue green white red Fire detector Locking circuit Safety sensor Impulse input +V out LED NC C NO LED NC C NO OPERATION: When the fi re detection system reacts, it s relay switches on. Then the (-) is disconnected from the operator s control unit (connector ). The operator doesn t open the door from impulse but it can be opened manually. The door closer of the operator closes the door after manual opening. Detection activation -> The door closes Power failure -> The door closes by spring After detection activation, one manual opening is required to re-energise the operator to chosen program selector mode. Note! A mechanical door coordinator is needed to ensure correct closing in double fi re doors! 6
27 SELF DIAGNOSTICS Fault codes - detect malfunctions - to ensure safe operation where possible during malfunction - to restore the operator to its required status If the door operator is unrecoverable it will revert to manual operation only. Both LED s will blink. Control units LED s TEACH CLOSED Yellow led = Y TEACH OPEN POWER ON TEACH Green led = G Indication G not lit Y not lit Possible fault No power. Faulty power supply unit. Faulty control board. Corrective user interventions in defi ned order ) Check the mains. ) Disconnect 0 pin connector from the control board. ) Measure the voltage of the power supply (7 pin connector, pins and ). If voltage is under VDC, change the power supply unit. ) Measure the voltage from 0 pin connector (pins 9 and 0). If voltage is not VDC, change the control board. G lit Y lit The door close and open positions are not successfully taught. Impulse device is active all the time. Fire Detector is active. ) Teach the door open and close positions. ) Check all impulse devices and connections. ) Check fi re detector connection and fi re N.C. jumper. G lit Y fl ash Flash short...short...short...: 000 ohm resistor is missing or cable of safety sensor is cut. ) Check that 000 ohm resistor is connected in control board or in safety sensor. ) Check that cables are not damaged. Flash short...long...short...long...: Safety sensor is active or cable of safety sensor is short-circuited. ) Move obstacle from safety sensor detection area. If sensor sees the wall, adjust detection area. ) Check that cables are not damaged. G fl ash Y fl ash Internal fault in the control board. Door motion is stopped. ) Switch main off for 0 seconds. ) Check that all applicable jumpers are in place (one of two arms is selected, one door size is selected, single is selected). ) Teach the door open and close positions. ) Change the control board. G fl ash Y fl ash alternates Internal fault in the position sensor board. Door motion is stopped. ) Switch main off for 0 seconds. ) Check that all applicable jumpers are in place (one of two arms is selected, one door size is selected, single is selected). ) Check position sensors cable and connector. ) Teach the door positions. ) Change the position sensor. 7
28 MAINTENANCE Door operators require periodic maintenance. Only trained personel are equiped to work on Abloy DA products. Door leaf is moving sensitively and locking works well. Regular annual services are made: - Under 00 openings per day; service once a year openings per day; service two times a year - Over 00 openings per day; service... times a year Inspections made in service: - Fixing of the operator and arm - Clearance of the clutch (see p.9) - Function and adjustments of impulse and safety devices - Programming and adjustments of the operator - Movement of the door, taught door positions 8
29 . Adjusting the clearance of the electromagnetic clutch The clearance of the electromagnetic clutch has to be checked during regular service (see timescales on page 8). The clearance should be 0, mm. Re-adjust the clutch if needed. Incorrect clearance causes, clutch drag or clutch slip, preventing the correct operation of the Abloy door operator. Holding screws Remove the position sensor before adjusting the clutch (see p.). Loosen two holding screws. Move the clutch plate with a screwdriver and mallet, if necessary. Note! Do not insert any object between clutch plates, as damage may occur. To adjust clearance of the clutch, use clearance gauge (0, mm). Insert the gauge between the clutch plates and adjust the clearance by pushing the clutch from area showed in the drawing. Check that the clearance is equal in the whole clutch. Note! Do not adjust the clearance by pushing from the clutch plate. Tighten two holding screws. Re-install the position sensor. Clearance gauge Do not grease the clutch! 9
30 SPARE PARTS Head panel 807 Motor and clutch 8 Position sensor 89 Control unit 8990 Transformer 877 (0V) 8 (00V) Mode switch 86 Door closer 870 closing side 87 opening side Adapter 0 aluminium 0 white Main switch 8077 DA7/00000 A DA7/ V DA7/ E DA8/00000 A DA8/ V DA8/ E DA9/00000 A DA9/ V DA9/ E Cover 06 aluminium 06 white 0
32 Some of the materials in this product, such as electronic components, require specialist recycling techniques. Nimike Päiväys /008 DOOR CONTROL PRODUCT MANAGEMENT/ /InDcs Abloy Oy Wahlforssinkatu 0 P.O. Box 08 FI-800 JOENSUU FINLAND Tel Fax ISO 900 ISO 00 CERTIFIED ORGANISATION An ASSA ABLOY Group brand Abloy Oy is one of the leading manufacturers of locks, locking systems and architectural hardware and the world s leading developer of products in the field of electromechanical locking technology. ASSA ABLOY is the global leader in door opening solutions, dedicated to satisfying end-user needs for security, safety and convenience.
ABLOY DA60 SWING DOOR OPERATOR Installation and commissioning manual Abloy Oy An ASSA ABLOY Group company APPROVALS / STANDARDS Low Voltage directive 7//EEC as amended by the directive 9/68/EEC EMC directive
ABLOY DOOR AUTOMATICS Easy access for all types of swing doors Automatic door operators bring additional convenience in situations where the doors opening manually would be inconvenient or laborious. Recommended
ABLOY EL490 AND EL590 SCANDINAVIAN RANGE MOTOR LOCKS Flexible multifunctional locking ABLOY EL490 and EL590 motor locks have been developed to further increase both the security and safety of the entire
Securitron Magnalock Corp. www.securitron.com ASSA ABLOY, the global leader Tel 800.624.5625 email@example.com in door opening solutions INSTALLATION AND OPERATING INSTRUCTIONS For Model GL1 Gate
K3 K4 www.sebury.com.cn Digital Keypad Use s Manual Contents Introduction Introduction Specifications Intramural Interface Circuit 3 Mounting 3 Wiring 5 Power UP 7 Engineer Programming Mode 7 The K3/K4
INSTALLATION GUIDE Card Reader & Controller with KIM Swipe Reader for Solitaire 850 / 950 / 850L Learnlok PK2930 Card Reader and Controller Model 3.5 with KIM Swipe Reader Table of Contents 1. Features..................................
TS EMR T/PT/TDE Surface applied door closer Installation instructions: Pull side track mount door closer with smoke detector (EMR T) Push side track mount door closer with smoke detector (EMR PT) Double
ABLOY EL426, EL526 Europrofile multipoint motor locks New ABLOY multipoint locks are the latest extension to the wide ABLOY Europrofile electromechanical lock case range. An ASSA ABLOY Group brand FUNCTION
Features: INSTALLATION Install in accordance with NFPA 70. DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS Up to 1.95 Amps Load Capacity Class 2 Rated Outputs Overload, Over Voltage, and Short
ABLOY EL466, EL566 Europrofile handle controlled multipoint locks New ABLOY multipoint locks are the latest extension to the wide ABLOY Europrofile electromechanical lock case range. An ASSA ABLOY Group
ABLOY DC 240 DOOR CLOSER Heavy duty door closer ABLOY DC240 heavy duty door closer offers a wide variety of functional options. ABLOY DC240 DOOR CLOSER The ABLOY DC240 have been developed to meet the exacting
ABLOY EL4, EL5 Europrofile motor locks ABLOY Europrofile locks can be installed with long plates or roses. An ASSA ABLOY Group brand Convenience, High security, High durability - Europrofile motor locks
Installation and user manual for the FX range of fire panels 1, 2, 4 and 8 zone panels Contents Panel installation 3 Panel connections 3 Wiring connection drawings 4 Panel facilities 6 Installation check
GB VariEco868 roller shutter/awning drive Keep these instructions in a safe place! After installation of the tubular drive attach these instructions to the cable for the electrician. Device function: Commissioning
TECHNICAL INFORMATION Models No. Description HP2070, HP2070F, HP2071, HP2071F 20mm (3/4") 2-Speed Hammer Drill CONCEPT AND MAIN APPLICATIONS L W NEW TOOL P 1 /13 W L These hammer drills have been developed
Operating instructions Diffuse reflection sensor OJ50xx 7096 / 0 07 / 004 Contents Preliminary note. Symbols used Function and features Installation. Installation of the supplied mounting fixture 4 4 Electrical
JANUS INTERNATIONAL CORPORATION INSTALLATION INSTRUCTIONS Pantheon Mini Operator The Janus Pantheon mini operator does not typically require the provision of any additional site requirements other than
Page 1 of 5 WD-AMX Water Detection Controllers Features: Benefit: LED Status of leak status VFC output Audible alarm Auto or manual reset alarm output Uses an isolated AC signal which prevents oxidation
HM-W536 Install Guide 9/13/2013 IMPORTANT SAFETY INSTRUCTIONS Warning - When using electrical devices, basic safety precautions should be followed to reduce the risk of fire, electrical shock or injury.
Multi-application heat tracing Control and Monitoring in commercial and residential buildings Roof & Gutter de-icing sensor module Technical Information Approvals Module IP rating Ambient operating temperature
Manual for Fire Suppression & Methane Detection System Fogmaker North America Post address: 150 Gordon Dr Exton, PA 19341 Delivery address: 150 Gordon Dr Exton, PA 19341 Tel: 610-265-3610 Fax: 610-265-8327
EC DECLARATION OF CONFORMITY FOR MACHINES (DIRECTIVE 98/37/EC) Manufacturer: Address: Declares that: FAAC S.p.A. Via Benini, 1-40069 Zola Predosa BOLOGNA - ITALY 770 mod. operator is built to be integrated
ANTI-THEFT SYSTEM 1995 Volvo 850 1995-96 ACCESSORIES & EQUIPMENT Volvo Anti-Theft Systems 850 DESCRIPTION & OPERATION WARNING: Deactivate air bag system before performing any service operation. For 1995
Product and Applications Description The power supply units N 125/x2 can supply DC 24 V power from an additional pair of terminals (yellowwhite). This DC 24 V output voltage can be used to power e.g. an
INSTALLATION INSTRUCTION SECURITY SYSTEM ADP-CAN Introduction Motorcar security system ADP-CAN is for motorcars provided with CAN net. It is for the work with the motorcar factory security systems or remote
MODEL NUMBER: ISC910-1-0-GB-XX ISC911-5-0-GB-XX IXP20 CONTROLLER SPECIFICATIONS Working Environment Plastic Housing... Power ImproX IXP20 Controller INSTALLATION MANUAL Designed to work in an indoor (dry)
Wespot SecNurse A NEW GENERATION TECHNICAL AIDS USER S GUIDE EN This manual is published by OPTEX, without any warranty. Improvements and changes to this manual necessitated by typographical errors, inaccuracies
Mechanism Diagram 15-1-1 GENERAL During assembly/installation, use the torque values and service products as in this section. WARNING! Torque wrench tightening specifications must be strictly adhered to.
Important information: These instructions contain safety information, read and follow them carefully. Dialight will not accept any responsibility for injury, damage or loss which may occur due to incorrect
MOUNTING AND OPERATING INSTRUCTIONS CF 51/55 1. Delivery CF 51/55-1 calculator with battery (optionally with mains power supply) - 1 wall mounting bracket - package with material for sealing, screws, wall
00 EMR (WITH ) GENERAL DESCRIPTION Each 00 EMR series unit contains a door closer, hold open electromagnet and smoke detector. The unit can be used as a single installation or as a series of singles powered
EMF/EMR Holder/Release Devices with Integral Door Closers EMR TECHNICAL DETAILS DORMA EMR SERIESHOLDER/RELEASE DEVICE The DORMA EMR Series holder/ release device incorporates a photoelectric detector and
TMS TANK MANAGEMENT SYSTEM Page 1 of 9 Operating Instructions GENERAL The Tank Management System is a bespoke design to control, monitor and accommodate efficient storage and dispensing of TMS. FUNCTIONS
4 3. SEISCO PARTS & SERVICE REMOVAL AND REPAIR GUIDE A. Changing the Control Board B. Replacing a Heating Element C. Thermistor Replacement D. High Limit Switch Replacement E. Level Detector Replacement
EC8666 Statement Automatic Door Operator is a reliable and quiet door opening and closing device. This product is ideal for enabling access to areas for people with disabilities or simply for convenience
English AUTOMATION SYSTEMS FOR SLIDING GATES Operating and installation instructions SLIDE SERIES v.0 Rev /202 INDEX ) General Safety Regulations... pág. 0 2) Description... pág. 02 3) Technical Specifications...
Version: January 2004 Contents Alarm System Activation unit Deactivation unit Digital locking cylinder or Smart Relay 1.0 Method of Operation 4 1.1 General 4 1.2 Turning the Alarm System On 4 1.3 Turning
PULL CHAIN SPEED CONTROL REVERSE SWITCH The Casablanca 4-Speed series of fans feature a 4-speed, pull chain fan control and a forward/reverse slide switch. XTR MOTOR PRINTED CIRCUIT BOARD LIGHT KIT PULL
90 STEALTH The MOST Versatile and Easiest To Use Towed Vehicle Braking System available! PROFESSIONAL INSTALLERS: Please return these instructions to the owner, for the owner s future reference INSTALLATION
SECTION G2: CABLE PROCESSOR MODULE MAINTENANCE Cable Processor Module overview WARNING! When tipping the Cable Processor Module back, (after removing the toggle arm pin), use extreme caution not to drop
Cylindrical Sensor E2E/E2E2 A New Series of Easy-to-use and Tough E2E/E2E2 Models Long-size E2E2 Sensor Conforms to CENELEC Ideal for a variety of applications. With a metal connector that can be tightened
EL460, EL461, EL560, EL561 Europrofile handle controlled locks Europrofile locks offer intelligent solution for medium traffic doors. Locks can be installed with long plates or roses. An ASSA Group brand
Fire Alarm Control Panel Family Operating Manual CONTENTS System Description AH-03312 System Characteristics... Fire Signal Receiving Board Description-4L... Fire Signal Receiving Board Description-8L...
Mounting instructions Contents Page 1. For your safety 2-4 2. Technical specifications 5-6 3. System setup 7 4. Accessories 8 5. Mounting on hinge side with 12.5 mm pivot pin 9 6. Mounting on hinge side
Outdoor 33.6W Dual Port Passive Power-over-Ethernet Midspan For External Security Cameras and Wireless Access Points Features SELV Compliant No Detection Passive Injector Gigabit Compatible Full Protection
W Ith I ntelligent Control S Ave E lectricity INTELLIGENT HOT WATER CYLINDER CONTROL INSTRUCTION MANUAL Thank you for purchasing our controller Before operating and installation carefully read all instructions.
Data sheet Electronic timer CT-AHD.12 OFF-delayed with 1 c/o (SPDT) contact The CT-AHD.12 is an electronic time relay with OFF-delay. It is from the CT-D range. With their MDRC profile and a width of only
DESCRIPTION MODEL 5010 DUAL CHANNEL SMOKE/FIRE DETECTION MODULE DESCRIPTION The SST Model 5010 Two Channel Smoke/Fire Detection Module provides two independent detection input channels for the NOVA-5000
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia
TX GSM SMS Auto-dial Alarm System Installation and User Manual Product Features: 1. 16 wireless zones, 3 wired zones alarm system, suitable for small to medium size offices and homes. 2. The system uses
Electronic Pressure Switch EDS 300 User manual Page 2 of 16 Content 1. Functions of the EDS 300...3 2. Mounting...3 3. Operating keys on the membrane keypad...4 4. Digital display...4 5. Output function...5
INFRARED QUARTZ WALL HEATER MODEL NO: IQ2000 PART NO: 6939004 MOUNTING & OPERATION INSTRUCTIONS GC0715 INTRODUCTION Thank you for purchasing this CLARKE Infrared Wall Heater. Before attempting to use this
Business/Home GSM Alarm System Installation and User Manual Brief Introduction: GSM 900/1800/1900 bands, can be used in most parts of the world Full duplex communication with the host Monitor the scene
TECHNICAL INFORMATION Models No. Description GN900 Cordless Clipped Head Framing Nailer CONCEPT AND MAIN APPLICATIONS Model GN900 is a cordless clipped head nailer developed for a wide range of framing
Model 2300DR Installation Guide POWER ACCESS CORPORATION P.O. BOX 1050 170 MAIN STREET NEW HARTFORD, CT 06057 800-344-0088 WEBSITE: www.power-access.com EMAIL: firstname.lastname@example.org 1 STANDARD PARTS
68 Flexible, high specification system Choice of 1, 2, 4 or 8 zones Simple one-shot auto-reset user test facility Approved to EN54 Maintenance free poly switch circuit protection, with auto reset Class
DORMA ED 800 SERIES Service Manual ED 800J ED 800T software level 3.27M www.dorma-usa.com 1-800-523-8483 INSPK NO. 08280020 Rev.08/07 08280021 08/07 TABLE OF CONTENTS Page Status Light...3 Status Light
DEVICES COVERED IN THIS DOCUMENT: 4940 Alarm Kit (ALT, ALM, ALL) 2-649-0168 Latch Monitor Switch 2-649-1090 Tamper Switch OVERVIEW Page 1 of 8 ALARM KIT INSTALLATION STEP ONE Disassemble device if it was
SERIES EBVA/B & TEBVA/B MULTI-VOLTAGE ELECTRIC ACTUATORS Installation, Operation & Maintenance Instructions Damage caused by non-compliance to these instructions will not be covered by our warranty. Read
1-10 1 Safety information The product was developed, manufactured and inspected according to the basic safety requirements of EC Guidelines and state-of-the-art technology. The unit is designed for use
33.6W Power over Ethernet Waterproof Adapter PoE Plus Single Port Injector for Outdoor Application Features Compliant with the IEEE802.3at Standard -40 to +60 C Temperature Range Diagnostic LEDs Full Protection
CSP Combined Series Telephone Door Entry with Proximity Keyfob Access PD-094 Issue 3 General Description The CSP series systems are combined Door Entry Telephone and Proximity Access Systems. The entrance
Stove Guard Kit User Manual Innohome improves the Safety of your Home. inno home www.innohome.com Stove Guard Kit User Manual Stove Guard Kit User Manual Congratulations! You now own one of the most intelligent