1 The Data Furnace: Heating Up with Cloud Computing Jie Liu, Michel Goraczko, Sean James, Christian Belady Microsoft Research One Microsoft Way Redmond, WA Jiakang Lu, Kamin Whitehouse Computer Science Department University of Virginia Charlottesville, VA Abstract In this paper, we argue that servers can be sent to homes and office buildings and used as a primary heat source. We call this approach the Data Furnace or DF. Data Furances have three advantages over traditional data centers: 1) a smaller carbon footprint 2) reduced total cost of ownership per server 3) closer proximity to the users. From the home owner s perspective, a DF is equivalent to a typical heating system: a metal cabinet is shipped to the home and added to the ductwork or hot water pipes. From a technical perspective, DFs create new opportunities for both lower cost and improved quality of service, if cloud computing applications can exploit the differences in the cost structure and resource profile between Data Furances and conventional data centers. 1 Introduction Cloud computing is hot, literally. Electricity consumed by computers and other IT equipment has been skyrocketing in recent years, and has become a substantial part of the global energy market. In 2006, the IT industry used 61 Billion kwh electricity (or 3% of total energy consumption in the U.S.), and is the fastest growing industrial sector . Energy efficiency is not only important to reduce operational costs, but is also a matter of social responsiblity for the entire IT industry. The emergence of cloud computing, online services, and digital media distribution has lead to more computing tasks being offloaded to service providers and increasing demand on datacenters infrastructure. For this reason, it is not surprising that data center efficiency has been one of the focuses of cloud computing and data center design and operation. In this paper, we argue that the problem of heat generation can be turned into an advantage: computers can be placed directly into buildings to provide low latency cloud computing for its offices or residents, and the heat that is generated can be used to heat the building. This approach improves quality of service by moving storage and computation closer to the consumer, and simultaneously improves energy efficiency and reduces costs by reusing the electricity and electrical infrastructure that would normally be used for space heating alone. Physically, a computer server is a metal box that converts electricity into heat 1. The temperature of the exhaust air (usually around C) is too low to regenerate electricity efficiently, but is perfect for heating purposes, including home/building space heating, cloth dryers, water heaters, and agriculture. We propose to replace electric resistive heating elements with silicon heating elements, thereby reducing societal energy footprint by using electricity for heating to also perform computation. The energy budget allocated for heating would provide an ample energy supply for computing. For example, home heating alone constitutes about 6% of the U.S. energy usage 2. By piggy-backing on only half of this energy, the IT industry could double in size without increasing its carbon footprint or its load on the power grid and generation systems. Technological and economical trends also make energy reuse a promising direction. After years of development of cloud computing infrastructure, system management capabilities are getting mature. Servers can be remotely re-imaged, re-purposed, and rebooted. Virtual machine encapsulation ensures certain degree of isolation. Secure executions on untrusted devices are feasible. Sensor networks have make high physical security within reach. At the same time, computers are getting cheaper, network connectivity is getting faster, yet energy becomes a scarce resource and its price is on the 1 At the same time, some energy is used by the fans to move the air for cooling and a very small amount of energy is used to drive electrons or photons on the network interface 2 According to the Energy Information Administration (EIA), U.S. households used 154 billion kwh for home heating, 116 billion kwh of which goes to the heating element
2 trend of fast rise. From a manageability and physical security point of view, the easiest adopters of this idea are office buildings and apartment complexes. A mid-sized data center (e.g. hundreds of killowatts) can be hosted inside the building and the heat it generates will be circulated to heat the building. Dedicated networking and physical security infrastructure can be built around it, and a dedicated operator can be hired to manage one or more of them. Their operation cost will be similar to operating other urban data centers, and can leverage the current trend toward sealed server containers that are replaced as a unit to save repair/replacement costs. As a thought provoking exercise, we push this vision to the extreme in this paper. We investigate the feasibility of Data Furances or DFs, which are micro-datacenters, on the order of 40 to 400 CPUs, that serve as the primary heat source for a single-family home. These microdatacenters use the home broadband network to connect to the cloud, and can be used to host customer virtual machines or dedicated Internet services. They are integrated into the home heating system the same way as a conventional electrical furnace, using the same power system, ductwork, and circulation fan. Thus, DFs reduce the cost per server in comparison to conventional data centers by leveraging the home s existing infrastructure, and precluding the cost of real estate and construction of new brick and mortar structures. Furthermore, they naturally co-locate computational power and storage close to the user population. DFs are managed remotely and do not require more physical maintenance than conventional furnaces. The cloud service operators may further incentivize the host families by providing free heat in exchange for occasion physical touches such as replacing air filters and, in extreme cases, turning on/off servers. Previous studies also suggest bringing microdatacenters close to the users, including the idea of renting condos to host servers  and to use home routers as a nano-datacenter for content caching . In this paper, we suggest that a quantum leap is achieved when this idea scaled to the size of a furnace; at this scale, the micro-datacenter cannot only leverage existing residential infrastructure for power, networking, and air circulation, but it can also reuse the energy that would otherwise be consumed for home heating. In the rest of the paper, we first compare the cost of Data Furances versus building and operating conventional data centers, by analyzing the heating demand in various climate zones to understand the capacity and utilization requirements. Then, in Section 3 we discuss what kind of services can run on DFs given different investment levels. Finally, we discuss technical challenges including security, power management and system man- Climate Zones Locations Outdoor Temperature < 21 C > 35 C Zone 1 Minneapolis, MN 82.20% 0.11% Zone 2 Pittsburgh, PA 82.46% 0.00% Zone 3 Washington, D.C % 0.13% Zone 4 San Francisco, CA 96.44% 0.00% Zone 5 Houston, TX 46.51% 0.15% Table 1: Representative locations used in simulations Figure 1: Average monthly heating rate across the year agement. 2 Home Heating with Data Furances In this section, we evaluate the financial viability of Data Furances from the perspective of cloud service providers. Because DFs serve as a primary heat source in homes, we first perform a simulation study to understand the heating demands for a single family house across the climatic zones in the U.S.. Based on the results, we discuss the expected savings if DFs were used in each zone. We use ballpark figures and back-of-the-envelope calculations; the exact numbers depend on the specific households and data centers under consideration. DFs reduce the total cost of conventional datacenters in three main ways. First, much of the initial capital investment to build the infrastructure for a datacenter is avoided, including real estate, construction costs, and the cost of new power distribution, networking equipment, and other facilities. A second and related benefit is that operating costs are reduced. For example, cooling cost is significant in centralized data centers due to the power density , but DFs have essentially no additional cooling or air circulation costs since the heat distribution system in the house already circulates air. Thus, DFs increase the power usage efficiencies (PUE) over conventional datacenters. Finally, the money to buy and operate 2
3 a furnace for home heating is avoided, and can be used instead to offset the cost of servers: the cloud service provider can sell DFs at the price of a furnace, and charge household owners for home heating. By doing this, the heating cost remains the same for the host family, while costs are reduced for the cloud service provider. One disadvantage of DFs is that the retail price of electricity is usually higher in the residential areas by 10% to 50% than industrial areas . Another potential disadvantage is that the network bandwidth can cost more in homes if the home broadband link cannot satisfy the service and a high bandwidth link must be purchased. Finally, maintenance costs will increase because the machines will be geographically distributed. To weigh these advantages and disadvantages, we perform a total cost of ownership (TCO) analysis for both DFs and conventional data centers. The initial and operating cost can change based on climate zone, so we first measure the actual heating demand for homes using the U.S. Department of Energy s EnergyPlus simulator . This simulator calculates the heating load (BTU) required each minute to keep a home warm, using actual weather traces recorded at airports. We simulate a 1700 square foot residential house that is moderately insulated and sealed with a heating setpoint of 21 C (70 F). We use weather data of Typical Meteorological Year 3 (TMY3) , and replay the entire year for cities in each of the five climate zones in the U.S., as listed in Table 1. The last two columns show the percentage of time (in minutes granularity) that the outside temperature is less than 21 C, (thus heating is useful) and that the outside temperature is greater than 35 C (thus the server may have to be shut down for thermo protection since we do not expect cooling the furnace.). The percentage of time in between is when the servers can be run but the heat must be pumped outside. Table 2 summarizes the results of our TCO analysis for a DF in each climate zone. Row 1 indicates the maximum heating rate required for the coldest day of the year in each zone, based on our simulations. Row 2 indicates the number of servers required in a DF to satisfy these requirements, assuming a typical server such as the Dell PowerEdge 1850 consumes 350 W generating 1, BTU/h heat dissipation . The third row shows the estimated home heating cost for each zone, assuming the consumer pays an amount equal to the cost of operating either an appropriately sized oil furnace in Zones 1 and 2, or a heat pump in Zones 3, 4 and 5. This number is calculated based on the data in Figure 1, which shows the average heating rate required for each month in each climate zone, as determined by our simulations. The actual home heating cost certainly varies based on the heating technology and thermostat setting. This is the incentive to the host family that the cloud operator can claim. The fourth row shows the income per year from selling the DF to the consumer, assuming the consumer pays $4000 for a comparably sized heat pump or furnace. Based on the electricity price data, the fifth row shows the increased cost of electricity for the data center owner, due to residential electricity rates being higher than commercial electricity rates; we assume that the residential electricity rate in the U.S. is $0.10/kWh while the industrial rate is $0.05/kWh. The sixth and seventh rows indicate the cost per DF for each zone, and the cost per server based on the number of servers in each zone. These numbers represent overhead costs and do not include the costs of the servers themselves, since those costs must also be paid in a conventional data center. The eighth row indicates the optional cost of upgrading the network link at the home to a T1, which is assumed to cost $2,640 for the home per year. In all regions, the overhead cost is less than $90 per server per year. In comparison, the overhead cost per server per year for a conventional datacenter is approximately $400. This cost is taken from James Hamilton s spreadsheet analysis , which estimates the cost of running a datacenter of over 45,000 servers, using a 3-year server amortization and a 15-year facilities amortization. These overhead costs include construction for a brick and mortar building, network equipment, cooling costs, and other equipment and operational costs that are not needed for DFs. Based on these numbers, the last row of Table 2 indicates the cost savings per server per year of running a DF, in comparison to a conventional datacenter. These savings would be higher for data centers that run applications that do not necessitate an upgrade to the network connection, or when comparing to urban data centers that pay more for electricity and real estate. Designed correctly, Data Furances may not require frequent touch for maintenance. Studies have shown that on average 9% servers fail in 14-month of operation . In other industries, the cost to roll a truck is approximately $100 per maintenance visit, which is only necessary for a Data Furnace when a few physical failures occur that cannot be managed remotely. Even if these occur three times per year, it is an amortized cost of less than ten dollars per server per year and therefore does not substantially change the TCO analysis. 3 Types of Service The overhead costs for Data Furances are very small compared to centralized mega datacenters, but the true value proposition depends on the types of services it can provide. DFs will present both opportunities and challenges for cloud computing services. One one hand, DFs can improve performance for many applications because they are close to areas of high population density. On 3
4 Heating Requirements Zone 1 Zone 2 Zone 3 Zone 4 Zone 5 Sizing for coldest day of year (BTU/h) 133, , ,650 54,949 44,198 Number of 350W Servers in Furnace Est. normal home heating cost $ $ $ $ $711.0 Amortized cost/gain Income from selling DF -$ $ $ $ $400.0 (per furnace per year) Cost increase due to residential rates $ $ $ $ $ Amortized overhead expense per server per year $81.5 $55.56 $52.9 $67.7 $34.2 Optional Cost (per year) Amortized network upgrade per server $22.0 $21.6 $24.4 $53.5 $66.5 Savings per server per year $298.1 $324.4 $324.3 $280.4 $300.9 (compare to $401.6 per server for conventional DC) Table 2: Cost benefit to run a DF over a conventional datacenter (from the perspective of cloud service provider) the other hand, the new cost structure for bandwidth and energy may make DFs less attractive for other types of applications. We envision at least three classes of DFs, as described below: Type A: Low-cost seasonal DFs The least expensive DFs will use the existing home broadband connection and will perform computation predominantly when the house needs heating (e.g. at nights or during winters), providing seasonal computing capacity with almost no operational cost. These low-cost DFs can also reduce initial costs by using recycled, older models of servers hundreds of thousands of which are decommissioned from existing datacenters every year to make space for servers with latest hardware technology. These older servers are often less energy efficient and less cost effective in a conventional datacenter, but ideal for providing heat and maintaining basic disk and network operations year-round. Because of the population distribution on the planet, the computing capacity of this class of DFs will be skewed toward the northern hemisphere s winter months. Despite their bandwidth-limited and seasonal nature, Type A DFs can still support a wide range of services. For example, many delay-tolerant batch jobs can be performed opportunistically, such as non-real-time web crawling, content indexing, and the processing of large scientific data sets (e.g. astronomical data, genome sequencing operations, and Type A DFs can also help developing communities, societal services, hobbiests, and other organizations looking for extremely low cost computing resources. Finally, governments currently subsidize home heating for developing communities 3. With the same fund, Type A DFs can have extended operation time for education, scientific, and social services, doubling the benefits. Type B: Low-bandwidth neighborhood DFs A lower-cost DF can also operate year-round using 3 e.g. Wisconsin Home Energy Assistance Program (WHEAP) (http://homeenergyplus.wi.gov/category.asp? linkcatid=239&linkid=118) the broadband channel of the home instead of upgrading the network link, thereby supporting typical computation loads but with a relatively slow egress link. The least expensive cable modem package from Comcast today provides 12 Mbps download and 2 Mbps upload speed, in comparison to a conventional data center, which may have a 10 Gbps link (shared among hundreds of thousands of machines). This new resource profile makes financial sense for DFs, particularly in warmer climates, where it will reduce overhead costs by up to 80% per server, as shown in Table 2. Despite bandwidth limitations, Type B DF can nevertheless provide high quality computing services due to geographic proximity to the customers. For example, Internet television services and on-line video rental services could use pre-fetching based on local programming schedules or video queues of people in the local vicinity. Similarly, location-based services such as map serving, traffic estimation, local navigation, and advertisements for local stores are typically requested by customers from the local region. Network latency can be reduced by creating more data centers closer to customers , particularly for cloud applications such as , multimedia distribution [3, 10], and low-hit rate Web pages and services that are delay tolerant, embarrassingly distributable, and/or can benefit from large-scale replication and geo-distribution. Type C: Eco-friendly urban DFs. Closest to the current operation modes, high-end DFs will upgrade the communication link at the home to FiOS or a T1, and can operate year-round even when heat is not needed in the home by pumping excess heat directly outside. This is particular promising for business buildings and apartments. Having comparable resources per server, these DFs would give service providers the ability to expand into urban areas more quickly and easily without urban real estate and infrastructure expenses, as long as the application scale to the number of servers. On the other hand, Type C DFs also present new challenges. First, summer operation costs more because higher elec- 4
5 tricity rates are not compensated by sale of heat. However, this additional cost would be marginal compared to the cost advantages of DFs, especially since many data centers only have about 20% server utilization anyway. Furthermore, urban areas present opportunities for larger DFs in commercial buildings, business parks, and apartment complexes where lower commercial energy rates are available and where the larger heating units have an energy footprint close to containerized datacenters that are used for edge services. A second challenge is that DFs may break large services into many small pieces, thereby introducing a different granularity to perform massively distributed computations, like MapReduce. 4 Technical Challenges Despite the facts that server hardware is getting more robust and less sensitive to operation conditions, and that cluster-level management software is getting mature, DF present new unique challenges due to its distribution in residential households, including: Isolation: DFs use the existing power and network infrastructure of a normal residence or business, and they must not affect normal building operations. A DF must monitor and react to the total power and broadband usage of its hosts in order not to exceed capacity (e.g. 24kW and 12Mbps for a typical home in Seattle), and cloud services must be designed to accommodate this low-priority operation. Security: One difference between DFs and dedicated datacenters is the challenge of physical security, and DFs should be treated as being in the most insecure environment. For example, each server should have an individual tamper proofing device, such as a networked sensor. This will allow them to be individually swapped out by the hosting party only when necessary (e.g. due to unrecoverable device failure). Furthermore, all stored data and network traffic must be encrypted. Software running on the servers should be sandboxed and secured from the hosting party. Zero-touch management: Automated solutions exist for monitoring server and network health, remotely re-purpose and re-image machines, and remotely diagnose faults and power cycle machines (e.g. ). However, without dedicated system operators and in a residential environment, DFs require high heating reliability and zero-touch management. Even at the event of software failure, the system should continue to provide heat until receiving physical services. 5 Conclusion With continuously increasing demand for computing, the community must explore novel ways to expand computing capacity without increasing financial burden and energy costs. Data Furances will reuse the facilities and energy already allocated for heating purposes to provide computing services with low cost and energy footprint. In this paper, we focus on homes as an illustrating example, but a similar approach could be used to heat water tanks, office buildings, apartment complexes, vegetable farms, and large campuses with central facilities. References  Dell PowerEdge 1850 Environmental Data Sheet. http: //www.dell.com/downloads/global/corporate/ environ/pe_1850.pdf.  EnergyPlus Energy Simulation Software. eere.energy.gov/buildings/energyplus/.  CHURCH, K., GREENBERG, A., AND HAMILTON, J. On delivering embarrassingly distributed cloud services. In ACM SIG- COMM Hotnets VII, Calgary Alberta, Canada (2008).  ENERGY INFORMATION ADMINISTRATION, IN THE US DE- PARTMENT OF ENERGY. End-Use Consumption of Electricity Survey. recs2001/enduse2001/enduse2001.html,  HAMILTON, J. Overall Data Center Costs. http: //perspectives.mvdirona.com/2010/09/18/ OverallDataCenterCosts.aspx.  ISARD, M. Autopilot: automatic data center management. SIGOPS Oper. Syst. Rev. 41 (April 2007),  LI, A., YANG, X., KANDULA, S., AND ZHANG, M. Cloudcmp: Comparing public cloud providers. In Internet Measurement Conference, Melbourne, Australia (2010).  U.S. ENERGY INFORMATION ADMINISTRATION. Average Retail Price of Electricity to Ultimate Customers by End-Use Sector, by State.  U.S. ENVIRONMENTAL PROTECTION AGENCY EN- ERGY STAR PROGRAM. Report to congress on server and data center energy efficiency public law prod_development/downloads/epa_datacenter_ Report_Congress_Final1.pdf.  VALANCIUS, V., LAOUTARIS, N., MASSOULIE, L., DIOT, C., AND RODRIGUEZ, P. Greening the internet with nano data centers. In ACM CoNEXT 09, Rome, Italy (2009).  VISHWANATH, K. V., AND NAGAPPAN, N. Characterizing cloud computing hardware reliability. In Proceedings of the 1st ACM symposium on Cloud computing (New York, NY, USA, 2010), SoCC 10, ACM, pp  WILCOX, S., MARION, W., AND NATIONAL RENEWABLE EN- ERGY LABORATORY (U.S.). Users Manual for TMY3 Data Sets. National Renewable Energy Laboratory,  WOODS, A. Cooling the data center. ACM Queue 8, 10:10 10:19. 5
Bytes and BTUs: Holistic Approaches to Data Center Energy Efficiency NREL 1 National Renewable Energy Laboratory Presentation Road Map A Holistic Approach to Efficiency: Power, Packaging, Cooling, Integration
Leveraging Renewable Energy in Data Centers: Present and Future Ricardo Bianchini Department of Computer Science Collaborators: Josep L. Berral, Inigo Goiri, Jordi Guitart, Md. Haque, William Katsak, Kien
Glossary of Heating, Ventilation and Air Conditioning Terms Air Change: Unlike re-circulated air, this is the total air required to completely replace the air in a room or building. Air Conditioner: Equipment
Introduction to AWS Economics Reducing Costs and Complexity May 2015 2015, Amazon Web Services, Inc. or its affiliates. All rights reserved. Notices This document is provided for informational purposes
Internet Content Distribution Chapter 2: Server-Side Techniques (TUD Student Use Only) Chapter Outline Server-side techniques for content distribution Goals Mirrors Server farms Surrogates DNS load balancing
EarthCents (DSM) Program Summary Renewable Energy EarthCents Programs Solar Water Heating This program is available to residential customers for the installation of a qualifying solar thermal water heater.
Greener IT Practices Anthony Suda Network Manager marketing + technology 701.235.5525 888.9.sundog fax: 701.235.8941 2000 44th st s floor 6 fargo, nd 58103 www.sundog.net In our world today, individuals
Market Potential Study for Water Heater Demand Management Rebecca Farrell Troutfetter, Frontier Associates LLC, Austin, TX INTRODUCTION Water heating represents between 13 and 17 percent of residential
UT DALLAS Erik Jonsson School of Engineering & Computer Science Cloud Computing Trends What is cloud computing? Cloud computing refers to the apps and services delivered over the internet. Software delivered
Superfast Business Wales Are you prepared for the arrival of superfast broadband? Superfast Business Wales Broadband and business Contents What exactly is superfast broadband?... 4 How fast is superfast?...
Superfast Business Wales Are you prepared for the arrival of superfast broadband? Superfast Business Wales Contents What exactly is superfast broadband?... 4 How fast is superfast?... 5 What will superfast
Energy Efficiency Energy Efficient Water Heating: Purchasing a new electric water heater. Water heating accounts for about 18 percent of your home energy bill. Only space heating and cooling account for
Residential Heating Oil Prices: What Consumers Should know Introduction Heating oil is a petroleum product used by many Americans to heat their homes. Historically, heating oil prices have fluctuated from
Free Cooling in Data Centers John Speck, RCDD, DCDC JFC Solutions Why this topic Many data center projects or retrofits do not have a comprehensive analyses of systems power consumption completed in the
When Does Colocation Become Competitive With The Public Cloud? WHITE PAPER SEPTEMBER 2014 Table of Contents Executive Summary... 2 Case Study: Amazon Ec2 Vs In-House Private Cloud... 3 Aim... 3 Participants...
When Does Colocation Become Competitive With The Public Cloud? PLEXXI WHITE PAPER Affinity Networking for Data Centers and Clouds Table of Contents EXECUTIVE SUMMARY... 2 CASE STUDY: AMAZON EC2 vs IN-HOUSE
Copyright www.agileload.com 1 INTRODUCTION Performance testing is a complex activity where dozens of factors contribute to its success and effective usage of all those factors is necessary to get the accurate
Metering, Billing & Remote Surveillance Solutions for Communal Heating Systems - Including SmartTalk Two-Way Communication 1 Metering, Billing & Remote Surveillance Solutions Evinox Energy specialise in
Cloud computing for noise monitoring Thorvald Wetlesen 1 1 Norsonic Gunnersbråtan 2, 3421 Lierskogen, Norway ABSTRACT Cloud computing is the use of computing resources that are delivered as a service over
Real World Considerations for Implementing Desktop Virtualization The Essentials Series sponsored by En suring Desktop Virtualization Success... 1 Siz ing Your Desktop Virtualization Environment... 2 Ap
PacketStorm Communications, Inc. was founded in November 1998 by a group of engineers from the prestigious Bell Laboratories. PacketStorm develops, manufactures, and supports high end testing solutions
Guideline for Water and Energy Considerations During Federal Data Center Consolidations Prepared for the U.S. Department of Energy Federal Energy Management Program By Lawrence Berkeley National Laboratory
Overview of Green Energy Strategies and Techniques for Modern Data Centers Introduction Data centers ensure the operation of critical business IT equipment including servers, networking and storage devices.
Comparing the TCO of Physical PCs, VDI, and Cloud-hosted Desktops as a Service (Daas) A Desktone Whitepaper Contents Executive Summary.1 Desktops: Ripe for Change.1 Solutions for Comparison.2 Key Findings..3
Appendix J Demand Response Pilot City Light s power resources are unusual for an electric utility serving a major urban area. About 90% of the energy served to Seattle originates from water, or hydropower.
Fuel Monitoring & Remote Diagnostic System: The Complete Story Honeywell is pleased to offer a series of solutions to the Oil industry and it s homeowner customers that reduce industry costs and expand
Data Center & IT Infrastructure Optimization Trends & Best Practices Mickey Iqbal - IBM Distinguished Engineer IBM Global Technology Services IT Organizations are Challenged by a Set of Operational Issues
A FieldView White Paper How Next Generation Monitoring Improves Data Center Infrastructure Management (DCIM) Introduction According to a global survey by DatacenterDynamics (DCD), data centers in the U.S.
DataCenter : first results for energy-optimization at existing data centers July Powered by WHITE PAPER: DataCenter DataCenter : first results for energy-optimization at existing data centers Introduction
Serenbe Green Geothermal Solutions with Bosch Thermotechnology Geothermal Heating and Cooling boschheatingandcooling.com C1 Residential Geothermal Heat Pumps The Bosch Complete Solution The Serenbe Community,
October 2015 CUBFacts Smart Ideas(R) Energy Efficiency Program for ComEd Customers **New Appliance and Smart Thermostat Rebates Available!** Discounts on Energy Efficient Lighting You can receive instant
OKTOBER 2010 CONSOLIDATING MULTIPLE NETWORK APPLIANCES It is possible to consolidate multiple network appliances into a single server using intelligent flow distribution, data sharing and virtualization
Unico, Inc. 7401 Alabama Ave. St. Louis, MO 63111 Unico, Inc. manufacturing plant and sub-assembly plant +1 800 527 0896 +1 314 481 9000 www.unicosystem.com Unico, Inc. is the leader in Small Duct High
Making a Case for Including WAN Optimization in your Global SharePoint Deployment Written by: Mauro Cardarelli Mauro Cardarelli is co-author of "Essential SharePoint 2007 -Delivering High Impact Collaboration"
Best Practices in Business Recovery: Colocation or DRaaS? By Brien M. Posey axcient.com 1 Introduction In the not-too-distant past, protecting an organization s data meant shipping backup tapes offsite
HyperQ Hybrid Flash Storage Made Easy White Paper Parsec Labs, LLC. 7101 Northland Circle North, Suite 105 Brooklyn Park, MN 55428 USA 1-763-219-8811 www.parseclabs.com email@example.com firstname.lastname@example.org
Server room guide helps energy managers reduce server consumption Jan Viegand Viegand Maagøe Nr. Farimagsgade 37 1364 Copenhagen K Denmark email@example.com Keywords servers, guidelines, server rooms,
Green IT Solutions From Desktop to Datacenter Dave Spear Sr. Engagement Manager & Sustainability Advocate firstname.lastname@example.org Agenda Our Commitment Today s Environment PC, Server, Storage Computerworld
W H I T E P A P E R S O L U T I O N : D I S A S T E R R E C O V E R Y T E C H N O L O G Y : R E M O T E R E P L I C A T I O N Disaster Recovery Strategies: Business Continuity through Remote Backup Replication
October 2010 Consolidating Multiple s Space and power are major concerns for enterprises and carriers. There is therefore focus on consolidating the number of physical servers in data centers. Application
Energy Efficiency and Availability Management in Consolidated Data Centers Abstract The Federal Data Center Consolidation Initiative (FDCCI) was driven by the recognition that growth in the number of Federal
5 Reasons Your Business Needs Network Monitoring Intivix.com (415) 543 1033 5 REASONS YOUR BUSINESS NEEDS NETWORK MONITORING Your business depends on the health of your network for office productivity.
EXECUTIVE STRATEGY BRIEF Operating highly-efficient datacenters is imperative as more consumers and companies move to a cloud computing environment. With high energy costs and pressure to reduce carbon
Solar Power at Vernier Software & Technology Having an eco-friendly business is important to Vernier. Towards that end, we have recently completed a two-phase project to add solar panels to our building
AIA Provider: Colorado Green Building Guild Provider Number: 50111120 Office Efficiency: Get Plugged In AIA Course Number: EW10.15.14 Speaker: Geoff Overland Credit(s) earned on completion of this course
OCTOBER 2012 TECHNOLOGY NATURAL GAS IN COMMERCIAL BUILDINGS Discussion Questions: 1. If natural gas promises lower operating costs, lower emissions, and greater efficiency over utility grid delivered electricity,
Energy'Saving,'Thermal'Comfort'and'Solar'Power'Information'Sheet' We ve prepared this information sheet to help you to minimise energy consumption and energy costs while maximising thermal comfort at home.
THE ROOFPOINT ENERGY AND CARBON CALCULATOR A NEW MODELING TOOL FOR ROOFING PROFESSIONALS James L. Hoff, VP of Research Center for Environmental Innovation in Roofing Tools and Models Tools require models
HyperQ Storage Tiering White Paper An Easy Way to Deal with Data Growth Parsec Labs, LLC. 7101 Northland Circle North, Suite 105 Brooklyn Park, MN 55428 USA 1-763-219-8811 www.parseclabs.com email@example.com
Heating and cooling Heating and cooling your home can be one of the biggest users of energy. Efficency in this area can bring great savings. Heating and cooling depend on many contributing factors. The
24 th USAEE/IAEE North American Conference July 8-10, 2004, Washington, DC Residential Energy Consumption: Longer Term Response to Climate Change Christian Crowley and Frederick L. Joutz GWU Department
How Using V3 Appliances Virtual Desktop (TCO) is Reduced: A Superior Desktop Experience For Less Money www. ipro-i nc.com/i t Contents VDI Overview...3 Introduction...3 Examining V3 s VDI...3 General Benefits
First Time Home Buyers Energy Efficiency Workshop Guide Why is efficiency important when buying a home? Affordability: lower utility bills Environmental responsibility: reduces your carbon footprint and
Building Energy Management: Using Data as a Tool Issue Brief Melissa Donnelly Program Analyst, Institute for Building Efficiency, Johnson Controls October 2012 1 http://www.energystar. gov/index.cfm?c=comm_
Geothermal A SMARTER WAY TO HEAT AND COOL FOR NEW HOMES ARR-12712 Builder brochure-v2.indd 1 Thanks for Taking a Look. We know that initial cost is only one portion of the investment when deciding to purchase
Preparing Your IT for the Holidays A quick start guide to take your e-commerce to the Cloud September 2011 Preparing your IT for the Holidays: Contents Introduction E-Commerce Landscape...2 Introduction
Automated file management with IBM Active Cloud Engine Redefining what it means to deliver the right data to the right place at the right time Highlights Enable ubiquitous access to files from across the
Business Case for BTI Intelligent Cloud Connect for Content, Co-lo and Network Providers s Executive Summary Cloud computing, video streaming, and social media are contributing to a dramatic rise in metro
September 2010 White Paper The Value of a Content Delivery Network Table of Contents Introduction... 3 Performance... 3 The Second Generation of CDNs... 6 Conclusion... 7 About NTT America... 8 Introduction
A Business Case for Scaling the Next-Generation Network with the Cisco ASR 9000 System: Now with Converged Services Executive Summary In a previous whitepaper ACG Research described the business case for
General information about solar power 1. How do I get solar power? Solar Power Frequently Asked Questions Many companies install solar power systems including some electricity retailers. It is worth comparing
Why and how to save energy at home John Irwin, Sierra Club DE, home owner firstname.lastname@example.org Jack Sol-Church, weatherization instructor Presentation will be posted on DE chapter Sierra Club s website
Efficiency for the Homeowner How to Reduce Your Home s Bills October 2009 National Mall Washington, DC A Quick Test Using Efficient Products and Practices Can: A. Make your home more affordable B. Make
Accelerating Cloud Based Services A White Paper February 2011 1.1 Replify 2011 Table of Contents Executive Summary... 3 Introduction... 4 The Network a Barrier to Cloud Adoption... 4 Current Solutions...
Agenda EasyStreet Online Services, Inc. Data Center Design and Energy Management Introduction to EasyStreet Speaker Bio EasyStreet Sustainability Data Center 1 (Retrofit completed May 2010) Data Center
DataCenter 2020: hot aisle and cold aisle containment efficiencies reveal no significant differences November 2011 Powered by DataCenter 2020: hot aisle and cold aisle containment efficiencies reveal no
Carnegie Mellon University School of Architecture, Department of Mechanical Engineering Center for Building Performance and Diagnostics A Presentation of Work in Progress 4 October 2006 in the Intelligent
Expert Reference Series of White Papers Visions of My Datacenter Virtualized 1-800-COURSES www.globalknowledge.com Visions of My Datacenter Virtualized John A. Davis, VMware Certified Instructor (VCI),
Saving Energy Savings with HVLS Fans Josh Eddy LEED-AP National Sales Manager Big Ass Fans Outline Who is Big Ass Fans HVLS fan types How HVLS fans save energy HVLS fan applications How utilities are helping
AccuLink Zoning Systems PRECISE CONTROL. COMFORTABLE AIR THROUGHOUT. WELCOME TO A HIGHER STANDARD OF COMFORT. INTRODUCING AN INNOVATION FOR THE FUTURE THAT GIVES YOU COMFORT AND CONTROL TODAY. With the
V3 Appliance FAQ Why is the V3 appliance so effective as a physical desktop replacement? The V3 appliance leverages local solid-state storage in the appliance. This design allows V3 to dramatically reduce
WINDOWS SERVER Server uptime, all of the time CNS Windows Server Monitoring provides organizations with the ability to monitor the health and availability of their Windows server infrastructure. Through
WHITE PAPER Solving I/O Bottlenecks to Enable Superior Cloud Efficiency Overview...1 Mellanox I/O Virtualization Features and Benefits...2 Summary...6 Overview We already have 8 or even 16 cores on one
Journal of Scientific & Industrial Research Vol. 73, January 2014, pp. 11-15 Metrics for Computing Performance of Data Center for Instigating Energy Efficient Data Centers Mueen Uddin* 1, Asadullah Shah
Parallels Virtuozzo Containers White Paper Greener Virtualization www.parallels.com Version 1.0 Greener Virtualization Operating system virtualization by Parallels Virtuozzo Containers from Parallels is
Building a better branch office www.citrix.com Introduction The majority of workers today are in branch offices, not in a headquarters facility. In many instances, all of the applications used by branch
Business Case for S/Gi Network Simplification Executive Summary Mobile broadband traffic growth is driving large cost increases but revenue is failing to keep pace. Service providers, consequently, are
White Paper The Benefits of Virtualizing Citrix XenApp with Citrix XenServer This white paper will discuss how customers can achieve faster deployment, higher reliability, easier management, and reduced
Building the Energy-Smart Datacenter How Dell PowerEdge servers, services, tools and partnerships can help customers save money by saving energy. As businesses grow, they need more computational capacity.
White paper on the comparative energy efficiency of zoned electric heaters Convectair, Inc. / Convectair-NMT Inc. September 2004 Contents : 1. Introduction 2. Fundamentals of heating 3. Temperature distribution
Making the Case for Satellite: Ensuring Business Continuity and Beyond July 2008 Ensuring Business Continuity and Beyond Ensuring business continuity is a major concern of any company in today s technology
Amazon Web Services Primer William Strickland COP 6938 Fall 2012 University of Central Florida AWS Overview Amazon Web Services (AWS) is a collection of varying remote computing provided by Amazon.com.
Leveraging Radware s ADC-VX to Reduce Data Center TCO An ROI Paper on Radware s Industry-First ADC Hypervisor Table of Contents Executive Summary... 3 Virtual Data Center Trends... 3 Reducing Data Center
Heating Oil Conservation and Fuel Switching Summary: Demand Side Management for Heating Oil Demand side management (DSM) is the modification of consumer demand for energy through various methods such as
Center for Energy and Environment Energy Savings with Window Retrofits Presentation to Energy Design Conference & Expo Duluth, MN February 25, 2014 Agenda v Background v Introduction: What are window retrofits?
Chapter 1: Networking with Microsoft Learning Objectives Plan what network model to apply to your network Compare the differences between Windows 2000 Professional, Server, Advanced Server, and Datacenter
Goals Cloud Computing COMP755 Understand what cloud computing is and how it functions Understand the challenges and advantages of cloud computing Many slides were created by Peter Mell, Tim Grance of NIST
Your consent to our cookies if you continue to use this website.