1 24 1. NETWORK CONFIGURATIONS definition Standard IEC 38 defines voltage ratings as follows: - Low voltage () For a phase-to-phase voltage between 100 V and 1000 V. The standard ratings are: 400 V V V (at 50 Hz) - Medium voltage () - High voltage (HV) For a phase-to-phase voltage between 1000 V and 35 kv. The standard ratings are: 3.3 kv kv - 11 kv - 22 kv - 33 kv For a phase-to-phase voltage between 35 kv and 230 kv. The standard ratings are: 45 kv - 66 kv kv kv kv kv General structure of the private distribution network Generally, with an HV power supply, a private distribution network comprises (see fig. 1-1): - an HV consumer substation fed by one or more sources and made up of one or more busbars and circuit-breakers - an internal production source - one or more HV/ transformers - a main switchboard made up of one or more busbars - an internal network feeding secondary switchboards or / substations - loads - / transformers - low voltage switchboards and networks - low voltage loads.
2 25 supply source HV consumer substation internal production HV main distribution switchboard load load load internal distribution network secondary distribution switchboards switchboards and distribution load load Figure 1-1: general structure of a private distribution network
3 The supply source The power supply of industrial networks can be in, or HV. The voltage rating of the supply source depends on the consumer supply power. The greater the power, the higher the voltage must be HV consumer substations The most usual supply arrangements adopted in HV consumer substations are: single power supply (see fig. 1-2) supply source HV busbar to main switchboard Figure 1-2: single fed HV consumer substation advantage: drawback: Reduced cost Low availability N.B.: the isolators associated with the HV circuit-breakers have not been shown.
4 27 dual power supply (see fig. 1-3) source 1 source 2 devices operated bythe utility HV busbar HV HV to main switchboard Figure 1-3: dual fed HV consumer substation operating mode: - normal: Both incoming circuit-breakers are closed, as well as the coupler isolator. The transformers are thus simultaneously fed by 2 sources. - disturbed: If one source is lost, the other provides the total power supply. advantages: - good availability in that each source can supply the entire network - maintenance of the busbar possible while it is still partially operating drawbacks: - more costly solution than the single power supply system - only allows partial operation of the busbar if maintenance is being carried out on it N.B.: the isolators associated with the HV circuit-breakers have not been shown.
5 28 dual fed double bus system (see fig. 1-4) source 1 source 2 coupler or BB1 BB2 HV double busbar Out1 Out2 Out3 Out4 HV HV to main switchboard Figure 1-4: dual fed double bus HV consumer substation operating mode: - normal: Source 1 feeds busbar BB1 and feeders Out1 and Out2. Source 2 feeds busbar BB2 and feeders Out3 and Out4. The bus coupler circuit-breaker can be kept closed or open. - disturbed: If one source is lost the other provides the total power supply. If a fault occurs on a busbar (or maintenance is carried out on it), the bus coupler circuit-breaker is tripped and the other busbar feeds all the outgoing lines. advantages : - good supply availability - highly flexible use for the attribution of sources and loads and for busbar maintenance - busbar transfer possible without interruption (when the busbars are coupled, it is possible to operate an isolator if its adjacent isolator is closed). drawback: - more costly in relation to the single busbar system N.B.: the isolators associated with the HV circuit-breakers have not been shown.
6 power supply We shall first look at the different service connections and then the consumer substation Different service connections According to the type of network, the following supply arrangements are commonly adopted. single line service (see fig. 1-5) overhead line Figure 1-5: single line service The substation is fed by a single circuit tee-off from an distribution (cable or line). Up to transformer ratings of 160 kva this type of service is very common in rural areas. It has one supply source via the utility.
7 31 ring main principle (see fig. 1-6) underground cable ring main Figure 1-6: ring main service Ring main units (RMU) are normally connected to form an ring main or interconnectordistributor, such that the RMU busbars carry the full ring main or interconnector current. This arrangement provides the user with a two-source supply, thereby reducing considerably any interruption of service due to system faults or switching operations by the supply authority. The main application for RMU's is in public-supply underground cable networks in urban areas.
8 32 parallel feeder (see fig. 1-7) parallel underground-cable utility Figure 1-7: duplicated supply service When an supply connection to two lines or cables originating from the same busbar of a substation is possible, a similar switchboard to that of an RMU is commonly used. The main operational difference between this arrangement and that of an RMU is that the two incoming panels are mutually interlocked, such that only one incoming switch can be closed at a time, i.e. its closure prevents that of the other. On loss of power supply, the closed incoming switch must be opened and the (formerly open) switch can then be closed. The sequence may be carried out manually or automatically. This type of switchboard is used particularly in networks of high load density and in rapidly expanding urban areas supplied by underground cable systems.
9 consumer substations The consumer substation may comprise several transformers and outgoing feeders. The power supply may be a single line service, ring main principle or parallel feeder (see 1.4.1). Figure 1.8 shows the arrangement of an consumer substation using a ring main supply with transformers and outgoing feeders CT VT feeders Figure 1-8: consumer substation
10 networks inside the site networks are made up of switchboards and the connections feeding them. We shall first of all look at the different supply modes of these switchboards, then the different network structures allowing them to be fed. Note: the isolators and drawout systems which allow maintenance to be carried out on the installation have not been shown on the diagrams switchboard power supply modes We shall start with the main power supply solutions of an switchboard, regardless of its place in the network. The number of sources and the complexity of the switchboard differ according to the level of dependability required. The diagrams have been classed in order of improving dependability but increasing installation cost. 1 busbar, 1 supply source (see fig. 1-9) source busbar feeders Figure 1-9: 1 busbar, 1 supply source operation: if the supply source is lost, the busbar is put out of service until the fault is repaired.
11 35 1 busbar with no coupler, 2 supply sources (see fig. 1-10) source 1 source 2 or busbar feeders Figure 1-10: 1 busbar with no coupler, 2 supply sources operation: both sources can operate in parallel or one source can back up the other. If a fault occurs on the busbar (or maintenance is carried out on it), the outgoing feeders are no longer fed. 2 bus sections with coupler, 2 supply sources (see fig. 1-11) source 1 source 2 or busbar feeders Figure 1-11: 2 bus sections with coupler, 2 supply sources operation: the coupler circuit-breaker can be held closed or open. If it is open, each source feeds one bus section. If one source is lost, the coupler circuit-breaker is closed and the other source feeds both bus sections. If a fault occurs on a bus section (or maintenance is carried out on it), only one part of the outgoing feeders is no longer fed.
12 36 1 busbar with no coupler, 3 supply sources (see fig. 1-12) source 1 source 2 source 3 or busbar feeders Figure 1-12: 1 busbar with no coupler, 3 supply sources operation: the three sources can operate in parallel or one source can back up the other two. If If a fault occurs on a bus section (or maintenance is carried out on it), the outgoing feeders are no longer fed. 3 bus sections with couplers, 3 supply sources (see fig. 1-13) source 1 source 2 source 3 or or busbar feeders Figure 1-13: 3 bus sections with couplers, 3 supply sources operation: both bus coupler circuit-breakers can be kept open or closed. If they are open, each supply source feeds its own bus section. If one source is lost, the associated coupler circuit-breaker is closed, one source feeds 2 bus sections and the other feeds one bus section. If a fault occurs on one bus section (or if maintenance is carried out on it), only one part of the outgoing feeders is no longer fed.
13 37 "duplex" distribution system (see fig. 1-14) source 1 source 2 coupler BB1 BB2 double busbar Out1 Out2 Out3 Out4 feeders Figure 1-14: "duplex" distribution system operation: The coupler circuit-breaker is held open during normal operation. Each source can feed one or other of the busbars via its two drawout circuit-breaker cubicles. For economic reasons, there is only one circuit-breaker for the two drawout cubicles which are installed alongside one another. It is thus easy to move the circuit-breaker from one cubicle to the other. Thus, if source 1 is to feed busbar BB2, the circuit-breaker is moved into the other cubicle associated with source 1. The same principle is used for the outgoing feeders. Thus, there are two drawout cubicles and only one circuit-breaker associated with each outgoing feeder. Each outgoing feeder can be fed by one or other of the busbars depending on where the circuit-breaker is positioned. For example, source 1 feeds busbar BB1 and feeders Out1 and Out2. Source 2 feeds busbar BB2 and feeders Out3 and Out4. If one source is lost, the coupler circuit-breaker is closed and the other source provides the total power supply. If a fault occurs on one of the busbars (or maintenance is carried out on it), the coupler circuitbreaker is opened and each circuit-breaker is placed on the busbar in service, so that all the outgoing feeders are fed. The drawback of the "duplex" system is that it does not allow automatic switching. If a fault occurs, each changeover lasts several minutes and requires the busbars to be de-energized.
14 38 2 busbars, 2 connections per outgoing feeder, 2 supply sources (see fig. 1-15) source 1 source 2 coupler BB1 BB2 double busbar Out1 Out2 Out3 Out4 feeders Figure 1-15: 2 busbars, 2 connections per outgoing feeder, 2 supply sources operation: the coupler circuit-breaker is held open during normal operation. Each outgoing feeder can be fed by one or other of the busbars depending on the state of the isolators which are associated with it and only one isolator per outgoing feeder must be closed. For example, source 1 feeds busbar BB1 and feeders Out1 and Out2. Source 2 feeds busbar BB2 and feeders Out3 and Out4. If one source is lost, the coupler circuit-breaker is closed and the other source provides the total power supply. If a fault occurs on a busbar (or maintenance is carried out on it), the coupler circuit-breaker is opened and the other busbar feeds all the outgoing feeders.
15 39 2 interconnected double busbars (see fig. 1-16) source 1 source 2 CB1 BB1 2double bus switchboards CB2 BB2 Out1 Out2 Out3 Out4 feeders Figure 1-16: 2 interconnected double busbars operation: this arrangement is almost identical to the previous one (2 busbars, 2 connections per feeder, 2 supply sources). The splitting up of the double busbars into two switchboards with coupler (via CB1 and CB2) provides greater operating flexibility. Each busbar feeds a smaller number of feeders during normal operation.
16 network structures We shall now look at the main network structures used to feed secondary switchboards and / transformers. The complexity of the structure differs depending on the level of dependability required. The following network supply arrangements are the ones most commonly adopted: single fed radial network (see fig. 1-17) source 1 source 2 main switchboard switchboard1 switchboard2 Figure 1-17: single fed radial network - the transformers and switchboards 1 and 2 are fed by a single source and there is no back-up supply - this structure should be used when availability is not a high requirement and it is often adopted for cement works networks.
17 41 dual fed radial network with no coupler (see fig. 1-18) source 1 source 2 main switchboard switchboard1 switchboard2 Figure 1-18: dual fed radial network with no coupler - switchboards 1 and 2 are fed by 2 sources with no coupler, the one backing up the other - availability is good - the fact that there is no source coupler for switchboards 1 and 2 renders the network less flexible to use.
18 42 dual fed radial network with coupler (see fig. 1-19) source 1 source 2 main switchboard switchboard1 switchboard2 Figure 1-19: dual fed radial network with coupler Switchboards 1 and 2 are fed by 2 sources with coupler. During normal operation, the bus coupler circuit-breakers are open. - each bus section can be backed up and fed by one or other of the sources - this structure should be used when good availability is required and it is often adopted in the iron and steel and petrochemical industries.
19 43 loop system This system is suitable for widespread networks with large future extensions. There are two types depending on whether operation. the loop is open or closed during normal open loop (see fig a) source 1 source 2 or main switchboard A B switchboard 1 switchboard 2 switchboard 3 Figure 1-20 a: open loop system - the loop heads in A and B are fitted with circuit-breakers. - switchboards 1, 2 and 3 are fitted with switches. - during normal operation, the loop is open (on the figure it is open at switchboard 2). - the switchboards can be fed by one or other of the sources. - reconfiguration of the loop enables the supply to be restored upon occurrence of a fault or loss of a source (see of the Protection guide). - this reconfiguration causes a power cut of several seconds if an automatic loop reconfiguration control has been installed. The cut lasts at least several minutes or dozens of minutes if the loop reconfiguration is carried out manually by operators.
20 44 closed loop (see fig b) source 1 source 2 main switchboard switchboard 1 switchboard 2 switchboard 3 Figure 1-20 b: closed loop system - all the loop switching devices are circuit-breakers. - during normal operation, the loop is closed. - the protection system ensures against power cuts due to a fault (see of the Protection guide). This system is more efficient than the open loop since it avoids power cuts. On the other hand, it is more costly since it requires circuit-breakers in each switchboard and a more developed protection system.
21 45 parallel feeder (see fig. 1-21) source 1 source 2 or main switchboard switchboard 1 switchboard 2 switchboard 3 Figure 1-21: parallel feeder network - switchboards 1, 2 and 3 can be backed up and fed by one or other of the sources independently. - this structure is suitable for widespread networks with limited future extensions and which require good availability.
22 networks inside the site We shall first of all study the different low voltage switchboard supply modes. Next, we shall look at the supply schemes for switchboards backed up by generators or an uninterruptible power supply switchboard supply modes We are now going to study the main supply arrangements for an switchboard, regardless of its place in the network. The number of supply sources possible and the complexity of the switchboard differ according to the level of dependability required. single fed switchboards example (see fig. 1-22) : supply source S1 S2 S3 Figure 1-22: single fed switchboards Switchboards S1, S2 and S3 have only one supply source. The network is said to be of the arborescent radial type. If a switchboard supply source is lost, the switchboard is put out of service until the supply is restored.
23 47 dual fed switchboards with no coupler example (see fig. 1-23): source 1 source 2 CB1 CB2 source 3 S1 CB3 CB4 S2 Figure 1-23: dual fed switchboards with no coupler Switchboard S1 has a dual power supply with no coupler via 2 / transformers. Operation of the S1 power supply : - both sources feed switchboard S1 in parallel. - during normal operation only one circuit-breaker is closed (CB1 or CB2). Switchboard S2 has a dual power supply with no coupler via an / transformer and outgoing feeder coming from another switchboard. Operation of the S2 power supply: - one source feeds switchboard S2 and the second provides a back-up supply. - during normal operation only one circuit-breaker is closed (CB3 or CB4)
24 48 dual fed switchboards with coupler example (see fig. 1-24): source 1 source 2 S1 CB1 CB3 CB2 source 3 CB4 CB5 S2 CB6 Figure 1-24: dual fed switchboards with coupler Switchboard S1 has a dual power supply with coupler via 2 / transformers. Operation of the S1 power supply: during normal operation, the coupler circuit-breaker CB3 is open. Each transformer feeds a part of S1. If a supply source is lost, the circuit-breaker CB3 is closed and a single transformer feeds all of S1. Switchboard S2 has a dual power supply with coupler via an / transformer and an outgoing feeder coming from another switchboard. Operation of the S2 power supply: during normal operation, the circuit-breaker CB6 is open. Each source feeds part of S2. If a source is lost, the coupler circuit-breaker is closed and a single source feeds all of S2.
25 49 triple fed switchboards with no coupler example (see fig. 1-25): source 1 source 2 source 3 S1 Figure 1-25: triple fed switchboards with no coupler Switchboard S1 has a triple power supply with no coupler via 2 / transformers and an outgoing feeder coming from another switchboard. During normal operation, the switchboard is fed by 2 transformers in parallel. If one or both of the transformers fail, switchboard S1 is fed by the outgoing feeder coming from another switchboard.
26 50 triple fed switchboards with coupler example (see fig. 1-26): source 1 source 2 source 3 CB1 CB2 S1 Figure 1-26: triple fed switchboards with coupler Switchboard S1 has a triple power supply with coupler via 2 / transformers and an outgoing feeder coming from another switchboard. During normal operation, the two coupler circuit-breakers are open and switchboard S1 is fed by 3 supply sources. If one source fails, the circuit-breaker of the associated source is closed and the incoming circuit-breaker of the source that has been lost is tripped.
27 switchboards backed up by generators example 1: 1 transformer and 1 generator (see fig. 1-27) source 1 S1 G CB1 mains/standby CB2 S2 non priority circuits priority circuits Figure 1-27: 1 transformer and 1 generator During normal operation CB1 is closed and CB2 open. Switchboard S2 is fed by the transformer. If the main source is lost, the following steps are carried out: 1. The mains/standby changeover switch is operated and CB1 is tripped. 2. Load shedding if necessary of part of the loads on the priority circuit in order to limit the load impact on the generator. 3. Start-up of the generator. 4. CB2 is closed when the frequency and voltage of the generator are within the required ranges. 5. Reloading of loads which may have been shed during step 2. Once the main source has been restored, the mains/standby changeover device switches the S2 supply to the mains and the generator is stopped.
28 52 example 2: 2 transformers and 2 generators (see fig. 1-28) source 1 source 2 TR1 TR2 G G CB4 CB5 S2 S3 CB1 CB2 mains/ standby CB3 S1 non priority circuits priority circuits Figure 1-28: 2 transformers and 2 generators During normal operation, the coupler circuit-breaker CB1 is open and the mains/standby changeover device is in position CB2 closed and CB3 open. Switchboard S1 is fed by transformer TR2. If source 2 is lost or there is a breakdown on TR2, the S1 (and part of S2) standby supply is given priority by transformer TR1, after reclosing of the coupler circuit-breaker CB1. The generators are only started-up after the loss of the 2 main supply sources or the S2 busbar. The steps for saving the priority circuit supply are carried out in the same way as in example 1.
29 switchboards backed up by an uninterruptible power supply (UPS) The main devices making up a UPS system are shown in figure 1-29 and table 1-1. (5) manual by-pass network 2 supply network incoming feeders network 1 (7) switch or circuit-breaker (8) switch (4) static contactor _ ~ _ ~ (1) rectifiercharger (3) inverter (9) switch (6) battery circuit-breaker load (2) battery Figure 1-29: uninterruptible power supply system
30 54 Device name Ref. n Function Rectifier-charger (1) Transforms the alternating voltage of a supply network into a direct voltage which will: - feed the inverter on the one hand, - continually provide the charge of the storage battery on the other Storage battery (2) Provides a back-up supply to feed the inverter in case: - the supply network disappears, - the supply network is disturbed. Inverter (3) Transforms the direct voltage from the rectifier-charger or storage battery into alternating voltage with more severe tolerances than those of the network (supplies an alternating current close to the theoretical sine curve). Static contactor (4) Switches over the load supply from the inverter to network 2 (standby), and vice versa, without interruption (no cut due to mechanical switching device changeover time - the switchover is carried out using electronic components in a time < 1 ms). This switchover is performed if the inverter stops working for one of the following reasons: - switched off, - overload beyond the limiting capacities of the inverter, - internal anomaly. Manual by-pass (5) Manual switch which allows the user to be fed by network 2 (standby), while maintenance is being carried out. Manual switches Battery circuitbreakers (6) (7) (8) (9) Provides insulation of the different parts when maintenance is being carried out Tableau 1-1: function of different devices making up an uninterruptible power supply system
31 55 network incoming feeder(s) The terms network 1 and network 2 designate two independent incoming feeders on the same network: - network 1 (or mains) designates the incoming feeder usually supplying the rectifier-charger, - network 2 (or standby) is said to be a back-up feeder. The inverter's frequency and phase are synchronised with network 2. Thus, the static contactor can instantaneously switch the power supply to network 2 (in less than 1 ms). The connection of a UPS system to a second independent network is recommended since it increases the reliability of the system. It is nevertheless possible to have only one common incoming feeder. The choice of an uninterruptible power supply structure depends on the quality of networks 1 and 2, the use and the availability required. The manufacturer must provide the designer with sufficient elements for him to choose the most suitable structure. The following examples show the most common structures. example 1: switchboard backed up by an inverter, with a generator to eliminate the problem of the limited autonomy of the battery (usually about 15 mn) (see fig. 1-30) G non priority circuits filter ~ ~ Figure 1-30: switchboard backed up by an inverter The filter allows harmonic currents travelling up the supply network to be reduced.
32 56 example 2: switchboard backed up by 2 inverters in parallel with no redundancy (voir fig. 1-31) source G network 2 non priority circuits network 1 filter filter ~ ~ ~ ~ P 2 P 2 P priority circuits Figure 1-31: switchboard backed up by 2 inverters in parallel with no redundancy This configuration only allows an overall power capacity above that of a single rectifier/inverter unit. The power P to be supplied is also divided between the 2 inverters. A fault in one of the units leads to the load being switched to network 2 without interruption, except if the network is beyond its tolerance level.
33 57 example 3: switchboard backed up by 3 inverters one of which is actively redundant (see fig. 1-32) source G non priority circuits filter filter filter ~ ~ ~ ~ ~ ~ P 2 P 2 P 2 P priority circuits Figure 1-32: switchboard backed up by 3 inverters one of which is actively redundant Let P be the maximum load rating of the priority circuit. P Each inverter has a rated power of, which means that when one inverter breaks down, the 2 other two inverters provide the total load power supply. This is referred to as a parallel-connected unit with 1/3 active redundancy.
34 58 example 4: switchboard backed up by 3 inverters one of which is on standby redundancy (see fig. 1-33) source G non priority circuits 3 ~ ~ 1 network 2 network 1 ~ ~ priority circuits ~ _ 2 _ ~ priority circuits Figure 1-33: switchboard backed up by 3 inverters one of which is on standby redundancy Inverter 3 is not charged, it is on standby ready to back up inverters 1 or 2. There is no power cut during switchover due to static contactors 1 and 2. Static contactor 3 provides back-up via network 2 in case there is a failure on network 1, or the 2 inverters break down. This is referred to as a parallel-connected unit with standby redundancy.
35 Industrial networks with internal production example (see fig. 1-34) : Network structure: - consumer substation - the main switchboard is fed by the internal production station - some outgoing feeders are fed by the utility and cannot be backed up by the internal production station - an loop system and some outgoing feeders are fed during normal operation by the internal production station. If the production station breaks down, this loop system and its outgoing feeders can be fed by the utility. The publication, translation and reproduction, either wholly or partly, of this document are not allowed without our written consent.
36 61 The publication, translation and reproduction, either wholly or partly, of this document are not allowed without our written consent.
37 Examples of standard networks example 1 (see fig. 1-35) Network structure: - consumer substation in a ring main system with two incoming feeders - main low voltage switchboard backed up by a generator - a priority switchboard fed by an uninterruptible power supply - the low voltage network is the arborescent radial type. The secondary switchboard and terminal boxes are fed by a single source. The publication, translation and reproduction, either wholly or partly, of this document are not allowed without our written consent.
38 63 consumer substation incoming feeders from utility G m meter main switchboard UPS priority switchboard secondary switchboard terminal box terminal box Figure 1-35: example 1 The publication, translation and reproduction, either wholly or partly, of this document are not allowed without our written consent.
39 64 example 2 (see fig. 1-36) Network structure: - consumer substation - the main switchboard can be backed up by a generator set and it feeds 3 transformers - an earthing transformer allows impedance earthing of the neutral when the network is fed by generators - the main low voltage switchboards MS1, MS2 and MS3 are independent and each one has an outgoing feeder to an uninterruptible power supply feeding a priority circuit - the low voltage network is the arborescent radial type. The motor control centres and terminal boxes are fed by a single source. The publication, translation and reproduction, either wholly or partly, of this document are not allowed without our written consent.
40 65 Figure 1-36: example 2 The publication, translation and reproduction, either wholly or partly, of this document are not allowed without our written consent.
41 66 example 3 (see fig. 1-37) Network structure: - consumer substation - the main switchboard can be backed up by a generator set and it feeds 2 / transformers - an earthing transformer allows impedance earthing of the neutral when the network is fed by generators - the main low voltage switchboard has a dual power supply with coupler - each bus section of the main low voltage switchboard has a UPS system feeding a priority circuit - the secondary switchboards, terminal boxes and motor control centres are fed by a single source The publication, translation and reproduction, either wholly or partly, of this document are not allowed without our written consent.
42 67 Figure 1-37: example 3 The publication, translation and reproduction, either wholly or partly, of this document are not allowed without our written consent.
43 68 example 4 (see fig. 1-38) Network structure: - consumer substation - the main switchboard can be backed up by a generator set. It feeds two / transformers in a single line supply system, 4 secondary switchboards in a loop system and a secondary switchboard in a single line supply system - the low voltage network is the arborescent radial type The publication, translation and reproduction, either wholly or partly, of this document are not allowed without our written consent.
44 69 The publication, translation and reproduction, either wholly or partly, of this document are not allowed without our written consent.
45 70 example 5 (see fig. 1-39) Network structure: - consumer substation. - two ratings: 20 kv and 6 kv. - the main switchboard fed in 20 kv can be backed up by a set of 4 generators. It feeds:. an 20 kv network in a loop system comprising 3 secondary switchboards 4, 5 and 6. two 20 kv/6kv transormers in a single line supply system - an earthing transformer allows impedance earthing of the neutral when the network is fed by generators - the main switchboard is made up 2 bus sections fed in 6 kv by 2 sources with coupler. It feeds 3 secondary switchboards and two 6 kv/ transformers in a single line supply system. - the secondary switchboard 2 is fed by 2 sources with coupler and is made up of 2 bus sections. It feeds two 6 kv motors and two 6kV/ transformers in a single line supply system. - the secondary switchboards 1 and 3 are fed by a single source. Each feeds a 6 kv/ transformer and a 6 kv motor. - the main low voltage switchboard MS1 can be backed up by a generator. - the main low voltage switchboard MS2 is fed by 2 sources with coupler. - the main low voltage switchboard MS3 is fed by a single source. - the motor control centres 1 and 3 are fed by a single source. - the motor control centre 2 is fed by 2 sources with no coupler. The publication, translation and reproduction, either wholly or partly, of this document are not allowed without our written consent.
Chapter 1 Network Structures Definition Standard IEC 60038 defines voltage ratings as follows: Low voltage (): for a phase-to-phase voltage of between 100 V and 1,000 V, the standard ratings are: 400 V
ELECTRIC POWER DISTRIBUTION SYSTEMS F.C. Chan General Manager, CLP Engineering Ltd., Hong Kong SAR, China Keywords: Distribution system planning, Load characteristics, Subtransmission Lines, Distribution
Transformerless UPS systems and the 9900 By: John Steele, EIT Engineering Manager Introduction There is a growing trend in the UPS industry to create a highly efficient, more lightweight and smaller UPS
873 13. Electrical network design methodology and application example 874 13. ELECTRICAL NETWORK DESIGN METHODOLOGY AND APPLICATION EXAMPLE The profitability of an industrial installation is directly linked
17 Circuit diagram symbols E 18 CIRCUIT DIAGRAM SYMBOLS electrical network elements three-phase line or cable single-phase line or cable short circuit earth electrode outgoing feeder supply incoming feeder
EVALUATION OF ALTERNATIVE BACKUP PROTECTION SCHEMES ON A 66KV DISTRIBUTION NETWORK F. Malone*, P.D. Doyle *ESB International, Ireland firstname.lastname@example.org ESB International, Ireland email@example.com
How the National Grid System Operates Chris Gorman Lead Account Executive Syracuse 2 Parts of the Electric System Parts of the Electric System 1. Generating Station: Produces Electricity. 2. Transmission
CE - BF - C - en - REV.00 2012.4 APPLICATION CE-BF Switchbords up to 40.5 kv are designed for use in public and industrial distribution system up to 40,5KV for the operation and protection of lines, transformers,
300 300 Principles of Power System CHAPTER CHAPTER 12 Distribution Systems General 12.1 Distribution System 12.2 Classification of Distribution Systems 12.3 A.C. Distribution 12.4 D.C. Distribution 12.5
1 Generator Stator Protection, under/over voltage, under /over frequency and unbalanced loading By Ramandeep Kaur Aujla S.NO 250447392 ES 586b: Theory and applications of protective relays Department of
14 SWITCHGEAR Secondary Unit Substations Overview Siemens offers a wide variety of unit substation designs to meet customer requirements. A unit substation consists of one or more transformers mechanically
Transformers Special transformers Reactors products Reactors Custom designed, custom built ABB Oy Transformers has extensive experience and numerous references from different reactor applications, having
LIMITING SHORT-CIRCUIT CURRENTS IN MEDIUM-VOLTAGE APPLICATIONS Terence Hazel Senior Member IEEE Schneider Electric 38050 Grenoble France Abstract The power requirements for large industrial sites is increasing.
Basis of Design This section applies to the design relating to low voltage switchboards. Design Criteria UW Class N1 facilities main switchboards shall be rear accessible. The main, tie and feeder breakers
NATUS NES / NES-H Draw-out Type Medium Voltage Switchgear Systems Safe energy distribution that meets the highest industrial requirements NATUS switchgear systems your advantages minimal use of insulant
PTCC Controller Nu-Lec Training Modules Product Training Operator Training PTCC The Basics An overview of the construction and physical features of the Pole Top Control Cubicle PTCC Operation and Features
CEMEP UPS The high environmental performance solution for power supply to high-availability data centers Exchanges of information and communication needs are growing at an exponential rate. That growth
Relion Power system protection and automation reference Extending substation life cycle with IEC 61850 Extending substation life cycle with IEC 61850 A step-by-step power system retrofit approach for optimizing
Collection Technique... Cahier technique no. 196 Integration of local power generation in industrial sites and commercial buildings T. Hazel "Cahiers Techniques" is a collection of documents intended for
White Paper: HMRP-WP001-A5 June 5, 2012 415V DISTRIBUTION FOR GREEN DATA CENTERS Prepared by: Anthony (Tony) Hoevenaars, P. Eng President and CEO Mirus International Inc. Copyright 2012 Mirus International
Secure your electrical network The Safety Solution for Healthcare Institutions Fast Secure : the solution for fault isolation and electrical network restoration in less than 500 ms 03 A Real Time System
THE MERLIN GERIN KNOW-HOW UPS topologies and standards UPS topologies and standards Authors: J.P. BEAUDET - J.N. FIORINA - O. PINON Contents 1. abstract... 2 2. standards... 3 the need for a new standard...
he Application and Benefits of Multi-phase Auto-reclosing etsuya Miyoshi*, Atsushi Kasai* Abstract - In this paper we explain the disadvantages in using single- and three-phase auto-reclosing on double
Relion Power system protection and automation reference Fast substation busbar protection with IEC 61850 and GOOSE Fast substation busbar protection with IEC 61850 and GOOSE Falu Elnät AB applies new power
Medium Voltage (MV) & High Voltage (HV) Training Module 6 Date of the presentation Electrical System Basics MV vs. HV - Definitions Differences between USA and the rest of the world IEC define a high voltage
1 Nuclear Power Plant Electrical Power Supply System Requirements Željko Jurković, Krško NPP, firstname.lastname@example.org Abstract Various regulations and standards require from electrical power system of the
PROPOSAL FOR A NEW ELECTRICAL SUPPLY OF THE COMPUTER CENTRE FOR LHC A. Funken Abstract To handle the future LHC experiment needs, the Computer Centre will go through a complete change of data processing
Bruno Rivas, Guarulhos - Brazil, April 2015 Jornadas Técnicas de ABB en Perú Innovation on Medium Voltage Switchgear May 5, 2015 Slide 1 Application 5. Mai 2015 Slide 2 Unigear ZS1 Design concepts: Single
Chapter D MV & architecture selection guide 1 2 3 4 5 6 7 8 Contents Stakes for the user Simplified architecture design process 2.1 The architecture design D4 2.2 The whole process D5 Electrical installation
Design of electrical power system for a 1000MW nuclear power generating station K Raja, K Yesunadam Dept. of Electrical & Electronics Engineering, Lingaya s Institute of Management & Technology, Vijayawada,
Comparison of GIS and AIS systems for urban supply networks Studies carried out by ABB show that for urban supply networks the combination of HV gas-insulated switchgear (GIS) and HV cable has important
IEC 61850 in ZX Gas-insulated medium voltage switchgear IEC 61850 in ZX Just as the supply of electrical power is becoming more and more important in a networked world, demands for the integration of electrical
Primary and Secondary Electrical Distribution Systems Critical Facilities Round Table 12th Quarterly Membership Meeting June 2, 2006 David D. Roybal. P.E. Eaton Electrical Cutler-Hammer Products Utility
Product overview brochure ABB Medium Voltage Products Our one-stop approach for every medium voltage application Overview ABB meets every need for reliable, safe and energy-efficient medium voltage switchgear,
30 ms High Speed Transfer System (HSTS) Product Description 2 30 ms High Speed Transfer System (HSTS) Product Description Content Page 1 General 5 1.1 Description of the 30 ms high speed transfer system
What will MV switchgear look like in the future? by Jean-Marc Biasse Table of contents Introduction... 2 Brief history of the technologies used in medium voltage switchgear and control gear... 4 Evolution
Power products and systems Intelligent solutions for power distribution Zone concept Securing continuous power supply ABB is one of the world's leading power and automation technology companies whose products,
SWITCHEA EP Switchgear Cat generator set paralleling switchgear has been designed to integrate with Cat EMCP3 generator set controls. Now you can get greater efficiency, reliability and dependability all
Defining data center availability via a tier classification system MIETEK GLIKOWSKI All systems can fail this is a simple fact that every industry must deal with. The paramount concern for the data center
Power Voltage Transformers for Air Insulated Substations THE PROVEN POWER. Introduction Trench Power Voltage Transformers (Power VTs) combine the attributes of an inductive voltage transformer with the
CONSOLIDATED EDISON COMPANY OF NEW YORK, INC. 4 IRVING PLACE NEW YORK, NY 10003 DISTRIBUTION ENGINEERING, NETWORK SYSTEMS SECTION SPECIFICATION EO-2134 REVISION 2 DECEMBER, 2012 CLOSED TRANSITION TRANSFER
Rectiverter Wiki The RECTIVERTER is a technology created by Eltek. The Rectiverter is a three port module with an AC input port, an AC output port, and a bidirectional DC port. It is intended for the use
Power Voltage Transformers for Air Insulated Switchgear Introduction Trench Power Voltage Transformers (Power VTs) combine the attributes of an inductive voltage transformer with the application of a small
OPTIMIZING POWER SYSTEM PROTECTION FOR MODERN DATA CENTERS Data center power systems are constructed with a premium on reliability at a significant cost. The return on this investment is realized if it
Current and voltage measuring relays RXIK 1, RXEEB 1 and Page 1 Issued June 1999 Changed since July 1998 Data subject to change without notice RXIK 1 RXEEB 1 (SE980082) (SE980081) (SE970869) Features Application
ES281 COMPANY-SPECIFIC APPENDICES TO ENA ENGINEERING RECOMMENDATION G81 PART 1 Design and Planning Specification for New Low Voltage Installations for Housing Developments 1. SCOPE This appendix to ENA
Technical Specification Of Substation Protection & Control System with IEC 61850 BHEL s Perspective India Core Events 2008 September 24 th 2008 1 Background Stability & Reliability Data Storage Communication
Advantages of Fixed Circuit Breaker Switchgear by Lionel Mackay, EDF Energy, and Mike Adams, Schneider Electric Ltd Introduction The purpose of this paper is to review the advantages of fixed circuit breaker
POWER SUPPLY SYSTEMS AND ELECTRICAL EQUIPMENT FOR DESALINATION PLANTS Y.M. Hamud and A.H. Anwar Abu Dhabi Water and Electricity Authority, Abu Dhabi, UAE Keywords : Electrical System, Network for Desalination,
STATIC TRANSFER SWITCHES SS, SSN, SST, SSTN SERIES STS AC & DC POWER SOLUTIONS APPLICATION Static Transfer Switches (STS) are designed to transfer supply between independent one-phase or three-phase AC
Fundamentals of Modern Electrical Substations Part 1: Mission of Electrical Substations and their Main Components Course No: E02-010 Credit: 2 PDH Boris Shvartsberg, Ph.D., P.E., P.M.P. Continuing Education
Distribution Inside Large Buildings In large buildings the type of distribution depends on the building type, dimension, the length of supply cables, and the loads. The distribution system can be divided
1. SCOPE This document details PowerSystems requirements for electrical testing of HV Equipment up to and including 33kV. 2. ISSUE RECORD This is a Reference document. The current version of Controlled
MUST 30-120 3 Phase Modular UPS Finally the benefits of Modular ups are for all MUST 30-120 MUST means Modular UPS System Three-phase MUST 30-120 is an uninterruptible power supply with double conversion
Title: Australian Guidelines for grid connection of energy systems via inverters. Foreword 28 April, 1998 The guidelines have been developed by a group of utility, photovoltaic and inverter industry experts
Switchgear pplication Issues for Mission Critical Power Systems, Part One BSTRCT With the advent of high reliability data centers and telecommunication facilities, designers of commercial power face new
Customer Installations Advice No. 1367 19/8/ 2011 Doc. Ref. Service and Installation Rules of NSW TO: Customers, Service Providers, Electrical Contractors and Ausgrid Staff Amendments to the Service and
ABB s Disconnecting Circuit Breakers Higher substation availability and lower environmental impact Authors Carl Ejnar Sölver, ABB High Voltage Products Rasmus Larsson, ABB High Voltage Products 2 ABB ABB
Quality Uninterruptible Supply In the electrical system environment, power disturbances will occur. These can be caused by faults on the distribution system, the operation of nearby equipment, lightning
Medium voltage products UniSec for Smart Grid Air-insulated medium-voltage secondary distribution switchgear Index 3 Overview 4 Standard Levels 6 Monitoring & Control 7 Measurements 8 Protection & Logic
Critical-Power Automatic Transfer Systems Design and Application Bill Brown, P.E., Jay Guditis, Square D Critical Power Competency Center 1. INTRODUCTION An important requirement of mission-critical electric
White Paper: HMRP-WP001-A1 October 1, 2010 415V DISTRIBUTION FOR GREEN DATA CENTERS Prepared by: Anthony (Tony) Hoevenaars, P. Eng President and CEO Mirus International Inc. Copyright 2005 Mirus International
AUTOMATIC TRANSFER SWITCH Changeover Type from 250A to 2500A Table of Contents Preamble 1.1 Theoretical base 1.2 Selection the size of automatic transfer switch 1.3 Automatic transfer switch components
Specification Requirements DBL 700MX and 1000MX Series UPS Theory of Operation Upon loss of utility power, the UPS inverter shall continue to provide seamless pure sine-wave AC from the batteries without
Electrical Network Management System Optimisation of the electrical network Measure to understand Understand to control Control to optimise Cost of power and fluids Power quality Power availability 2 Improvement
Advances in Medium and Low Voltage Power Distribution ESS Metron Expo and Technical Seminars Presented By: Greg Pelster & Robert Schmid FFI Ferrie, Franzmann Industries LOW VOLTAGE SWITCHGEAR & LOW VOLTAGE
Guide for High Voltage Shore Connection GUIDE FOR HIGH VOLTAGE SHORE CONNECTION NOVEMBER 2011 American Bureau of Shipping Incorporated by Act of Legislature of the State of New York 1862 Copyright 2011
ECE 586b Course Project Report Auto-Reclosing Srichand Injeti May 5, 2008 Department Of Electrical and computer Engineering University Of Western Ontario, London Ontario Table of contents 1. Introduction...1
ATS - Automatic Changeover Manufacturers of Electrical Switchgear Choosing an Automatic Transfer System Switchgear Systems offer a variety of solutions for multiple supply switching needs. As well as our
RIELLO ELETTRONICA Master HP LOCAL AREA NETWORKS (LAN) SERVERS DATA CENTRES TELECOM- MUNICATIONS DEVICES E-BUSINESS (Servers Farms, ISP/ASP/POP) INDUSTRIAL PROCESSES INDUSTRIAL PLCS ELECTRO- MEDICAL DEVICES
SHORT-CIRCUIT CALCULATION INTRODUCTION Designing an electrical system is easy and simple, if only the normal operation of the network is taken into consideration. However, abnormal conditions which are
08/17/12 Rev2 LTR Series General Specification 700 VA to 2.1 KVA 1.0 General LTR Series Uninterruptible Power Systems 700 VA - 2.1 KVA General Specification This specification describes the features and
Paralleling Switchgear By Maurice D Mello, P.Eng. Systems Engineer, GE Consumer & Industrial, Canada What is Paralleling? Paralleling is the operation in which multiple power sources, usually two or more
Guideline for Energy Efficient Electrical systems for building Presentation by TERI Objective of study The study highlights how BBMP can implement energy efficiency measures in building in co-ordination
Active protection for switchgear ABB AG Oberhausener Strasse 4047 Ratingen, Germany Phone: +49 0-0 Fax: +49 0-7 77 Note: We reserve the right to make technical changes or modify the contents of this document
Rule 5.500 Fast Track Analysis for National Life Insurance Co. For a 500 kw Solar array to be located at 155 Northfield Street in Montpelier, Vermont Green Mountain Power Pam Allen Date: 5/31/13 SECTION
MULTILIN GER-3178 GE Power Management Local Back-up Protection for an Electric Power System LOCAL BACK UP PROTECTION FOR AN ELECTRIC POWER SYSTEM J. BERDY TABLE OF CONTENTS Transmission Line Back-Up Protection...............................................