1 Installation Operation Maintenance 2008 Heat Transfer Products, Inc. Phoenix Water Heater Models* PH / / PH / / PH / / Phoenix Sanitizer Booster Models* SA / SA *A suffix of LP denotes propane gas
2 If the information in this manual is not followed exactly, a fire or explosion may result causing property damage, personal injury or loss of life. Do not try to light any appliance. Do not touch any electrical switch: do not use any phone in your building. Immediately call your gas supplier from a neighbor's phone. Follow the n WARNING WHAT TO DO IF YOU SMELL GAS WARNINGS Do not store or use gasoline or other flammable vapors and liquids in the vicinity of this or any other appliance. gas supplier's instructions. If you cannot reach your gas supplier, call the fire department. Installation and service must be performed by a qualified installer, service agency or the gas supplier. 1
3 CONTENTS CONTENTS Part 1 Product and Safety Information Part 2 How The Phoenix Operates Part 3 Prepare Water Heater Location A. Installations Must Comply With: B. Before Locating the Phoenix C. Clearances for Service Access D. Residential Garage Installation E. Exhaust Vent and Intake Air Vent F. Prevent Combustion Air Contamination G. When Removing a Water Heater from an Existing Common Vent System H. Water Chemistry I. Temperature and Pressure Relief Valve J. Potable Expansion Tank K. Water Piping L. Auxiliary Connection Part 4 Prepare Water Heater A. Electrical Connection B. Gas Connection C. Gas Piping D. Gas Table E. Dungs Gas Valve Part 5 Venting Combustion Air And Condensate Removal A. Installing Exhaust Vent and Intake Air Vent B. General C. Approved Materials for Exhaust Vent and Intake Air Vent D. Exhaust Vent and Intake Air Vent Pipe Location E. Exhaust Vent and Intake Air Vent Sizing F. Longer Vent Runs G. Exhaust Vent and Intake Air Pipe Installation H. Water Heater Removal from a Common Vent System I. Condensate Removal System J. Diagrams for Venting Part 6 Start-up Procedure A. Operating Instructions B. Overall Appliance and Control Operation C. Status Menu D. Test Mode E. Maintenance F. Internal Wiring Part 7 Shutdown A. Shutdown Procedure B. Vacation Procedure C. Failure to Operate Part 8 Troubleshooting A. Phoenix Error Code B. Phoenix Error C. Phoenix Fault 2
4 PRODUCT AND SAFETY INFORMATION PART 1: PRODUCT AND SAFETY INFORMATION n WARNING Installer Read all instructions in this manual, and the Venting section, before installing. Perform steps in the order given. User This manual is for use only by a qualified heating installer/service technician. Refer to User s Information Manual for your reference. User Have this water heater serviced/ inspected by a qualified service technician annually. Failure to comply with the above could result in severe personal injury, death or substantial property damage. n WARNING Failure to adhere to the guidelines on this page can result in severe personal injury, death or substantial property damage. n WARNING WHAT TO DO IF YOU SMELL GAS Do not try to light any appliance. Do not touch any electric switch; do not use any phone in your building. Immediately call your gas supplier from a neighbor's phone. Follow the gas suppliers' instructions. If you cannot reach your gas supplier, call the fire department. SPECIAL ATTENTION BOXES The following defined terms are used throughout this manual to bring attention to the presence of hazards of various risk levels or to important information concerning the product. DEFINITIONS n DANGER DANGER indicates an imminently hazardous situation which, if not avoided, will result in death or serious injury. n CAUTION CAUTION Indicates a potentially hazardous situation which, if not avoided, may result in minor or moderate injury. n WARNING WARNING indicates a potentially hazardous situation which, if not avoided, could result in death or serious injury. CAUTION CAUTION used without the safety alert symbol indicates a potentially hazardous situation which, if not avoided, may result in property damage. 3
5 HOW THE PHOENIX OPERATES PART 2: HOW THE PHOENIX OPERATES Phoenix Modulation Condensing Technology is an intelligent system that delivers highly efficient water heating, while maximizing efficiency by measuring the Data Parameters of your water heating system. 1. Stainless Steel Water Storage Tank The Stainless Steel Water storage tank has a combustion chamber submerged into the tank water. When the water heater is fired, the combustion gases heat the combustion chamber walls, transferring the heat directly into the surrounding water. The hot gases are blown into the secondary heat exchanger coils, where even more heat is transferred into the water, wringing even more heat from the gases. 2. Modulating Combustion System Modulation during the water heating operation is based on the tank temperature. The control monitors the system to regulate the output of the burner during operation to match the system demand. This increase in efficiency allows for substantial fuel savings. 3. Gas Valve The gas valve senses suction from the blower, allowing gas to flow only if the gas valve is energized and combustion air is flowing. 4. Upper Supply Tank Sensor This sensor monitors water heater upper portion water temperature (system supply). The control module adjusts the burner firing rate so the outlet temperature is correct. 5. Lower Return Tank Sensor This sensor monitors the lower portion of the water heater return water temperature (system return). The control module reduces or increases the input, depending on how close the water temperature is to the outlet water temperature set point. 6. Control The integrated control system monitors the upper and lower water temperature and regulates the fan speed to regulate the unit s BTU output. This allows the unit to only deliver the amount of heated energy required and nothing more! 7. Burner Constructed of high grade stainless steel construction, the burner uses pre-mixed air and gas and provides a wide range of firing rates. 8. Condensate drain connection This is a condensing high efficiency appliance, therefore this unit has a condensate removal system. Condensate is nothing more than water vapor, derived from the combustion products, similar to an automobile when it is initially started. It is very important that the condensate line is sloped away from the water heater and down to a suitable inside drain. If the condensate outlet on the Phoenix is lower than the drain, you must use a condensate removal pump (kit p/n available from Heat Transfer Products, Inc.) A condensate neutralizer, if required by local authorities can be made up of lime crystals, marble or phosphate chips and will neutralize the condensate. This can be done in the field by the installer or you may purchase one from Heat Transfer Products, Inc. (P/N N1100). It is also very important that the condensate line is not exposed to freezing temperatures or any other type of blockage. Plastic tubing must be the only material used for the condensate line. Steel, brass, copper or others will be subject to corrosion or deterioration. A second vent may be necessary to prevent condensate line vacuum lock if a long horizontal run is used. Also, an increase in pipe size may be necessary to drain properly. Support of the condensation line may be necessary to avoid blockage of the condensate flow. 4
6 HOW THE PHOENIX OPERATES PART 2: HOW THE PHOENIX OPERATES (CONTINUED) 9. Spark ignition The burner flame is ignited by applying a high voltage to the system spark electrode. This causes a spark from electrode to ground. n DANGER Water temperature over 125 degrees F. can cause severe burns instantly, or death from scalds. Children, disabled, and elderly are at highest risk of being scalded. See instruction manual before setting temperature at water heater. Feel water before bathing or showering! Temperature limiting valves are available. PART 3: PREPARE WATER HEATER LOCATION A. INSTALLATIONS MUST COMPLY WITH: Local, state, provincial, and national codes, laws, regulations and ordinances. National Fuel Gas Code, ANSI Z223.1 latest edition. National Electrical Code. For Canada only: B149.1 or B149.2 Installation Code, CSA C22.1 Canadian Electrical Code Part 1 and any local codes. NOTICE The Phoenix gas manifold and controls met safe lighting and other performance criteria when undergoing tests specified in ANSI Z latest edition. B. BEFORE LOCATING THE PHOENIX 1. Check for nearby connection to: System water piping Venting connections Gas supply piping Electrical power 2. Check area around water heater. Remove any combustible materials, gasoline and other flammable liquids. n WARNING Failure to keep water heater area clear and free of combustible materials, gasoline and other flammable liquids and vapors can result in severe personal injury, death or substantial property damage. 3. The Phoenix gas control system components are protected from dripping or spraying water or rain during operation or service. 4. If the Phoenix Water Heater is to replace an existing water heater, check for and correct any existing system problems such as: 5
7 PREPARATION PART 3: PREPARE WATER HEATER LOCATION (CONTINUED) System leaks. Incorrectly-sized expansion tank. C. CLEARANCES FOR SERVICE ACCESS 1. If you do not provide minimum clearances, it might not be possible to service the water heater without removing it from the space. (See Fig. 3-1 at right) RECOMMENDED SERVICE CLEARANCE SERVICE CLEARANCE ZERO CLEARANCE 12" MIN. 12" MIN. CLEARANCE CLEARANCE MAXIMUM 2" DIAMETER OF WATER HEATER PLUS 2" MINIMUM TO OPEN DRAIN. LINE SHOULD BE AT LEAST 3/4" ID AND PITCHED FOR PROPER DRAINAGE. 24" MIN. CLEARANCE LP-179-W 07/11/07 Fig. 3-1 Phoenix Top View LP-179-T 03/22/07 LP-179-T 03/22/07 n WARNING The space must be provided with combustion/ventilation air openings correctly sized for all other appliances located in the same space as the Phoenix. Failure to comply with the above warnings could result in severe personal injury, death or substantial property damage. D. RESIDENTIAL GARAGE INSTALLATION Precautions Take the following special precautions when installing the water heater in a residential garage. If the heater is located in a residential garage, per ANSI Z223.1, paragraph 5.1.9: Place the Phoenix with a minimum of 18 inches above the floor of the garage to the bottom of the heater to ensure the burner and ignition devices will be no less than 18 inches above the floor. Locate or protect the water heater so it cannot be damaged by a moving vehicle. E. EXHAUST VENT AND INTAKE AIR VENT The Phoenix requires a special vent system, designed for pressurized venting. Phoenix Water Heaters are rated ANSI Z Category IV (pressurized vent, likely to condense in the vent). You must also install air intake piping from outside to the water heater flue adaptor. The resultant installation is categorized as direct vent (sealed combustion). Note: To prevent combustion air contamination see Table 3-2 in this section for examples of areas to avoid when considering exhaust vent and intake air vent termination. 6
8 PREPARATION PART 3: PREPARE WATER HEATER LOCATION (CONTINUED) Intake and exhaust must terminate near each other and may be vented vertically through the roof or through a side wall. The intake and exhuast venting methods are detailed in the Venting Section. Do not attempt to install the Phoenix Water Heater using any other venting means. Be sure to locate the Phoenix such that the air intake and exhaust vent piping can be routed through the building and properly terminated outdoors. The air intake and exhaust vent piping lengths, routing and termination method must all comply with the methods and limits given in the Venting section. F. PREVENT COMBUSTION AIR CONTAMINATION Install intake air piping for the Phoenix Water Heater as described in the Venting section. Do not terminate exhaust in locations that can allow contamination of intake air. n WARNING You must pipe outside air to the water heater air intake. Ensure that the intake air will not contain any of the contaminants below. Contaminated air will damage the water heater, resulting in possible severe personal injury, death or substantial property damage. For example, do not pipe intake air vent near a swimming pool. Also avoid areas subject to exhaust fumes from laundry facilities. These areas will always contain contaminants. Table 3-2: Corrosive contaminants and sources Products to avoid Spray cans containing fluorocarbons Permanent wave solutions Chlorinated waxes/cleaners Chlorine-based swimming pool chemicals Calcium chloride used for thawing Sodium chloride used for water softening Refrigerant leaks Paint or varnish removers Hydrochloric acid/muriatic acid Cements and glues Antistatic fabric softeners used in clothes dryers Chlorine-type bleaches, detergents, and cleaning solvents found in household laundry rooms Adhesives used to fasten building products and other similar products Areas likely to have contaminants Dry cleaning/laundry areas and establishments Swimming pools Metal fabrication plants Beauty shops Refrigeration repair shops Photo processing plants Auto body shops Plastic manufacturing plants Furniture refinishing areas and establishments New building construction Remodeling areas Garages and workshops G. WHEN REMOVING A WATER HEATER FROM AN EXISTING COMMON VENT SYSTEM At the time of removal of an existing gas water heater, the following steps shall be followed with 7 n DANGER Do not install the Phoenix into a common vent with any other appliance. This will cause flue gas spillage or appliance malfunction, resulting in possible severe personal injury, death or substantial property damage. n WARNING Failure to follow all instructions can result in flue gas spillage and carbon monoxide emissions, causing severe personal injury or death.
9 PREPARATION PART 3: PREPARE WATER HEATER LOCATION (CONTINUED) each appliance remaining connected to the common venting system placed in operation, while the other appliances remaining connected to the common venting system are not in operation. a. Seal any unused openings in the common venting system. b. Visually inspect the venting system for proper size and horizontal pitch and determine there is no blockage or restriction, leakage, corrosion and other deficiencies which could cause an unsafe condition. c. Insofar as is practical, close all building doors and windows and all doors between the space in which the appliances remaining connected to the common venting system are located and other spaces of the building. Turn on clothes dryers and any appliance not connected to the common venting system. Turn on any exhaust fans, such as range hoods and bathroom exhausts, so they will operate at maximum speed. Do not operate a summer exhaust fan. Close fireplace dampers. d. Place in operation the appliance being inspected. Follow the lighting instructions. Adjust thermostat so appliance will operate continuously. e. Test for spillage after 5 minutes of main burner operation. Use the flame of a match or candle, or smoke from a cigarette, cigar, pipe, or aerosol smoke (synthetic smoke). f. After it has been determined that each appliance remaining connected to the common venting system properly vents when tested as outlined herein, return doors, windows, exhaust fans, fireplace dampers, and any other gas-burning appliance to their previous conditions of use. g. Any improper operation of common venting system should be corrected so the installation conforms with the National Fuel Gas Code, ANSI Z223.1 latest edition. Correct by resizing to approach the minimum size as determined using the appropriate tables in Table 13 of NFPA54 ANSI Z of that code. Canadian installations must comply with B149.1 or B149.2 Installation Code. n CAUTION Chemical imbalance of your water can cause severe damage to your water heater and associated equipment and may also affect the efficiency. You may have to have your water quality professionally analyzed to determine whether you need to install a water softener. Failure of a heat exchanger due to lime scale build-up on the heating surface, low ph or other chemical imbalance is non-warrantable. H. WATER CHEMISTRY 1. Water Hardness Water hardness is mainly due to the presence of calcium and magnesium salts dissolved in the water. The concentration of these salts is expressed in mg/l, ppm or grains per gallon, as a measure of relative hardness of water. Grains per gallon is the common reference measurement used in the U.S. water heater industry. Hardness expresses as mg/l or ppm may be divided by 17.1 to convert to grains per gallon. Water may be classified as very soft, slightly hard, moderately 8
10 PREPARATION PART 3: PREPARE WATER HEATER LOCATION (CONTINUED) hard or hard based on its hardness number. The minerals in the water will precipitate out when the water is heated and will cause accelerated lime and scale accumulation on a heat transfer surface. If the hardness of the water exceeds the maximum level of 25 grains per gallon, water should be softened to a hardness level no lower than 5 grains per gallon. Water softened as low as 0 to 1 grain per gallon may be under-saturated with respect to calcium carbonate resulting in water that is aggressive and corrosive. 2. ph of Water ph is a measure of relative acidity, neutrality or alkalinity. Dissolved minerals and gases affect water's ph. The ph scale ranges from 0 to 14. Water with a ph of 7.0 is considered neutral. Water with a ph lower than 7 is considered acidic. Water with a ph higher than 7 is considered alkaline. A neutral ph (around 7) is desirable for most potable water applications. Corrosion damage and heater failures resulting from water ph levels of lower than 6 or higher than 8 are non-warrantable. The ideal ph range for water used in a storage tank or a water heater system is 7.2 to Total Dissolved Solids Total dissolved solids (TDS) is a measure of all minerals and solids that are dissolved in the water. The concentration of total dissolved solids is usually expressed in parts per million (ppm) as measured in a water sample. Water with a high TDS concentration will greatly accelerate lime and scale formation in the hot water system. Most high TDS concentrations will precipitate out of the water when heated. This can generate a scale accumulation on the heat transfer surface that will greatly reduce the service life of a water heater. This scale accumulation can also impede the ability of the heat exchanger to transfer heat into the water. A heat exchanger that is damaged or blocked by lime/scale accumulation must be replaced. Failure of a water heater due to lime scale build up on the heating surface is non-warrantable. The manufacturer of the water heater has no control of the water quality, especially the TDS levels in your system. Total dissolved solids in excess of 2,000 ppm will accelerate lime and scale formation in the heat exchanger. Heat exchanger failure due to total dissolved solids in excess of 2,000 ppm is a non-warrantable condition. CAUTION Failure of a heat exchanger due to lime scale build-up on the heating surface, low ph or other chemical imbalance is non-warrantable. 9
11 PREPARATION PART 3: PREPARE WATER HEATER LOCATION (CONTINUED) I. TEMPERATURE AND PRESSURE RELIEF VALVE A temperature and pressure relief valve is installed into the marked port (upper right). We recommend a WATTS 100XL-4 valve or equivalent for 100,000 BTU models, 40XL5 valve or equivalent for 130,000 BTU models or above input, meeting the requirements for relief valves for hot water heaters as per ANSI Z21.22B by a nationally recognized lab that maintains a periodic inspection of production of such listed safety device. The pressure rating of the valve must not exceed the listed working pressure of this appliance, and must be rated to the proper BTU/hr capacity of the water heater. Do not, under any circumstances, thread a cap or plug into the relief valve! Explosion, serious injury or death may result! Relief valve piping must be directed to the floor or to an open drain, but not connected directly. There must be a 6" space between the outlet of relief valve piping and drain or floor. Do not hook up to drain system directly without an air space. The relief valve must be periodically checked for proper operation. J. POTABLE EXPANSION TANK n WARNING Following installation of the T & P Relief Valve, the valve lever MUST be operated AT LEAST ONCE A YEAR by the water heater owner to ensure that waterways are clear. Certain naturally occurring mineral deposits may adhere to the valve, blocking waterways, rendering it inoperative. When the lever is operated, hot water will discharge if the waterways are clear. PRECAUTIONS MUST BE TAKEN TO AVOID PERSONAL INJURY FROM CONTACT WITH HOT WATER AND TO AVOID PROPERTY DAMAGE. BEFORE operating lever, check to see that a discharge line is connected to the valve, directing the flow of hot water from the valve to a proper place of disposal. If no water flows when the lever is operated, replacement of the valve is required. TURN THE WATER HEATER OFF AND CALL A PLUMBER IMMEDIATELY. This device is designed for emergency safety relief and shall not be used as an operating control. A relief valve functions, in an emergency, by discharging water. Therefore, it is essential that a discharge line be piped from the valve in order to carry the overflow to a safe place of disposal. The discharge line must be same size as the valve outlet must pitch downward from the valve and terminate at least 6" above a drain where any discharge will be clearly visible. A potable hot water expansion tank is required to offset the water expansion as the water is heated. In most city plumbing systems, the water meter has a no return or back flow device built into the system to prevent back flowing of water back into city mains. Some local codes require back flow preventers on all incoming water supplies. The hot water expansion tank must be listed for potable water use. The expansion tank should be located on the cold inlet piping close to the water heater. n CAUTION The expansion tank must be suitable for hot potable water. 10
12 PREPARATION PART 3: PREPARE WATER HEATER LOCATION (CONTINUED) K. WATER PIPING The domestic water connections must be installed in accordance to all local and national plumbing codes, or any applicable standard which prevails. The inlet and outlet ports of the Phoenix are 1" on 55 gallon models. On the 80 and 119 gallon models, the inlet and outlet ports are 1 ½". On the cold inlet, (bottom left), install a 1" brass tee on 55 gallon models, or a 1 ½" tee on 80 and 119 gallon models. On the run of the 1" brass tee, install with pipe sealant compound, a 1" brass drain cock or equivalent. Into the branch of the 1" or a 1 ½" brass tee, install a copper male adapter to match your copper plumbing system. For convenience, you may install a sweat shut off valve and a union in the cold inlet piping to ease servicing in the future. If there is a back flow preventer, or any type of a no return valve in the system, then you must install an additional tee here for a suitable potable hot water expansion tank. In the hot outlet, (top left), install a suitable adapter to match the copper tubing of the plumbing system. A thermal trap or heat trap loop may be installed here, to provide additional energy savings and prevent the thermal siphoning of domestic hot water. L. AUXILIARY CONNECTIONS n CAUTION NEVER USE DIELECTRIC UNIONS OR GALVANIZED STEEL FITTINGS ON ANY DOMESTIC WATER CONNECTIONS OR AUXILIARY CONNECTIONS. USE ONLY COPPER OR BRASS FITTINGS. TEFLON THREAD SEALANT MUST BE USED ON ALL CONNECTIONS. The auxiliary connections are additional connections for an air handlers, plate exchangers or other devices that supply hot water. These connections must be installed in accordance with all local and national codes or any applicable standard that prevails. The auxiliary connections are 1" on all Phoenix Models. Never use dielectric unions or galvanized steel fittings. Use only copper or brass fittings. Teflon Sealant must be used on all connections. The top port is the supply outlet and the bottom port is the return inlet. n WARNING Never connect auxiliary connections to any system that uses glycol or other solutions formulated for hydronic systems. These auxiliary connections are to be used only in a potable water system. Failure to follow this warning could result in death or serious injury. 11
13 PREPARATION AIR HANDLER UNITS MOUNTED TO CEILING* *CHECK WITH AIR HANDLER MANUFACTURER FOR PROPER SIZING. PHOENIX WITH PHOENIX AIR WITH HANDLERS AIR HANDLER ABOVE CIRCULATOR WITH INTREGAL CHECK VALVE (if you are installing a circulator WITHOUT a check valve, you must install a spring check valve) HOT OUT GAS SPARCO AQUAMIX SHOWN. FOR OTHER VALVES, CONSULT VALVE MANUFACTURER HOT WATER OUTLET 8.00" MAX AUXILIARY CONNECTION EXPANSION TANK COLD IN AUXILIARY CONNECTION BALL VALVE BACKFLOW PREVENTER DRAIN VALVE COLD WATER INLET NOTES: 1. Minimum pipe size should match connection size on Phoenix. If you require greater flow, upsize the pipe accordingly. 2. A Thermal Expansion tank suitable for potable water must be sized and installed within this piping system between the backflow preventer and the cold water inlet of the Phoenix. 3. Gas line must be rated to the maximum input capacity of the unit. Unit must have 10 feet of pipe after gas regulator. 4. All circulators shall have an integral flow check. NOTES: FOR AIR HANDLER APPLICATION 1. MASSACHUSETTS STATE PLUMBING CODE REQUIRES A DISTANCE NO GREATER THAN 50 FEET FROM THE WATER HEATER TO THE FAN COIL IN THE AIR HAN- DLER. 2. MASSACHUSETTS STATE PLUMBING CODE REQUIRES AN ELECTRONICALLY TIMED CIRCULATOR PUMP REQUIRED TO ACTIVATE EVERY SIX HOURS FOR 60 SECONDS. THIS CIRCULATOR IS REQUIRED TO BE BRONZE OR STAINLESS. 3. ALL WATER PIPING MUST BE INSULATED. 4. YOU MUST INSTALL A VACUUM RELIEF VALVE PER 248 CMR. NOTE: This drawing is meant to show system piping only. The installer is responsible for all equipment and detailing required by local codes. LP-179-L 7/13/07 12
14 PREPARATION PHOENIX WITH AIR HANDLER ON SIDE CIRCULATOR ( REQUIRED IN-LINE IF NOT ON AIR HANDLER UNIT) ( SEE NOTE 4) 135 TO 140 GAS SPARCO AQUAMIX MIXING VALVE SHOWN. FOR OTHER VALVES, CONSULT VALVE MANUFACTURER 120 TO 130 HOT OUT HOT WATER OUTLET AUXILIARY CONNECTION 8.00" MAX. EXPANSION TANK COLD IN AUXILIARY CONNECTION BALL VALVE BACKFLOW PREVENTER DRAIN VALVE COLD WATER INLET AIR HANDLER* * CHECKWITH AIR HANDLER MANUFACTURER FOR PROPER SIZING. NOTES: 1. Minimum pipe size should match connection size on Phoenix. If you require greater flow, upsize the pipe accordingly. 2. A Thermal Expansion tank suitable for potable water must be sized and installed within this piping system between the check valve and the cold water inlet of the Phoenix. 3. Gas line must be rated to the maximum input capacity of the unit. Unit must have 10 feet of pipe after gas regulator. 4. All circulators shall have an integral flow check. NOTES: FOR AIR HANDLER APPLICATION 1. MASSACHUSETTS STATE PLUMBING CODE REQUIRES A DISTANCE NO GREATER THAN 50 FEET FROM THE WATER HEATER TO THE FAN COIL IN THE AIR HANDLER. 2. MASSACHUSETTS STATE PLUMBING CODE REQUIRES AN ELECTRONICALLY TIMED CIRCULATOR PUMP REQUIRED TO ACTIVATE EVERY SIX HOURS FOR 60 SECONDS. THIS CIRCULATOR IS REQUIRED TO BE BRONZE OR STAINLESS. 3. ALL WATER PIPING MUST BE INSULATED. 4. YOU MUST INSTALL A VACUUM RELIEF VALVE PER 248 CMR. NOTE: This drawing is meant to show system piping only. The installer is responsible for all equipment and detailing required by local codes. LP-179-M 4/13/07 13
15 PREPARATION SHUT-OFF BALL VALVE COLD BACKFLOW PREVENTER REVERSE MANIFOLD AND PIPING DIAGRAM FOR PHOENIX EXPANSION TANK GAS GAS GAS COLD WATER COLD WATER HOT WATER HOT WATER HOT WATER CHECK VALVE CIRCULATOR (SEE NOTE 4) HOT WATER OUTLET AUXILIARY CONNECTION NOTES: 1. Minimum pipe size should match connection size on Phoenix. If you require greater flow, upsize the pipe accordingly. 2. A Thermal Expansion tank suitable for potable water must be sized and installed within this piping system between the check valve and the cold water inlet of the Phoenix. Check with the Manufacturer of the Thermal Expansion tank for proper sizing. 3. Gas Line must be rated to the maximum input capacity of the unit. Unit must have 10 feet of pipe after gas regulator. 4. All circulators shall have an integral flow check. NOTES: 1. Minimum pipe size should match connection size on Phoenix. If you require greater flow, upsize the pipe accordingly. 2. A Thermal Expansion tank suitable for potable water must be sized and installed within this piping system between the check valve and the cold water inlet of the Phoenix. 3. Gas Line must be rated to the maximum input capacity of the unit. Unit must have 10 feet of pipe after gas regulator. 4. All circulators shall have an integral flow check. NOTE: COLD WATER INLET This drawing is meant to show system piping only. The installer is responsible for all equipment and detailing required by local codes. This application may not be allowed in Massachusetts. In Massachusetts you must install a vacuum relief valve per 248 CMR. CLOSED LOOP RADIANT HEATING AUXILIARY CONNECTION BACKFLOW PREVENTER BALL VALVE MAKE-UP WATER CIRCULATOR (See note 4) BALL VALVE BRAZED PLATE* BALL VALVE AIR ELIMINATOR PURGE VALVE PRESSURE REDUCING VALVE PRESSURE GAUGE BALL VALVE EXPANSION TANK CIRCULATOR ( see note 4) AUXILIARY CONNECTION LP-179-N 7/16/07 RADIANT HEAT AUXILIARY CONNECTION NOTE: This drawing is meant to show system piping only. The installer is responsible for all equipment and detailing required by local codes. In Massachusetts you must install a vacuum relief valve per 248 CMR. *You should check with the manufacturer of the brazed plate for correct plate connections. Orientation may vary by manufacturer. SYSTEM DRAIN LP-179-U 11/1/07 14
16 PREPARATION PHOENIX WITH STORAGE TANK EXPANSION TANK HOT OUT COLD IN GAS BACKFLOW PREVENTER SHUT-OFF BALL VALVE HOT WATER OUTLET AUXILIARY CONNECTION CIRCULATOR (see note 4) AQUASTAT CONTROL AUXILIARY CONNECTION NOTES: SPRING CHECK VALVE DRAIN VALVE COLD WATER INLET 1. Minimum pipe size should match connection size on Phoenix. If you require greater flow, upsize the pipe accordingly. 2. A Thermal Expansion tank suitable for potable water must be sized and installed within this piping system between the check valve and the cold water inlet of the Phoenix. Check with the Manufacturer of the Thermal Expansion Tank for proper sizing. 3. Gas line must be rated to the maximum input capacity of the unit. Unit must have 10 feet of pipe after gas regulator. 4. All circulators shall have an integral flow check SPECIAL NOTE: Drains and Check valve connected between the Phoenix and the Storage Tank will assist in purging air from system. NOTE: This drawing is meant to show system piping only. The installer is responsible for all equipment and detailing required by local codes. In Massachusetts you must intall a vacuum relief valve per 248 CMR. 15 LP-179-O 7/13/07
17 NOTICE PREPARATION The standard Phoenix Water Heater does not meet the required temperature settings for sanitizer booster applications. The maximum temperature setting for the Phoenix Sanitizer Booster is 184. #09 #08 #13 #14 #14 #09 #04 PHOENIX SANITIZER BOOSTER INSTALLATION P/N PH130-55SA / PH199-55SA #07 3/4" Return 3/4 Gas #05 # Return #01 #03 # Supply #10 Pressure Regulator Pressure Gauge Thermometer 1' Supply PHOENIX SANITZER DISHWASHER DRAIN VALVE #01 #03 #02 WARNING; INCOMING SUPPLY MUST BE NO FURTHER THAN 5' FROM THE SANITZER VERY IMPORTANT: INSULATE ALL PIPES ON RECIRCULATION LINE TO AND FROM SANITIZER THE ITEMS LISTED BELOW ARE THE ITEMS AND PART NUMBERS IN THE VSBK-1200 SANITIZER BOOSTER KIT. ITEM PART DESCRIPTION PART NUMBER ITEM PART DESCRIPTION PART NUMBER #01 NIBCO TEE 1"X1"X 1/2" #08 PRESSURE GAUGE #02 FEMALE ADAPTER 1" #09 NIBCO TEE 1" X 1" X 3/4" 712R #03 DIAL THERMOMETER #10 NIBCO TEE 1" X 1/2" X 1" COPPER #04 EXPANSION TANK 4.5 GAL #11 NIBCO TEE 1" X 1/2" X 1"R #05 GRUNDFOS 3 SPEED PUMP W/ CHECK VALVE #12 REDUCING COUPLING #06 NIBCO TEE 1/2" X 1/2" FITTING AIR CHAMBER #13 PRESSURE REDUCING VALVE #07 VACUUM RELIEF VALVE #14 NIBCO MALE ADAPTERS NOTE: In Massachusetts you must intall a vacuum relief valve per 248 CMR LP-179-SA 10/6/09 16
18 PREPARATION PART 4: PREPARE WATER HEATER A. ELECTRICAL CONNECTION The Phoenix Water Heater must be wired to a 120 volt circuit by a qualified electrician. It is recommended that the Phoenix Water Heater be wired on its own circuit to minimize the possibility of circuit failure due to outside causes. The Phoenix Water Heater requires a maximum of 6 amps at 120 volts in use. To wire the Phoenix Water Heater 1. Remove the screws on each side of the cover of the Phoenix burner control, then tilt the cover up and remover it from the back plate. 2. Following all local and national wiring codes; route the incoming power wiring through the knockout near the lower right corner of the back plate of the Phoenix burner control from the rear to the inside of the burner control. KNOCKOUT NOTE: Some earlier versions of the back plate may require drilling of the hole to increase its size to ½ conduit trade size (7/8 diameter) 3. Connect the line power wire (usually black) to the terminal marked 120V 4. Connect the neutral wire (usually white) to the terminals marked Neut. 5. Connect the ground wire (usually green) to the terminal marked GND 6. Place the cover back on the Phoenix burner control and secure it with the screws you removed B. GAS CONNECTION n WARNING It is of extreme importance that this unit be properly grounded. It is very important that the building system ground is inspected by a qualified electrician, prior to making this connection. It is very important that the electrical power is only turned on when the Phoenix is completely filled with cold water. n WARNING Failure to follow all precautions could result in fire, explosion or death! The gas supply shall have a maximum inlet pressure of less than 14" water column (350 mm), ½ pound pressure (3.5 kpa), and a minimum of 3.5" water column. The entire piping system, gas meter and regulator must be sized properly to prevent pressure drop greater than 0.5" WC as stated in the National Fuel Gas Code. This information is listed on the rating plate. It is very important that you are connected to the type of gas as noted on the rating plate. "LP" for liquefied petroleum, propane gas or, "Nat" natural or city gas. All gas connections UNION MIN 3/4" DRIP LEG Fig
19 PREPARATION PART 4: PREPARE WATER HEATER (CONTINUED) must be approved by the local gas supplier, or utility in addition to the governing authority, prior to turning the gas supply on. Do not remove this adaptor! It is mandatory that this fitting is used for connection to a field fabricated drip leg as shown in the illustration at right per the National Fuel Gas Code. You must ensure that the entire gas line to the connection at the Phoenix Water Heater is no smaller than ¾". Once all the inspections have been performed, the piping must be leak tested. If the leak test requirement is a higher test pressure than the maximum gas inlet pressure, you must isolate the Phoenix from the gas line to continue leak testing. In order to do this, you must turn off the factory and field-installed gas cocks. This will minimize the possibility of damaging the Phoenix gas valve. Failure to do so may damage the gas valve. In the event the gas valve is exposed to a pressure greater than ½ PSI, 14" water column, the gas valve must be replaced. Never use an open flame (match, lighter, etc.) to check gas connections. C. GAS PIPING 1. Run the gas supply line in accordance with all applicable codes. 2. Locate and install manual shutoff valves in accordance with state and local requirements. D. GAS TABLE Refer to the below table to size the supply piping to minimize pressure drop between meter or regulator and unit. Maximum Capacity of Pipe in Cubic Feet of Gas per Hour for Gas Pressures of 0.5 psi or Less and a Pressure Drop of 0.3 Inch water Column Gas Table (Nominal Iron Pipe Internal Length of Pipe (Feet) Size Diameter (inches) (inches) / } BTU'S PER 1 1/ , HOUR 1 1/ ,600 1, x1,000 It is recommended that a soapy solution be used to detect leaks. Bubbles will appear on the pipe to indicate a leak is present. The gas piping must be sized for the proper flow and length of pipe, to avoid excessive pressure drop. Both the gas meter and the gas regulator must be properly sized for the total gas load. If you experience a pressure drop greater than 1" WC, the meter, regulator or gas line is undersized or in need of service. You can attach a manometer to the incoming gas drip leg, by removing the cap and installing the manometer. The gas pressure must remain between 3.5" WC and 14" WC during stand-by (static) mode and while in operating (dynamic) mode at full output. If an inline regulator is used, it must be a minimum of 10 feet from the Phoenix. It is very important that the gas line is properly purged by the gas supplier or utility. Failure to properly purge the lines or improper line sizing, will result in ignition failure. This problem is especially noticeable in NEW LP installations and also in empty tank situations. This can also occur when a utility company shuts off service to an area to provide maintenance to their lines. The gas valve must not be replaced with a conventional gas valve under any circumstances. As an additional safety feature in the Phoenix water heater, the gas valve in this appliance has a flanged connection to the swirl plate and blower. 18
20 PREPARATION / VENTING PART 4: PREPARE WATER HEATER (CONTINUED) E. DUNGS GAS VALVE GAS SHUT-OFF VALVE PRESSURE TAP INLET THROTTLE ADJUSTER NOTE: If for any reason the throttle needs to be adjusted, it is very important that a "COMBUSTION ANALYZER" be used to ensure safe and proper operation. Turn the adjuster to the (+) to increase the gas supply or the (-) to decrease the gas supply. This adjustment will affect CO/CO% levels. Make sure the levels correspond to the chart in combustion settings. COMBUSTION AIR OFFSET ADJUSTMENT CAUTION: Do not remove this screw or attempt to make any adjustment to this screw without a combustion analyzer. PRESSURE TAP OUTLET Fig. 4-2 GAS VALVE n WARNING LP-179-P 3/13/07 Do not do a gas conversion on this water heater without an officially approved conversion kit and instructions supplied by Heat Transfer Products, Inc. PART 5: VENTING, COMBUSTION AIR & CONDENSATE REMOVAL A. INSTALLING EXHAUST VENT AND INTAKE AIR VENT n DANGER The Phoenix must be vented as detailed in Venting section. Ensure the exhaust and intake piping comply with these instructions regarding vent system. Inspect finished combustion air intake and exhaust piping thoroughly to ensure all joints are well secured and airtight and comply with all applicable code requirements, as well as with the instructions provided in this manual. Failure to provide a properly installed vent system will cause severe personal injury or death. 19
41 PART 7: VENTING, COMBUSTION AIR, AND CONDENSATE REMOVAL The heater must be vented as detailed in this Venting Section. Ensure exhaust and intake piping complies with these instructions regarding vent
28 2. Connect DHW (domestic hot water) piping to indirect storage water heater. L. ZONING WITH CIRCULATORS 1. Connect the boiler to the system when using circulator zoning as shown in Boiler Piping Details.
PART 6: VENTING, COMBUSTION AIR & CONDENSATE REMOVAL Boiler Manual A. INSTALLING EXHAUST VENT AND INTAKE AIR VENT B. GENERAL n DANGER The Elite Heating Boiler must be vented as detailed in this section.
Tankless Water Heater USER S INFORMATION MANUAL Models WGRTNG199 / WGRTLP199 WGRTCNG199 / WGRTCLP199 NOTICE: Westinghouse reserves the right to make product changes or updates without notice and will not
Phoenix Light Commercial INSTALLATION START-UP MAINTENANCE PARTS Models* PH76-50 / PH76-60 / PH76-80 *A suffix of LP denotes propane gas This manual must only be used by a qualified heating installer/service
High Efficiency Commercial Gas Water Heater USE & CARE MANUAL WITH INSTALLATION INSTRUCTIONS FOR THE CONTRACTOR This Use & Care Manual covers the following model numbers: HE55-100N HE119-130N HE55-199LP
Elite Fire Tube Combi Floor and Wall Mount Models USER S INFORMATION MANUAL Models EFTC-140F / 199F EFTC-140W / 199W NOTICE: HTP reserves the right to make product changes or updates without notice and
CROWN BOILER COMPANY BWF SERIES BOILER CATEGORY I VENT KIT INSTALLATION AND OPERATING INSTRUCTIONS WARNING Improper installation, adjustment, alteration, service, or maintenance of this product can cause
2010 Residential Water Heater Replacement Check List The intent of this check list is to provide installers a general reference for the enforcement of code requirements in the Greater San Diego Area. This
Phoenix Plus Water Heater Installation Start-Up Maintenance Parts Warranty PHP Models* * LP Denotes Propane Gas Operation This manual must only be used by a qualified installer / service technician. Read
NATURAL GAS TO PROPANE CONVERSION KIT 090 INSTALLATION INSTRUCTIONS FOR ALTITUDES 0 -,00 FT. ONLY PROPANE CONVERSION KIT SAFETY... INSTALLATION REQUIREMENTS... Tools and Parts... LP Gas Requirements...
18 H. PIPING DIAGRAMS Figure 4 Phoenix With Air Handler - 5. Check with air handler manufacturer for proper sizing. 6. This drawing is meant to demonstrate system piping only. The installer is responsible
INSTALLATION INSTRUCTIONS 4" COMBUSTION AIR INLET KIT TUBULAR GAS FIRED DIRECT SPARK PROPELLER UNIT HEATERS UNIT CONVERSION & CATEGORY III VENTING FOR SEPARATED COMBUSTION For 30,000 to 75,000 BTU/HR SUPPLEMENT
Installing, Operating & Maintaining MUNCHKIN HIGH EFFICIENCY 399M COMMERCIAL BOILER WARNING If the information in this manual is not followed exactly, a fire or explosion may result causing property damage,
UP TO 96% THERMAL EFFICIENCY, DIRECT-VENT FEATURES TM BTH-120 through BTH-500 The A. O. Smith Cyclone Xi family of products represents the industry s most technologically advanced commercial water heaters.
CASE STUDY 1 COMMISSIONING A GAS FIRED STEAM BOILER A steam boiler has been built and installed at a factory for the provision of process steam. The following lists the requirements used in the commissioning
Indirect-Fired Storage Water Heater Models WH-30 through WH-80 INSTALLATION AND OPERATING INSTRUCTIONS Contents Page Ratings and Specifications..................... 2 Installation Requirements......................
Installing, Operating & Maintaining MUNCHKIN HIGH EFFICIENCY HEATER with the 925 Controller WARNING If the information in this manual is not followed exactly, a fire or explosion may result causing property
Boiler Manual Installation Startup Maintenance Parts WARNING This manual must only be used by a qualified heating installer/service technician. Read all instructions in this manual before installing. Perform
Navien America Inc. Specification Details for the Navien models: CC-240 CC-240A For Potable Water Heating and Space Heating NAVIEN AMERICA INC. 17855 FITCH AVENUE IRVINE, CALIFORNIA, USA 92614 Toll Free:
Electric Water Heater OWNER S MANUAL FORCE 10 MARINE COMPANY 23080 HAMILTON ROAD RICHMOND, BC CANADA V6V 1C9 TEL: (604) 522-0233 FAX: (604) 522-9608 If your water Heater is Damaged or you have questions
SECTION 15459 PART 1 - GENERAL 1.1 RELATED DOCUMENTS: A. Drawings and general provisions of Contract, including General and Supplementary Conditions and Division-1 Specification sections, apply to work
ELECTRIC WATER HEATER A Spanish language version of these instructions is available by contacting the manufacturer listed on the rating plate. La version espanola de estas instruccions se puede obtener
! WARNING: This water heater is not suitable for use in manufactured (mobile) homes! Use & Care Manual With Installation Instructions for the Installer Residential Gas - FVIR Certified Water Heaters Residential
Operator: Save these instructions for future use! FAILURE TO READ AND FOLLOW ALL INSTRUCTIONS CAREFULLY BEFORE INSTALLING OR OPERATING THIS CONTROL COULD CAUSE PERSONAL INJURY AND/OR PROPERTY DAMAGE. DESCRIPTION
SWH-I-S Rev K TM Installation & Service Manual Models: SNR150-100, SNR200-100, SNA285-125, SNA400-125, AND SNA500-125 WARNING: If the information in these instructions is not followed exactly, a fire or
4658.4500 PLUMBING SYSTEMS; NEW CONSTRUCTION. Subpart 1. Installation. All plumbing systems must be installed and tested according to this chapter and chapter 4715, the Minnesota Plumbing Code. Subp. 2.
RECON WATER HEATER INSTALLATION FORM Please complete ONE (1) form for each SITE and return to AERCO for warranty validation within 30 days of start-up. After completion, e-mail this form to: STARTUP@AERCO.COM.
Instruction Manual for Residential Manufactured Home Gas Water Heaters FOR USE ONLY IN MANUFACTURED HOMES GAMA certification applies to all residential gas water heaters with capacities of 20 to 100 gallons
Plumbing Installations A homeowner guide to the City of Winnipeg plumbing requirements for a single-family dwelling February 2001 contents General Information 3 Inspection 4 New Drain and Vent Installations
Installing, Operating & Maintaining EVO 79-599 HIGH EFFICIENCY WATER HEATERS AND HEATING BOILERS INNOVA TIVE CONDENSING TECHNOLOGY By Hamilton Engineering, Inc. ICRO BTU/hr BTU/hr BTU/hr BTU/hr EVO DUO
CYCLONE Mxi MODULATING MODULATING BURNER ADVANCES THE CYCLONE TO HIGHER LEVELS OF EFFICIENCY The full line of A. O. Smith Cyclone Mxi condensing water heaters has been designed to provide years of dependable
PlumbingCode06_ch05 5/29/06 8:12 AM Page 1 CHAPTER 5 WATER HEATERS Water heaters are only a small portion of a plumbing system, but they are important, and they can be dangerous. Many plumbers take water
Electric Water Heater Operation and Installation Manual (LIMITED WARRANTY AND TANK REPLACEMENT POLICY) The following information should be noted at time of installation and retained for future reference.
User Manual TABLE OF CONTENTS Product and Safety Information............................................. 2,3 Service and Maintenance Munchkin Operation Primary Water Section I Combustion Air Prevention
Twin Pipe PVC / CPVC Venting options for Rinnai Ultra Series Condensing Tankless Water Heaters. Purpose: The purpose of this presentation is to provide information concerning new venting options available
Instruction Manual for Residential Gas Water Heaters NOT FOR USE IN MANUFACTURED (MOBILE) HOMES GAMA certification applies to all residential gas water heaters with capacities of 20 to 100 gallons with
Residential/Commercial Gas Condensing High Efficiency Tankless Water Heaters FEATURES ULTRA-LOW NOx CONDENSING TECHNOLOGY PROVIDES UNPRECEDENTED 0.95 ENERGY FACTOR DURABLE HEAT EXCHANGER Primary Heat Exchanger
! Warning: This water heater is not suitable for use in manufactured (mobile) homes! Use & Care Manual With Installation Instructions for the Installer Residential Gas Water Heaters The purpose of this
prestige Solo 60 Solo 175 Solo 250 Solo 399 Water Boiler L I S T E D * I N S T A L L A T I O N A N D M A I N T E N A N C E * M A N U A L NOTICE Warranty Registration Card must be filled out by the customer
TANKLESS WATER HEATER INSTALLATION DIAGRAMS Installation Diagrams Tankless Installation / Optional Return Small 10-15 Gallon Point-of-Use Water Single and Optional Return : One single, small capacity water
INSTALLATION INSTRUCTIONS & HOME OWNERS MANUAL ECO 18 ECO 24 ECO 27 IMPORTANT SAFETY INFORMATION As when installing or using any high voltage electrical appliance, basic safety precautions should always
Use & Care Manual With Installation Instructions for the Installer Electric Tankless Water Heaters The purpose of this manual is twofold: one, to provide the installer with the basic directions and recommendations
PLANNING, PROPERTY AND DEVELOPMENT DEPARTMENT Plumbing Installations A homeowner guide to the City of Winnipeg plumbing requirements for a single-family dwelling October 2014 contents General Information
Superstor Ultra Indirect Fired Installation Water Heaters Start-Up Maintenance Parts Warranty For Residential and Commercial Use SSU Models The surfaces of these products contacted by potable (consumable)
LIGHT DUTY COMMERCIAL ELECTRIC WATER HEATER A Spanish language version of these instructions is available by contacting the company listed on the rating plate. La versión espãnola de estas instrucciones
Arapahoe County Residential Water Heater Installation and Inspection Guide The attached handout is designed to be a general permit submittal and inspection guide covering most installation instances, however
POWERED DIRECT VENT GAS WATER HEATER A Spanish language version of these instructions is available by contacting the company listed on the rating plate. La version espanola de estas instrucciones se puede
! WARNING: This water heater is not suitable for use in manufactured (mobile) homes! Use & Care Manual With Installation Instructions for the Installer Gas Residential Water Heaters Model: HG Series, GG
Instruction No. AERCO INTERNATIONAL, Inc., Northvale, New Jersey, 07647 USA PIPING GUIDE GF-115-P Modulex Gas Fired Boiler Systems Modular, Condensing, Hot Water Boilers Models: 303, 454, 606, 757, 909,
INSTALLATION AND OPERATIONS GUIDE FOR GRAND CANYON GAS LOG SYSTEMS Installation and service must be provided by a qualified installer, service agency or gas supplier Grand Canyon Gas Logs, logs are made
PART 1 - GENERAL 1.01 OVERVIEW A. This section addresses domestic cold, hot and hot water return distribution systems within and to five feet beyond building perimeter. PART 2 - DESIGN CRITERIA 2.01 GENERAL
Instruction Manual COMMERCIAL GAS WATER HEATERS POWER VENTED GAS MODELS W/HOT SURFACE IGNITION MODEL BTX-80 SERIES 100 500 Tennessee Waltz Parkway Ashland City, TN 37015 Low Lead Content For Your Safety
Commercial Gas-Fired Water Heaters Installation Start-Up Maintenance Parts Warranty CG***N73 / CG***N65 Models A Suffix of X Denotes Model Set for Low NOx Operation This manual must only be used by a qualified
This manual covers model numbers: United States Canada PG10* 34-100-2NV or 2PV PG10* 34-130-2NV or 2PV PG10* 50-130-2NV or 2PV PG10* 34-150-2NV or 2PV PG10* 50-175-3NV or 3PV PG10* 50-199-3NV or 3PV PG10*
WARNING: If the information in these instructions is not followed exactly, a fire or explosion may result, causing death, personal injury, or property damage. For Your Safety! Do not store or use gasoline
Report for Dick and Jane Homeowner 1234 Lovers Lane, Houston, Texas 77000 March 17, 2004 I NI NP R Inspection Item I. STRUCTURAL SYSTEMS o o o A. Foundations (If all crawl space areas are not inspected,
Replacement parts DO NOT SERVICE THE BOILER WITHOUT A WM97+ MAINTENANCE KIT AVAILABLE Failure to adhere to these guidelines can result in severe personal injury, death or substantial property damage. The
INSTALLATION, OPERATION, AND SERVICE MANUAL RESIDENTIAL STORAGE TYPE GAS WATER HEATER THESE INSTRUCTIONS ARE INTENDED AS AN AID TO QUALIFIED SERVICE PERSONNEL FOR PROPER INSTALLATION, ADJUSTMENT AND OPERATION
SECTION 23 81 03 - PACKAGED ROOFTOP AIR CONDITIONING UNITS NON-CUSTOM PART 1 - GENERAL 1.1 SUMMARY A. Section Includes: 1. Packaged rooftop air conditioning unit (5 tons and smaller). 2. Roof curb. 1.2
Condensing Water Heater Operation Manual Model NPE-180A/ 210A/ 240A NPE-180S/ 210S/ 240S * Lead Free Keep this manual near this water heater for future reference whenever maintenance or service is required.
WARNING: If the information in these instructions is not followed exactly, a fire or explosion may result causing property damage, personal injury or death. Do not store or use gasoline or other flammable
prestige Solo 110 Water Boiler * I N S T A L L A T I O N A N D M A I N T E N A N C E * M A N U A L Warranty Registration Card must be filled out by the customer and mailed within thirty (30) days of installation
Instruction Manual RESIDENTIAL GAS WATER HEATERS FOR USE ONLY IN MANUFACTURED HOMES GAMA certification applies to all residential gas water heaters with capacities of 20 to 100 gallons with input rating
I N S T ALLATION INSTRUCTIONS & HOME OWNERS MANUAL MODELS: HA018240 HA024240 HA027240 HA036240 IMPORTANT SAFETY INFORMATION As when installing or using any high voltage electrical appliance, basic safety
One Year Warranty ELECTRIC Stock U.S. # of Volts Weight CONN. Height Dia. Watts # GAL. Elements INS. Inches Fused Ceramic Shield tank lining is corrosion-resistant for years of dependability. Adjustable
Solar Skies Stainless Tank Series Water Heater Installation Operation Maintenance Solar Skies Stainless Tank CD1051A.doc Last Revision: 1/31/2011 1 CONTENTS Part 1 Product and Safety Information.....................................
INSTALLATION, OPERATION, AND SERVICE MANUAL POWER VENT STORAGE TYPE GAS WATER HEATER MODELS PVG/PVCG THESE INSTRUCTIONS ARE INTENDED AS AN AID TO QUALIFIED SERVICE PERSONNEL FOR PROPER INSTALLATION, ADJUSTMENT
SWIMMING POOL HEAT PUMP Installation & User Manual Model HP40B HP50B HP65B Hayward Pool Products Canada, Inc. T: 1-888-238-7665 www.haywardpool.ca CONTENT I. Application 4 II. Features 4 III. Technical
Seaward Products WATER HEATERS OWNER S MANUAL Serial Number: IMPORTANT SAFETY INSTRUCTIONS WARNING When using electrical appliances, basic safety precautions to reduce the risk of fire, electrical shock,
City of Sonoma Building Department Informational Handout Residential Water Heaters Handout No: 15 Revised: 5/18/15 A water heater is an appliance designed to supply hot water and is equipped with automatic
Texas State Board of Plumbing Examiners Plumbing Inspector Examination Review Course The following Examination Review Course is designed to assist an applicant in preparing for the Plumbing Inspector examination.
Service Literature G26 SERIES UNITS G26 series units are high-efficiency upflow gas furnaces manufactured with DuralokPlust aluminized steel clamshell-type heat exchangers. G26 units are available in heating
Residential 30, 40 and 50 Gallon Use & Care Manual With Installation Instructions for the Contractor Gas Residential Water Heaters Model: HG Series, GG Series, GP Series, PG Series, SG Series, SG Series
Solar Hybrid Energy Systems Patent(s) Pending Sun Bandit Hybrid Water Heater Installation, Operation and Solar Hybrid Energy Systems Patent(s) Pending Maintenance Manual Solar Hybrid Energy Systems Patent(s)
Installation Manual DIAPHRAGM WELL TANK IN-LINE SERIES: 2-5 & 7 GALLON VERTICAL SERIES: 14-20-25-32-36-52-65-86-96-119 GALLON HORIZONTAL SERIES: 7-14 & 20 GALLON NO LEAD NO LEAD: The weighted average of
INSTALLATION, OPERATING, AND SERVICE INSTRUCTIONS HEAT-FLO HOT WATER STORAGE/ BOOSTER TANKS MODELS 30-ST, 40-ST, 40L-ST, 60-ST, 60L-ST 80-ST, 115-ST, 80-ST-C, 115-ST-C Conforms to UL STD 174 and NSF/ANSI