# Using Computational Fluid Dynamics (CFD) for improving cooling system efficiency for Data centers

Save this PDF as:

Size: px
Start display at page:

Download "Using Computational Fluid Dynamics (CFD) for improving cooling system efficiency for Data centers"

## Transcription

1 Data Centre Best Practises Workshop Using Computational Fluid Dynamics (CFD) for improving cooling system efficiency for Data centers Shishir Gupta 17 th March 2009

2 You are Here Introduction to CFD Data Centre Case Study Geometrical Details CFD while designing of HVAC system CFD during installation of Data Centre CFD for maintenance of Data Centre Feedforward System

3 Introduction to CFD Computational (having to do with mathematics & computation) Fluid Dynamics (the dynamics of things that flow) CFD is built upon fundamental physics equations: equations of motion and conservation. CFD applications range from numerical weather prediction to vehicular aerodynamics design. CFD applications are linked with advances in computing software and hardware. CFD software is characterized by the physical models in the software. Fine-scale CFD applications closely match the true geometry of the physical objects and processes being modeled.

4 What is CFD? Fluid Mechanics Fluid Problem Comparison& Analysis Mathematics Physics of Fluid Navier-Stokes Equations Numerical Methods Discretized Form C F D Geometry Simulation Results Computer Computer Program Grids Programming Language

5 Why use CFD? Cost Time Scale Information Repeatable Security Simulation(CFD) Cheap Short Any All All Safe Experiment Expensive Long Small/Middle Measured Points Some Some Dangerous

6 Where use CFD? Chemical Processing HVAC(Heat Ventilation Air Condition) Hydraulics Aerospace Automotive Biomedical Power Generation Sports Marine Chemical Processing reactor vessel - prediction of flow separation and residence time effects. Hydraulics HVAC Streamlines for workstation ventilation

7 Where use CFD? Aerospace Chemical Processing HVAC Hydraulics Aerospace Automotive Biomedical Power Generation Sports Marine Biomedicine Automotive Temperature and natural convection currents in the eye following laser heating.

8 Where use CFD? Chemical Processing HVAC Hydraulics Aerospace Automotive Biomedical Power Generation Sports Marine Sports Power Generation Flow around cooling towers Marine

9 You are Here Introduction to CFD Data Centre Case Study Geometrical Details CFD while designing of HVAC system CFD while installation of Data Centre CFD for maintenance of Data Centre Feedforward System

10 CFD Case Study for Data Centre

11 Introduction to the Case Study Case Study is taken from one of the project that we did for a Data Centre in India The case study includes what we did for the client also extends it for what could have been done for the same project using CFD There were two software applications used for the project : OpenSource CFD platform of OpenFoam and commercial CFD package of Fluent Both packages produced about the same results, in this presentation the results from OpenFoam are being shown

12 Case Description The analyzed Data Centre is rectangular with of area 516m 2 and height 3.35mt Cooling is to be provided using raised flooring layout and demarcation is done for Cold Aisle and Hot Aisle The sources of heat gain inside the data centre are listed below: Heat gain through exterior walls accounting for thermal resistance of the wall Heat gain from Server Racks, 154 Server racks each providing about 8 KW combine to about 1.26 MW Three fans of about 500CMH were assumed to transport air from cool aisle to hot aisle in each rack unit (Since detailed blade specification is not known)

13 HVAC System Specification 10 CRAC units, 1 Standby Specification: Each CRAC unit of 30,585 CMH Cooling capacity of Each Rack is 150 KW Temperature of supply air is 9.4 o C Return Air opening area (On top surface): 2.23 m 2 Supply Air Diffuser (Cold Aisle) Specifications: Dimension of 600mm X 600mm 70% open area 1 supply diffuser per rack (Total 154) Supply air velocity can be controlled using under floor fan Return Air Diffuser (Hot Aisle) Specification: Dimension of 600mm X 600mm 50% open area Total no. of diffusers: 242

14 Objective of the Study To maintain recommended temperature by ASHRAE for Class 1data centre The recommended atmosphere is defined as: Temperature of 20 o C - 25 o C Relative humidity of 40% - 55 % The allowed change in temperature should be less than 5 o C/hr

15 Recommended Operating Conditions

16 Design Parameters Number of CRAC s Location of CRAC s Velocity of supply air

17 You are Here Introduction to CFD Data Centre Case Study Geometrical Details CFD while designing of HVAC system CFD while installation of Data Centre CFD for maintenance of Data Centre Feedforward System

18 Base Case Design CRAC Units (11 Nos.) Return Diffusers Supply Diffusers Server Racks False Flooring False Ceiling Isometric View of the Designed Data Centre

19 Case Study Cont COLD AISLE Diffusers HOT AISLE Diffusers CRAC Units (11 Nos.) Server Racks Top View of the Designed Data Centre

20 CFD Simulation of Base Case Temperatures across Y-Z plane

21 Temperature Contour Temperature Profile at vertical planes along the racks and cold aisle.

22 CFD Simulation of Base Case Temperatures across X-Y plane

23 Temperature Contour Temperature Profile at Horizontal planes along the racks and cold aisle. Lets look at the mid-plane contour in more detail..

24 Temperature Contour in Middle Plane The temperature contour at the Horizontal plane at the middle portion of the rack

25 CFD Simulation of Base Case Temperatures across X-Z plane

26 Temperature Contour Temperature Profile at the middle plane is showing most uneven distribution. Lets analyse the middle plane in detail

27 Temperature Contour in Middle Plane The temperature contour at the vertical plane at the middle portion of the rack

28 Velocity Vectors in Middle Plane The Velocity Vectors at the vertical plane at the middle portion of the rack

29 Conclusion from the base case CFD 1. The Average temperature on the rack surface at the cold Aisle side is The temperature at Cold Aisle is varying from 12 to The Average temperature on the rack surface at the Hot Aisle side is The temperature at Hot Aisle is varying from 18 to The simulation shows that a good number of servers are experiencing temperature well above and below the ASHRAE recommended temperature levels 6. Short circuiting of cold air is clearly visible in the simulation

30 Optimizing number of CRAC units & Supply Air Velocity 1. Maximum heat load : 154 X 8 = 1264 KW (1.26 MW) 2. Heat capacity of each CRAC : 150 KW 3. Minimum number of CRAC required: [8.4] = 9 4. The system was designed with 9 CRAC units and velocity of supply air was adjusted to avoid short circuiting and temperature stratification 5. In this case the velocity of 2.2 m/s is coming out to be higher 6. The simulation was conducted with velocity of 1.6, 1.7, 1.8, 1.9, 2.0 & 2.1 m/s 7. The results with 1.8 m/s showed best results

31 Temperature Distribution with 9 CRACs & 1.8 m/s The temperature contour at the vertical plane at the middle portion of the rack

32 Velocity Vectors with 9 CRACs & 1.8 m/s The Velocity Vector at the vertical plane at the middle portion of the rack

33 Results of improved design CFD 1. The Average temperature on the rack surface at the cold Aisle side is The temperature at Cold Aisle is varying from 13 to The Average temperature on the rack surface at the Hot Aisle side is The temperature at Hot Aisle is varying from 19 to Short circuiting of cold air is reduced to a substantial level, however still prevalent 6. The simulation shows that a most of the servers are experiencing temperature as recommended by ASHRAE

34 Conclusion Using Computational Fluid Dynamics the system was designed to reduce to 90% of original design, thus bringing about first cost saving of 10% in the capital cost. The new system uses less energy and produces better result than the initial design based on thumb rules

35 You are Here Introduction to CFD Data Centre Case Study Geometrical Details CFD while designing of HVAC system CFD during installation of Data Centre CFD for maintenance of Data Centre Feedforward System

36 Case Description The capacity of this data centre of of 42 X 154 = 6,468 Server Blades 4,000 server blades are to be installed 1,000 servers are by Dell, 2,000 by IBM & 1000 by Sun The design variables are: Number of CRAC units Which CRAC unit should be operational Location of Server Blades in the racking system Velocity of supply air inlet

37 CFD Simulation Setup The power requirement of 3000 Server is minimum 713 KW 5 CRAC (750KW) are minimum number of units which can provide the required tonnage The CFD simulation were conducted with various locations of Servers, CRAC s and Supply air velocity The best result was found with following parameters: Top Racks are empty Alternative CRACs are operating Velocity of Supply air is 1.2 m/s

38 CFD Simulation Results Server Positions in the Racks

39 CFD Simulation Results Operational CRAC s

40 Temperature Distribution with 5 CRACs & 1.2 m/s The temperature contour at the vertical plane at the middle portion of the rack

41 Velocity Vectors in Middle Plane The Velocity Vectors at the vertical plane at the middle portion of the rack

42 Calibration during Installation Temperature Sensors The Result from CFD shall be compared with average reading shown by temperature and velocity sensors If there is any difference, the modeling shall be improved to arrive at the actual values.

43 You are Here Introduction to CFD Data Centre Case Study Geometrical Details CFD while designing of HVAC system CFD during installation of Data Centre CFD for maintenance of Data Centre Feedforward System

44 Feedforward System Whenever capacity of the data centre is to be increased, the design parameters like number of CRACs and supply air velocity should be determined using CFD If the capacity ramp up is not that frequent than CFD simulation can be conducted at that stage to arrive at design parameters If ramp-up/ramp-down is very frequent then a custom made CFD code should be developed using OpenSource Libraries. This would enable data centre administrator to conduct CFD s for his data centre and analyze various design options

45 Conclusion CFD can help design and operate the data centre HVAC system with optimum efficiency Thank You

### Fundamentals of CFD and Data Center Cooling Amir Radmehr, Ph.D. Innovative Research, Inc. radmehr@inres.com

Minneapolis Symposium September 30 th, 2015 Fundamentals of CFD and Data Center Cooling Amir Radmehr, Ph.D. Innovative Research, Inc. radmehr@inres.com Learning Objectives 1. Gain familiarity with Computational

### The CEETHERM Data Center Laboratory

The CEETHERM Data Center Laboratory A Platform for Transformative Research on Green Data Centers Yogendra Joshi and Pramod Kumar G.W. Woodruff School of Mechanical Engineering Georgia Institute of Technology

### Air, Fluid Flow, and Thermal Simulation of Data Centers with Autodesk Revit 2013 and Autodesk BIM 360

Autodesk Revit 2013 Autodesk BIM 360 Air, Fluid Flow, and Thermal Simulation of Data Centers with Autodesk Revit 2013 and Autodesk BIM 360 Data centers consume approximately 200 terawatt hours of energy

### HPPR Data Center Improvements Projects Towards Energy Efficiency (CFD Analysis, Monitoring, etc.)

HPPR Data Center Improvements Projects Towards Energy Efficiency (CFD Analysis, Monitoring, etc.) Felipe Visbal / March 27, 2013 HPPR Data Center Technologies Team Services Data Centers: Thermal Assessments

### Effect of Rack Server Population on Temperatures in Data Centers

Effect of Rack Server Population on Temperatures in Data Centers Rajat Ghosh, Vikneshan Sundaralingam, Yogendra Joshi G.W. Woodruff School of Mechanical Engineering Georgia Institute of Technology, Atlanta,

### CFD SIMULATION OF SDHW STORAGE TANK WITH AND WITHOUT HEATER

International Journal of Advancements in Research & Technology, Volume 1, Issue2, July-2012 1 CFD SIMULATION OF SDHW STORAGE TANK WITH AND WITHOUT HEATER ABSTRACT (1) Mr. Mainak Bhaumik M.E. (Thermal Engg.)

### Application of CFD modelling to the Design of Modern Data Centres

Application of CFD modelling to the Design of Modern Data Centres White Paper March 2012 By Sam Wicks BEng CFD Applications Engineer Sudlows March 14, 2012 Application of CFD modelling to the Design of

### Computational Fluid Dynamic Investigation of Liquid Rack Cooling in Data Centres

School of something School of Mechanical Engineering FACULTY OF OTHER ENGINEERING Computational Fluid Dynamic Investigation of Liquid Rack Cooling in Data Centres A. Almoli 1, A. Thompson 1, N. Kapur 1,

### Heating of large agricultural and industrial buildings

Agronomy Research 12(1), 237 244, 2014 Heating of large agricultural and industrial buildings M. Zajicek 1,* and P. Kic 2 1 Institute of Information Theory and Automation, The Academy of Science of The

### FAC 2.1: Data Center Cooling Simulation. Jacob Harris, Application Engineer Yue Ma, Senior Product Manager

FAC 2.1: Data Center Cooling Simulation Jacob Harris, Application Engineer Yue Ma, Senior Product Manager FAC 2.1: Data Center Cooling Simulation Computational Fluid Dynamics (CFD) can be used to numerically

### The New Data Center Cooling Paradigm The Tiered Approach

Product Footprint - Heat Density Trends The New Data Center Cooling Paradigm The Tiered Approach Lennart Ståhl Amdahl, Cisco, Compaq, Cray, Dell, EMC, HP, IBM, Intel, Lucent, Motorola, Nokia, Nortel, Sun,

### The Use and Application of CFD in the Air Conditioning. and Fire Protection Industry

The Use and Application of CFD in the Air Conditioning and Fire Protection Industry AIRAH NSW February 2008 The Use and Application of CFD in the Air Conditioning and Fire Protection Industry An Introduction

### Verizon SMARTS Data Center Design Phase 1 Conceptual Study Report Ms. Leah Zabarenko Verizon Business 2606A Carsins Run Road Aberdeen, MD 21001

Verizon SMARTS Data Center Design Phase 1 Conceptual Study Report Ms. Leah Zabarenko Verizon Business 2606A Carsins Run Road Aberdeen, MD 21001 Presented by: Liberty Engineering, LLP 1609 Connecticut Avenue

### Airflow Simulation Solves Data Centre Cooling Problem

Airflow Simulation Solves Data Centre Cooling Problem The owner s initial design for a data centre in China utilized 40 equipment racks filled with blade servers spread out in three rows along the length

### Using CFD for optimal thermal management and cooling design in data centers

www.siemens.com/datacenters Using CFD for optimal thermal management and cooling design in data centers Introduction As the power density of IT equipment within a rack increases and energy costs rise,

### Energy Efficient Data Center Design. Can Ozcan Ozen Engineering Emre Türköz Ozen Engineering

Energy Efficient Data Center Design Can Ozcan Ozen Engineering Emre Türköz Ozen Engineering 1 Bio Can Ozcan received his Master of Science in Mechanical Engineering from Bogazici University of Turkey in

### Specialty Environment Design Mission Critical Facilities

Brian M. Medina PE Associate Brett M. Griffin PE, LEED AP Vice President Environmental Systems Design, Inc. Mission Critical Facilities Specialty Environment Design Mission Critical Facilities March 25,

### Data Center Cooling & Air Flow Management. Arnold Murphy, CDCEP, CDCAP March 3, 2015

Data Center Cooling & Air Flow Management Arnold Murphy, CDCEP, CDCAP March 3, 2015 Strategic Clean Technology Inc Focus on improving cooling and air flow management to achieve energy cost savings and

### CFD-Based Operational Thermal Efficiency Improvement of a Production Data Center

CFD-Based Operational Thermal Efficiency Improvement of a Production Data Center Umesh Singh, Amarendra K Singh, Parvez S and Anand Sivasubramaniam Tata Consultancy Services Ltd., India ABSTRACT Effective

### Benefits of. Air Flow Management. Data Center

Benefits of Passive Air Flow Management in the Data Center Learning Objectives At the end of this program, participants will be able to: Readily identify if opportunities i where networking equipment

### - White Paper - Data Centre Cooling. Best Practice

- White Paper - Data Centre Cooling Best Practice Release 2, April 2008 Contents INTRODUCTION... 3 1. AIR FLOW LEAKAGE... 3 2. PERFORATED TILES: NUMBER AND OPENING FACTOR... 4 3. PERFORATED TILES: WITH

### Georgia Institute of Technology. Yogendra Joshi G.W. Woodruff School of Mechanical Engineering

Georgia Institute of Technology Yogendra Joshi G.W. Woodruff School of Mechanical Engineering Site Personnel Site Director: Dr. Yogendra Joshi Faculty team: Dr. Satish Kumar Dr. Minami Yoda Researchers/Students:

### Boosting the Energy efficiency of a Server Room: experimental + virtual approach.

Boosting the Energy efficiency of a Server Room: experimental + virtual approach. Nowadays, the increase in computing power allows the successful applications of the CFD simulation methods in civil environments.

### Dealing with Thermal Issues in Data Center Universal Aisle Containment

Dealing with Thermal Issues in Data Center Universal Aisle Containment Daniele Tordin BICSI RCDD Technical System Engineer - Panduit Europe Daniele.Tordin@Panduit.com AGENDA Business Drivers Challenges

### AIR STREAMS IN BUILDING FOR BROILERS

AIR STREAMS IN BUILDING FOR BROILERS PAVEL KIC - MILAN ZAJÍČEK ABSTRACT The Fluent CFD software is used to do numerical analysis of existing poultry house during the summer and winter periods. Principal

### Great Lakes Data Room Case Study

Great Lakes Data Room Case Study WeRackYourWorld.com Problem: During a warm summer period in 2008, Great Lakes experienced a network outage due to a switch failure in the network enclosure. After an equipment

### Data Center Operating Cost Savings Realized by Air Flow Management and Increased Rack Inlet Temperatures

Data Center Operating Cost Savings Realized by Air Flow Management and Increased Rack Inlet Temperatures William Seeber Stephen Seeber Mid Atlantic Infrared Services, Inc. 5309 Mohican Road Bethesda, MD

### Data Center Components Overview

Data Center Components Overview Power Power Outside Transformer Takes grid power and transforms it from 113KV to 480V Utility (grid) power Supply of high voltage power to the Data Center Electrical Room

### Managing Cooling Capacity & Redundancy In Data Centers Today

Managing Cooling Capacity & Redundancy In Data Centers Today About AdaptivCOOL 15+ Years Thermal & Airflow Expertise Global Presence U.S., India, Japan, China Standards & Compliances: ISO 9001:2008 RoHS

### Data Centers. Datacom Airflow Patterns

The following article was published in ASHRAE Journal, April 2005. Copyright 2005 American Society of Heating, Refrigerating and Air- Conditioning Engineers, Inc. It is presented for educational purposes

### Role of the PI System in Research @ Georgia Tech Data Center Laboratory

Role of the PI System in Research @ Georgia Tech Data Center Laboratory Presented by Vaibhav K. Arghode Prepared by Vikneshan Sundaralingam Outline Data center laboratory general information Current use

### AIR DISTRIBUTION FOR COMFORT AND IAQ

AIR DISTRIBUTION FOR COMFORT AND IAQ Heating Piping and Air Conditioning March 1998 Dan Int-Hout Chief Engineer KRUEGER EXCELLENCE IN AIR DISTRIBUTION Modern environmentally controlled spaces consume significant

### Optimum Climate Control For Datacenter - Case Study. T. Prabu March 17 th 2009

Optimum Climate Control For Datacenter - Case Study T. Prabu March 17 th 2009 Agenda 2 About EDEC (Emerson) Facility Data Center Details Design Considerations & Challenges Layout Design CFD Analysis Of

### Prompt Engineering applies successfully CFD analysis on large Server Room for a simulation driven Energy saving approach.

Prompt Engineering applies successfully CFD analysis on large Server Room for a simulation driven Energy saving approach.. ABSTRACT The Energy Saving approach is the target of this case story. The problem

### How to Build a Data Centre Cooling Budget. Ian Cathcart

How to Build a Data Centre Cooling Budget Ian Cathcart Chatsworth Products Topics We ll Cover Availability objectives Space and Load planning Equipment and design options Using CFD to evaluate options

### GUIDE TO ICT SERVER ROOM ENERGY EFFICIENCY. Public Sector ICT Special Working Group

GUIDE TO ICT SERVER ROOM ENERGY EFFICIENCY Public Sector ICT Special Working Group SERVER ROOM ENERGY EFFICIENCY This guide is one of a suite of documents that aims to provide guidance on ICT energy efficiency.

### Problem Statement In order to satisfy production and storage requirements, small and medium-scale industrial

Problem Statement In order to satisfy production and storage requirements, small and medium-scale industrial facilities commonly occupy spaces with ceilings ranging between twenty and thirty feet in height.

### CFD Application on Food Industry; Energy Saving on the Bread Oven

Middle-East Journal of Scientific Research 13 (8): 1095-1100, 2013 ISSN 1990-9233 IDOSI Publications, 2013 DOI: 10.5829/idosi.mejsr.2013.13.8.548 CFD Application on Food Industry; Energy Saving on the

### Data Center 2020: Delivering high density in the Data Center; efficiently and reliably

Data Center 2020: Delivering high density in the Data Center; efficiently and reliably March 2011 Powered by Data Center 2020: Delivering high density in the Data Center; efficiently and reliably Review:

### Introducing Computational Fluid Dynamics Virtual Facility 6SigmaDC

IT Infrastructure Services Ltd Holborn Gate, 330 High Holborn, London, WC1V 7QT Telephone: +44 (0)20 7849 6848 Fax: +44 (0)20 7203 6701 Email: info@itisltd.co.uk www.itisltd.com Introducing Computational

### PIV Measurement of Air Flow in a Hydro Power Generator Model

PIV Measurement of Air Flow in a Hydro Power Generator Model Erwin A. Hartono *, Maxim Golubev, Pirooz Moradnia, Valery Chernoray, Håkan Nilsson Department of Applied Mechanics, Chalmers University of

### APC APPLICATION NOTE #92

#92 Best Practices for Designing Data Centers with the InfraStruXure InRow RC By John Niemann Abstract The InfraStruXure InRow RC is designed to provide cooling at the row and rack level of a data center

### Design and Optimization of a Displacement Ventilation System for a Large Retail Store

Design and Optimization of a Displacement Ventilation System for a Large Retail Store Isabelle Lavedrine, Peter Alspach, Alisdair McGregor, and Sean Timmons, Arup ABSTRACT This paper describes the use

### BRUNS-PAK Presents MARK S. EVANKO, Principal

BRUNS-PAK Presents MARK S. EVANKO, Principal Data Centers of the Future and the Impact of High Density Computing on Facility Infrastructures - Trends, Air-Flow, Green/LEED, Cost, and Schedule Considerations

### CFD ANALYSIS CHALLENGES IN BUILDING SIMULATION FOR SIMBUILD2004 CONFERENCE. Ferdinand Schmid and Galen Burrell Architectural Energy Corporation

CFD ANALYSIS CHALLENGES IN BUILDING SIMULATION FOR SIMBUILD2004 CONFERENCE Ferdinand Schmid and Galen Burrell Architectural Energy Corporation ABSTRACT This paper discusses the capabilities and challenges

### Analysis and Performance Prediction of Data Centre with Different Configurations using CFD

Analysis and Performance Prediction of Data Centre with Different Configurations using CFD Mohammed Faisal K, PG Scholar Department of Mechanical Engineering, M. A College of Engg Kothamangalam,.. Ernakulam

### 2013 Code_Saturne User Group Meeting. EDF R&D Chatou, France. 9 th April 2013

2013 Code_Saturne User Group Meeting EDF R&D Chatou, France 9 th April 2013 Thermal Comfort in Train Passenger Cars Contact For further information please contact: Brian ANGEL Director RENUDA France brian.angel@renuda.com

### Prediction Is Better Than Cure CFD Simulation For Data Center Operation.

Prediction Is Better Than Cure CFD Simulation For Data Center Operation. This paper was written to support/reflect a seminar presented at ASHRAE Winter meeting 2014, January 21 st, by, Future Facilities.

### Sealing Gaps Under IT Racks: CFD Analysis Reveals Significant Savings Potential

TECHNICAL REPORT Sealing Gaps Under IT Racks: CFD Analysis Reveals Significant Savings Potential By Lars Strong, P.E., Upsite Technologies, Inc. Bruce Long, Upsite Technologies, Inc. +1.888.982.7800 upsite.com

### Server Room Thermal Assessment

PREPARED FOR CUSTOMER Server Room Thermal Assessment Analysis of Server Room COMMERCIAL IN CONFIDENCE MAY 2011 Contents 1 Document Information... 3 2 Executive Summary... 4 2.1 Recommendation Summary...

### Best Practices for Wire-free Environmental Monitoring in the Data Center

White Paper Best Practices for Wire-free Environmental Monitoring in the Data Center April 2012 Introduction Monitoring for environmental threats in the data center is not a new concept. Since the beginning

### Data Center Power Consumption

Data Center Power Consumption A new look at a growing problem Fact - Data center power density up 10x in the last 10 years 2.1 kw/rack (1992); 14 kw/rack (2007) Racks are not fully populated due to power/cooling

### Using CFD for Data Center Design and Analysis

Applied Math Modeling White Paper Using CFD for Data Center Design and Analysis By Liz Marshall and Paul Bemis, Applied Math Modeling Inc., Concord, NH January, 2011 Introduction Computational fluid dynamics

### COMPARATIVE ANALYSIS OF WIDELY USED AIR CONTAINMENT SYSTEMS IN COMMERCIAL DATA CENTERS FOR MAXIMUM COOLING PERFORMANCE KASTURI RANGAN RAJAGOPALAN

COMPARATIVE ANALYSIS OF WIDELY USED AIR CONTAINMENT SYSTEMS IN COMMERCIAL DATA CENTERS FOR MAXIMUM COOLING PERFORMANCE by KASTURI RANGAN RAJAGOPALAN Presented to the Faculty of the Graduate School of The

### DataCenter 2020: first results for energy-optimization at existing data centers

DataCenter : first results for energy-optimization at existing data centers July Powered by WHITE PAPER: DataCenter DataCenter : first results for energy-optimization at existing data centers Introduction

### Flow in data racks. 1 Aim/Motivation. 3 Data rack modification. 2 Current state. EPJ Web of Conferences 67, 02070 (2014)

EPJ Web of Conferences 67, 02070 (2014) DOI: 10.1051/ epjconf/20146702070 C Owned by the authors, published by EDP Sciences, 2014 Flow in data racks Lukáš Manoch 1,a, Jan Matěcha 1,b, Jan Novotný 1,c,JiříNožička

### Optimizing Network Performance through PASSIVE AIR FLOW MANAGEMENT IN THE DATA CENTER

Optimizing Network Performance through PASSIVE AIR FLOW MANAGEMENT IN THE DATA CENTER Lylette Macdonald, RCDD Legrand Ortronics BICSI Baltimore 2011 Agenda: Discuss passive thermal management at the Rack

### Eco Pelmet Modelling and Assessment. CFD Based Study. Report Number 610.14351-R1D1. 13 January 2015

EcoPelmet Pty Ltd c/- Geoff Hesford Engineering 45 Market Street FREMANTLE WA 6160 Version: Page 2 PREPARED BY: ABN 29 001 584 612 2 Lincoln Street Lane Cove NSW 2066 Australia (PO Box 176 Lane Cove NSW

### Modeling and Simulation of Axial Fan Using CFD Hemant Kumawat

Modeling and Simulation of Axial Fan Using CFD Hemant Kumawat Abstract Axial flow fans, while incapable of developing high pressures, they are well suitable for handling large volumes of air at relatively

### POWER USAGE EFFECTIVENESS. Developing Best Practices Manual for Indian Data Centers. Presentation by HVAC Core Group

POWER USAGE EFFECTIVENESS Developing Best Practices Manual for Indian Data Centers PUE - Power usage effectiveness is Total incoming power( IT equipment + electrical And mechanical support system ) / Presentation

### Driving Data Center Efficiency Through the Adoption of Best Practices

Data Center Solutions 2008 Driving Data Center Efficiency Through the Adoption of Best Practices Data Center Solutions Driving Data Center Efficiency Through the Adoption of Best Practices Executive Summary

### INTERNATIONAL JOURNAL OF MECHANICAL ENGINEERING AND TECHNOLOGY (IJMET)

INTERNATIONAL JOURNAL OF MECHANICAL ENGINEERING AND TECHNOLOGY (IJMET) Proceedings of the 2 nd International Conference on Current Trends in Engineering and Management ICCTEM -2014 ISSN 0976 6340 (Print)

### Statement Of Work Professional Services

Statement Of Work Professional Services Data Center Cooling Analysis using CFD Data Center Cooling Analysis Using Computational Fluid Dynamics Service 1.0 Executive Summary Table of Contents 1.0 Executive

### TWO-DIMENSIONAL FINITE ELEMENT ANALYSIS OF FORCED CONVECTION FLOW AND HEAT TRANSFER IN A LAMINAR CHANNEL FLOW

TWO-DIMENSIONAL FINITE ELEMENT ANALYSIS OF FORCED CONVECTION FLOW AND HEAT TRANSFER IN A LAMINAR CHANNEL FLOW Rajesh Khatri 1, 1 M.Tech Scholar, Department of Mechanical Engineering, S.A.T.I., vidisha

### A White Paper from the Experts in Business-Critical Continuity TM. Data Center Cooling Assessments What They Can Do for You

A White Paper from the Experts in Business-Critical Continuity TM Data Center Cooling Assessments What They Can Do for You Executive Summary Managing data centers and IT facilities is becoming increasingly

### Thermal Mass Availability for Cooling Data Centers during Power Shutdown

2010 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. (www.ashrae.org). Published in ASHRAE Transactions (2010, vol 116, part 2). For personal use only. Additional reproduction,

### TRANSIENT AIR TEMPERATURE MEASUREMENTS IN A DATA CENTER

Proceedings of the 21st National & 10TH ISHMT-ASME Heat and Mass Transfer Conference December 27-30, 2011, IIT Madras, India Paper ID: ISHMT_USA_013 TRANSIENT AIR TEMPERATURE MEASUREMENTS IN A DATA CENTER

### NUCLEAR ENERGY RESEARCH INITIATIVE

NUCLEAR ENERGY RESEARCH INITIATIVE Experimental and CFD Analysis of Advanced Convective Cooling Systems PI: Victor M. Ugaz and Yassin A. Hassan, Texas Engineering Experiment Station Collaborators: None

### I-STUTE Project - WP2.3 Data Centre Cooling. Project Review Meeting 8, Loughborough University, 29 th June 2015

I-STUTE Project - WP2.3 Data Centre Cooling Project Review Meeting 8, Loughborough University, 29 th June 2015 Topics to be considered 1. Progress on project tasks 2. Development of data centre test facility

### High Density Data Centers Fraught with Peril. Richard A. Greco, Principal EYP Mission Critical Facilities, Inc.

High Density Data Centers Fraught with Peril Richard A. Greco, Principal EYP Mission Critical Facilities, Inc. Microprocessors Trends Reprinted with the permission of The Uptime Institute from a white

### CCTech TM. ICEM-CFD & FLUENT Software Training. Course Brochure. Simulation is The Future

. CCTech TM Simulation is The Future ICEM-CFD & FLUENT Software Training Course Brochure About. CCTech Established in 2006 by alumni of IIT Bombay. Our motive is to establish a knowledge centric organization

### Development of Ventilation Strategy in Diesel Engine Power Plant by Using CFD Modelling

Development of Ventilation Strategy in Diesel Engine Power Plant by Using CFD Modelling Panu Mustakallio and Risto Kosonen Halton Oy, Haltonintie 1-3, 47400 Kausala, Finland E-mail: panu.mustakallio@halton.com

### Reducing the Annual Cost of a Telecommunications Data Center

Applied Math Modeling White Paper Reducing the Annual Cost of a Telecommunications Data Center By Paul Bemis and Liz Marshall, Applied Math Modeling Inc., Concord, NH March, 2011 Introduction The facilities

### O.F.Wind Wind Site Assessment Simulation in complex terrain based on OpenFOAM. Darmstadt, 27.06.2012

O.F.Wind Wind Site Assessment Simulation in complex terrain based on OpenFOAM Darmstadt, 27.06.2012 Michael Ehlen IB Fischer CFD+engineering GmbH Lipowskystr. 12 81373 München Tel. 089/74118743 Fax 089/74118749

### Elements of Energy Efficiency in Data Centre Cooling Architecture

Elements of Energy Efficiency in Data Centre Cooling Architecture Energy Efficient Data Center Cooling 1 STULZ Group of Companies Turnover 2006 Plastics Technology 400 Mio A/C Technology 200 Mio Total

### The Influence of Aerodynamics on the Design of High-Performance Road Vehicles

The Influence of Aerodynamics on the Design of High-Performance Road Vehicles Guido Buresti Department of Aerospace Engineering University of Pisa (Italy) 1 CONTENTS ELEMENTS OF AERODYNAMICS AERODYNAMICS

### Google s Green Data Centers: Network POP Case Study

Google s Green Data Centers: Network POP Case Study Table of Contents Introduction... 2 Best practices: Measuring. performance, optimizing air flow,. and turning up the thermostat... 2...Best Practice

### Integrated Cabinets and Thermal Systems May 15, 2014 Panduit Korea Technical System Engineer Chester Ki

1 Integrated Cabinets and Thermal Systems May 15, 2014 Panduit Korea Technical System Engineer Chester Ki 4/10/2014 2 Agenda Market Trends Thermal Architectures Data Centre Cabinet Systems Net-Access Cabinet

### Andrea Basti* Italian National Institute of Nuclear Physics (INFN) Gran Sasso National Laboratory (LNGS) *Research Grant Holder

Evaluation of the possibility to use waterscreen for people evacuation from the Gran Sasso National Laboratory inside the Gran Sasso highway tunnel in case of fire The case of The Gran Sasso National Laboratory

### Validation of Computational Fluid Dynamics Based. Data Center Cyber-Physical Models. Rose Robin Gilbert

Validation of Computational Fluid Dynamics Based Data Center Cyber-Physical Models by Rose Robin Gilbert A Thesis Presented in Partial Fulfillment of the Requirements for the Degree Master of Science Approved

### CFD MODELLING FOR SWIRL DIFFUSER AND ITS IMPLICATIONS ON AIR CHANGE EFFECTIVENESS ASSESSMENT TO GREEN STAR'S IEQ-2

CFD MODELLING FOR SWIRL DIFFUSER AND ITS IMPLICATIONS ON AIR CHANGE EFFECTIVENESS ASSESSMENT TO GREEN STAR'S IEQ-2 Eddy Rusly 1 and Mirek Piechowski 2 1,2 Meinhardt (VIC), Melbourne, Australia ABSTRACT

### Managing Data Centre Heat Issues

Managing Data Centre Heat Issues Victor Banuelos Field Applications Engineer Chatsworth Products, Inc. 2010 Managing Data Centre Heat Issues Thermal trends in the data centre Hot Aisle / Cold Aisle design

### Heattransferina tankintank combi store

Søren Knudsen Heattransferina tankintank combi store DANMARKS TEKNISKE UNIVERSITET Rapport BYG DTU R-025 2002 ISSN 1601-2917 ISBN 87-7877-083-1 1 Contents Contents...1 Preface...2 Summary...3 1. Introduction...4

### Numerical Simulation of the External Flow Field. Around a Bluff Car*

Numerical Simulation of the External Flow Field Around a Bluff Car* Sun Yongling, Wu Guangqiang, Xieshuo Automotive Engineering Department Shanghai Tongji University Shanghai, China E-mail: wuqjuhyk@online.sh.cn

### Legacy Data Centres Upgrading the cooling capabilities What are the options?

Legacy Data Centres Upgrading the cooling capabilities What are the options? Presentation Structure What is a Legacy Data Centre? What is CRAC cooling? ASHRAE Standards Overview Available Cooling Systems

### FLOW ANALYSIS OF EFFECT OF STRUTS IN AN ANNULAR DIFFUSER

FLOW ANALYSIS OF EFFECT OF STRUTS IN AN ANNULAR DIFFUSER 1, 2, 3 Raghul., DANUSHKOTTI., Nanda Gopal. B.E Student, Department of Mechanical Engineering, Velammal Engg College, Chennai ABSTRACT Some recent

### Best Practices for Wire-free Environmental Monitoring in the Data Center

White Paper 11800 Ridge Parkway Broomfiled, CO 80021 1-800-638-2638 http://www.42u.com sales@42u.com Best Practices for Wire-free Environmental Monitoring in the Data Center Introduction Monitoring for

### CoolTop. Main advantages: CoolTop. + Does not occupy any floor space + Extremely low power consumption + Maximal flexibility + Unique solution

Main advantages: + Does not occupy any floor space + Extremely low power consumption + Maximal flexibility + Unique solution Modularity = More units in one system Basic dimensions: Length 2400 mm (3 racks

### Improving Data Center Energy Efficiency Through Environmental Optimization

Improving Data Center Energy Efficiency Through Environmental Optimization How Fine-Tuning Humidity, Airflows, and Temperature Dramatically Cuts Cooling Costs William Seeber Stephen Seeber Mid Atlantic

### Thermal Monitoring Best Practices Benefits gained through proper deployment and utilizing sensors that work with evolving monitoring systems

NER Data Corporation White Paper Thermal Monitoring Best Practices Benefits gained through proper deployment and utilizing sensors that work with evolving monitoring systems Introduction Data centers are

### NUMERICAL SIMULATION OF FLOW FIELDS IN CASE OF FIRE AND FORCED VENTILATION IN A CLOSED CAR PARK

FACULTY OF ENGINEERING NUMERICAL SIMULATION OF FLOW FIELDS IN CASE OF FIRE AND FORCED VENTILATION IN A CLOSED CAR PARK Xavier Deckers, Mehdi Jangi, Siri Haga and Bart Merci Department of Flow, Heat and

### AEGIS DATA CENTER SERVICES POWER AND COOLING ANALYSIS SERVICE SUMMARY

AEGIS DATA CENTER SERVICES POWER AND COOLING ANALYSIS SERVICE SUMMARY The Aegis Services Power and Assessment Service provides an assessment and analysis of your data center facility and critical physical

### DCIM Data Center Infrastructure Monitoring

DCIM Data Center Infrastructure Monitoring ServersCheck offers a flexible, modular and affordable DCIM solution. It is based on our range of IP & SNMP hardware environmental sensors and management software.

### Best Practices in HVAC Design/Retrofit

Best Practices in HVAC Design/Retrofit Little Server Room BIG \$AVINGS Justin Lewis, P.E., LEED AP, DCEP Sr Energy Project Manager C:530.400.6042 O:530.754.4870 jlewis@ucdavis.edu 1 What s the problem here?

### Ravi Kumar Singh*, K. B. Sahu**, Thakur Debasis Mishra***

Ravi Kumar Singh, K. B. Sahu, Thakur Debasis Mishra / International Journal of Engineering Research and Applications (IJERA) ISSN: 48-96 www.ijera.com Vol. 3, Issue 3, May-Jun 3, pp.766-77 Analysis of

### CFD Application on Food Industry; Energy Saving on the Bread Oven

Iranica Journal of Energy & Environment 3 (3): 241-245, 2012 ISSN 2079-2115 IJEE an Official Peer Reviewed Journal of Babol Noshirvani University of Technology DOI: 10.5829/idosi.ijee.2012.03.03.0548 CFD

### CFD SIMULATION ENHANCES A DATA CENTER S EXPANSION PROCESS

CFD SIMULATION ENHANCES A DATA CENTER S EXPANSION PROCESS Gang Tan 1, Kevin S. Venerable 2 1 Department of Civil and Architectural Engineering, University of Wyoming, Laramie, WY 2 IT Division, Data Centers,

### Data Centre Energy Efficiency Operating for Optimisation Robert M Pe / Sept. 20, 2012 National Energy Efficiency Conference Singapore

Data Centre Energy Efficiency Operating for Optimisation Robert M Pe / Sept. 20, 2012 National Energy Efficiency Conference Singapore Introduction Agenda Introduction Overview of Data Centres DC Operational