# University of Ljubljana, Faculty of Mechanical Engineering, Slovenia

Size: px
Start display at page:

## Transcription

2 function of cooling degree days and latent enthalpy days. In this paper, different approaches for addressing the above-mentioned issues surrounding the use of cooling degree days as predictive and monitoring tools are tested on real building performance data and compared with each other. are explained in [5] and [6], which enable to estimate monthly cooling degree days with monthly average temperature and standard deviation of daily average temperature. 1 THEORY Different ways of calculating cooling degree days and methods for determining base temperature as well as a simple way to capture latent loads with cooling degree days are described in this part of the article. 1.1 Calculation of Degree-Days From a strictly mathematical viewpoint cooling degree days are a time integral of temperature differences between a defined base temperature and outside air temperatures above it. Hence only the positive area between the outdoor temperature curve and the base temperature line is considered (Fig. 1). The calculation procedures for CDD differ in the quality of used weather data (i.e. temperature). When hourly temperature data is available CDD can be calculated simply by subtracting the base temperature θ b from hourly outside air temperatures θ o,i and by averaging the sum of positive hourly differences, which are called cooling degree hours (CDH) analogously to cooling degree days, over the day: ( ) > 24 θ i oi θ = 1, b ( θoi, θb ) CDD =. 24 (3) The simplest technique for calculating cooling degree days is to calculate CDD from the mean daily temperature θ o, (Eq. (4)). This method is mathematically less accurate than the above mentioned mean cooling degree hours method (MCDH) because it considers only days with an average daily temperature higher than the base temperature. In practice this means that when calculating CDD with the same base temperature the mean daily temperature method (MDT) would produce less cooling degree days than the MCDH method for the same time period since it would leave out some days. n CDD = i ( θoi θb ). (4) = 1, ( θoi, > θb ) For cases where even less detailed climate data are available, more complex calculation methods (compared to the previously described procedures) Fig. 1. Principle of cooling degree-day calculation 1.2 Determination of Base Temperature Although one can determine the base temperature can be analytically determined for simple single zone constant air volume (CAV) air-conditioning systems as shown in [7], statistical methods are mostly preferred, since analytical determination for more complex systems is difficult and time-consuming. One of these methods is the energy signature method [8]. A building energy signature is a plot of building s daily electric energy consumption E d against mean daily temperature (Fig. 2a). The intercept of weather independent and dependent electric energy consumption represents the building s base temperature and can be calculated with piecewise linear regression as shown in Fig. 2b. The main disadvantage of this approach is that it requires high resolution energy consumption data (i.e. daily consumption), which is not always available. Therefore, a more practical approach for most users is to determine the base temperature via the performance line method. Performance lines are essentially bestfit straight lines through data on scatter plots of monthly electric energy consumption E m against monthly cooling degree days CDD m (Fig. 3a) and are primarily used for monitoring and analyzing energy consumption of existing buildings by means of degree days. The base temperature of a building is determined by putting a best-fit second order polynomial through data on a CDD m versus E m scatter plot and by varying the base until the polynomial best is almost equal to linear, i.e. the quadratic term s regression becomes zero as shown in Fig. 3b. A concave upward polynomial indicates a too low base temperature, 108 Krese, G. Prek, M. Butala, V.

3 Fig. 2. Energy signature; a) example, b) base temperature determination while a concave downward polynomial indicates a too high base value. 1.3 Wet-Bulb Temperature Cooling Degree Days The easiest way to include latent loads in cooling degree days is to calculate them with wet-bulb temperature θ w instead of dry-bulb temperature as briefly mentioned in [9]. The wet-bulb temperature is the minimum temperature to which air can be cooled by evaporative cooling, and, as such, contains information about air temperature as well as moisture content. On the Mollier psychrometric chart points with the same wet-bulb temperature lie on fog region isotherms, which are almost parallel with the isenthalps, hence wet-bulb temperature differences are equivalent to enthalpy differences. The main advantage of wet-bulb cooling degree days (CDD w ) over enthalpy days (summations of enthalpy differences over time) is that they have the same unit (K day) as ordinary (i.e. dry-bulb) cooling degree days and are therefore easily comparable to them. Calculation procedures and methods for base temperature determination are simply taken over from dry-bulb cooling degree days (sections 1.1 and 1.2). Nevertheless, the physical meaning of wetbulb cooling degree days is quite different from that of cooling degree days. Whereas the CDD method presumes that moist air, regardless of state, cools down at constant absolute humidity (Fig. 4a), the CDD w method leaves open both possibilities of cooling moist air; i.e. cooling with and without dehumidification (condensation) as shown in Fig. 4b. 2 DATA The statistical analysis was carried out on energy performance data of an office building located in Ljubljana, Slovenia. It is a 13 story building with 7200 m 2 of air conditioned spaces. The double glazed facade with a g-value of 0.75 (coefficient of the permeability of total solar radiation energy) has an area of 2340 m 2 and internal blinds. The building is equipped with two centralised heating ventilation and air conditioning (HVAC) systems with moisture control, one for the inner and one for the exterior Fig. 3. Performance line; a) example, b) base temperature determination Analysis of Building Electric Energy Consumption Data Using an Improved Cooling Degree Day Method 109

4 zone. The air-conditioning system for the external zone is a 4-pipe air and water induction system, while air-conditioning for internal zone is provided by a CAV system. Cooling is provided by two water cooled vapor-compression liquid chillers each with a nominal cooling capacity of 550 kw and by an additional cooling system for the server room with a capacity of 32 kw. Building performance data was provided by a local electricity distribution company in form of 15- min total electric power readings, which were hourly averaged in order to get hourly total electric energy consumption. The data were gathered for the period between February 1 st, 2009 and January 31 st, In addition, hourly meteorological data for the building location for the same time interval was obtained. 3 RESULTS Before calculating degree days for the selected time period we determined the building s base (dry-bulb and wet-bulb) temperature with the methods described in section 1.2. The energy signature method was used first. Initially all available data (i.e. daily electric energy consumption and mean daily temperature) were used to plot the dry-bulb and wet-bulb energy signature. Both of the resulting energy signatures indicated the existence of two energy consumption levels as shown in Fig. 5a. Since this was clearly the consequence of occupancy variation, the non-working days (weekends and holydays) were filtered out and the base temperatures were determined with piecewise linear regression from the energy signatures reploted with the filtered data (Fig. 5b). The thus obtained regression lines on the left side of base values had noticeably positive slopes, which was not in accordance with the theory of the energy signature method. By definition the left side of energy signatures is weather independent, so the regression lines should have been parallel to the temperature axis (zero slope). A detailed analysis of hourly data revealed that the root cause of this deviation lies in the use of building overall electric energy consumption. The problem is that space cooling is not the only contributor to energy consumption, thus changes in operation of building systems and equipment whose energy consumption Fig. 4. Cooling load assumptions; a) CDD method; b) CDD w method 110 Krese, G. Prek, M. Butala, V.

5 represents the base load, i.e. the non-weather related energy consumption, also influence the determination of base temperatures. In our case the reduction of night-time ventilation rate in winter resulted in considerably lower energy consumption in days in which the HVAC system operated under the winter regime compared to the days when space cooling was off and the ventilation rate was not dropped. For this reason, the building base load seemed to increase with temperature. In order to eliminate the influence of base load variation, hours outside the working schedule (7 a.m. to 5 p.m.) were removed from the working day data. The so filtered data was then used to plot the energy signatures for a third time and to calculate the dry-bulb and wet-bulb base temperature (Fig. 5c). All the base values obtained from the energy signature method are listed in Table 1. Table 1. Base temperatures determined using the energy signature method Working days Working days 7 a.m. to 5 p.m. R 2 R 2 θ b [ C] θ w,b [ C] Next, the performance line method was applied. Each base temperature was determined twice, once with degree days calculated from daily averaged hourly dry-bulb/wet-bulb temperature differences (Eq. (3)) and once with daily differences (Eq. (4)) as shown in Fig. 6. The results are listed in Table 2. Base temperatures determined using hourly values are higher than those determined with daily values, which can be explained with the fact that hours are too small time increments to capture the thermal storage effect. In contrast, the wet-bulb base values are almost equal. The reason for this is very simple and lies in the meteorological data. The outdoor wet-bulb temperature varies little throughout the day compared to the dry-bulb temperature (Fig. 7), therefore the mean daily wet-bulb temperature differs very little from individual hourly values, i.e. the daily standard deviation of wet-bulb temperature is small. Table 2. Base temperatures determined using the performance line method Hourly values Daily values θ b [ C] θ w,b [ C] In comparison with base temperatures determined via energy signature method from filtered workday data (7 a.m. to 5 p.m.), the base values obtained from performance lines using daily temperature differences (Eq. (4)) are slightly lower. The differences are due to the chosen time interval for base temperature determination from energy signatures. Because the lowest temperatures of a day occur at the filtered out hours, the mean temperatures calculated for the selected averaging period are higher than the mean daily temperatures, hence the energy signatures and with them the base temperatures are shifted forward on the temperature axis. As a result monthly dry-bulb Fig. 5. Base temperature determination via energy signatures; a) unfiltered data, b) working days, c) working days 7 a.m. to 5 p.m. Analysis of Building Electric Energy Consumption Data Using an Improved Cooling Degree Day Method 111

6 Fig. 6. Base temperature determination via performance lines; a) CDD calculated from hourly differences, b) CDD calculated from daily differences and wet-bulb cooling degree days (Table 3) were calculated only for base temperatures determined via performance lines using daily values. Whereby degree days were calculated only with the calculation procedure, which was employed in determination of base values (i.e. mean daily temperature method). To find out which cooling degree day method is more accurate, performance lines were constructed (linear regression) from monthly total electric energy consumption and each set of monthly degree day data (Fig. 8), and predictions of monthly energy consumptions were made using the performance lines equations (Table 4). The predicted monthly consumptions were then compared against actual consumptions: Ep Ea E (%)= 100 %, (5) E a Fig. 7. Daily progress of dry-bulb and wet-bulb outdoor temperature on July 23 rd, 2009 Although the annual sums of dry-bulb and wetbulb cooling degree days differ marginally, the differences between degree days totals for transitional months are up to 123% (October percentage difference in relation to CDD). where ΔE is the percentage difference between actual and predicted monthly electric energy consumption, E p is the predicted monthly energy consumption and E a is the actual monthly energy consumption. As seen in Fig. 9 the wet-bulb cooling degree method better predicted energy consumption for three of five months during the cooling season and for eight months overall. The dry-bulb cooling degree method had smaller prediction errors for June and August (besides for November and December), whereby the predicted values were 0.7 % for June and 0.1 % for August more accurate as the values predicted with the 112 Krese, G. Prek, M. Butala, V.

7 Table 3. Monthly dry-bulb and wet-bulb cooling degree days calculated to θ b = 16.1 C and θ w,b = 12.1 C Month CDD [K day] CDD w [K day] Feb Mar Apr May Jun Jul Aug Sept Oct Nov Dec Jan Σ Table 4. Predicted and actual monthly total electric energy consumption Month E p [kwh] CDD CDD w E a [kwh] Feb Mar Apr May Jun Jul Aug Sept Oct Nov Dec Jan CDD w method. The biggest difference was between the energy consumptions predicted for September, where consumption predicted with the CDD w performance line was 5.9 % closer to the actual energy consumption. While February energy consumption was most underestimated as a consequence of that February has the least number of days, consumptions for October and November were most overrated by both performance lines. In comparison with May, the cooling degree values (dry-bulb and wet-bulb) for October were significantly lower, but the total electric energy was higher. It was similar for November, i.e. total energy consumption in November was considerably higher than in other months with zero degree days. Both of these deviations can be explained by base load modification. 4 CONCLUSSION Cooling degree days are the summation of temperature differences between the outside air and a reference Fig. 9. Percentage differences between actual and predicted monthly electric energy consumptions temperature over time, and can be applied to estimate future building energy consumption due to space cooling or to monitor energy performance of existing buildings. Although the cooling degree day method is superior to other simplified methods for analysing weather related energy consumption in buildings, because CDD capture both the extremity and duration Fig. 8. Performance line; a) constructed with CDD, b) constructed with CDD w Analysis of Building Electric Energy Consumption Data Using an Improved Cooling Degree Day Method 113

8 of outdoor temperatures, there are several issues in the application of degree days to cooling energy use in buildings. A key issue, apart from selecting a calculation procedure for degree days, is the definition of a proper base temperature, because the building s balance point varies together with heat gains and the indoor temperature. However, the main problem lies in the definition of CDD method itself, since it neglects the influence of latent cooling loads on cooling energy, as a consequence from being derived from the heating degree day (HDD) method. In this article an improved cooling degree method the so-called wet-bulb cooling degree method, which takes into account both the sensible and latent loads, is used to analyse electric energy consumption data from an existing building and compared against the conventional cooling degree day approach, whereby different degree day calculation techniques and statistical methods for determining base temperature are applied. The results of the analysis are unambiguous, i.e. the CDD w method outperformed the CDD method in the majority of cases. Not only was the correlation between CDD w and electric energy consumption considerably higher (5% higher explained variance), but it was also revealed that the value of wet-bulb base temperature is less dependent on the method chosen for determination (energy signature and performance line method) and on the used degree day calculation procedure (daily averaged hourly and daily temperature differences). Nevertheless, the results obtained by any of the tested methods should be interpreted carefully when dealing with energy consumption data consisting of weather related and non-related energy consumption (i.e. total energy consumption). In spite of the fact that the wet-bulb cooling degree approach performed well on the selected total electric energy consumption data, it will have to be additionally tested on the data obtained from other existing buildings with different types of airconditioning systems, preferably on chiller power consumption data. 5 NOMENCLATURE List of symbols: CDD Cooling degree days [K day] E Total electric energy consumption [kwh] ELD Enthalpy latent days [kj/kg day] h Specific enthalpy of air [kj/kg] HDD Heating degree days [K day] t Time [day] x Absolute humidity of air [kg/kg] θ Temperature of air [ C] List of abbreviations: a Actual b Base d Day m Month o Outdoor p Predicted w Wet-bulb 6 REFERENCES [1] Košir, M., Krainer A., Dovjak M., Rudolf, P., Kristl, Ž. (2010). Alternative to the Conventional Heating and Cooling Systems in Public Buildings. Strojniški vestnik Journal of Mechanical Engineering, vol. 56, no. 9, p [2] Day, A.R., Knight, I., Dunn, G., Gaddas, R. (2003). Improved methods for evaluating base temperature for use in building energy performance lines. Building Service Engineering Research & Technology, vol. 24, no. 4, p , DOI: / bt073oa. [3] Huang, Y.J., Ritschard, R., Bull, J., Chang, L. (1986). Climatic indicators for estimating residential heating and cooling loads. Report LBL Lawrence Berkley Laboratory, Berkley. [4] Krese, G., Prek, M., Butala, V. (2011). Incorporation of latent loads into the cooling degree days concept. Energy and building, vol. 43, no. 7, p , DOI: /j.enbuild [5] ASHRAE (2009). Handbook fundamentals (SI). American Society of Heating, Refrigerating and Air- Conditioning Engineers, Atlanta. [6] Hitchin, E.R. (1983). Estimating monthly degree days. Building Service Engineering Research & Technology, vol. 4, no. 4, p. 159, DOI: / [7] Day, A.R., Maidment, G.G., Ratcliffe, M.S. (2000). Cooling degree-days and their applicability to building energy estimation. 20:20 Vision: CIBSE/ASHRAE Conference. [8] Jacobsen, F.R. (1985). Energy signature and energy monitoring in building energy management systems. Proceeding of CLIMA 2000 World Congress, vol. 3: Energy Management, p [9] Guan, L. (2009). Preparation of future weather data to study the impact of climate change on buildings. Building and Environment, vol. 44, no. 4, p , DOI: /j.buildenv Krese, G. Prek, M. Butala, V.

### Subtropical Cities September 2006. Design for Energy Efficiency in Commercial Buildings in Queensland

Subtropical Cities September 2006 Design for Energy Efficiency in Commercial Buildings in Queensland Contents Typical Building Constraints & Requirements Understanding Energy Consumption in Buildings HVAC

### CHAPTER 3. BUILDING THERMAL LOAD ESTIMATION

CHAPTER 3. BUILDING THERMAL LOAD ESTIMATION 3.1 Purpose of Thermal Load Estimation 3.2 Heating Load versus Cooling Load 3.3 Critical Conditions for Design 3.4 Manual versus Computer Calculations 3.5 Heating

for A Probabilistic Approach Taperit Tongshoob 1 Chirdpun Vitooraporn 2 Cooling Load Calculation Abstract 1 Ph.D Student 2 Lecturer at Building Technology Environment Laboratory, Mechanical Engineering

### Software Development for Cooling Load Estimation by CLTD Method

IOSR Journal of Mechanical and Civil Engineering (IOSR-JMCE) ISSN: 2278-1684Volume 3, Issue 6 (Nov. - Dec. 2012), PP 01-06 Software Development for Cooling Load Estimation by CLTD Method Tousif Ahmed Department

### MODELLING AND OPTIMIZATION OF DIRECT EXPANSION AIR CONDITIONING SYSTEM FOR COMMERCIAL BUILDING ENERGY SAVING

MODELLING AND OPTIMIZATION OF DIRECT EXPANSION AIR CONDITIONING SYSTEM FOR COMMERCIAL BUILDING ENERGY SAVING V. Vakiloroaya*, J.G. Zhu, and Q.P. Ha School of Electrical, Mechanical and Mechatronic Systems,

### Carnegie Mellon University School of Architecture, Department of Mechanical Engineering Center for Building Performance and Diagnostics

Carnegie Mellon University School of Architecture, Department of Mechanical Engineering Center for Building Performance and Diagnostics A Presentation of Work in Progress 4 October 2006 in the Intelligent

### Energy Efficiency: Integrated Design and HVAC Systems HEALTHCARE - TOP 5 GREEN BUILDING STRATEGIES

EPA Publication 909-F-07-001 What? Energy use in healthcare facilities is higher than nearly all other building types. With rising energy costs and climate change concerns energy efficiency is financially

### International Telecommunication Union SERIES L: CONSTRUCTION, INSTALLATION AND PROTECTION OF TELECOMMUNICATION CABLES IN PUBLIC NETWORKS

International Telecommunication Union ITU-T TELECOMMUNICATION STANDARDIZATION SECTOR OF ITU Technical Paper (13 December 2013) SERIES L: CONSTRUCTION, INSTALLATION AND PROTECTION OF TELECOMMUNICATION CABLES

### Climate and Weather. This document explains where we obtain weather and climate data and how we incorporate it into metrics:

OVERVIEW Climate and Weather The climate of the area where your property is located and the annual fluctuations you experience in weather conditions can affect how much energy you need to operate your

### ENERGY STAR for Data Centers

ENERGY STAR for Data Centers Alexandra Sullivan US EPA, ENERGY STAR February 4, 2010 Agenda ENERGY STAR Buildings Overview Energy Performance Ratings Portfolio Manager Data Center Initiative Objective

### ENERGY AUDITS (OR SURVEYS) & ENERGY MANAGEMENT PROGRAMS SECTION B

ENERGY AUDITS (OR SURVEYS) & ENERGY MANAGEMENT PROGRAMS SECTION B GOALS OF THE ENERGY AUDIT Clearly identify types and costs of energy use Understand how energy is being used--and possibly wasted Identify

Calculations -1- AIRCONDITIONING Cooling s Calculations Employer : 4M SA Project Location : ASHRAE Office Room : Example from ASHRAE 2013 Handbook - Fundamentals : Chapter 18, Single Room Example (p. 18.37)

### Optimization of Water - Cooled Chiller Cooling Tower Combinations

Optimization of Water - Cooled Chiller Cooling Tower Combinations by: James W. Furlong & Frank T. Morrison Baltimore Aircoil Company The warm water leaving the chilled water coils is pumped to the evaporator

### Moisture Content in Insulated Basement Walls

Moisture Content in Insulated Basement Walls Peter Blom,PhD, SINTEF Building and Infrastructure; peter.blom@sintef.no, www.sintef.no/byggforsk Sverre B. Holøs M.Sc. SINTEF Building and Infrastructure;

### Prepared for: Prepared by: Science Applications International Corporation (SAIC Canada) November 2012 CM002171 PROPRIETARY

Annual Report for 211-212 Prepared for: Natural Resources Canada Ressources naturelles Canada Prepared by: November 212 CM2171 Third Party Use Statement of Limitations This report has been prepared for

### ASHRAE Climatic Data Activities. Dru Crawley Didier Thevenard

ASHRAE Climatic Data Activities Dru Crawley Didier Thevenard ASHRAE American Society of Heating Refrigerating and Air- Conditioning Engineers >50,000 members Major products: Handbooks (Fundamentals, Systems

### Absolute and relative humidity Precise and comfort air-conditioning

Absolute and relative humidity Precise and comfort air-conditioning Trends and best practices in data centers Compiled by: CONTEG Date: 30. 3. 2010 Version: 1.11 EN 2013 CONTEG. All rights reserved. No

### Comparisons of HVAC Simulations between EnergyPlus and DOE-2.2 for Data Centers

ERNEST ORLANDO LAWRENCE BERKELEY NATIONAL LABORATORY Comparisons of HVAC Simulations between EnergyPlus and DOE-2.2 for Data Centers Tianzhen Hong, Dale Sartor, Paul Mathew, Mehry Yazdanian Environmental

### Comparing Air Cooler Ratings Part 1: Not All Rating Methods are Created Equal

Technical Bulletin By Bruce I. Nelson, P.E., President, Colmac Coil Manufacturing, Inc. Comparing Air Cooler Ratings Part 1: Not All Rating Methods are Created Equal SUMMARY Refrigeration air coolers (evaporators)

### Green Building Handbook for South Africa Chapter: Heating, Ventilation and Cooling Luke Osburn CSIR Built Environment

Green Building Handbook for South Africa Chapter: Heating, Ventilation and Cooling Luke Osburn CSIR Built Environment The heating, ventilation and cooling loads of typical commercial office space can range

### Application of Building Energy Simulation to Air-conditioning Design

Hui, S. C. M. and K. P. Cheung, 1998. Application of building energy simulation to air-conditioning design, In Proc. of the Mainland-Hong Kong HVAC Seminar '98, 23-25 March 1998, Beijing, pp. 12-20. (in

### Theoretical Study on Separate Sensible and Latent Cooling Air-Conditioning System

Purdue University Purdue e-pubs International Refrigeration and Air Conditioning Conference School of Mechanical Engineering 2008 Theoretical Study on Separate Sensible and Latent Cooling Air-Conditioning

### FIRST RADIANT COOLED COMMERCIAL BUILDING IN INDIA CRITICAL ANALYSIS OF ENERGY, COMFORT AND COST

FIRST RADIANT COOLED COMMERCIAL BUILDING IN INDIA CRITICAL ANALYSIS OF ENERGY, COMFORT AND COST Guruprakash Sastry, Senior Manager Green Initiatives Infosys Limited, Bangalore, INDIA ABSTRACT Radiation

### FORECASTING. Operations Management

2013 FORECASTING Brad Fink CIT 492 Operations Management Executive Summary Woodlawn hospital needs to forecast type A blood so there is no shortage for the week of 12 October, to correctly forecast, a

### Total Heat Versus Sensible Heat Evaporator Selection Methods & Application

Total Heat Versus Sensible Heat Evaporator Selection Methods & Application Scope The purpose of this paper is to provide specifying engineers, purchasers and users of evaporators in industrial refrigeration

### Saving Heating Costs In Warehouses

2005, American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. (www.ashrae.org). Reprinted by permission from ASHRAE Journal, (Vol. 47, No. 12, December 2005). This article may not

### Optimum Solar Orientation: Miami, Florida

Optimum Solar Orientation: Miami, Florida The orientation of architecture in relation to the sun is likely the most significant connection that we can make to place in regards to energy efficiency. In

### Simulation of hygroscopic materials in the HVAC system of an office building

Simulation of hygroscopic materials in the HVAC system of an office building IEA/ECBCS Annex 41 Porto Meeting Melanie Fauchoux, Carey Simonson and David Torvi Department of Mechanical Engineering, University

### International Telecommunication Union SERIES L: CONSTRUCTION, INSTALLATION AND PROTECTION OF TELECOMMUNICATION CABLES IN PUBLIC NETWORKS

International Telecommunication Union ITU-T TELECOMMUNICATION STANDARDIZATION SECTOR OF ITU Technical Paper (13 December 2013) SERIES L: CONSTRUCTION, INSTALLATION AND PROTECTION OF TELECOMMUNICATION CABLES

### Mario Guarracino. Regression

Regression Introduction In the last lesson, we saw how to aggregate data from different sources, identify measures and dimensions, to build data marts for business analysis. Some techniques were introduced

### FLORIDA SOLAR ENERGY CENTER

FLORIDA SOLAR ENERGY CENTER Creating Energy Independence Since 1975 Impact of Energy-Efficiency Parameters on Home Humidity Rob Vieira Florida Solar Energy Center A Research Institute of the University

### CO2 Emissions. Indirect CO 2. Emissions Electricity and Heat Production 25 % Direct Emissions AFOLU 24 % Energy 1,4% Buildings 6,4 % Industry 11 %

CO2 Emissions Direct Emissions AFOLU 24 % Buildings 6,4 % Transport 14 % 49 Gt CO2 eq (2010) Indirect CO 2 Emissions Electricity and Heat Production 25 % Energy 1,4% Industry 11 % Transport 0,3 % Industry

### SIMULATION OF RADIANT COOLING PERFORMANCE WITH

SUMMARY REPORT MAY 2008 SIMULATION OF RADIANT COOLING PERFORMANCE WITH EVAPORATIVE COOLING SOURCES Timothy Moore Center for the Built Environment (CBE) University of California, Berkeley May 2008 EXECUTIVE

### Degree-days: theory and application

Degree-days: theory and application TM41: 2006 The Chartered Institution of Building Services Engineers 222 Balham High Road, London SW12 9BS CIBSE The rights of publication or translation are reserved.

### A benchmarking guide adapted to air conditioning based on electricity bills

Technical guides for owner/manager of an air conditioning system: volume 7 A benchmarking guide adapted to air conditioning based on electricity bills 1 Team France (Project coordinator) Armines - Mines

### FINAL REPORT LIFE-CYCLE COST STUDY OF A GEOTHERMAL HEAT PUMP SYSTEM BIA OFFICE BLDG., WINNEBAGO, NE

FINAL REPORT LIFE-CYCLE COST STUDY OF A GEOTHERMAL HEAT PUMP SYSTEM BIA OFFICE BLDG., WINNEBAGO, NE February 2006 FINAL REPORT LIFE-CYCLE COST STUDY OF A GEOTHERMAL HEAT PUMP SYSTEM BIA OFFICE BLDG., WINNEBAGO,

### Using Street Surveys to Establish Air Conditioning Incidence in UK s Commercial Offices Stock

Using Street Surveys to Establish Air Conditioning Incidence in UK s Commercial Offices Stock Jorge Caeiro, Hector Altamirano-Medina, Harry Bruhns Bartlett School of Graduate Studies, University College

### Comfort Conditioning & Indoor Air Quality

This article was published in ASHRAE Journal, May 2011. Copyright 2011 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. Reprinted here by permission from ASHRAE at www.newellinstruments.com.

### Improving comfort and energy efficiency in a nursery school design process S. Ferrari, G. Masera, D. Dell Oro

Improving comfort and energy efficiency in a nursery school design process S. Ferrari, G. Masera, D. Dell Oro Dept. Building Environment Science &Technologies Politecnico di Milano Italy Research funded

### Direct Fresh Air Free Cooling of Data Centres

White Paper Introduction There have been many different cooling systems deployed in Data Centres in the past to maintain an acceptable environment for the equipment and for Data Centre operatives. The

### ENERGY AUDITS IN DWELLING BUILDINGS IN LATVIA. DATA ANALYSIS

ENERGY AUDITS IN DWELLING BUILDINGS IN LATVIA. DATA ANALYSIS SUMMARY D. BLUMBERGA*, A. BLUMBERGA, V. VITOLINS Riga Technical University Kronvalda bulvaris 1, LV1010, Riga, Latvia dagnija@btv.lv Tel.: +

### Validation of a building simulation tool using field data for three identical. configuration full-serve restaurants using different HVAC Systems

Validation of a building simulation tool using field data for three identical configuration full-serve restaurants using different HVAC Systems Paul L. Brillhart, PhD nstructor University of llinois, Chicago

### Evaluation of Window Energy Rating Models for Different Houses and European Climates

Evaluation of Window Energy Rating Models for Different Houses and European Climates J. and A. Roos Department of Materials Science, The Ångström Laboratory Uppsala University P.O. Box 534, S-751 21 Uppsala

### Moisture Control. It s The Dew Point. Stupid! Its not the humidity.

Moisture Control Its not the humidity. It s The Dew Point Stupid! Mike Schell EpiphanyTec Inc. Santa Barbara, CA mschell@epiphanytec.com 805 687-3175 Matching great technology to market need! Topics SHR

### Residential HVAC System Sizing

Residential HVAC System Sizing William P. Goss University of Massachusetts, Amherst, Massachusetts, USA Corresponding email: goss@acad.umass.edu SUMMARY Heating, ventilating and air-conditioning (HVAC)

### Studies energy efficiency of the renewable sources use considering climate in Latvia

Available online at www.sciencedirect.com ScienceDirect Energy Procedia (25) www.elsevier.com/locate/procedia 6th International Building Physics Conference, IBPC 25 Studies energy efficiency of the renewable

### Daikin Altherma Hybrid Heat Pump

Daikin Altherma Hybrid Heat Pump Smart technology for the best of both worlds NATIONAL HEAT PUMP 19 JUNE 2014 ICC BIRMINGHAM WINNER Forward thinking Now is the time to rethink the way we heat our homes

### Creating Efficient HVAC Systems

Creating Efficient HVAC Systems Heating and Cooling Fundamentals for Commercial Buildings Heating, ventilating, and air conditioning (HVAC) systems account for nearly half of the energy used in a typical

### PROTOCOL FOR BUILDING ENERGY ANALYSIS SOFTWARE For Class 3, 5, 6, 7, 8 and 9 buildings

PROTOCOL FOR BUILDING ENERGY ANALYSIS SOFTWARE For Class 3, 5, 6, 7, 8 and 9 buildings Version 2006.1 AUSTRALIAN BUILDING CODES BOARD JANUARY 2006 TABLE OF CONTENTS Foreword 1. Scope 2. Purpose and context

### Models and Methods in Applied Sciences

Energy consumption and energy saving in Malaysian office buildings S.Sadrzadehrafiei, K.Sopian S.Mat, C.Lim Solar Energy Research Institute University Kebangsaan Malaysia 43600, Bangi, Malaysia s.sadr.r@gmail.com,

### Methodology For Illinois Electric Customers and Sales Forecasts: 2016-2025

Methodology For Illinois Electric Customers and Sales Forecasts: 2016-2025 In December 2014, an electric rate case was finalized in MEC s Illinois service territory. As a result of the implementation of

### Chapter 14. At temperatures below the critical temperature, the gas GAS VAPOR MIXTURES AND AIR-CONDITIONING. Objectives

Chapter 14 GAS VAPOR MIXTURES AND -CONDITIONING At temperatures below the critical temperature, the gas phase of a substance is frequently referred to as a vapor. The term vapor implies a gaseous state

### Data driven approach in analyzing energy consumption data in buildings. Office of Environmental Sustainability Ian Tan

Data driven approach in analyzing energy consumption data in buildings Office of Environmental Sustainability Ian Tan Background Real time energy consumption data of buildings in terms of electricity (kwh)

### Climatic Influences on the Energy Consumption in Domestic and Commercial Sectors in Hong Kong

Climatic Influences on the Energy Consumption in Domestic and Commercial Sectors in Hong Kong T.C. Lee, M.H. Kok and K.Y. Chan Hong Kong Observatory 134A Nathan Road, Hong Kong, China Abstract In subtropical

### By Tom Brooke PE, CEM

Air conditioning applications can be broadly categorized as either standard or critical. The former, often called comfort cooling, traditionally just controlled to maintain a zone setpoint dry bulb temperature

### Energy savings in commercial refrigeration. Low pressure control

Energy savings in commercial refrigeration equipment : Low pressure control August 2011/White paper by Christophe Borlein AFF and l IIF-IIR member Make the most of your energy Summary Executive summary

### Legacy Data Centres Upgrading the cooling capabilities What are the options?

Legacy Data Centres Upgrading the cooling capabilities What are the options? Presentation Structure What is a Legacy Data Centre? What is CRAC cooling? ASHRAE Standards Overview Available Cooling Systems

### Daikin Altherma Hybrid Heat Pump

your comfort. our world. Daikin Altherma Hybrid Heat Pump Smart heating technology for the best of both worlds Heating Integrated Solutions Ventilation Air Conditioning Refrigeration Forward thinking About

### HVAC Calculations and Duct Sizing

PDH Course M199 HVAC Calculations and Duct Sizing Gary D. Beckfeld, M.S.E., P.E. 2007 PDH Center 2410 Dakota Lakes Drive Herndon, VA 20171-2995 Phone: 703-478-6833 Fax: 703-481-9535 www.pdhcenter.com An

### The Impact of Demand-Controlled and Economizer Ventilation Strategies on Energy Use in Buildings

4276 The Impact of Demand-Controlled and Economizer Ventilation Strategies on Energy Use in Buildings Michael J. Brandemuehl, Ph.D., P.E. Member ASHRAE James E. Braun, Ph.D., P.E. Member ASHRAE ABSTRACT

### COMPARISON OF FIXED & VARIABLE RATES (25 YEARS) CHARTERED BANK ADMINISTERED INTEREST RATES - PRIME BUSINESS*

COMPARISON OF FIXED & VARIABLE RATES (25 YEARS) 2 Fixed Rates Variable Rates FIXED RATES OF THE PAST 25 YEARS AVERAGE RESIDENTIAL MORTGAGE LENDING RATE - 5 YEAR* (Per cent) Year Jan Feb Mar Apr May Jun

### COMPARISON OF FIXED & VARIABLE RATES (25 YEARS) CHARTERED BANK ADMINISTERED INTEREST RATES - PRIME BUSINESS*

COMPARISON OF FIXED & VARIABLE RATES (25 YEARS) 2 Fixed Rates Variable Rates FIXED RATES OF THE PAST 25 YEARS AVERAGE RESIDENTIAL MORTGAGE LENDING RATE - 5 YEAR* (Per cent) Year Jan Feb Mar Apr May Jun

### AP Physics 1 and 2 Lab Investigations

AP Physics 1 and 2 Lab Investigations Student Guide to Data Analysis New York, NY. College Board, Advanced Placement, Advanced Placement Program, AP, AP Central, and the acorn logo are registered trademarks

### Arizona State University. Understanding the Impact of Urban Heat Island in Phoenix

Understanding the Impact of Urban Heat Island in Phoenix ( ) Summer Night-time 'min-low' temperatures and its impact on the energy consumption of various building typologies Presented By: Sandeep Doddaballapur

### Get the FACTS about SEER and Deliver Better Customer Value

What is SEER? SEER stands for Seasonal Energy Efficiency Ratio. It s a number that describes how well air-conditioning equipment works. A higher SEER means better efficiency and lower energy bills. SEER

### Dedicated Outdoor Air-Dual Wheel System Control Requirements

4428 Dedicated Outdoor Air-Dual Wheel System Control Requirements Stanley A. Mumma, Ph.D., P.E. Fellow ASHRAE ABSTRACT The central thrust of this paper is to develop a clear understanding of the performance

### EFFECTS OF INDOOR RELATIVE HUMIDITY ON REFRIGERATED DISPLAY CASE PERFORMANCE

P (5, EFFECTS OF INDOOR RELATIVE HUMIDITY ON REFRIGERATED DISPLAY CASE PERFORMANCE Ronald H. Howell, Professor Luis Rosario, Graduate Student Antonio Bula, Graduate Student Department of Mechanical Engineering

### Renewable Energy. Solar Power. Courseware Sample 86352-F0

Renewable Energy Solar Power Courseware Sample 86352-F0 A RENEWABLE ENERGY SOLAR POWER Courseware Sample by the staff of Lab-Volt Ltd. Copyright 2009 Lab-Volt Ltd. All rights reserved. No part of this

### Climate and Energy Responsive Housing in Continental Climates. The Suitability of Passive Houses for Iran's Dry and Cold Climate. Farshad Nasrollahi

Climate and Energy Responsive Housing in Continental Climates The Suitability of Passive Houses for Iran's Dry and Cold Climate Farshad Nasrollahi Table of Contents Abstract German Abstract Introduction

### APPLICATION GUIDE. Comparison of Latent Cooling Performance of Various HVAC systems in a Classroom Application

APPLICATION GUIDE Comparison of Latent Cooling Performance of Various HVAC systems in a Classroom Application Section Comparison of Latent Cooling Performance of Introduction Most commercial HVAC systems

### Optimal Drying of Flooded Brickwork Masonry

Optimal Drying of Flooded Brickwork Masonry John Grunewald, Dr.-Ing., Research Professor, Dresden University of Technology, Institute of Building Climatology, Germany grunewald@ibk.arch.tu-dresden.de,

### Wet Bulb Temperature and Its Impact on Building Performance

Wet Bulb Temperature and Its Impact on Building Performance By: Kurmit Rockwell, PE, CEM, LEED AP and Justin Lee, PE, LEED, AP BD+C Energy Solution Services, AtSite, Inc. 1 What is Wet Bulb Temperature?

### About the audit of air conditioning systems: Customer advising with the help of case studies and benchmarks, modelling and simulation

About the audit of air conditioning systems: Customer advising with the help of case studies and benchmarks, modelling and simulation Alexandre José Luís, Universidade do Porto Knight Ian, Welsh School

### HEATING-COOLING WALL PANELS SYSTEM IN SLOVENE ETHNOGRAPHIC MUSEUM

01-147 The 2005 World Sustainable Building Conference, HEATING-COOLING WALL PANELS SYSTEM IN SLOVENE ETHNOGRAPHIC MUSEUM Aleš KRAINER Prof. Dr. 1 Rudi Perdan 2 Gal Krainer 3 1 2 Faculty of Civil Engineering,

### Yijun Gao, Wei Wu, Zongwei Han, Xianting Li *

Study on the performance of air conditioning system combining heat pipe and vapor compression based on ground source energy-bus for commercial buildings in north China Yijun Gao, Wei Wu, Zongwei Han, Xianting

### Yield Reduction due to Shading:

1x4 1x16 10 x CBC Energy A/S x Danfoss Solar Inverters CBC-40W Poly 40 W TLX 1,5k 5 ; 1x11 3x4 0 1,5kW 1536 x CBC Energy A/S 1 x Power-One CBC-40W Poly 40 W TRIO-7,6-TL-OUTD 30 ; 4x14 0 7,6kW Location:

### Climate change and heating/cooling degree days in Freiburg

339 Climate change and heating/cooling degree days in Freiburg Finn Thomsen, Andreas Matzatrakis Meteorological Institute, Albert-Ludwigs-University of Freiburg, Germany Abstract The discussion of climate

### Field Comparison of Conventional HVAC Systems with a Residential Gas-Engine-Driven Heat Pump

Field Comparison of Conventional HVAC Systems with a Residential Gas-Engine-Driven Heat Pump James D. Miller, Pacific Northwest Laboratory Through its Office of Federal Energy Management Program (FEMP),

### Exploring the Building Energy Impacts of Green Roof Design Decisions - A Modeling Study of Buildings in 4 Distinct Climates

Final version for publication: Exploring the Building Energy Impacts of Green Roof Design Decisions - A Modeling Study of Buildings in 4 Distinct Climates David J. Sailor 1, Timothy B. Elley 2, and Max

### An overview of energy efficient products used at reducing energy consumptions in buildings

An overview of energy efficient products used at reducing energy consumptions in buildings LIGIA MOGA, ATTILA PUSKAS Buildings and Management Department Technical University of Cluj-Napoca Baritiu 25 th

### SIMULATION - ASSISTED AUDIT OF AN AIR CONDITIONED OFFICE BUILDING

SIMULATION - ASSISTED AUDIT OF AN AIR CONDITIONED OFFICE BUILDING Stephane Bertagnolio Research Assistant Jean Lebrun Professor Jules Hannay Research Engineer Cleide Aparecida Silva Research Engineer Thermodynamics

### Evaporative Cooling for Residential and Light-Commercial

EMERGING TECHNOLOGIES This article was published in ASHRAE Journal, October 2011. Copyright 2011 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. Posted at www.ashrae.org.

### Sino-Italian Environment & Energy Building S I E E B

MOST Ministry of Science and Technology Republic of China Sino-Italian Environment & Energy Building S I E E B Concept The Sino-Italy Environment & Energy Building (SIEEB) is an intelligent, ecological

### A Roof Integrated Solar Heating System Without Storage

M. and W. Saman Sustainable Energy Centre University of South Australia Mawson Lakes Boulevard, Mawson Lakes, SA 5095, Australia E-mail: martin.belusko@unisa.edu.au Abstract A prototype of a roof integrated

### Influence of Solar Radiation Models in the Calibration of Building Simulation Models

Influence of Solar Radiation Models in the Calibration of Building Simulation Models J.K. Copper, A.B. Sproul 1 1 School of Photovoltaics and Renewable Energy Engineering, University of New South Wales,

### Akton Psychrometric Chart Tutorial and Examples

Akton Psychrometric Chart Tutorial and Examples December 1999 Akton Associates Inc. 3600 Clayton Road, Suite D Concord, California 94521 (925) 688-0333 http://www.aktonassoc.com Copyright 1999 Akton Associates

### Tips and Tricks for Estimating Energy Savings. Celeste Cizik, P.E. Project Manager E M C Engineers, Inc.

Tips and Tricks for Estimating Energy Savings Celeste Cizik, P.E. Project Manager E M C Engineers, Inc. AIA Quality Assurance Learning Objectives 1. Understand the pros and cons of various energy calculation

### ENGINEERING WEATHER DATA

INTRODUCTION ENGINEERING WEATHER DATA Background. The data in this handbook were compiled by the Air Force Combat Climatology Center (AFCCC) at the request of the Air Force Civil Engineer Support Agency

### Daikin Altherma Hybrid Heat Pump

your comfort. our world. Daikin Altherma Hybrid Heat Pump The natural combination Heating Integrated Solutions Ventilation Air Conditioning Refrigeration About Daikin Forward thinking... Daikin has a worldwide

### AT&T Global Network Client for Windows Product Support Matrix January 29, 2015

AT&T Global Network Client for Windows Product Support Matrix January 29, 2015 Product Support Matrix Following is the Product Support Matrix for the AT&T Global Network Client. See the AT&T Global Network

### ENERGY SAVING STUDY IN A HOTEL HVAC SYSTEM

ENERGY SAVING STUDY IN A HOTEL HVAC SYSTEM J.S. Hu, Philip C.W. Kwong, and Christopher Y.H. Chao Department of Mechanical Engineering, The Hong Kong University of Science and Technology Clear Water Bay,

### Catalyst RTU Controller Study Report

Catalyst RTU Controller Study Report Sacramento Municipal Utility District December 15, 2014 Prepared by: Daniel J. Chapmand, ADM and Bruce Baccei, SMUD Project # ET13SMUD1037 The information in this report

### Opening the Bonnet. Prof Darren Woolf WYSINWYG 1

Opening the Bonnet Prof Darren Woolf WYSINWYG 1 WYSINWYG What You See Is NOT What You Get: Looking inside the Pandora s Box Prof Darren Woolf WYSINWYG 2 WYSIWYG implies a user interface that allows the

### ENERGY PERFORMANCE MODELLING AND HEAT RECOVERY UNIT EFFICIENCY ASSESSMENT OF AN OFFICE BUILDING

THERMAL SCIENCE: Year 2015, Vol. 19, No. 3, pp. 865-880 865 ENERGY PERFORMANCE MODELLING AND HEAT RECOVERY UNIT EFFICIENCY ASSESSMENT OF AN OFFICE BUILDING by Norbert L. HARMATI a*, Radomir J. FOLI] a,

### Energy Recovery Ventilation Equipment

AHRI Standard 1060 (I-P) 2013 Standard for Performance Rating of Airto-Air Exchangers for Energy Recovery Ventilation Equipment IMPORTANT SAFETY DISCLAIMER AHRI does not set safety standards and does not

### A heat pump system with a latent heat storage utilizing seawater installed in an aquarium

Energy and Buildings xxx (2005) xxx xxx www.elsevier.com/locate/enbuild A heat pump system with a latent heat storage utilizing seawater installed in an aquarium Satoru Okamoto * Department of Mathematics

### THE PSYCHROMETRIC CHART AND ITS USE

Service Application Manual SAM Chapter 630-16 Section 3A THE PSYCHROMETRIC CHART AND ITS USE Psychrometry is an impressive word which is defined as the measurement of the moisture content of air. In broader

### THERMAL LOSSES Thermal Losses Calculations

Calculations -1- THERMAL LOSSES Thermal Losses Calculations Employer : 4M SA Project Location : ASHRAE Office Room : Example from ASHRAE 2013 Handbook - Fundamentals : Chapter 18, Single Room Example Peak