1 Water Loss Auditing and Water Leak Detection: How Much is Being Lost and Where Does it Go? PNWS-AWWA Annual Conference Michael W. Grimm, P.E. April 29,
2 2 What Will Be Covered Determining the magnitude of water loss Quantity Risk level Calculation methods Determining the cost of water loss Determining how to reduce water loss
3 3 What is Water Loss? Once upon a time, the water industry defined this unaccounted for water and that was part of the problem. We CAN account for this water and we SHOULD account for all the water in the system so now, the water industry term is Non- Revenue Water or NRW
4 4 Determining the Cost of Water Loss It is not enough to know the quantity of NRW. It is also important to know what type of loss is present and what is the cost of each type of water loss is impacting the water utility.
5 Cost of Water Loss Losing Money 5 Wasting chemicals Wasting electricity Paying more for purchased water Lost revenue from theft, inadequate billing process and meter inaccuracy
6 Cost of Water Loss Customer Perspective 6 Heightens inconvenience from interrupting water service and commerce Hurts perception of utility as a steward of resources (environmental and financial) Brings unwanted negative publicity
7 Cost of Water Loss Damage 7 Potential damage Damage to property and other utilities Surface hazards ice, ponding, hydroplaning Water supply Systems with limited water can be threatened Excessive loss can accelerate the need for more resources, facilities and capital expense. Water quality Compromising system integrity possible contamination Potential backflow
8 Water Audit Process: Component Analysis 8 Own Sources Water Imported Total Total System System Input Input (allow ( allow for for known known errors) errors ) Water Exported Water Supplied Authorized Authorized Consumption Consumption Water Water Losses Losses Billed Authorized Consumption Unbilled Authorized Consumption Apparent Losses Revenue Water Non- Revenue Water Billed Water Exported Billed Metered Consumption Billed Unmetered Consumption Unbilled Metered Consumption Unbilled Unmetered Consumption Unauthorized Consumption Customer Metering Inaccuracies Systematic Data Handling Error Leakage on Mains Real Losses Leakage on Service Lines Leakage & Overflows at Storage
9 9 Export water Water Into System Customer Consumption Unbilled Authorized Consumption Apparent Losses Real Losses (Leaks) Leaks = water in - export water out-billed volumeestimated unbilled authorized-apparent loss estimate
10 10 Billed Consumption Water exported Usually to another water system Master metered Billed Customer Consumption Metered Unmetered but estimated Unmetered - flat rate charge Export water Customer Consumption
11 Billed Consumption Biggest User of Water Export water 11 Exports If you are the seller, make sure the meter is accurate. Residential customer use Usually the prime component of small system use Commercial customer use Many are not significant water users Industrial customer use Can be the most significant user in a small system may be as factor in night use Customer Consumption Photo courtesy Denver Water
12 12 Unbilled Authorized Consumption Water use that is not billed Fire fighting Flushing Public parks and golf courses Street cleaning Municipal facilities (pools, City Hall) How do you account for the amount of water that is being used? Metered Unmetered but estimated Unmetered Unbilled Authorized Consumption Can your utility control this use more effectively?
13 13 Apparent Losses Unauthorized use Illegal taps Theft at hydrants Open unmetered bypasses Illegal use of fire services Meter tampering Customer meter inaccuracies Apparent Losses Billing handling errors
14 14 Real Losses Leakage on mains Real losses Leakage on service lines Storage leaks and overflows
15 Identify where water loss could be occurring. Define as unbilled, apparent, or real loss. 15
16 16 What if Customer Use is not Metered? Billing options to meters Part of general user fee (fixed fee) Fixture count Property size Maybe they should be metered Equity and fairness Accountability Regulation
17 17 Unmetered Look at System Use Patterns Daily usage patterns Somewhat predictable usage pattern especially if no industry Usually minimal flow at night Some unmetered systems have successfully estimated night flow to calculate leak loss Take storage changes into account Night flow analysis Utilities can compare actual volume at night with projected use to evaluate the amount of leakage Minimum night flow
18 18 What is an Acceptable Leakage Amount? What is the appropriate level of non-revenue water? Facility and supply limits and economics will help you decide the level of action and you should take and equipment to buy. Regulations may apply Washington DOH: < 10% water loss Oregon: Idaho: California: < 10% water loss
19 19 Metrics - What is Best to Use? Percentage of NRW is helpful but not best Comparison between systems can be impacted by differences in consumption major customers and yearly fluctuations. Heavy summer consumption can distort NRW percentage when comparing year to year. Percentage not as helpful as volume for small systems that need to be careful with limited water. Using water loss per connection per year is more useful.
20 20 Export water Customer Consumption Water Into System Non Revenue Water Unbilled Authorized Consumption Apparent Losses Real losses
21 Authorized Unbilled Use Meter, estimate, report Unbilled Authorized Consumption 21 Municipal services Metering for fountains, municipal buildings, parks Flushing Filling mains compute volume Fire flow tests measure time and flow Flushing measure time and flow Fire fighting Estimating flows and duration Metering usually not an option Other uses??
22 Apparent Losses Difficult to Estimate Apparent Losses 22 Illegal use of hydrants Meter Tampering Customers opening bypasses Illegal connections Billing Errors
23 Apparent Losses Evaluate Meter Accuracy 23 Project loss from random testing Test customer meters/master meters Are you metering everyone Are you billing everyone?
24 Calculating and Identifying Real Losses 24 Real losses Real Loss is the difference between all NRW and the other forms of NRW (we just covered) Authorized unbilled consumption Apparent loss
25 25 The Focus is Usually on Leakage Leakage and break types and tools Unavoidable Detectable Observable Proactive leak detection and repair Improve speed of repair
26 26 How Much Does NRW Cost Unit Costs Real losses and unbilled authorized use cost the amount of money it takes to produce the water (sale price if bought, treatment and electrical costs if produced). Apparent losses could have been sold at retail price (if used but not stolen or otherwise avoiding payment), so its value is greater at the retail rate, the rate customers pay.
27 Water Balance Example A Water Utility produces 5000 MG annually (13.7 MGD) An audit determines Utility has 1000 MG in water losses (250 MG in apparent losses and 750 MG in real losses) The cost of production is $0.50/1000 gal ($500/MG); Retail charge = $3/1000 gal ($3000/MG). Most of the expense of the production cost is in energy Lost revenue in apparent losses = $3000/MG x 250 MG = $750,000 annually 27
28 Water Balance Example Cont d Added cost to the utility for the real losses = $500 x 750 MG = $375,000 annually Total annual cost for apparent and real losses is over $1 million!! Bottom Line: Getting a handle on real losses will mean less pumping which means less energy purchased which mean lower energy costs 28
29 29 Estimating Leakage - Summary Start by getting an estimate of the non-revenue water by components Then see if you can estimate areas of authorized unbilled and other losses Work to minimize different categories of loss (note it may vary within your system)
30 30 Useful Tool for Water Audits AWWA Manual M36, 3rd edition (2009) Section devoted to small systems The AWWA Water Loss Control Committee (WLCC) working on 4 th edition Free software available on AWWA website Version 5.0 released in 2014
31 SUMMARY How to Get the Free AWWA Water Audit 31 Go to awwa.org Enter water audit software in the search box (upper right) Navigate to the Water Loss Control page Click on AWWA Water Loss Control Committee Free Water Audit Software v5.0 (2014) (XLS) Click on the compiler AWWA Water Loss Control Committee Water Audit Software Compiler v5.0 (2014) (XLS)
32 32 Determining Amount of NRW Start with what is known and readily obtainable Compare water leaving the treatment facility with consumer billing records Estimate unbilled authorized consumption and sources of apparent loss Leakage (Real loss) = Measured Total Water Production less Total Revenue Sales Volume less Estimated Apparent Loss Volumes less Calculated Authorized Unbilled Water Volume
33 Determining NRW Leakage Component 33 Own Sources Water Imported Total Total System System Input Input (allow ( allow for for known known errors) errors ) Water Exported Water Supplied Authorized Authorized Consumption Consumption Water Water Losses Losses Billed Authorized Consumption Unbilled Authorized Consumption Apparent Losses Revenue Water Non- Revenue Water Billed Water Exported Billed Metered Consumption Billed Unmetered Consumption Unbilled Metered Consumption Unbilled Unmetered Consumption Unauthorized Consumption Customer Metering Inaccuracies Systematic Data Handling Error Leakage on Mains Real Losses Leakage on Service Lines Leakage & Overflows at Storage
34 34 How Good is the Data? The Audit is only as good as the supporting data Check into data that is missing, poor or questionable quality Work to improve weak or missing data Focus on critical data (like master meters) Worry about the big stuff first
35 35 Focus on the Economics Make your best estimate of leakage Use water audit and night flow to gauge how much volume you lose per year. Calculate what that avoidable leakage is costing you Multiply the annual loss by the cost to produce the water (higher if purchased as finished water) Examine possible leak detection approaches and costs Leak surveys (in house, consultant, step tests, district metering)
36 36 The Economics of Leak Reduction Compare cost of a program with potential savings. Expect that you can only reduce part of leakage with any leak detection program Contingency plan - be prepared to deal with a severe break that may threaten your supply. Know where to get help
37 37 Approaches to finding pipe Using maps Finding surface items and using physical clues Finding metallic pipe Finding nonmetallic pipe
38 38 Components of good maps Good maps show pipe location horizontally relative to permanent surface points. Good maps provide reference information about significant changes in depth. Good maps show pipe material and size. To remain good maps there should be a plan to adjust them when new pipe installed or need correction.
39 39 Surface locating Hydrants, blow-off pipe discharges, valve boxes, meter pits, curb boxes are either visible and contain some steel or iron. Magnetic locaters are common in the industry.
40 Valve Layout for Water Lines to & from a Pump Station 40
41 Valve Layout at a Road Intersection (3 Water Lines, 5 Valves) 41
42 Operating valves? A study for the City of Houston (Wachs Water Services, 2011) evaluated more than 4,000 valves Could not locate 17% of the valves initially (lowered to 12% after locating effort) Map discrepancies, 14% Paved-over valves, 6% 45% initially inoperable (lowered to 19%) 10% in the wrong position (closed/open) 42
43 43 Finding metallic pipe Numerous manufacturers (and distributors) provide inductive/conductive transmitter/receiver devices to locate pipe.
44 44 Locater Issues Signal can jump to other nearby pipes; best to work slowly away from transmitter. Watch for cable lines give strong signals as they are shallow and good conductors. When using conductive method, the transmitter needs a good ground. Some devices can provide depth; this is usually center of pipe not top of pipe. Failing batteries can cause erratic signals.
45 45 Finding nonmetallic pipe Not conductive, limited ability to locate. Some devices induce vibration for acoustic sensing limited range. No reliable method for readily signaling through water mains is available at this time.
46 What should you have in your toolbox? 46 A good metal detector (think about time saved finding valve box buried under paving, snow, soil and landscaping). An inductive/conductive locator if the system has mostly metallic mains or services. If the system is nonmetallic, divining rods with access to more sophisticated methods for emergencies recommended.
47 Thanks for listening to the presentation Questions or Comments? Michael W. Grimm, P.E. (503)
February 2008 DOH 331-388 Reduce Leaks Using water audits and leak detection surveys In 2000, public water suppliers in Washington produced a total of 1,020 million gallons of drinking water per day to
City of Gorman DWSRF GREEN PROJECT RESERVE BUSINESS CASE EVALUATION STATE FISCAL YEAR 2015 INTENDED USE PLAN PROJECT NUMBER 62660 COMMITMENT DATE: January 29, 2015 DATE OF LOAN CLOSING: May 21, 2015 GREEN
Acoustic Leak Detection Gander Newfoundland 2006 Overview Background on Leakage and leak Detection Water Loss Management Fundamentals of Correlation Leakage The unintentional escape or loss of water from
Analysis of Calendar Year 2012 Water Audit Data from Public Water Supply Systems in the Delaware River Basin DELAWARE RIVER BASIN COMMISSION February 2015 Acknowledgements This report was prepared by the
CITY OF TORONTO WATER LOSS STUDY & PRESSURE MANAGEMENT PILOT Alain M. Lalonde, P.Eng. Principal, Veritec Consulting Inc.* Candice Au, P.Eng. Engineer, Toronto Water, City of Toronto Paul Fanner, C.Eng.
Barbados Water Authority Leak Detection By: Gary Fricke- Sales Manager Hetek Solutions Inc. Shelley Chase- Engineer, Waste Control/ Distribution, Barbados Water Authority Abstract Water suppliers are under
Technical Losses in Natural Gas Transportation, Distribution, and Storage Paul Metro Pennsylvania Public Utility Commission 1 Unaccounted for Gas (UFG or Technical Losses) Unaccounted for gas is the difference
Leakage Management & Control (An overview) Saroj Sharma April 2008 Delft, The Netherlands Contents Introduction Causes of leaks and benefits of leakage control Leakage management strategy Economic level
LAKE VICTORIA WATER & SANITATION INITIATIVE FAST TRACK CAPACITY BUILDING PROGRAMME WATER AUDIT MANUAL Prepared by: NWSC- External Services, Uganda July 2008 Preamble This manual is specifically meant to
WATER METER CALIBRATION, REPAIR, AND REPLACEMENT PROGRAM EPD Guidance Document AUGUST 2007 TABLE OF CONTENTS Part 1: OVERVIEW OF WATER METERING 3 SUMMARY 3 NECESSITY OF METERS 3 TYPES OF WATER METERS 4
Ithriam Leukes Water Business Development Manager / Agent South Africa Holistic NRW Reduction Solution Losses Segmentation Apparent Losses represent 34% of overall losses REAL LOSSES Calculated by substraction,
, as published in July 2008 Opflow Question of the Month Thanks to: Mike Grahek, Los Angeles Department of Water, Los Angeles, California Ahmad Havivian, Black & Veatch, Gaithersburg, Maryland David Kroon,
AWWA Free Water Audit Software v5.0 Overview Brian Skeens Georgia Water Loss Manual v1.0 September 2011 v1.1 January 2014 Release Number of Version Date Worksheets v1 2005/6 5 v2 2006 5 v3 2007 7 v4-4.2
Water Supply and Drainage for Buildings, 29th Int. Symposium, Turkey WATER LEAKAGE AND DETECTION IN MUNICIPAL WATER DISTRIBUTION NETWORKS N. Merzi (1) and T. Özkan (2) (1)firstname.lastname@example.org (2)email@example.com
EPA 816-D-09-001 November 2009 REVIEW DRAFT CONTROL AND MITIGATION OF DRINKING WATER LOSSES IN DISTRIBUTION SYSTEMS Office of Water (OW/OGWDW/DWPD) EPA MC-4606M EPA 816-D-09-001 www.epa.gov/safewater November
Georgia Water System Audits and Water Loss Control Manual Produced for: Georgia Department of Natural Resources Georgia Environmental Protection Division Georgia Watershed Protection Branch January 2015
WATER LEAK DETECTION AND REPAIR PROGRAM EPD Guidance Document August 2007 TABLE OF CONTENTS PART 1: ESSENTIALS OF LEAK DETECTION AND REPAIR 3 SUMMARY 3 Benefits of Leak Detection and Repair 3 Unaccounted-for
Remote Pressure Monitoring System* Reduce water main breaks and customer complaints *Patent pending Remote Pressure Monitoring System Intelligent Water Technology About The System Several years ago, Mueller
Table of Contents Section Page Executive Summary i Introduction iii Five Year Goals iii Performance Measure Types iv Performance Plan Logic Model v Benchmarking, Strategic Planning, Performance Accountability
Training Guide An Introduction to Water Loss and Leak Detection TGR 17 Rural and Small Water Systems Training Guide An Introduction to Water Loss and Leak Detection Charles Jeffs, Rural Water Association
Construction Technology Update No. 40 Detecting Leaks in Water-Distribution Pipes by Osama Hunaidi This Update gives an overview of techniques and equipment used to detect leaks in water-distribution systems.
Water Loss Audit Manual for Texas Utilities by Mark Mathis George Kunkel, P.E. Andrew Chastain Howley Report 367 March 2008 Texas Water Development Board www.twdb.state.tx.us Texas Water Development Board
OFFICE OF THE CITY AUDITOR AUDIT OF THE PERFORMANCE OF DALLAS WATER UTILITIES (DWU S) FINANCE AND ACCOUNTING SYSTEMS AND WATER OPERATIONS Thomas M. Taylor, CPA City Auditor Prepared by: Paul Garner, CCP,
Maureen Duffy 856-309-4546 firstname.lastname@example.org Innovative Solutions in the Water Industry: Leak Detection Introduction Meeting current water demand and supplying water for future generations is a
VILLAGE OF GRANVILLE SEWER BACK-UP and WATER LEAK POLICIES SEWER BACK-UP POLICY General Sewer back-ups are an unfortunate, but common problem in older communities. A sewer back-up can create a health or
COMPREHENSIVE DRINKING WATER SOURCE-TO-TAP ASSESSMENT GUIDELINE MODULE 4 EVALUATE WATER SYSTEM MANAGEMENT, OPERATION AND MAINTENANCE PRACTICES Source Protection Emergency Response Training Treatment Multiple
4th DAAAM International Conference on Advanced Technologies for Developing Countries September 21-24, 2005 Slavonski Brod, Croatia LEAK DETECTION IN UNDERGROUND PIPELINES OF MUNICIPAL WATER DISTRIBUTION
PUBLIC WORKS TECHNICAL BULLETIN 420-46-2 30 SEPTEMBER 1993 PROCEDURE TO DETECT WATER DISTRIBUTION SYSTEM LEAKS Public Works Technical Bulletins are published by the U.S. Army Center for Public Works, Ft.
4 AWWA Free Water Audit Software v5. American Water Works Association Copyright 214, All Rights Reserved. This spreadsheet-based water audit tool is designed to help quantify and track water losses associated
Infrastructure Leakage Index (ILI) as a Regulatory and Provider Tool David Michael Delgado Advisor: Kevin Lansey. Department of Civil Engineering & Engineering Mechanics College of Engineering Acknowledgement:
Schneider Electric s Advanced Water Leakage Detection February 2010 / White paper by Ivan Nazzaretto, Schneider Electric solutions manager - water utilities Make the most of your energy SM Summary Executive
NuRON Water Network Monitoring Detect problems in real time before they turn into headaches The SEW Journey Non Revenue Water o Proactive Acoustics since 2003 Walkers/Listening Sticks (10m range) Correlators
Village of Shorewood, Wisconsin SEWER BACKUPS & BASEMENT FLOODING PREVENTATIVE SOLUTIONS FOR THE BUILDING OWNER Prepared By: Thomas A. Zoulek, P.E., LEED A.P. Vice President Mid City Plumbing & Heating
Leak Detection and Abatement in the Water Utility of Iasi Transferable Solution Project Summary Project Activities Project Benefits Lessons Learned Contact Information Project Title: Leak Detection and
The Water and Sanitation Program is an international partnership for improving water and sanitation sector policies, practices, and capacities to serve poor people April 2008 Field Note Performance Improvement
Underground Storage Tanks An Informational and Guidance Document for the University Community. Please contact Yale Environmental Health and Safety for latest Regulatory Requirements. A typical UST installation
Reduced Pressure Principle Assembly 3 Valve Procedure A. Initial Setup 1. Flush test cocks by: a. opening test cock #4 to establish flow through the unit. (Leave this test cock open until others are flushed)
CHAPTER 26 PLUMBING CODE 26.01 PLUMBING CODE The Illinois Plumbing Code as promulgated by the Illinois Department of Public Health at 77 Illinois Administrative Code, Part 890, is hereby adopted as the
Section 10632 of the California Water Code states that the Urban Water Management Plan shall provide an urban water shortage contingency analysis that includes information on the estimated three-year minimum
WHAT DO YOU KNOW? HOW TO GET THE BEST INFORMATION OUT OF YOUR SYSTEM AND THE FOLKS THAT RUN IT. ABSTRACT Steve Shoaf, City Of Asheville Nicholas Dierkes, Brown and Caldwell Understanding how well our Utilities
I. Introduction 10 minutes Introduction (1 of 2) An uninterrupted water supply is: The primary weapon for extinguishment Essential for fire fighter safety Ensuring a dependable water supply is a critical
Texas Water Development Board Report 362 Water Conservation Implementation Task Force Water Conservation Best Management Practices Guide November 2004 This page intentionally blank. i Texas Water Development
DEVELOPING AND IMPLEMENTING A WATER CONSERVATION PLAN Guidance For Maryland Public Water Systems On Best Management Practices For Improving Water Conservation And Water Use Efficiency Maryland Department
Lost Water, Lost Revenue: A Guide to Effectively Reduce NonNon Revenue Producing Water (NRPW) Loss Lost Water, Lost Revenue: United States Estimated DailyWater Loss? 6 Billion Gallons/Day (Source: American
Township of Enniskillen Asset Management Plan 2014 1 TABLE OF CONTENTS Page A. Introduction 3 B. State of Local Infrastructure 4 C. Desired Levels of Service 7 D. Asset Management Strategy 8 E. Financing
International Journal of Scientific and Research Publications, Volume 4, Issue 10, October 2014 1 Leakage Detection Using PLUMBOAT Pratiksha Kulkarni Electronics & Telecommunication Department, R.A.I.T
Meter & Backflow Services, a Division of E.J. Prescott, Inc. Meter and Backflow Services (MBS) is a subsidiary of E.J. Prescott, Inc. which provides specialized services in the areas of engineered water
Water Distribution Asset Inventory: An Asset Management Approach for Valves & Hydrants Why is it so hard to do the right thing? How Many of You? Brush your teeth three times per day? How Many of You? Exercise
Record MAP KEYS GLOSSARY FOR THE DRAINAGE AND WATER REPORT Abandoned Gravity Private Combined Gravity Private Foul Gravity Private Surface Water Gravity Public Combined Gravity Public Foul Gravity Public
City of Houston Asset Management In The Fast Lane: Final Report Sandeep Aggarwal PE, Managing Engineer, City of Houston Yvonne W. Forrest, Senior Assistant Director, City of Houston Paul Schumi, Director,
WATER MAIN CONSTRUCTION TECHNIQUES Overview Water Main - Materials Specifications Installation Future? Water Main Materials Material Types There are various material types used for water mains, these include:
Inexpensive Leak Detection for Small Waterworks Virginia Department of Heath Office of Drinking Water Catalog Number: HTO/005/2015 Page 2 Virginia Department of Heath Office of Drinking Water Page 9 The
WATER SUPPLY SYSTEMS FOR 150/5220-4B AAS-100 AIRCRAFT FIRE AND RESCUE PROTECTION 1. PURPOSE. This Advisory Circular (AC) provides guidance for the selection of a water source and standards for the design
SPECIFICATIONS FOR THE INSTALLATION OF FIRE ALARM SYSTEMS, SPRINKLER SYSTEMS, AND MASTER BOXES IN THE POQUONNOCK BRIDGE FIRE DISTRICT The purpose of these specifications is to insure that there are minimum
STANDARD SPECIFICATIONS SECTION 02512 CLEANING AND LINING WATER MAINS PART 1 GENERAL 1.1 DESCRIPTION A. Section includes requirements for cleaning and lining existing cast iron and ductile iron water mains
This guide will provide you with a summary of the water main extension process for Indiana American Water. While it is our goal to make this guide as complete and easy to follow as possible, it is recommended
Number 2014-20 September 2014. SEWER LIABILITY Sewer Backups: Most of us take the use of our wastewater and sewer systems for granted, while municipalities must be vigilant to ensure that citizens of the
BEACONSFIELD PREVENTATIVE MEASURES TO BE TAKEN BY THE OWNER FOR BASEMENT FLOODING OF A RESIDENCE The flooding of numerous basements that occurred in 1998 and in 2005 has led municipal authorities to identify
Backflow Preventer Presentation ASSE/ASPE Conference New York City May 2015 What is Backflow? Backflow is the undesirable reversal of flow of water or mixture of water and / or other substances into the
SECTION 33 11 00.15 DUCTILE IRON PIPE AND FITTINGS PART 1: GENERAL 1.01 COORDINATION OF WORK Connection to existing pipelines may require shutdown of AW facilities. Closely coordinate construction work
The Manager s Non-Revenue Water Handbook A Guide to Understanding Water Losses The Manager s Non-Revenue Water Handbook A Guide to Understanding Water Losses Publication Team Authors: Malcolm Farley Gary
Reference Guide for Obtaining Permits and Utility Services For New Construction (Revised 04-2012) Table of Contents City Offices Telephone Numbers...1 Application for Utilities...2 Building Permits New
CITY OF NORTH RIDGEVILLE 7307 AVON BELDEN ROAD NORTH RIDGEVILLE, OH 44039 (440) 353-0819 WWW.NRIDGEVILLE.ORG WHY IS THERE WATER IN MY BASEMENT? There are two major sources of water in a basement as the
Clark University Water Outage Preparedness and Response Plan Revised January 11, 2013 Contents Introduction... 3 Definitions... 3 Risks Associated with Water Outages... 3 Preparedness... 4 Responses/Action
PART 1 - GENERAL 1.01 OVERVIEW A. This section addresses domestic cold, hot and hot water return distribution systems within and to five feet beyond building perimeter. PART 2 - DESIGN CRITERIA 2.01 GENERAL
CITY OF ST. CATHARINES BY-LAW NO. 2r05-2ro A By-law to regulate the supply of water and to provide for the maintenance and management of the water distribution system. WHEREAS the City deems it expedient
Residential Plumbing BCN 1058 CHAPTER 7 Plumbing Fixtures and Sizing the Drain, Waste, and Vent System MICHAEL KNOTEK 74 Plumbing Fixtures and Sizing the Drain, Waste, and Vent System PLUMBING FIXTURES
The data compiled in this rate survey can be used extensively for comparative analysis. Because of the site-specific nature of rate development implementation, users are cautioned not to broadly generalize
EXHIBIT "A Technical Specifications for Water and Sewer Service Lines Water and Sewer Line Bedding and Backfill: Drawings show cross-section of trench, pipe laid on top of 6" min. bedding material, bedding
SWPPP for Park Operations 2 Chapter 2 Stormwater Pollution Prevention Plan (SWPPP) for Park Operations Bordered by Lake Washington & Lake Sammamish, the City of Bellevue has more than 60 miles of streams,
Remote Pressure Monitoring System* Reduce water main breaks and customer complaints *Patent pending Hydro-Guard Remote Pressure Monitoring System Intelligent Water Technology About The System Introduced
Protect Your Home From Flooding A guide for Lethbridge Residents Every year, millions of litres of water flow into the City of Lethbridge s stormwater and wastewater collection systems from residential
2.0 DESIGN CRITERIA FOR WATER DISTRIBUTION SYSTEMS Water system improvements proposed for inclusion into Western s service area shall be designed in accordance with all appropriate AWWA standards, include
PREVENTING WET OR FLO ODED BASEMENTS TABLE OF CONTENTS Prevention Tips...Page 1 Why is there Water in my Basement?...Page 2 City of Saskatoon Sewer Systems...Page 3 Why Does Saskatoon Have Two Separate
All about insurance and water damage Water damage: Tops the list of home insurance claims Water damage now accounts for nearly half of the amounts paid for home insurance claims in Quebec, well ahead of
Florida Department of Environmental Protection Background Mobile vehicle and equipment washing involves washing at a location where vehicles are based (such as a trucking company, warehouse, bus station,
Local Government s Asset Management Tools and Trainings for facilitating more transparent and accountable role UTVSI Presented by: Dr. P. Kolovopoulos Vienna, 07th May 2015 Utility External Pressures &
Section 19.0 Cross Connection Control Policy 19.1 Responsibility 19.1.1 The Elkhart Water Utility has the responsibility to supply safe, potable water from the source to the point of delivery defined as
Texas Commission on Environmental Quality Page 1 SUBCHAPTER H: UTILITY SUBMETERING AND ALLOCATION 291.121-291.127 Effective January 6, 2011 291.121. General Rules and Definitions. (a) Purpose and scope.
2014 ANNUAL REPORT Endicott Water Department Public Water Supply ID# 0301665 Report to Customers on Water Quality Endicott Municipal Water Department Water Quality For Supply Year 2014 Introduction: To
JET PUMP INSTALLATION MANUAL SHALLOW WELL JET PUMPS STEP 1 Make sure the well is pumped clean and that sand and grit are absent. STEP 2 Before installing a shallow well or centrifugal pump make sure the