1 Air Injection Filter For Iron removal Product Manual
2 Your Neotec Air Injection Iron Filter (Birm Filter) Congratulations on choosing the Neotec Air Injection Iron Filter (NAIF). This system will remove iron from your water in addition to visible impurities. The Neotec System is designed for years of reliable & trouble-free service. Problems caused by Iron in water? Iron is a common element found in most water supplies, particularly well water. The human body needs iron as an essential nutrient for development. However, high iron content in water causes several problems making it essential to remove Iron from the water supply. Excessive Iron causes deposits on pipelines, pressure tanks, water heaters and water softeners, reducing the available water flow and pressure. It affects the flavor and color of food and water. It may react with tannins in coffee, tea and some alcoholic beverages to produce a black sludge, which affects both taste and appearance. Iron causes reddish-brown staining of laundry, porcelain, dishes, utensils and even glassware. Soaps and detergents do not remove these stains, and use of chlorine bleach and alkaline builders (such as sodium and carbonate) may intensify the stains. A problem that frequently results from iron in water is iron bacteria. These nonpathogenic (not health threatening) bacteria occur in soil, shallow aquifers and some surface waters. The bacteria feed on iron in water and form red-brown (iron) slime in toilet tanks and can also clog water systems. The Neotec Air Injection Iron Filter removes iron, giving you clean water continuously. You can now say good-bye to those rusty red stains that spoil your washroom, sink, kitchen & bathtub &, of course, iron bacteria. How does Air Injection remove iron? Air injection iron filters use oxygen in the air to oxidize iron in water. A small venturi type air injector is installed between the pump and pressure tank to draw the air into the water. The iron oxidizes to form rust particles, which are then strained out by a filter medium (birm).
3 Functional Description The purification process involves suction of air into the water line by an air-injector. Upon contact with air, iron (present in the ferrous form) gets oxidized (to ferric form) and precipitates out. These precipitates are then filtered in a media (birm) bed and removed by backwashing (an automatically controlled process where the flow of water is reversed). An automatic control valve that is mounted on the media tank carries out the entire backwashing process. AIR INJECTOR AUTOMATIC VALVE RISER BRIM Automatic Control Valve TANK JACKET DRAIN MEDIA TANK Air-Injection Iron filters are generally installed at the point-of-entry. A qualified Neotec Service Representative can install the system wherever you desire*. Another manual explaining the settings and features of the control valve is included with your system. *Extra Service Charges may apply. It is recommended to have the system at the point of entry with proper drainage and electrical connection. Please allow sufficient space for maintenance. How Different is the Neotec Air Injection Iron Filter from Ordinary Filters? Neotec Air Injection Filters are manufactured to stringent quality parameters with the best available components. Each system features: Fully automatic backwash valve High quality components Reliability Ease of operation Very low on maintenance
4 Maintenance As the Neotec Air-Injection iron filter is designed for automatic backwashing and chemical free cleaning, the system is virtually maintenance-free. Troubleshooting In the rare event that you experience any problem with your system, the following table may be useful. In most cases you can rectify the problem on your own. Problem I still get stains on my plumbing fixtures Possible Solution Make sure the bypass valve is in service position. Make sure the power-cord for the valve is plugged in. Check the valve injector for plugging. Clean if required If you are still unable to get the system running properly or there is a different problem, please call your dealer immediately for assistance. ******
5 Warranty NEOTEC Water Treatment (referred to as The Company) hereby warrants its equipment as follows: 1) The company warrants its Air-Injection Iron Filter controls to be free of defects due to workmanship or materials, under normal use and service for FOUR YEARS from date of purchase. If defective due to workmanship or materials, and if reported within one (1) month from equipment failure, the Company will, at its option, repair or replace the product. 2) FIBREGLASS TANKS are warranted for a period of ten (10) years from the date of manufacture against defects due to poor workmanship or materials. 3) This warranty is valid only when the unit is installed and adjusted according to factory specifications by Neotec authorized personnel only. It does not include standard maintenance items. 4) If the system performance is affected due to any of the following reasons, the warranty will be void and necessary charges, as may be determined from time to time by The Company, will be applicable: Change in raw water quality Damage from abuse, neglect, accident, fire, flood or any other act of God. Damage resulting from unauthorized alterations, attachments, or repairs. Failure or malfunction occurring due to the system being operated in a corrosive and contaminated atmosphere. Failure due to repair or service performed by any person or company other than those approved by Neotec. 5) The obligation to repair defective parts does not require replacement of the complete unit. Service which includes replacement of defective parts, repair work or adjustments within the warranty period should be handled by, or through the authorized dealer from whom the system was purchased. 6) This warranty becomes void if the serial number is removed or defaced. 7) In no event shall Neotec be liable for incidental, special, direct, indirect, consequential or multiple damages such as, but not limited to, water damage, lost business or profits arising out of the sale or use of the Neotec AC System even if advised of the possibility of such damages. 8) NO OTHER WARRANTY EXPRESSED OR IMPLIED IS APPLICABLE TO THIS UNIT. MODEL NUMBER... SERIAL NUMBER... DATE INSTALLED... INSTALLED BY... DEALER NAME..
6 Authorized Dealer: Made in Canada Neotec Water Treatment 36, Industrial Parkway South, Aurora L4G3W2, ON, Canada
AGS Owner's Manual Xantrex Automatic Generator Start Control System TABLE OF CONTENTS INTRODUCTION...3 Main Features...3 Safety Summary...3 THINGS YOU SHOULD KNOW...4 THEORY OF OPERATION...5 System...5
1/3 HP Submersible Sump with Vertical Float Switch Item 68476 Specifications Float Switch Operation Height 7.1 IN. ON / 2.8 IN. OFF Electrical Requirements 120V~ / 60Hz / 7.6A Power Length Maximum Capacity
Owner s Manual & Safety Instructions Save This Manual Keep this manual for the safety warnings and precautions, assembly, operating, inspection, maintenance and cleaning procedures. Write the product s
State Hygienic Laboratory at The University of Iowa Well Water Quality and Home Treatment Systems A HISTORY OF WATER TREATMENT Water is necessary for life. It is not surprising, then, that concerns about
Improving your water quality and answering questions about your water Developed and Prepared by 2013 Reynolds Water Conditioning Co. Water Filtration & Purification Guide Including answers to common water
S33 Sump Pump INSTRUCTIONS AND SERVICE MANUAL VERTICAL FLOAT SWITCH S33V1 & S33V1C AUTOMATIC S33P1 & S33PC-1 (CONTROL WITH SERIES PLUG) NOT SHOWN AUTOMATIC S33A1 & S33A1C R WARNING risk of electric shock.
HomeCare Range Terms and Conditions In your world everything should be clear Contents 1. Introduction to your Terms and Conditions 3 2. About our Packages 3 3. What we can look after 4 4. Definitions 5
Installation and Operation Smart-UPS SUA22000-BR/SUA3000-BR 120 VAC English This manual and the safety guide are available in English on the enclosed CD and the APC Web site, www.apc.com. Este manual e
USB Internet Phone Quick Installation Guide R24.0583.00 rev 3 1/06 USB Internet Phone Quick Installation Guide U.S. Robotics Corporation 935 National Parkway Schaumburg, Illinois 60173-5157 USA No part
FUTURE CALL PICTURE CARE PHONE MODEL: FC-1007 USER MANUAL Please follow instructions for repairing if any otherwise do not alter or repair any parts of device except specified. IMPORTANT SAFETY INSTRUCTIONS
6731i IP Phone Installation Guide 41-001266-00 Rev 02 Callers Conf. Transfer Software License Agreement Aastra Telecom Inc., hereinafter known as "Seller", grants to Customer a personal, worldwide, non-transferable,
Installation Manual with Service Replacement Parts For Champion Models: DH-1000, DL-1000 Moyer Diebel Models: MD1000HT, MD1000LT Valu-Clean Models: VC1000, VC1000HT Door-type Dishwasher Model: 1000 Series
OPERATIONS AND MAINTENANCE INFORMATION FOR: THE CANPLAS BACKWATER VALVE THE CHEMTROL BALL SHUT OFF VALVE SUMP PUMPS AND WASTEWATER EJECTOR PUMPS THE LOUISVILLE AND JEFFERSON COUNTY METROPOLITAN SEWER DISTRICT
Managing Steam Sterilization Process By Patricia H. Nothum, RN, BSN, CRCST, CHL A research paper submitted to the International Association of Central Service Health Care Material Management as Partial
Owner s Operator and Maintenance Manual Get-U-Up Lift DEALER: This manual MUST be given to the user of the patient lift. USER: BEFORE using this patient lift, read this manual and save for future reference.
Linear Scanner Option 92-2435-01 Rev.C Overview With the H-Class Linear Scanner option and menu-selectable functions that include voiding and replacement generation, labels can be interrogated at up to
Before You Construct an On-site Sewage System Facts a homeowner should know Before You Construct an On-site Sewage System Facts a homeowner should know Before You Construct an On-site Sewage System Facts
Owner s Manual What you need to know about your system for now and for the future. Maintain Your System Annually! Rev 5/15/14 Page 1 Homeowner s guide important information Please read the following information:
Virtual Keyboard You ve never typed like this before Table of contents Warnings and Cautions... 2 Bluetooth Compatibility...................................................10 Location of Controls... 11
Introduction OPTI TRI PAR Rev. 5/09 User Instructions Elation Professional 6122 S. Eastern Ave. Los Angeles CA. 90040 www.elationlighting.com Unpacking: Thank you for purchasing the by Elation Professional.
Land&Water Conserving Natural Resources in Illinois University of Illinois at Urbana - Champaign, College of Agriculture, Cooperative Extension Service Planning Your Well Guidelines for Safe, Dependable
Owners Manual Battery Backup Sump Pump System WARNING! PUBLIC SAFETY NOTICE Lots of rain and violent thunderstorms that cause power outages can result in flooded basements. DO NOT, under any circumstances,
Installation Manual 4414000B Model 441 Battery Backup System *Do not throw away or lose this manual. IMPORTANT: Prior to installation, record Model, Serial Number, and Code Number from pump nameplate for
What to expect from your new home New Home Limited Warranty and Performance Standards Relax. 2 You ve made the right decision by choosing Pulte Homes. You are now the proud owner of an exceptionally well-crafted