Calculating Total Cooling Requirements for Data Centers

Save this PDF as:

Size: px
Start display at page:

Transcription

1 Calculating Total Cooling Requirements for Data Centers By Neil Rasmussen White Paper #25 Revision 2

2 Executive Summary This document describes how to estimate heat output from Information Technology equipment and other devices in a data center such as UPS, for purposes of sizing air conditioning systems. A number of common conversion factors and design guideline values are also included. 2

3 Introduction All electrical equipment produces heat, which must be removed to prevent the equipment temperature from rising to an unacceptable level. Most Information Technology equipment and other equipment found in a data center or network room is air-cooled. Sizing a cooling system requires an understanding of the amount of heat produced by the equipment contained in the enclosed space, along with the heat produced by the other heat sources typically encountered. Measuring Heat Output Heat is energy and is commonly expressed in Joules, BTU, Tons, or Calories. Common measures of heat output rate for equipment are BTU per hour, Tons per day, and Joules per second (Joules per second is equal to Watts). There is no compelling reason why all of these different measures are used to express the same commodities, yet any and all of them might be used to express power or cooling capacities. The mixed use of these measures causes a great deal of senseless confusion for users and specifiers. Fortunately, there is a worldwide trend among standard-setting organizations to move all power and cooling capacity measurements to a common standard, the Watt. The archaic terms of BTU and Tons will be phased out over time 1. For this reason, this paper will discuss cooling and power capacities in Watts. The use of the Watt as the common standard is fortuitous, because it simplifies the work associated with data center design as will be explained later. In North America, specifications for power and cooling capability are still often provided in the legacy BTU and Tons terms. For this reason, the following conversions are provided to assist the reader: Given a value in Multiply by To Get BTU per Hour Watts Watts 3.41 BTU per Hour Tons 3,530 Watts Watts Tons The power transmitted by computing or other information technology equipment through the data lines is negligible. Therefore, the power consumed from the AC power mains is essentially all converted to heat. This fact allows the thermal output of IT equipment in Watts to simply equal its power consumption in 1 The term Tons refers to the cooling capacity of ice and is a relic of the period from when refrigeration and air conditioning capacity were provided by the daily delivery of ice blocks. 3

4 Watts. BTU per hour, as is sometimes provided in datasheets, is not necessary in determining the thermal output of equipment. The thermal output is simply the same as the power input 2. Determining heat output of a complete system The total heat output of a system is the sum of the heat outputs of the components. The complete system includes the IT equipment, plus other items such as UPS, Power Distribution, Air Conditioning Units, Lighting, and People. Fortunately, the heat output rates of these items can be easily determined via simple and standardized rules. The heat output of UPS and Power Distribution systems consists of a fixed loss and a loss proportional to operating power. These losses are sufficiently consistent across equipment brands and models and so they can be approximated without significant error. Lighting and people can also be readily estimated using standard values. The only information needed to determine the cooling load for the complete system are a few readily available values, such as the floor area in square feet, and the rated electrical system power. Air conditioning units create a significant amount of heat from fans and compressors. This heat is exhausted to the outside and does not create a thermal load inside the data center. It does, however, detract from the efficiency of the air conditioning system and is normally accounted for when the air conditioner is sized. A detailed thermal analysis using thermal output data for every item in the data center is possible, but a quick estimate using simple rules gives results that are within the typical margin of error of the more complicated analysis. The quick estimate also has the advantage that it can be performed by anyone without specialized knowledge or training. A worksheet that allows the rapid calculation of the heat load is provided in Table 1. Using the worksheet, it is possible to determine the total heat output of a data center quickly and reliably. The use of the worksheet is described in the procedure below Table 1. 2 Note: the one exception to this rule is Voice Over IP (VOIP) Routers; in these devices up to 30% of the power consumed by the device may be transmitted to remote terminals, so their heat load may be lower than the electrical power they consume. Assuming that the entire electrical power is dissipated locally as is assumed in this paper will give a small overstatement of heat output for VOIP routers, an insignificant error in most cases. 4

5 Table 1 Data center or network room heat output calculation worksheet Item Data required Heat output calculation IT Equipment Total IT load power in Watts Same as total IT load power in watts UPS with Battery Power Distribution Lighting Power system rated power in Watts Power system rated power in Watts Floor area in square feet, or Floor area in square meters People Max # of personnel in data center 100 x Max # of personnel Heat output subtotal Watts (0.04 x Power system rating) + (0.05 x Total IT load power) Watts (0.01 x Power system rating) + (0.02 x Total IT load power) Watts 2.0 x floor area (sq ft), or x floor area (sq m) Watts Total Subtotals from above Sum of heat output subtotals Watts Watts Procedure Obtain the information required in the Data required column. Consult the data definitions below in case of questions. Perform the heat output calculations and put the results in the subtotal column. Add the subtotals to obtain the total heat output. Data Definitions Total IT load power in Watts - The sum of the power inputs of all the IT equipment. Power System Rated Power - The power rating of the UPS system. If a redundant system is used, do not include the capacity of the redundant UPS. Example of a typical system The thermal output of a typical system is described. A 5,000 ft 2, (465 m 2 ) 250 kw rated data center with 150 racks and a maximum staff of 20 is used as an example. In the example, it is assumed that the data center is loaded to 30% of capacity, which is typical. For a discussion of typical utilization, see APC White Paper #37, Avoiding Costs From Oversizing Data Center and Network Room Infrastructure. The total IT load of the data center in this case would be 30% of 250 kw, or 75 kw. Under this condition, the total data center thermal output is105 kw, or approximately 50% more than the IT load. In the typical example, the relative contribution of the various types of items in the data center to the total thermal output is shown in Figure 1. 5

6 Figure 1 Relative contributions to the total thermal output of a typical data center Pwr Dist 4% Personnel 2% Lighting 10% UPS 13% IT Loads 71% Note that the contributions to the thermal output of the UPS and the Power Distribution are amplified by the fact that the system is operating at only 30% of capacity. If the system was operating at 100% of capacity, the efficiency of the power systems would increase and their relative contributions to the thermal output of the system would decrease. The significant loss of efficiency is a real cost of oversizing a system. Other heat sources The prior analysis ignores sources of environmental heat such as sunlight through windows and heat conducted in from outside walls. Many small data centers and network rooms do not have walls or windows to the outside, so there is no error resulting from this assumption. However, for large data centers with walls or a roof exposed to the outdoors, additional heat enters the data center which must be removed by the air conditioning system. If the data room is located within the confines of an air-conditioned facility, the other heat sources may be ignored. If the data center has significant wall or ceiling exposure to the outside, then a HVAC consultant will need to assess the maximum thermal load and it must be added to the thermal requirement of the complete system determined in the previous section. 6

7 Humidification In addition to removing heat, an air conditioner system for a data center is designed to control humidity. Ideally, when the desired humidity is attained, the system would operate with a constant amount of water in the air and there would be no need for ongoing humidification. Unfortunately, in most air conditioning systems the air-cooling function of the air conditioning system causes significant condensation of water vapor and consequent humidity loss. Therefore, supplemental humidification is required to maintain the desired humidity level. Supplemental humidification creates an additional heat load on the CRAC unit, effectively decreasing the cooling capacity of the unit and consequently requiring oversizing. For small data rooms or large wiring closets, an air conditioning system which isolates the bulk return air from the bulk supply air by using ducting can result in a situation where no condensation occurs and therefore no continuous supplemental humidification is needed. This allows 100% of the rated air conditioning capacity to be utilized and maximizes efficiency. For large data centers with high amounts of air mixing, the CRAC unit must deliver air at low temperatures to overcome the recirculation effects of the higher temperature equipment exhaust air. This results in substantial dehumidification of the air and creates the need for supplemental humidification. This causes a significant decrease in the performance and capacity of the air conditioning system. The result is that the CRAC system must be oversized up to 30% The required oversizing for a CRAC unit therefore ranges from 0% for a small system with ducted exhaust air return, to 30% for a system with high levels of mixing within the room. For more information on humidification see APC White Paper #58, Humidification Strategies for Data Centers and Network Rooms. Sizing air conditioning Once the cooling requirements are determined, it is possible to size an air conditioning system. The following factors, which were described earlier in this paper, must be considered: The size of the cooling load of the equipment (including power equipment) The size of the cooling load of the building Oversizing to account for humidification effects Oversizing to create redundancy Oversizing for future requirements The Watt loads of each of these factors can be summed to determine the total thermal load. 7

8 Conclusion The determination of cooling requirements for IT systems can be reduced to a simple process that can be done by anyone without special training. Expressing all measures of power and cooling in Watts simplifies the process. A general rule is that a CRAC system rating must be 1.3 times the anticipated IT load rating plus any capacity added for redundancy. This approach works well with smaller network rooms of under 4,000 ft 2 (372 m 2 ). For larger data centers, the cooling requirements alone are typically not sufficient to select an air conditioner. Typically, the effects of other heat sources such as walls and roof, along with recirculation, are significant and must be examined for a particular installation. The design of the air handling ductwork or raised floor has a significant effect on the overall system performance, and also greatly affects the uniformity of temperature within the data center. The adoption of a simple, standardized, and modular air distribution system architecture, combined with the simple heat load estimation method described, could significantly reduce the engineering requirements for data center design. About the Author: Neil Rasmussen is a founder and the Chief Technical Officer of American Power Conversion. At APC, Neil directs the world s largest R&D budget devoted to Power, Cooling, and Rack infrastructure for critical networks, with principal product development centers in Massachusetts, Missouri, Denmark, Rhode Island, Taiwan, and Ireland. Neil is currently leading the effort at APC to develop modular scalable data center solutions. Prior to founding APC in 1981, Neil received his Bachelors and Masters degrees from MIT in electrical engineering where he did his thesis on the analysis of a 200MW power supply for a Tokamak Fusion reactor. From 1979 to 1981 he worked at MIT Lincoln Laboratories on flywheel energy storage systems and solar electric power systems. 8

Calculating Total Cooling Requirements for Data Centers

Calculating Total Cooling Requirements for Data Centers White Paper 25 Revision 3 by Neil Rasmussen > Executive summary This document describes how to estimate heat output from information technology (IT)

Electrical Efficiency Modeling of Data Centers

Electrical Efficiency Modeling of Data Centers By Neil Rasmussen White Paper 113 Executive Summary The conventional models used to estimate electrical efficiency of data centers are grossly inaccurate

Increasing Data Center Efficiency by Using Improved High Density Power Distribution

Increasing Data Center Efficiency by Using Improved High Density Power Distribution By Neil Rasmussen White Paper #128 Executive Summary A new approach to power distribution for high density server installations

Electrical Efficiency Modeling for Data Centers

Electrical Efficiency Modeling for Data Centers By Neil Rasmussen White Paper #113 Revision 1 Executive Summary Conventional models for estimating electrical efficiency of data centers are grossly inaccurate

Cooling Strategies for IT Wiring Closets and Small Rooms

Cooling Strategies for IT Wiring Closets and Small Rooms By Neil Rasmussen Brian Standley White Paper #68 Executive Summary Cooling for IT wiring closets is rarely planned and typically only implemented

Strategies for Deploying Blade Servers in Existing Data Centers

Strategies for Deploying Blade Servers in Existing Data Centers By Neil Rasmussen White Paper #125 Revision 1 Executive Summary When blade servers are densely packed, they can exceed the power and cooling

Implementing Energy Efficient Data Centers

Implementing Energy Efficient Data Centers By Neil Rasmussen White Paper #114 Executive Summary Electricity usage costs have become an increasing fraction of the total cost of ownership (TCO) for data

Cooling Strategies for IT Wiring Closets and Small Rooms

Cooling Strategies for IT Wiring Closets and Small Rooms White Paper 68 Revision 1 by Neil Rasmussen and Brian Standley > Executive summary Cooling for IT wiring closets is rarely planned and typically

The Different Types of UPS Systems

The Different Types of UPS Systems By Neil Rasmussen White Paper #1 Revision 5 Executive Summary There is much confusion in the marketplace about the different types of UPS systems and their characteristics.

Cooling Options for Rack Equipment with Side-to-Side Airflow

Cooling Options for Rack Equipment with Side-to-Side Airflow By Neil Rasmussen White Paper #50 Executive Summary Equipment with side-to-side airflow presents special cooling challenges in today s data

Re-examining the Suitability of the Raised Floor for Data Center Applications

Re-examining the Suitability of the Raised Floor for Data Center Applications By Neil Rasmussen White Paper #19 Revision 1 Executive Summary The circumstances that gave rise to the development and use

Improving Rack Cooling Performance Using Airflow Management Blanking Panels

Improving Rack Cooling Performance Using Airflow Management Blanking Panels By Neil Rasmussen White Paper #44 Revision 3 Executive Summary Unused vertical space in open frame racks and rack enclosures

Avoidable Mistakes that Compromise Cooling Performance in Data Centers and Network Rooms

Avoidable Mistakes that Compromise Cooling Performance in Data Centers and Network Rooms By Neil Rasmussen White Paper #49 Executive Summary Avoidable mistakes that are routinely made when installing cooling

Avoiding Costs from Oversizing Data Center and Network Room Infrastructure

Avoiding Costs from Oversizing Data Center and Network Room Infrastructure White Paper 37 Revision 6 by Neil Rasmussen > Executive summary The physical and power infrastructure of data centers and network

Avoiding Costs from Oversizing Data Center and Network Room Infrastructure

Avoiding Costs from Oversizing Data Center and Network Room Infrastructure White Paper 37 Revision 7 by Neil Rasmussen > Executive summary The physical infrastructure of data centers and network rooms

Calculating Total Power Requirements for Data Centers

Calculating Total Power Requirements for Data Centers By Richard Sawyer White Paper #3 Executive Summary Part of data center planning and design is to align the power and cooling requirements of the IT

Efficiency and Other Benefits of 208 Volt Over 120 Volt Input for IT Equipment

Efficiency and Other Benefits of 208 Volt Over 120 Volt Input for IT Equipment By Neil Rasmussen White Paper #27 Revision 2 Executive Summary Decisions made regarding the distribution of 208V or 120V power

Improving Rack Cooling Performance Using Airflow Management Blanking Panels

Improving Rack Cooling Performance Using Airflow Management Blanking Panels White Paper 44 Revision 4 by Neil Rasmussen > Executive summary Unused vertical space in open frame racks and rack enclosures

Cooling Audit for Identifying Potential Cooling Problems in Data Centers

Cooling Audit for Identifying Potential Cooling Problems in Data Centers By Kevin Dunlap White Paper #40 Revision 2 Executive Summary The compaction of information technology equipment and simultaneous

AC vs DC Power Distribution for Data Centers

AC vs DC Power Distribution for Data Centers By Neil Rasmussen White Paper #63 Revision 4 Executive Summary Various types of DC power distribution are examined as alternatives to AC distribution for data

Power and Cooling for Ultra-High Density Racks and Blade Servers

Power and Cooling for Ultra-High Density Racks and Blade Servers By Neil Rasmussen White Paper #46 Revision 3 Executive Summary Rack power of 10kW per rack or more can result from the deployment of information

An Improved Architecture for High-Efficiency, High-Density Data Centers

An Improved Architecture for High-Efficiency, High-Density Data Centers By Neil Rasmussen White Paper #126 Executive Summary Data center power and cooling infrastructure worldwide wastes more than 60,000,000

Power and Cooling Capacity Management for Data Centers

Power and Cooling Capacity for Data Centers By Neil Rasmussen White Paper #150 Executive Summary High density IT equipment stresses the power density capability of modern data centers. Installation and

The Advantages of Row and Rack- Oriented Cooling Architectures for Data Centers

The Advantages of Row and Rack- Oriented Cooling Architectures for Data Centers By Kevin Dunlap Neil Rasmussen White Paper #130 Executive Summary Room cooling is an ineffective approach for next-generation

Glossary of Heating, Ventilation and Air Conditioning Terms

Glossary of Heating, Ventilation and Air Conditioning Terms Air Change: Unlike re-circulated air, this is the total air required to completely replace the air in a room or building. Air Conditioner: Equipment

The following are general terms that we have found being used by tenants, landlords, IT Staff and consultants when discussing facility space.

The following are general terms that we have found being used by tenants, landlords, IT Staff and consultants when discussing facility space. Terminology: Telco: Dmarc: NOC: SAN: GENSET: Switch: Blade

Guidelines for Specification of Data Center Power Density

Guidelines for Specification of Data Center Power Density By Neil Rasmussen White Paper #120 Executive Summary Conventional methods for specifying data center density are ambiguous and misleading. Describing

2006 APC corporation. Cooling Solutions and Selling Strategies for Wiring Closets and Small IT Rooms

Cooling Solutions and Selling Strategies for Wiring Closets and Small IT Rooms Agenda Review of cooling challenge and strategies Solutions to deal with wiring closet cooling Opportunity and value Power

Residential HVAC Load Sizing Training October 14, 2015. David Kaiser Green Code Plan Reviewer

Residential HVAC Load Sizing Training October 14, 2015 David Kaiser Green Code Plan Reviewer DCRA - Green Building Division Regulations of green codes including: Green Building Act Green Construction Code

SUPPLEMENTING COMMERCIAL HVAC SYSTEMS WITH HVLS FANS

SUPPLEMENTING COMMERCIAL HVAC SYSTEMS WITH HVLS FANS Improving Energy Efficiency and Lowering Energy Costs with HVLS Fans As the cost of energy continues to rise, building designers and engineers are constantly

Presentation Outline. Common Terms / Concepts HVAC Building Blocks. Links. Plant Level Building Blocks. Air Distribution Building Blocks

Presentation Outline Common Terms / Concepts HVAC Building Blocks Plant Level Building Blocks Description / Application Data Green opportunities Selection Criteria Air Distribution Building Blocks same

How to Select a Colocation Provider Offering High Performance Computing

EXECUTIVE REPORT How to Select a Colocation Provider Offering High Performance Computing How to Select a Colocation HPC computing infrastructures can t use traditional computing environments. Due to the

Use of the Signal Reference Grid in Data Centers

Use of the Signal Reference Grid in Data Centers By Neil Rasmussen White Paper #87 Executive Summary Signal reference grids are automatically specified and installed in data centers despite the fact that

Cooling Small Server Rooms Can Be. - Jim Magallanes Computer Room Uptime: www.cruptime.com Uptime Racks: www.uptimeracks.com

Cooling Small Server Rooms Can Be Inexpensive, Efficient and Easy - Jim Magallanes Computer Room Uptime: www.cruptime.com Uptime Racks: www.uptimeracks.com Server Rooms Description & Heat Problem Trends

Small Data / Telecommunications Room on Slab Floor

Small Data / Telecommunications Room on Slab Floor Small Data / Telecommunications Room on Slab Floor During a warm summer period in 2008, Great Lakes experienced a network outage due to a switch failure

Choosing Close-Coupled IT Cooling Solutions

W H I T E P A P E R Choosing Close-Coupled IT Cooling Solutions Smart Strategies for Small to Mid-Size Data Centers Executive Summary As high-density IT equipment becomes the new normal, the amount of

Calculating Space and Power Density Requirements for Data Centers

Calculating Space and Power Density Requirements for Data Centers White Paper 155 Revision 0 by Neil Rasmussen Executive summary The historic method of specifying data center power density using a single

The Different Types of UPS Systems

White Paper 1 Revision 7 by Neil Rasmussen > Executive summary There is much confusion in the marketplace about the different types of UPS systems and their characteristics. Each of these UPS types is

Power and Cooling for Ultra-High Density Racks and Blade Servers

Power and Cooling for Ultra-High Density Racks and Blade Servers White Paper #46 Introduction The Problem Average rack in a typical data center is under 2 kw Dense deployment of blade servers (10-20 kw

Google s Green Data Centers: Network POP Case Study

Google s Green Data Centers: Network POP Case Study Table of Contents Introduction... 2 Best practices: Measuring. performance, optimizing air flow,. and turning up the thermostat... 2...Best Practice

Guidance for Calculation of Efficiency (PUE) in Data Centers

Guidance for Calculation of Efficiency (PUE) in Data Centers White Paper 158 Revision 1 by Victor Avelar > Executive summary Before data center infrastructure efficiency can be benchmarked using PUE or

The Different Types of UPS Systems

Systems White Paper 1 Revision 6 by Neil Rasmussen Contents Click on a section to jump to it > Executive summary There is much confusion in the marketplace about the different types of UPS systems and

Air Conditioning Contractors of America

Air Conditioning Contractors of America WHO IS ACCA???? Industry Manuals Residential D, J, S, H, RS, T, P A manual J load calculation is a measurement of how much heating and cooling capacity a home will

Tools to Simplify and Shorten Your Data Center Sales Cycle

Tools to Simplify and Shorten Your Data Center Sales Cycle May 14, 2009 Wendy Torell Data Center Science Center Data center planning and operation is under increasing pressures Increasing availability

Benefits of. Air Flow Management. Data Center

Benefits of Passive Air Flow Management in the Data Center Learning Objectives At the end of this program, participants will be able to: Readily identify if opportunities i where networking equipment

Selecting an Industry-Standard Metric for Data Center Efficiency

Selecting an Industry-Standard Metric for Data Center Efficiency By Neil Rasmussen White Paper #157 Executive Summary The development of standards for the measurement and specification of data center efficiency

Defining Quality. Building Comfort. Precision. Air Conditioning

Defining Quality. Building Comfort. Precision Air Conditioning Today s technology rooms require precise, stable environments in order for sensitive electronics to operate optimally. Standard comfort air

Energy Efficiency Opportunities in Federal High Performance Computing Data Centers

Energy Efficiency Opportunities in Federal High Performance Computing Data Centers Prepared for the U.S. Department of Energy Federal Energy Management Program By Lawrence Berkeley National Laboratory

Managing Data Centre Heat Issues

Managing Data Centre Heat Issues Victor Banuelos Field Applications Engineer Chatsworth Products, Inc. 2010 Managing Data Centre Heat Issues Thermal trends in the data centre Hot Aisle / Cold Aisle design

High-Efficiency AC Power Distribution for Data Centers

High-Efficiency AC Power Distribution for Data Centers White Paper 128 Revision 2 by Neil Rasmussen > Executive summary The use of 240 volt power distribution for data centers saves floor space, simplifies

Home Performance Guide Heat Pump Installation

Home Performance Guide Heat Pump Installation Something to fully understand about heat pumps is that they are a part of an overall system, the heating, ventilating and air conditioning (HVAC) system. That

Creating Efficient HVAC Systems

Creating Efficient HVAC Systems Heating and Cooling Fundamentals for Commercial Buildings Heating, ventilating, and air conditioning (HVAC) systems account for nearly half of the energy used in a typical

The Different Types of Air Conditioning Equipment for IT Environments

The Different Types of Air Conditioning Equipment for IT Environments By Tony Evans White Paper #59 Executive Summary Cooling equipment for an IT environment can be implemented in 10 basic configurations.

PTAC Selection Guide. Optimize your spend with the right PTAC equipment!

PTAC Selection Guide Optimize your spend with the right PTAC equipment! The Direct Supply Difference Direct Supply Equipment & Furnishings understands the challenges of securing equipment for your communities.

A Scalable, Reconfigurable, and Efficient Data Center Power Distribution Architecture

A Scalable, Reconfigurable, and Efficient Data Center Power Distribution Architecture By Neil Rasmussen White Paper #129 Executive Summary Significant improvements in efficiency, power density, power monitoring,

A Scalable, Reconfigurable, and Efficient Data Center Power Distribution Architecture

A Scalable, Reconfigurable, and Efficient Data Center Power Distribution Architecture White Paper 129 Revision 1 by Neil Rasmussen > Executive summary Significant improvements in efficiency, power density,

APC APPLICATION NOTE #112

#112 Best Practices for Deploying the InfraStruXure InRow SC By David Roden Abstract The InfraStruXure InRow SC (ACSC100 and ACSC101) is a self-contained air conditioner for server rooms and wiring closets.

Eco-mode: Benefits and Risks of Energy-saving Modes of UPS Operation

Eco-mode: Benefits and Risks of Energy-saving Modes of UPS Operation White Paper 157 Revision 0 by Neil Rasmussen > Executive summary Many newer UPS systems have an energy-saving operating mode known as

Overload Protection in a Dual-Corded Data Center Environment

Overload Protection in a Dual-Corded Data Center Environment White Paper 206 Revision 0 by Neil Rasmussen Executive summary In a dual-corded environment, the loss of power on one path will cause the load

Determining Total Cost of Ownership for Data Center and Network Room Infrastructure

Determining Total Cost of Ownership for Data Center and Network Room Infrastructure White Paper #6 Revision 3 Executive Summary An improved method for measuring Total Cost of Ownership of data center and

Electrical Efficiency Measurement for Data Centers

Electrical Efficiency Measurement for Data Centers White Paper 154 Revision 2 by Neil Rasmussen Contents Click on a section to jump to it > Executive summary A closer look at data center 3 Data center

Allocating Data Center Energy Costs and Carbon to IT Users

Allocating Data Center Energy Costs and Carbon to IT Users Paper 161 Revision 1 by Neil Rasmussen Executive summary Are complicated software and instrumentation needed to measure and allocate energy costs

CHAPTER III PHSYCHROMETRY AND THERMAL CONTROL

CHAPTER III PHSYCHROMETRY AND THERMAL CONTROL 3.1. INTRODUCTION Psychrometry studies the air properties. The psychrometric chart provides a visual picture of the changes that take place in the properties

Humidification Strategies for Data Centers and Network Rooms

Humidification Strategies for Data Centers and Network Rooms By Tony Evans White Paper #58 Revision 1 Executive Summary The control of humidity in Information Technology environments is essential to achieving

Data Bulletin. Mounting Variable Frequency Drives in Electrical Enclosures Thermal Concerns OVERVIEW WHY VARIABLE FREQUENCY DRIVES THERMAL MANAGEMENT?

Data Bulletin April 2001 Raleigh, NC, USA Mounting Variable Frequency Drives in Electrical Enclosures Thermal Concerns OVERVIEW Variable frequency drives are available from manufacturers as enclosed engineered

Airflow Simulation Solves Data Centre Cooling Problem

Airflow Simulation Solves Data Centre Cooling Problem The owner s initial design for a data centre in China utilized 40 equipment racks filled with blade servers spread out in three rows along the length

APC APPLICATION NOTE #92

#92 Best Practices for Designing Data Centers with the InfraStruXure InRow RC By John Niemann Abstract The InfraStruXure InRow RC is designed to provide cooling at the row and rack level of a data center

Blade Servers and Beyond: Adaptive Cooling for the Next Generation of IT Systems. A White Paper from the Experts in Business-Critical Continuity

Blade Servers and Beyond: Adaptive Cooling for the Next Generation of IT Systems A White Paper from the Experts in Business-Critical Continuity Executive Summary In enterprise data centers, designers face

High Performance Computing (HPC) Solutions in High Density Data Centers

EXECUTIVE REPORT High Performance Computing (HPC) Solutions in High Density Data Centers How s Houston West data center campus delivers the highest density solutions to customers Overview With the ever-increasing

Data Center Technology: Physical Infrastructure

Data Center Technology: Physical Infrastructure IT Trends Affecting New Technologies and Energy Efficiency Imperatives in the Data Center Hisham Elzahhar Regional Enterprise & System Manager, Schneider

Improving Data Center Energy Efficiency Through Environmental Optimization

Improving Data Center Energy Efficiency Through Environmental Optimization How Fine-Tuning Humidity, Airflows, and Temperature Dramatically Cuts Cooling Costs William Seeber Stephen Seeber Mid Atlantic

Power and Cooling for VoIP and IP Telephony Applications

Power and Cooling for VoIP and IP Telephony Applications By Viswas Purani White Paper #69 Executive Summary Voice Over IP (VoIP) deployments can cause unexpected or unplanned power and cooling requirements

Green Data Centre Design

Green Data Centre Design A Holistic Approach Stantec Consulting Ltd. Aleks Milojkovic, P.Eng., RCDD, LEED AP Tommy Chiu, EIT, RCDD, LEED AP STANDARDS ENERGY EQUIPMENT MATERIALS EXAMPLES CONCLUSION STANDARDS

DATA CENTER COOLING INNOVATIVE COOLING TECHNOLOGIES FOR YOUR DATA CENTER

DATA CENTER COOLING INNOVATIVE COOLING TECHNOLOGIES FOR YOUR DATA CENTER DATA CENTERS 2009 IT Emissions = Aviation Industry Emissions Nations Largest Commercial Consumers of Electric Power Greenpeace estimates

Knowledge for optimal efficiency

Engineering Onboard Climate Control Knowledge for optimal efficiency MARINE HVAC-R MARINE HVAC-R ADVANTAGES 2 KNOWLEDGE FOR OPTIMAL EFFICIENCY The BRONSWERK Advantage It s like the ideal day at sea when

Energy Efficient High-tech Buildings

Energy Efficient High-tech Buildings Can anything be done to improve Data Center and Cleanroom energy efficiency? Bill Tschudi Lawrence Berkeley National Laboratory Wftschudi@lbl.gov Acknowledgements California

Legacy Data Centres Upgrading the cooling capabilities What are the options?

Legacy Data Centres Upgrading the cooling capabilities What are the options? Presentation Structure What is a Legacy Data Centre? What is CRAC cooling? ASHRAE Standards Overview Available Cooling Systems

Engineering White Paper UTILIZING ECONOMIZERS EFFECTIVELY IN THE DATA CENTER

Engineering White Paper UTILIZING ECONOMIZERS EFFECTIVELY IN THE DATA CENTER SUMMARY A proper balance of temperature and humidity control is essential for efficient data center operation, and integral

Air Conditioning. The opportunity for energy efficiency. Low cost actions to reduce energy usage now

Fact Sheet #6 Air Conditioning In this fact sheet you will discover: The opportunity for energy efficiency How air conditioning works Low cost actions to reduce energy usage now Investments to reduce costs

Guidance for Calculation of Efficiency (PUE) in Data Centers

Guidance for Calculation of Efficiency (PUE) in Data Centers White Paper 158 Revision 3 by Victor Avelar Executive summary Before data center infrastructure efficiency can be benchmarked using PUE or other

Site Preparation Management Co., Ltd. March 1st 2013 By Nara Nonnapha, ATD UPTIME

Site Preparation Management Co., Ltd. March 1st 2013 By Nara Nonnapha, ATD UPTIME 2 AGENDA SESSION -1 What is Data Center? SESSION -2 Equipment and Components SESSION -3 Standard in designing Data Center

Energy Efficiency. Energy Efficient Home Cooling:

Energy Efficiency Energy Efficient Home Cooling: Choosing an air conditioning system is an important decision. A poor choice may be costly to purchase and operate and yet fail to provide the desired cooling

Design Challenges in Courthouses

Design Challenges in Courthouses Presented by Boggarm S. Setty, P.E. Setty & Associates, Ltd. ASHRAE Winter Meeting, New York, January 2008 Engineering Challenges State-of-the-Art New Architectural Trends

BRUNS-PAK Presents MARK S. EVANKO, Principal

BRUNS-PAK Presents MARK S. EVANKO, Principal Data Centers of the Future and the Impact of High Density Computing on Facility Infrastructures - Trends, Air-Flow, Green/LEED, Cost, and Schedule Considerations

Hot Aisle vs. Cold Aisle Containment

Hot Aisle vs. Cold Aisle Containment By John Niemann White Paper #135 Executive Summary Both hot and cold air containment can significantly improve the predictability and efficiency of data center cooling

UNIVERSITY OF MISSOURI 23 0000 - Heating Ventilating and Air-Conditioning (HVAC) March 2015.01

GENERAL: This section provides general standards for overall sizing and design of Heating, Ventilating, and Air Conditioning (HVAC) systems. Other sections contain specific standards for each system per

Tech Byte 27: Small Computer Room and IT Closet Cooling

Questions Answered in This Paper Sensible cooling capacity is the measuring stick for IT cooling capacity needs. What is the sensible cooling capacity of the comfort split system in comparison to the precision

ENHANCED LABORATORY HVAC SYSTEM

ENHANCED LABORATORY HVAC SYSTEM INTRODUCTION Since the early 1980's the attention to more energy efficient laboratory designs has been on the rise due to the increase in energy cost and the emergence of

HVACPowDen.xls An Easy-to-Use Tool for Recognizing Energy Efficient Buildings and HVAC Systems

HVACPowDen.xls An Easy-to-Use Tool for Recognizing Energy Efficient Buildings and HVAC Systems Fundamental Principles of Environmentally Responsible, Energy Efficient Buildings 1. Energy efficiency is

> Executive summary. Explanation of Cooling and Air Conditioning Terminology for IT Professionals. White Paper 11 Revision 2. Contents.

Explanation of Cooling and Air Conditioning Terminology for IT Professionals White Paper 11 Revision 2 by Tony Evans Click on a section to jump to it > Executive summary As power densities continue to

The Other Half of the Problem Server Closets and Small Server Rooms

The Other Half of the Problem Server Closets and Small Server Rooms Bill Tschudi Lawrence Berkeley National Laboratory October 24, 2012 wftschudi@lbl.gov SVLG Data Center Summit NEED TO CONVERT OT NON-STANFORD

AC vs. DC Power Distribution for Data Centers

AC vs. DC Power Distribution for Data Centers White Paper 63 Revision 6 by Neil Rasmussen > Executive summary DC power distribution has been proposed as an alternative to AC power distribution in data

Reducing Data Center Energy Consumption

Reducing Data Center Energy Consumption By John Judge, Member ASHRAE; Jack Pouchet, Anand Ekbote, and Sachin Dixit Rising data center energy consumption and increasing energy costs have combined to elevate

POWER USAGE EFFECTIVENESS. Developing Best Practices Manual for Indian Data Centers. Presentation by HVAC Core Group

POWER USAGE EFFECTIVENESS Developing Best Practices Manual for Indian Data Centers PUE - Power usage effectiveness is Total incoming power( IT equipment + electrical And mechanical support system ) / Presentation

air conditioners how to choose a cooling system

air conditioners how to choose a cooling system taking responsibility As an individual, your efficient use of energy brings benefits such as lower bills, improved comfort levels in your home and a reduced

Hybrid Geothermal / Solar Thermal HVAC System: Part1 Design (OU Human Health Building)

Integrating Large Scale, Innovative Solar Thermal Systems into the Built Environment June 26, 2013 11:00am 12:30PM Track: Renewable & Alternative Energy Sources Sponsor: 6.7 Solar Energy Utilization Hybrid

FUEL CONSUMPTION MEASUREMENT OF BUS HVAC UNITS

ID: 872 FUEL CONSUMPTION MEASUREMENT OF BUS HVAC UNITS KOPECKA M. (*), HEGAR M. (*), RYSKA A. (*) (*) Ingersoll Rand Engineering and Technology Center (IR ETC) Prague, Florianova 246, Hostivice, 253 Czech

Essential Cooling System Requirements for Next Generation Data Centers

Essential Cooling System Requirements for Next Generation Data Centers White Paper #5 Revision 3 Executive Summary Effective mission critical installations must address the known problems and challenges