1 IGNIS 1000 CONVENTIONAL FIRE DETECTION AND ALARM SYSTEM IGNIS 1240 FIRE DETECTION AND ALARM CONTROL PANEL Operation and Maintenance Documentation ID-E E IVA Edition
2 2 IK-E E The IGNIS 1240 conventional fire detection and alarm control panel covered by the present manual complies with the requirements of the following European Union Directives: CPD 89/106/EWG on construction materials; EMC 2004/108/WE on electromagnetic compatibility LVD 2006/95/WE on low-voltage electric equipment. The IGNIS 1240 control panel has been approved with the EC-Certificate of Conformity No. 1438/CPD/0152 issued by the Scientific and Research Centre for Fire Protection (CNBOP) Józefów, Poland, an EU notified authority No. 1438, confirming its compliance with the requirements of PN-EN 54-2:2002+A1:2007 standard. The certificate may be downloaded from web site. The device has been also approved with the Allowance Certificate No. 0508/2009 issued by CNBOP Polon-Alfa Spółka z ograniczoną odpowiedzialnością Sp. k. EN 54-2:1997+A1: , Glinki Street, PL Bydgoszcz, POLAND /CPD/0152 IGNIS 1240 fire detection and alarm control panel Conventional, for indoor use Provided options: - fire alarm devices output - output signal delays - interdependent alarming (A type dependence) - testing mode - alarm counter and additional functions, inputs and outputs: see technical data contained in ID-E manual Read the manual carefully before the detector assembling and commissioning. Any nonconformity with the instructions contained in the manual may be harmful or may cause violation of the law in force POLON-ALFA bears no responsibility for any damage resulting from usage inconsistent with the manual. A waste product, unsuitable for further use, shall be passed to a waste electric and electronic equipment collection point. NOTE: The manufacturer reserves the right to change specifications of products at any time without prior notice.
3 IK-E E 3 CONTENTS 1 INTRODUCTION DOCUMENTATION CONTENTS CONTROL PANEL APPLICATION SAFETY CONDITIONS Electric shock protection Installation and equipment safety Repairs and maintenance Fuse replacement DEFINITIONS DEVICE COMPLETENESS TECHNICAL SPECIFICATIONS GENERAL OPERATION PRINCIPLE CONTROL PANEL DESIGN OVERALL CONTROL PANEL DESCRIPTION HANDLING AND SIGNALLING ELEMENTS, ACCESS LEVELS Handling elements and indicators on front panel Handling elements inside the control panel CONTROL PANEL FUNCTIONALITY LCD INDICATIONS AT 1 ST AND 2 ND ACCESS LEVEL SERVICING CONTROL PANEL FUNCTIONS AT 2 ND ACCESS LEVEL Current date and time setting Zone (detection line) testing mode disablement/re-enablement Zone disablement/re-enablement Faults readout Disablement/re-enablement of all zones simultaneously Alarm counter readout CONTROL PANEL FUNCTIONS AT 3 RD ACCESS LEVEL Alarming lines (signalling devices) operation option setting General alarm relays actuation delay programming General alarm signal transmission delay disablement/re-enablement Event memory reset Standard configuration loading Alarm variants programming Zone relay programming QUIESCENT (SUPERVISION) MODE ALARM MODE Fire alarm signalling Fire alarm verification by the attending personnel Automatic alarm signal verification, alarming variants FAULT MODE DISABLEMENT MODE TESTING MODE SIGNAL TRANSMISSION/AUXILIARY EQUIPMENT CONTROLLING ACOUSTIC SIGNALLING DEVICES EXTERNAL DEVICE OPERATION INSPECTION... 26
4 4 IK-E E 5.12 CONTROL PANELS PARALLEL OPERATION POWER SUPPLY BASIC POWER SUPPLY RESERVE POWER SUPPLY INSTALLATION CONTROL PANEL MOUNTING WIRING COMMISSIONING AND CONFIGURATION COMMISSIONING STANDARD CONFIGURATION LOADING SOFTWARE FOR EVENT MEMORY READOUT EVENT MEMORY GENERAL DESCRIPTION HARDWARE REQUIREMENTS CONTROL PANEL-COMPUTER CONNECTION SOFTWARE LAUNCHING AND EVENT MEMORY READOUT CONTROL PANEL SPECIAL APPLICATIONS EXPLOSION ENDANGERED PREMISES PROTECTION INPUT AND OUTPUT CIRCUIT CONNECTING TERMINALS MAINTENANCE GENERAL RULES PERIODICAL TESTING FUSE REPLACEMENT PACKING, STORAGE AND TRANSPORTATION... 37
5 IK-E E 5 1 INTRODUCTION 1.1 DOCUMENTATION CONTENTS The purpose of this Operation and Maintenance Documentation (OMD) is to present the application, design and operation of the IGNIS 1240 fire detection and alarm control panel which constitute a part of the fire detection and alarm system. The documentation contains necessary information on the IGNIS 1240 control panels for designers, fitters and maintenance technicians. Together with the User Manual IO-E , intended for those who are on duty directly at the control panel, it makes the complete operating documentation attached to the control panel and delivered to its user. 1.2 CONTROL PANEL APPLICATION The IGNIS 1240 fire control panel is designed to: 1. signal a fire occurrence detected by an interoperating fire warning devices (automatic and manual), 2. indicate a fire endangered place by identification of the alarming detector line, 3. actuate fire protection equipment, 4. transmit a fire information to monitoring systems. The control panel interoperates with the 30 and 40 model range two-state (conventional) detectors manufactured by Polon-Alfa. It is intended for installation in medium-sized objects, e.g. offices, commercial and industrial buildings, etc. it is adapted for continuous operation in premises of low dust level at temperature range from - 5 C to + 40 C and air relative humidity up to 80 % at +40 C. 1.3 SAFETY CONDITIONS Electric shock protection The IGNIS 1240 fire control panels are ranked as the 1 st protection class devices and can be used only in the case of application of additional protection against electric shocks, such as zeroing or protective grounding. 230 V/50 Hz mains supply circuits insulation is reinforced and resists 2800 V voltage test; low-voltage circuits (below 42 V) insulation is able to resist test voltage of 700 V DC. After connecting the mains power supply conductors, the mains connection must be protected with a manufacturer's shield Installation and equipment safety Wire installation should be made using conductors of the required fire resistance and should be properly protected in passages through fire zone boundaries. In order to avoid undesirable interaction, a required distance between the low-voltage installation and a power installation and a lightning protection system should be maintained. From the system electromagnetic interference immunity, it is recommended to utilise protective grounding. Reserve power supply batteries should be connected to the panel at the final stage of the installation. The panel components are heat sensitive. The maximum ambient temperature should not exceed + 40 C. The space left around the device should be big enough to secure free air flow. Air humidity in the premises where the panel operates should not exceed 95 % Repairs and maintenance Maintenance works and periodic inspections should be executed by skilled personnel employed by companies authorised or trained by Polon-Alfa. Any repairs must be carried out by the manufacturer.
6 6 IK-E E Polon-Alfa bears no responsibility for the operation of any apparatus being serviced or repaired by unauthorised personnel Fuse replacement In the event of fuse replacement, an equivalent fuse replacement should be used: of the appropriate type and nominal value. The appropriate types and nominal values are contained in p DEFINITIONS Detection line - a two-core line with detectors installed in, terminated with an end-of-line resistor. Fire warning device - a fire detector or manual call point. Detection point a fire warning device, installed in the supervised premises, installed in a detection line. Detection zone - a separated area supervised by fire warning devices installed in one detection line. Monitoring line - a two-core line that supervises the monitoring contacts of external fire devices. Alarm line - a two-core monitored line that actuates external signalling devices or fire-fighting equipment. Output to monitoring a control panel relay output that enables transmission of fire and fault signals to a monitoring centre or to the Fire Brigades. Quiescent (supervision) mode - an operation mode, in which the control panel is power supplied from an electric energy source that meets the settled requirements, during which no other operation mode is indicated. Alarm (fire) mode - an operation mode the control panel triggers after receipt of a fire detection information from fire warning devices. Disablement mode - an operation mode, in which it is deliberately blocked the control panel ability to receive signals from any fire warning devices and to evoke alarms, or the control panel output and/or transmission path to any fire detection and alarm system component that is a part of alarm circuit. Testing mode - an operation mode in which the control panel indicates functions checking. Fault mode - an operation mode in which the control panel indicates a fault of any circuit in the alarm installation or its own circuits. 1.5 DEVICE COMPLETENESS Table 1 lists the items which compose the IGNIS 1240 control panel furnishings. Table 1 Item Description Quantity IGNIS 1240 fire detection and alarm control panel Operation and Maintenance Documentation (OMD) Servicing manual Warranty certificate Control panel unit package
7 IK-E E 7 Table 2 specifies the equipment for typical fire alarm systems, operating with the control panel in the IGNIS 1000 system, to be ordered separately in required quantities. In the standard execution, the control panel is equipped with 16 detection lines. The ML-3 module (ordered separately) enables extension by further 8 detection lines. Table 2.2 Item Description Remarks V/17 Ah battery ML-3 module Conventional fire detectors of 30 and 40 model range, including intrinsically safe execution Manual call points WZ-31 additional indicator two pcs required for control panel to extend panel capacity by 8 lines according to Appendix A according to Appendix A 2 TECHNICAL SPECIFICATIONS Overall dimensions L x H x G 392 x 482 x 190 mm Mass (without batteries) < 11 kg Ingress protection IP 30 Operation temperature range -5 C +40 C Allowable operation relative humidity 95 % at +40 C Transportation temperature range -25 C +55 C Power supply voltage: 50 Hz mains 230 V + 10 % - 15 % reserve battery: internal or outside 2 x 12 V/17 Ah, e.g. KOBE HV17-12W control panel of capacity 36 Ah Battery charging current 1.7 A (without current consumption by external devices) Current draw in quiescent mode: - from mains < 800 ma - from batteries (16/24 detection lines) < 170/228 ma Current draw in alarm mode: - from mains < 800 ma - from 17 Ah battery, max. < 600 ma External devices power supply voltage 24 V + 25 % - 15 % Admissible current draw from external devices power supply output, max. 800 ma Number of detection lines: - Standard 16 - with ML-3 module application 24 Detection line resistance, max. 2 x 120 Ω Detection line insulation resistance, min. Number of detectors installed in a detection line 32 Number of manual call points in a detection line kω Number of all detectors and manual call points 512 Number of beam smoke detectors (DOP) in a line 1 (without end-of-line resistor)
8 8 IK-E E End-of-line resistor in a detection line 5.6 kω, ±5 % 0.25 W Detection line quiescent current, max. 7 ma Allowable quiescent current of detectors in detection line 2 ma Number of monitoring lines 2 or 3 Allowable monitoring line resistance, max. 2 x 120 Ω Monitoring line insulation resistance, min. 100 kω Monitoring line end-of-line resistor 10 kω, ±5 % Number of external signalling device lines 2 or 3 Allowable signalling device line resistance 10 % of load resistance, but 50 Ω Signalling device line load resistance 200 Ω 10 kω Signalling device line insulation resistance, min. 100 kω Signalling device line operation voltage 24 V + 25 % - 15 % Signalling device allowable current, max. 140 ma Alarm transmission delay programmable from 0 to 10 min, 1-second interval Relay outputs: - general alarm 1 or 2 switchable contacts - general fault 1 switchable contact - zone alarm 16 or 24 switchable contacts Relay outputs load 1 A/30 V Control panel work time after mains voltage outage see Table 3 Event memory: - counter capacity of events that evoked alarm mode triggering 9,999 - event time registration accuracy 1 s - counter capacity of events not connected with alarm mode 512. Table 3. Control panel work time after mains voltage outage Control panel batteries capacity Maximum current consumption from external devices power supply output 72 h 17 Ah 0 ma 30 h 17 Ah 40 ma 12 h 17 Ah 800 ma 3 GENERAL OPERATION PRINCIPLE The IGNIS 1240 is a conventional fire alarm control panel interoperating with non-addressable fire detectors installed in detection lines that are terminated with end-of line resistors. Detection of a fire hazard by a detector evokes the control panel triggering an alarm mode and alarm signalling with indication of the number of the zone where a fire danger has occurred. The zone size is closely connected with the detection line length and the number of detectors installed therein. The control panel is equipped with a microprocessor-based controller that monitors the system operation, processes information delivered from detecting, monitoring and signalling lines as well as from the device handling elements. It controls optical and acoustic signalling devices and output
9 IK-E E 9 circuit operation. The circuit also contains a memory intended for registration of occurrences detected by the control panel, a real time clock and a RS 232 standard serial port for a computer connection. 4 CONTROL PANEL DESIGN 4.1 OVERALL CONTROL PANEL DESCRIPTION The control panel is made in the form of a metal cabinet intended for wall mounting. The device mounting method is shown in Fig. 3. The cabinet door, which is also the control panel front side, contains all signalling and handling elements, LCD display and a switch with a key that is provided for access level setting. The door can be opened after removing two fastening screws. Bushings for alarm system wiring and mains power supply conductors introduction are placed in the back wall of the cabinet. An RS opening covered with a cap, provided for routing a cable connecting the control panel with a computer during the event memory readout, is located on the left. Zone fields intended for zone description inserting are placed on the control panel door. Two sheets of paper (of 200 g/m basis weight) are delivered with the devices they are proposed for zone description strips preparation. After writing down an appropriate text and cutting pursuantly to the contour marked, they should be inserted into the slots located on the inner side of the control panel door, as it is shown in Fig. 5. Such a pattern is available on the manufacturer s web site that is useful for descriptions preparation by the means of computer printout. 4.2 HANDLING AND SIGNALLING ELEMENTS, ACCESS LEVELS In the IGNIS 1240 control panel, accessibility to the handling elements and particular functions is diversified and divided into four access levels. The 1 st access level is provided for persons who take first activities after a fire alarm or fault indication. At this level, only the ACKNOWLEDGEMENT push button is active and the control panel signalling elements testing function which is actuated with the PERSONNEL push button. The 2 nd access level is intended for the persons especially responsible for the premises security that are properly trained and authorised to operate the control panel. The access to the 2 nd level is obtained by turning the key. It allows for access to all push buttons located on the control panel front side. The 3 rd access level is designed for the personnel properly trained and authorised to change configuration data and perform maintenance works. The 3rd access level handling elements are located inside the control panel. The 4 th access level is provided for the persons trained and authorised by the manufacturer to change the factory (default) software and service the device Handling elements and indicators on front panel In the further part of this section, for easier identification, before the description of every element its number is given in the brackets according to the marking as in fig. 1. The control panel front plate is equipped with signalling and handling elements presented in Fig. 1. Each element has its own text description. Particular element function and operation method is described below. Numbers corresponding with the descriptions used in Fig. 1 are given in brackets.
10 10 IK-E E (1) 1 24 ZONE red colour zone diodes assigned to 1 24 detection lines accordingly. The diode illuminates with continuous light, if fire detectors in the corresponding detection line are in the alarm mode. The illumination lasts from the moment when a signal from a detection line is identified as a fire alarm until the ACKNOWLEDGEMENT push button is pressed. The zone, where an alarm mode has occurred first, is signalled with flashing light; the following zones with steady light. (2) 1 24 ZONE yellow colour zone diodes, allocated to 1 24 detection lines accordingly, indicate: with continuous light - the fault or testing mode (in the testing mode the diodes flashing frequency is higher than in the fault mode), with steady light the disablement mode (line switch off), no light the quiescent (supervision) mode. (3) TRANSMISSION a red colour diode signalling - with continuous light the general alarm relay contacts switching in the active position. (4) FIRE a red colour display indicating a fire detection with flashing light (1 Hz frequency). The indicator has the FIRE wording and is lit during the control panel alarm mode. The indication changes for continuous light after pressing the ACKNOWLEDGEMENT push button. (5) LCD display the displayed messages description is contained in p (6) POWER SUPPLY a green colour diode indicating that the control panel is connected to at least mains or battery power supply. (7) DISABLEMENT a yellow colour diode signalling collectively disablement of: at least one detection line, signalling devices, or alarm signal transmission (general alarm relays). (8) TESTING a yellow colour diode signalling the testing mode of at least one detection line; (9) FAULT a yellow colour diode indicating the fault mode (i.e. improper operation) of at least one circuit being under the control panel supervision. Five additional yellow diodes described below define which particular circuit is faulty. (10) POWER SUPPLY a yellow colour diode that signals: with steady light a battery fault, with flashing light mains fault. (11) SYSTEM a yellow colour diode signalling with steady light a fault in the microprocessor circuit operation or a falsification of the configuration data. (12) EXTERNAL DEVICES a yellow colour diode that signals with steady light a fault of at least one detection line. (13) SIGNALLING DEVICES a yellow colour diode indicating with steady light a fault of at least one external signalling device. (14) EARTH FAULT a yellow colour diode signalling with steady light an earth fault of at least one control panel circuit (connected with the earthing potential). (15) TRANSMISSION; OFF/ON a yellow colour diode placed near the push button that signals with steady light the alarm relay disablement mode.
11 IK-E E 11 (16) SIGNALLING DEVICES; OFF/ON a yellow colour diode placed near the push button indicates with steady light the disablement mode of external signalling devices. The signalling devices can operate only in the control panel fire alarm mode; (17) PERSONNEL; OFF/ON a yellow colour diode placed near the push button that signals with steady light the control panel PERSONNEL ABSENT mode. (18) ACKNOWLEDGEMENT a push button for acoustic signalling devices silencing and a fire alarm receipt acknowledgement by the attending personnel; active at the 1 st access level (without turning the key). (19) RESET a push button for the control panel or detectors in detector lines fire alarm mode reset; (20) PERSONNEL ACCESS LEVEL a switch (a lock with a key) to actuate the handling elements designed for usage at the 2 nd access level (all push buttons placed on the front panel). (21) FUNCTION SW.OVER, (22) SELECTION, (23) SET three push buttons enabling usage of the functions designated for the control panel parameters readout or change at the 2 nd access level: FUNCTION a function selection, SELECTION - moving the cursor to the right, SET - setting change Handling elements inside the control panel Fig. 5 depicts the handling elements mounted on the STR-1240 controller board located inside the control panel: (P1) FUNCTION, (P2) SELECTION, (P3) SET and (P4) SET four push buttons inside the control panel that enable usage of the functions dedicated to the control panel programming; (P13) RESET - the control panel controller restart. Table 4 Jumper No. Jumper position Function ZW1 ZW2 ZW3 ZW4 ZW Support of 16 detection lines two line modules 2-3 Support of 24 detection lines three line modules 1-2 Unused 2-3 Unused Unused ZW11 1-2
12 12 IK-E E 2-3 Service mode without alarm receipt delays ZW Software version display after pressing ACKNOWLEDGEMENT push button Fig. 6 presents the view of the MZ-4212 power supply unit module that contains: WŁ. AKU push button - used for switching the control panel on at the mains supply outage (essential when the batteries connection does not cause the control panel self-activation); ZW1 jumper - enables disconnection the earth fault monitoring circuit and anti-interference modules from the casing; ZW2 - a jumper enabling the earth fault monitoring circuit switch on/off; when the jumper is set in the position marked on the board - the earth fault monitoring circuit is switched on; BZ A battery cluster circuit protection; the T3,15L250V type melt fuse; BZ3 1 A external device power supply circuit protection; the F1L250V type melt fuse; BZ2 1 A the control panel reserve internal circuits power supply output; (unused in the current version); MAINS SWITCH - a two-pole mains power supply on/off switch. 5 CONTROL PANEL FUNCTIONALITY 5.1 LCD INDICATIONS AT 1 ST AND 2 ND ACCESS LEVEL SERVICING The IGNIS 1240 control panel is equipped with a 16-character alphanumeric liquid crystal display (LCD). Its main function is to set and display the exact time and date, as well as the control panel configuration parameters. The current time and date are used by the automatic event recording system. Additionally, the LCD supports the panel operating personnel displaying information concerning the control panel status or the functions of activated push buttons. During the control panel quiescent mode, the LCD displays the date and time. All other information, except the alarm mode, is displayed momentarily. After some seconds the control panel automatically switches to the date and time displaying mode. 1. Current date and time - exemplary display: :59 (year-month-day hour:min) 2. Control panel alarm mode The 1 st and 2 nd stage alarm
13 IK-E E 13 L.1 ALARM! 0 00 where: - L1 number of the line where the first alarm has been detected, current fire alarm transmission delay time ( range). 3. External signalling devices disablement/re-enablement SIGN.DEV. ON SIGN.DEV. OFF 4. Alarm signal transmission disablement/re-enablement TRANSMISSION ON TRANSMISSION OFF 5. Operation mode switch over between personnel present and personnel absent PERSONNEL PRESENT PERSONNEL ABSENT 6. Fire alarm mode reset RESET 7. Access denied ACCESS DENIED The above information is displayed in the case a function (push button) actuation trial without appropriate access level obtaining. 5.2 CONTROL PANEL FUNCTIONS AT 2 ND ACCESS LEVEL With the FUNCTION, SELECTION, SET push buttons available on the front panel it is possible to: set the date and time, switch a zone or zones in the testing mode, disable/re-enable a zone or zones, faults readout, disable/re-enable all zones simultaneously.
14 14 IK-E E A desired function recall is performed using the FUNCTION push button. The item that can be modified is distinguished by the flashing tag. The tag location can be changed with the help of the SELECTION push button. The selected value modification is possible using the SET push button Current date and time setting :59 (year-month-day hour:min) The current date and time setting should start from entering the date and time setting function using the FUNCTION push button. The LCD display shows a date with the first digit (tens of years) flashing. The digit flashing means that it is possible to alter its value with the SET push button. The SELECTION push button pressing moves the cursor to the next digit. In this way it is possible to set all the digits representing the current date and time (e.g :59). The SELECTION push button enables moving the cursor only to the right. A return to the beginning of the display is possible after passing all the digit positions. The SET push button acts similarly. The control panel is equipped with a lithium battery mounted on the controller board that supports the clock in the case of power supply voltage outage Zone (detection line) testing mode disablement/re-enablement The below described function allows for a zone testing mode disablement/re-enablement: TESTING ON z zone number 1 16 or 24 0 testing enabled 1 testing disabled Zone disablement/re-enablement A disablement/re-enablement of a zone (detection line) is possible using the following function: ZONE ON z zone number 1 16 or 24 0 zone enabled 1 zone disabled
15 IK-E E Faults readout In order to read the faults out, it is necessary to select with the FUNCTION push button the following indication on the display: FAULT READOUT Afterwards, using the SET push button recall the messages informing on the current faults registered in the system. The below table lists the possible faults with their clarifications. BZ3 FUSE FAULT BATT.VOLTAGE DECR. MAINS POW.SUP.FAULT BATTERY FAULT EARTH FAULT LACK OF CHARGING SYSTEM FAULT CONFIG.SET. FAULT CH. L 1 FAULT CH. L 2 FAULT CH. L 3 FAULT SDL 1 FAULT SDL 2 FAULT SDL 3 FAULT BREAK OF LINE 1 BREAK OF LINE 2... BREAK OF LINE 24 BZ3 fuse fault Battery voltage drop 230 V mains power supply fault Battery cluster or its circuit fault Damage of insulation between control panel and grounding Charging circuit fault of interruption Control panel controller program execution disruption Disruption in configuration settings saved in control panel memory Fault in detection line 1 circuit Fault in detection line 2 circuit Fault in detection line 3 circuit Fault in alarm signalling devices line 1 circuit Fault in alarm signalling devices line 2 circuit Fault in alarm signalling devices line 3 circuit Break in detection line 1 circuit Break in detection line 2 circuit Break in detection line 24 circuit...
16 16 IK-E E SHORT OF LINE 1 SHORT OF LINE 2... SHORT OF LINE 24 LACK OF FAULTS Short circuit in detection line 1 circuit Short circuit in detection line 2 circuit Short circuit in detection line 24 circuit No fault detected in IGNIS system Disablement/re-enablement of all zones simultaneously ZONES ON OFF - X X no changes 1 all zones disabled 0 zones enabled Note: Disablement or re-enablement of all zones takes place after typing 0/1 and the control panel restart using the RESTART push button inside the device Alarm counter readout In order to read the alarm counter out, it is necessary to select with the FUNCTION push button the following indication on the display (the pictures illustrate the counter exemplary indication): 0001 z (alarm number zone number year month-day) The zone number informs about the alarm source and is consistent with the detection line number (1 24). The display shows the latest alarm number, number of the zone where the alarm occurred, and its date. It is possible to read the alarm occurrence time with 1-second accuracy by pressing the SELECTION push button; then in the date place the alarm time is displayed as shown below: 0001 z2 17 : 15 : 48 (alarm number line number hour-minute-second) Pressing the SELECTION push button produces alternate display of the clock time and date. Preceding alarms readout is possible with the counter scrolling using the SET push button. The return to the latest alarm takes place after aborting the function by pressing the FUNCTION push button and selection of the alarm counter readout function again.
17 IK-E E CONTROL PANEL FUNCTIONS AT 3 RD ACCESS LEVEL It is possible to use the functions available at the 3 rd access level after the control panel door opening Fig. 5. The P1-FUNCTION, P2-SELECTION, P3-SET and P4-SET push buttons located inside the control panel allows for the following functions application: external signalling devices operation option setting, general alarm signal transmission delay value setting, event memory reset, general alarm signal transmission delay disablement/re-enablement, alarm variants programming, relays programming. A desired function recall is performed using the FUNCTION push button. The item that can be modified is distinguished by the flashing tag. The tag location can be changed with the help of the SELECTION push button. The selected value modification is possible using the SET and SET push buttons Alarming lines (signalling devices) operation option setting EXT.AL.OPTION sign. dev. operation acc. to 0 option 1 sign. dev. operation acc. to 1 option The description of the signalling devices operation in option 0 and 1 is contained in p General alarm relays actuation delay programming DELAY delay time (example) 1 minutes (1 9) 30 seconds (0 59) The delay time setting change is possible with the following push buttons: SET - increase SET - decrease.
18 18 IK-E E General alarm signal transmission delay disablement/re-enablement DELAYS ON z zone number 1 16 or 24 1 delays enabled 0 delays disabled The setting change - with the SET and SET push buttons. The function requires, apart from selecting the zone number (1 16 or 24), entering 1 if the delay is to be enabled or entering 0 if the delay is to be disabled. It allows for delay disablement of chosen detection lines, any alarm from which should actuate the general alarm relays immediately (e.g. a detection line with ROP manual call points installed). Any detecting line acknowledged alarm with a delay enabled (which value is set using the DELAY function) causes properly delayed general alarm relay activation. Lack of alarm acknowledgment shortens the delay time to 30 s. In the personnel absent mode the control panel reduces the delay time to zero. The described delay concerns only the general alarm relays; zone relays operate always without any delay. The general fire relay activation transmission delay programming is linked with alarm variant programming (see p ) Event memory reset MEMORY RESET reset function disabled 1 reset function enabled Note: The event memory reset performance is possible after the reset function initiation with the SET push button and pressing the (P13) RESET push button Standard configuration loading STAND. CONF loading function disabled 1 loading function enabled Note: The Standard configuration loading is possible after the loading function initiation with the SET push button and pressing the (P13) RESET push button.
19 IK-E E Alarm variants programming VARIANT z zone number 1 16 or 24 1 alarm variant number (0, 1 or 2) The setting change - with the SET and SET push buttons. Note: The variant 2 (zone interdependence) loading takes place automatically in both detection lines constituting the interdependent pair. One-stage alarm Programming: - using the FUNCTION push button, select the function VARIANT z with the SELECTION and SET push buttons, choose the proper zone number and variant number equal to 0 - using the FUNCTION push button, select the function DELAYS ON z with the SELECTION and SET push buttons, choose the proper zone number and 0 (on the last display position) that results in the chosen zone delay disablement. Two-stage alarm Programming: - using the FUNCTION push button, select the function - with the SELECTION and SET push buttons, choose the proper zone number and variant number equal to 0 - using the FUNCTION push button, select the function - with the SELECTION and SET push buttons, set the proper delay time in minutes (0..9) the X position in the display and in seconds (00 59) two following positions XX. Note: The delay value set is common for all zones. VARIANT z DELAY X XX
20 20 IK-E E - using the FUNCTION push button, select the function DELAYS ON z with the SELECTION and SET push buttons, choose the proper zone number and 1 (on the last display position) that results in the chosen zone delay disablement. One-stage alarm with a preliminary reset Programming: - using the FUNCTION push button, select the function VARIANT z with the SELECTION and SET push buttons, choose the proper zone number (z. 01) and variant number using the FUNCTION push button, select the function DELAYS ON z with the SELECTION and SET push buttons, choose the proper zone number and 0 (on the last display position) that results in the chosen zone delay disablement. Two-stage alarm with a preliminary reset Programming: - using the FUNCTION push button, select the function - with the SELECTION and SET push buttons, set the proper zone number and variant number equal to 1 - with the SELECTION and SET push buttons, set the proper delay time in minutes (0..9) the X position in the display and in seconds (00 59) two following positions XX. Note: The delay value set is common for all zones. VARIANT z DELAY X XX - using the FUNCTION push button, select the function DELAYS ON z with the SELECTION and SET push buttons, set the proper zone number and 1 (on the last display position) that results in the chosen zone delay enablement.
POLON 4000 INTERACTIVE FIRE DETECTION AND ALARM SYSTEM POLON 4100 FIRE DETECTION AND ALARM ADDRESSABLE CONTROL PANEL Operation and Maintenance Documentation ID E342 001GB IB Edition 2 ID E342 001GB The
Conventional Fire Detection and Extinguishant Control System Specification Page 1 of 9 Scope Furnish a complete 24VDC Conventional, electrically supervised, combined fire detection and extinguishant release
TECHNICAL SPECIFICATIONS Page 1 of 10 FIRE DETECTION AND ALARM SYSTEM Scope Furnish a complete 24V DC conventional, electrically supervised, zone annunciated, fire detection and alarm system as specified
Data, installation, operation and maintenance 4 & 8 Zone Fire Panels Zircon range BARDIC by Honeywell LED flashing LED Continuous FAULT DISABLE/TEST Power General Fault Sounder Fault/ Disable System Fault
Fire Alarm Control Panel Family Operating Manual CONTENTS System Description AH-03312 System Characteristics... Fire Signal Receiving Board Description-4L... Fire Signal Receiving Board Description-8L...
PK5500 v1.1 Installation Instructions 1 2 3 4 5 6 7 8 9 * 0 # WARNING: Please refer to the System Installation Manual for information on limitations regarding product use and function and information on
, GH Q631 0075 R0111 The 8-fold switch actuator is a DIN rail mounted device for insertion in the distribution board. It is connected to the EIB via a bus terminal. In the event of bus voltage failure,
EPSOLAR LS1024B / LS2024B/ LS3024B Solar Charge Controller USER MANUAL Thank you very much for selecting our product! This manual offers important information and suggestions with respect to installation,
DESCRIPTION MODEL 5010 DUAL CHANNEL SMOKE/FIRE DETECTION MODULE DESCRIPTION The SST Model 5010 Two Channel Smoke/Fire Detection Module provides two independent detection input channels for the NOVA-5000
AlarmSense 2-wire detection and alarm system Product Guide Contents What is AlarmSense? 2 The purpose of AlarmSense 4 How AlarmSense works 4 Alarmsense Features 5 Detector removal monitoring 5 Priority/non-priority
Installation and user manual for the FX range of fire panels 1, 2, 4 and 8 zone panels Contents Panel installation 3 Panel connections 3 Wiring connection drawings 4 Panel facilities 6 Installation check
Firmware version: 1.10 Issue: 7 AUTODIALER GD30.2 Instruction Manual Firmware version: 2.0.1 Issue: 0.6 Version of the GPRS transmitters configurator: 220.127.116.11 Date of issue: 07.03.2012 TABLE OF CONTENTS
FIRE ALARM SYSTEM reliable fire detection and alarm signalling system Satel fire alarm devices allow to implement reliable and modern systems responsible for fire safety. A combination of 20-year experience
CM705B - Universal Expander Module CM707B - Plug On Zone Expander Security Systems EN Security System CM705B CM705B - Universal Expander Module The CM705B universal expander provides a cost effective way
Automation System TROVIS 6400 TROVIS 6493 Compact Controller For panel mounting (front frame 48 x 96 mm/1.89 x 3.78 inch) Application Digital controller to automate industrial and process plants for general
PSDC 08128 v.1.2 PSDC 12V/8A/8x1A Power supply for up to 8 analog cameras PTC/TOPIC. EN** Edition: 9 from 25.05.2015 Supersedes the edition: 8 from 12.12.2014 the 8x 1A/12V DC power output for powering
INSTALLATION GUIDE Card Reader & Controller with KIM Swipe Reader for Solitaire 850 / 950 / 850L Learnlok PK2930 Card Reader and Controller Model 3.5 with KIM Swipe Reader Table of Contents 1. Features..................................
COMPUTHERM Q7 Programmable, digital room thermostat Operating Instructions GENERAL DESCRIPTION OF THE THERMOSTAT The COMPUTHERM Q7 type switched-mode room thermostat is suitable to regulate the overwhelming
EPGM1 HARDWIRED ZONE & PGM OUTPUT EXPANSION MODULE User manual v1.5 Compatible with: ESIM264 v7.09.02 and up. ESIM364 all versions. Main features: Hardwired zone expansion adding 16 additional zones per
HM-W536 Install Guide 9/13/2013 IMPORTANT SAFETY INSTRUCTIONS Warning - When using electrical devices, basic safety precautions should be followed to reduce the risk of fire, electrical shock or injury.
PD 100A Printing data system Operating instructions ENGLISH IMPORTANT: Read these instructions carefully before installing and using the device; do not forget following all additional information. Keep
AXIS 291 1U Video Server Rack Installation Guide About This Document This document describes how to install Axis blade video servers in the AXIS 291 1U Video Server Rack. Updated versions of this document
Documento: M-010.1-MGAS-ENG Edizione: 01/1997 Rev.: A.1 a Division of Pittway Corporation FRONT PANEL & VISUAL INDICATIONS GENERAL TROUBLE GENERAL PROGRAMMING IN PROGRESS ENABLE/ALARM/TROUBLE (ZONE 1 ALARM
USER MANUAL CHARGING STATIONS FOR ELECTRIC VEHICLES 204.CAxxx 204.CBxxx 204.UBxxx 204.WBxxx MP36289 1 ZP90856-GB-6 INDICE 1 SYSTEM DESCRIPTION... 4 1.1 MODES OF OPERATION... 4 2 USER INTERFACE... 6 2.1
CSP Combined Series Telephone Door Entry with Proximity Keyfob Access PD-094 Issue 3 General Description The CSP series systems are combined Door Entry Telephone and Proximity Access Systems. The entrance
MOUNTING AND OPERATING INSTRUCTIONS CF 51/55 1. Delivery CF 51/55-1 calculator with battery (optionally with mains power supply) - 1 wall mounting bracket - package with material for sealing, screws, wall
conventional system operation detection line operation Conventional detection systems normally operate on a 24VDC line. In the standby condition, the detectors will draw a low current, typically less than
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia
BRAVER UPS (Uninterruptible Power System) User s Manual Safety CAUTION! This UPS utilizes voltages that may be hazardous. Do not attempt to disassemble the unit. The unit contains no user replaceable parts.
Multi-application heat tracing Control and Monitoring in commercial and residential buildings Roof & Gutter de-icing sensor module Technical Information Approvals Module IP rating Ambient operating temperature
SECTION 13850 DETECTION AND ALARM PART 1 GENERAL 1.01 SUMMARY A. Section Includes 1. Control Panel 2 Associated Equipment B. Products Installed But Not Supplied Under This Section 1. Section 16140 - Wiring
RI-215A Operator s Manual Part Number: 71-0045RK Revision 0 Released: 10/3/05 Warranty RKI Instruments, Inc., warrants gas alarm equipment sold by us to be free from defects in materials and workmanship,
MILLENIUM Table of contents 1. INTRODUCTION 1 2. HARDWARE DESCRIPTION 2 3. INSTALLATION 5 4. CONNECTION 6 5. USER SAFETY AND PROTECTION OF EQUIPMENT 8 1. Introduction The MILLENIUM series has been designed
INSTALLATION GUIDE 1 Setting information MAC-558IF-E address(mac) MAC-558IF-E serial number(id) MAC-558IF-E code(pin) Indoor unit model name Indoor unit serial number Outdoor unit model name Outdoor unit
MODEL NUMBER: ISC910-1-0-GB-XX ISC911-5-0-GB-XX IXP20 CONTROLLER SPECIFICATIONS Working Environment Plastic Housing... Power ImproX IXP20 Controller INSTALLATION MANUAL Designed to work in an indoor (dry)
Programmable indoor transmitter of temperature T0118 Programmable indoor transmitter of atmospheric pressure T2118 Programmable indoor transmitter of temperature, relative humidity and other derived humidity
Inwall Room Temperature Unit TM11B01KNX TM11B11KNX TM11B21KNX Product Handbook Product: Inwall Room Temperature Unit Order Code: TM11B01KNX TM11B11KNX TM11B21KNX Application Program ETS: TM11B_1KNX Inwall
25 Years of Manufacturing Excellence Premier M Plus & Infinity 8 Conventional Fire Alarm Systems 007 Assessed to ISO 9001: 2008 Certificate number 330 Premier M Plus 8-24 Zone Conventional Fire Alarm Panel
Technical Description Transistor D.C. Chopper Controller Type GS 24 S Table of contents 1. Getting started guide 2. General information 2.1. Characteristics 2.2. Accessories 3. Information about the Machine
(68.52) X June 2000 Supercedes February 2000 xenex CONVENTIONAL FIRE DETECTION & ALARM SYSTEM.... we look @ business differently XENEX SYSTEM ARCHITECTURE Note: This schematic is for guidance only please
s 6 332 HOTEL SOLUTION Chipcard reader HCR3.2/.. Chipcard reader for hotel room access control Reads access code on chipcard Transfers access code to room controller Built-in optical display of messages
Important information: These instructions contain safety information, read and follow them carefully. Dialight will not accept any responsibility for injury, damage or loss which may occur due to incorrect
Communication bridge User Manual Copyright 2011 Studer Innotec SA - V1.0.1 Communication bridge : User Manual V1.0.1 Copyright 2011 Studer Innotec SA About the software This document applies to the software
68 Flexible, high specification system Choice of 1, 2, 4 or 8 zones Simple one-shot auto-reset user test facility Approved to EN54 Maintenance free poly switch circuit protection, with auto reset Class
SIGNAL REPEATER User manual v1.2 Compatible with: ESIM364 v02.07.11 and up EPIR3 v01.01.00 and up EWP1 v16 and up EKB3W v8 and up EW1 v33 and up EWS1 v16 and up EWD1 v19 and up EWK1 v19 and up EWS2 v15
Version: January 2004 Contents Alarm System Activation unit Deactivation unit Digital locking cylinder or Smart Relay 1.0 Method of Operation 4 1.1 General 4 1.2 Turning the Alarm System On 4 1.3 Turning
DC-8706K Auto Dial Alarm System User Guide Basic Contents: 1x the host unit; 1x wireless door (window) magnet; 1x wireless infrared detector; 2x remote control; 1x siren; 1x phone core; 1x AC to DC power
543-0032-00, 943-0032-00 User s Manual 1 Comfort Alert Diagnostics Faster Service And Improved Accuracy The Comfort Alert diagnostics module is a breakthrough innovation for troubleshooting heat pump and
Car Alarm Series 2 B 2 Buttons G22 SE (External - Shock Sensor) Version 3 Software 67 Plus www.geniuscaralarm.com 21 CAR ALARM GENIUS Series 2B 2 Buttons - G22 Se (External Shock Sensor) Module controlled
KNX Gateway RGK02-5023E-01 Table of contents Page 1 General Information 1.1 Technical data 5 1.2. Intended Use 6 1.3 Specifications 6 1.4 Compatibility 6 1.5 Scope of delivery 6 2 Information about the
DC/AC CLAMP METER Model CM-01 USERS MANUAL PROVA INSTRUMENTS INC. EN 61010-2-032 CAT II 600V CAT III 300V Pollution Degree 2 SYMBOLS showed on the clamp meter or in this manual: Caution, risk of danger.
RECOMMENDATION PCRA 009 June 2010 Rev. 0 Committee for Cathodic Protection and Associated Coatings Telemetry system for cathodic protection equipment of underground metal pipelines DISCLAIMER: The present
2 474 Heating Controller RVP300 Multifunctional heating controller for use in residential and non-residential buildings; suitable for weather-dependent flow temperature control of heating zones with or
transmitter (2 wire) / switch for continuous or On/Off Control Indication, monitoring, transmitting and continuous or On/Off control in one device Output signal 4...20 ma, 2-wire for continuous control
NELSON VOLTAGE MONITOR INSTALLATION & PROGRAMMING MANUAL CONTENTS GENERAL INFORMATION...3 INSTALLATION...3 FIELD WIRING...4 PROGRAMMING...4 Circuit Monitor Options...5 Power Frequency...5 Alarm Silence
Cell /Mobile phone home security system GSM HOME SECURITY SYSTEM Model : GSM-120 TABLE OF CONTENTS 1. FEATURES... 1 2. APPLICATION... 2 3. SPECIFICATIONS... 3 4. FRONT PANEL & LAYOUT DESCRIPTION...6 5.
ZONE ZONE 2 ZONE ZONE ZONE 5 ZONE 6 ZONE 7 ZONE Power PA XR2/ XR2+ Intruder alarm system Operating Instructions ZONE ZONE 2 ZONE ZONE ZONE 5 ZONE 6 ZONE 7 ZONE 0 2 5 6 7 9 Omit Prog Remote LED keypad 0
Installation and Operation Back-UPS 1250, 1300, 1500 Inventory bu001a Safety and General Information This unit is intended for indoor use only. Do not operate this unit in direct sunlight, in contact with
Ins-60005-GD-US Master Controller Installation Guide Mounting This housing should be fixed to the surface with suitable fasteners; screws and wall plugs are provided for this in the fitting kit. Also provided
IP Box Camera ACM-5711 Ver. 081016 Hardware User s Manual 0 0 PRECAUTIONS 1. Read these instructions All the safety and operating instructions should be read before the product is operated. 2. Heed all
, GH Q631 0076 R0111 2CDC 071 240 F0003 The Shutter Actuator Standard is used to control a maximum of four independent 230 VAC drives for positioning shutters, blinds, awnings and other hangings as well
TECHNICAL SPECIFICATIONS Page 1 of 19 FIRE DETECTION AND ALARM SYSTEM Scope Furnish a complete 24V DC analogue addressable, electrically supervised, zone annunciated, fire detection and alarm system as
K3 K4 www.sebury.com.cn Digital Keypad Use s Manual Contents Introduction Introduction Specifications Intramural Interface Circuit 3 Mounting 3 Wiring 5 Power UP 7 Engineer Programming Mode 7 The K3/K4
HONEYWELL COMMERCIAL FIRE/BURG PANEL UL LISTING REQUIREMENTS (Compiled from VistaFBPT Installation Instructions 800-09617V1 Rev A 11/12) UL864 (Commercial Fire) Compliance General Requirements The VISTA-128FBPT/VISTA250FBPT
INSTALLATION INSTRUCTION SECURITY SYSTEM ADP-CAN Introduction Motorcar security system ADP-CAN is for motorcars provided with CAN net. It is for the work with the motorcar factory security systems or remote
EDA-Z5008 & Z5020 Radio Fire Alarm System User Manual Electro-Detectors Ltd. Electro House, Edinburgh Way Harlow, Essex, CM20 2EG UK Tel: 01279 635668. Fax 01279 450185 Email: email@example.com
Short Form Catalogue Alarm Systems Reliable Supervision and Control Alarm Monitors and Indicators The SELCO product range includes a number of alarm monitors and indicator panels for use in numerous applications.
+ Installation and Operation Manual Back-UPS BX800CI-AS/BX1100CI-AS Inventory Safety and General Information bu001c This unit is intended for indoor use only. Do not operate this unit in direct sunlight,