1 OWNER S MANUAL SPLIT SYSTEM AIR CONDITIONER G Series Cooling A
2 O W N E R S MANUAL
3 Thank you for selecting Carrier! You can be justifiably proud of your purchase because the same pride in craftsmanship and engineering know-how that goes into Carrier equipment for cooling the Astrodome sports complex in Texas, the United States Capitol s Halls of Congress and countless other installations worldwide have been built into your unit. One of the pleasant benefits awaiting you with room air conditioning is that in addition to being cooled, the room air is filtered and dehumidified. This owner s manual is designed to help you be familiar with the many comforts and technological features your unit offers. Moreover, it contains vital information about maintenance, service and economical operation. Take the next few minutes to discover for yourself how to get the most in personal comfort and economical operation from your new Carrier room air conditioner. CONTENTS PRECAUTIONS BEFORE OPERATION UNIT DESCRIPTION REMOTE CONTROL DESCRIPTION REMOTE CONTROL PREPARATION UNIT OPERATION GENERAL OPERATION TIMER OPERATION DISCHARGE AIR LOUVER CONTROL EMERGENCY AND TEST OPERATION AIR CLEANING OPERATION CARE AND MAINTENANCE POINTS TO NOTE CLEANING THE FILTERS AND FRONT PANEL CLEANING THE MAIN UNIT AFTER-SEASON CARE TROUBLESHOOTING
4 O W N E R S MANUAL - 2 P R E C A U T I O N S Installing and servicing air conditioning equipment can be hazardous due to system pressure and electrical c o m p o n e n t s. Only trained and qualified service personnel should install or service this equipment. Untrained personnel can perform basic maintenance functions such as cleaning the coil and filters, and replacing f i l t e r s. All other operations should be performed by trained service personnel. When working on air conditioning equipment, observe precautions in the literature, tags and labels attached to the u n i t. Before performing service or maintenance operations on the system, turn off the main power of the unit. Electric shock can cause personal injury. Use the correct voltage. Using voltage other than specified will damage the unit. Check the power plug. If the power plug is not inserted tightly, or if there is any damage to the power cord, it could result in leakage or electric shock. Do not use the power cord as a means of turning off the unit.
5 O W N E R S MANUAL - 3 P R E C A U T I O N S Do not use flammable sprays near the unit. The unit can be damaged by gasoline, benzene, thinners, insecticides and other chemical agents. When unplugging the power plug, do not pull by the power cord. The power cord will get damaged and it can cause electric shock. To avoid the risk of serious electric shock, never splash the indoor and the outdoor unit with water. Do not put hands or objects into the discharge grille of outdoor unit. This unit has a fan running at high speed. It is very dangerous to touch the fan. Use only fuses of the proper amperage.
6 O W N E R S MANUAL - 4 P R E C A U T I O N S Be careful to keep the room temperature a comfortable level. Avoid continuous direct air flow to the occupant, especially in case of sleeping persons or hospital patients. Do not obstruct the front of the discharge grille of both units. This will block air flow, reduce the cooling effect and may result in unit malfunction. Ventilate the room when it becomes stuffy or filled with undesirable odors. Keep heat sources away from the unit, high temperature can cause damage. ;;; yyy ;;; yyy ;;; yyy ;;; yyy ;;; yyy Set a comfortable temperature. Very low or very high temperature setting considerably increases power consumption.
7 O W N E R S MANUAL - 5 P R E C A U T I O N S To circulate the room air only, operate at the FAN mode. In summer, if possible, prevent direct sunlight from entering the room, draw curtains or blinds. Use the timer correctly to maintain comfort conditions. ;;; yyy ;;; yyy ;;; yyy yy;; ;y ;; yy yy;; ;; yy;y ;; yy ;; yy ;; yy Please read this owner s manual carefully before operating the unit. It contains further important instructions for proper operation. ;; ;;
8 ON/OFF TEMP SLEEP O W N E R S MANUAL - 6 UNIT DESCRIPTION Indoor Unit BEFORE OPERAT I O N ROOM AIR INLET AIR FILTER ACTIVE CARBON FILTER & Option 1 : ELETROSTATIC FILTER Option 2 : PHOTO-CATALYST FILTER REMOTE CONTROL SIGNAL RECEIVER AIR SWING FLAP VERTICAL LOUVER ROOM AIR OUTLET POWER PLUG LCD REMOTE CONTROL OUTDOOR AIR OUTLET OUTDOOR AIR INLET INDOOR AND OUTDOOR CONNECTION DRAIN HOSE Outdoor Unit
9 O W N E R S MANUAL - 7 BEFORE OPERAT I O N Indoor Unit Display UNIT ON(Green): When the unit is switched on by the remote control, a green light will be displayed. TIMER(Orange) : When the unit is in reservation mode, an orange light will be displayed. Switch Panel EMERGENCY TEST EMERGENCY button : Can be used when the remote control is lost or inoperative. TEST button : Is only used by service men to test the unit operation. For the usage of E M E R G E N C Yand T E S Tbuttons, refer to EMERGENCY AND TEST OPERAT I O N,p. 2 0.
10 Names and Functions of the Buttons 1 ON/OFF BUTTON O W N E R S MANUAL - 8 BEFORE OPERAT I O N REMOTE CONTROL DESCRIPTION If you press this button, the unit will begin operation. Press the button again, and operation stops. ( You can hear a receiving beep. ) If you press this button immediately after turning off the unit, the compressor will not operate for 3 minutes to prevent overloading. ON/OFF A TEMP. SLEEP MODE FAN FLAP CLOCK EVERYDAY HOUR TIMER ON OFF SWING MINUTE RESERV. CANCEL TEMPERATURE SETTING BUTTONS If you set the desired room temperature, then the unit will maintain the room temperature at the set temperature. In COOL mode, if the room temperature is higher than setting, the compressor will automatically turn on to provide a cooling effect. On the other hand, if the room temperature is lower than the setting, the compressor will automatically turn off to stop cooling operation. However, the indoor fan will continue to circulate air even if the compressor is turned off. SLEEP TIMER BUTTON Press this button to set the SLEEP timer. ( Refer to p.18 ) OPERATION MODE SELECTING BUTTON Press this button to select the desired mode. In COOL mode, the unit will run at the normal cooling mode. In FAN mode, only the indoor fan will operate at the selected fan speed and circulate the room air. In DRY mode, the microcomputer of the unit controls the indoor fan motor and makes the outdoor unit automatically turn on and off according to the room temperature, which causes moisture to be removed more effectively.
11 O W N E R S MANUAL - 9 BEFORE OPERAT I O N 5 LR03(AM4)1.5V LR03(AM4)1.5V RST TA FAN SPEED SELECTING B U T TO N Press the button to select the desired fan speed of AUTO, LOW, MED or HIGH, and the indoor fan will operate at the selected fan speed. If you select A U T O, the fan speed will be controlled by the microcomputer of the unit. 6 FLAP CONTROL BUTTON Controls the discharge air flow direction up and down. ( Refer to p.19 ) On start up, the flaps open automatically according to the operation mode. If you press this button, the flap will move stepwise and the position will be displayed. If you press this button again, the unit operates at SWING mode. At operating mode SWING, the flap will swing up and down continuously. 7 ON/OFF TIMER AND CURRENT TIME BUTTONS 8 If you set the ON and OFF times, the unit will automatically turn on and off at the set times. ( Refer to pp ) If you press the CLOCK button during Timer operation, you will see the current time for 5 seconds. HOUR/MINUTE SETTING BUTTONS Adjust the current time (Refer Page 11) and the on/off times of timer operation, with these buttons. 9 RESERVATION AND CANCEL BUTTONS Press the RESERV. button to reserve the ON/OFF Timer and press the CANCEL button to cancel the reserved on/off time. ( Refer to pp ) 10 EVERYDAY TIMER BUTTON Press the EVERYDAY button and the on/off time you have reserved will be repeated until cancelled. ( Refer to pp ) 11 CURRENT TIME ADJUSTING BUTTON Press this button to adjust the current time. ( Refer to p.11 ) 12 RESET BUTTON Press this button when the remote control is not operating properly or after replacing batteries. ( Refer to p.11 ) 13 ADDRESS SWITCH If you have two indoor units in the same room, you can link one remote control with one indoor unit, and link the other remote control with the other indoor unit. ( Refer to p.11 )
12 O W N E R S MANUAL BEFORE OPERAT I O N Remote Control Display 5 Indicates the selected temperature. SWING 6 Indicates flap modes AUTO Automatic position User selected position A SWING Swing up and down 1 Indicates the selected operating mode. 7 Indicates the reserved status of SLEEP timer or EVERYDAY timer. COOL DRY FAN 8 Indicates the reservation time of ON timer and OFF timer or the current time. 2 Lights up when the signal from the remote control is transmitted. A receiving beep is heard from the unit. 9 Indicates the selected fan speed. 3 Lights up when the batteries must be replaced with new ones. When this mark appears, replace the batteries within a week. A AUTO LOW MED HIGH 4 Lights up when the unit is operating.
13 O W N E R S MANUAL - 11 BEFORE OPERATION REMOTE CONTROL PREPARATION Replacing Batteries 1 Remove the cover of the battery compartment at the back of the remote control by sliding it out in the direction of the arrow. 2 Remove the used batteries and insert new batteries. The remote control uses two alkaline batteries. ( 1.5V, LR03x2 ) 3 Press the R S Tbutton with a sharp object to reset the remote control before closing the cover of the battery compartment. RST TA RST TA LR03(AM4)1.5V LR03(AM4)1.5V LR03(AM4)1.5V LR03(AM4)1.5V RST TA LR03(AM4)1.5V LR03(AM4)1.5V N O T E Do not use the used batteries or batteries of different type. Such use may cause the unit to malfunction. Changing batteries should be done after turning off the unit. The average battery life during normal use is approximately one year. When the air conditioner does not operate normally after replacing thebatteries, remove the batteries, re f i t them and re p ress the R S Tbutton after 5 seconds. Setting Current Ti m e 4 Press the T Abutton with a sharp object and the current time indication symbol flashes. In the beginning, 6 : 0 0 A. M.will flash. 5 Set the current time with the hour and the minute buttons while the current time indication f l a s h e s. 6 Press the T Abutton again. The flashing will stop and the current time will be set. TEMP. MODE FAN FLAP CLOCK EVERYDAY HOUR MINUTE TIMER RESERV. CANCEL ON OFF RST TA RST TA LR03(AM4)1.5V LR03(AM4)1.5V LR03(AM4)1.5V LR03(AM4)1.5V Matching Address between Indoor Unit and Remote Contro l When two units are used in the same room, you can match the address of the remote control to that of the unit. Remove the lid of the battery case. Assign the address switch of one remote control as B. Press the RST button with a sharp object. Turn off the unit and pull out the power plug. Remove the front panel, Terminal block cover, and Frame grille. Pull out the PCB. Assign the address switch of one indoor unit as B. NOTE This function must only be performed by qualified service personnel.
14 O W N E R S MANUAL BEFORE OPERAT I O N Signal Receiving Use the remote control where its signals can reach the receiver of the air conditioner. (A distance of 5m is allowed) You can hear a beeping sound from the unit in the following cases, which indicates that the signal is received. 5m maximum CAUTION The air conditioner will not operate if curtains, doors or other materials block the signals from the remote control to the unit. If the infrared signal receiver on the unit is exposed to direct sunlight, the air conditioner may not work p r o p e r l y. Draw the curtains to avoid direct sunlight. Avoid spilling liquid onto the remote control or dropping it. This can cause deformation, discoloration and malfunction. A mounting bracket for the remote control is supplied with the unit. Install the mounting bracket on the wall 30 below the receiver of the unit.
15 O W N E R S MANUAL - 13 UNIT OPERAT I O N GENERAL OPERATION P R O C E D U R E 1 ON/OFF button Press this button and the COOL operation is indicated. A receiving beep is heard. The green UNIT ON lamp of the indoor unit display i l l u m i n a t e s. A ON/OFF SLEEP TEMP. MODE FAN FLAP CLOCK EVERYDAY HOUR MINUTE TIMER RESERV. CANCEL ON OFF MODE button Press this button to select the desired operation. C O O LFAN D R Y FAN SPEED button Press this button to select the desired fan speed. AUTO LOW MED H I G H T E M P. ( ) button Press these buttons to set the desired temperature. 5 FLAP button Press this button to control the desired air flow direction. 6 ON/OFF button Press this button to stop the unit operation. A receiving beep is heard. The UNIT ON lamp is extinguished. D RY OPERAT I O N Dry operation eliminates moisture economically by operating the compressor, indoor and outdoor fan motor intermittently, so that the room temperature is maintained at the set temperature.
16 O W N E R S MANUAL UNIT OPERAT I O N TIMER OPERAT I O N ON Ti m e r PROCEDURE 1 ON TIMER button Press this button. On start up, time is set at 6:00 A.M.. A 2 HOUR, MINUTE buttons Press these buttons to set the start-up time desired while the ON Timer symbol is flashing. Œ ON/OFF SLEEP TEMP. MODE FAN FLAP CLOCK EVERYDAY HOUR MINUTE 3 R E S E RV. button Press this button when pointing the remote control towards the receiver of the indoor unit. A receiving beep is heard. TIMER lamp of the indoor unit illuminates. TIMER ON OFF RESERV. CANCEL Ł Ø 4 MODE, FAN, FLAP and TEMP. buttons Set the desired operation mode with these buttons. About ON Timer When the ON Timer is set, the unit monitors the room temperature for 1hour before the set time to make sure the room condition is reached by the reserve time. The actual on time of the unit is earlier than the reserved on time by 0 to 40 minutes according to the difference between room temp. and set temp. NOTE The current time is not indicated during the reservation of ON/OFF Timer. When you want to know the current time, press the CLOCK button and you will see the current time for 5 seconds. If you reserve the ON Timer during operation, the unit will operate continuously.
17 O W N E R S MANUAL UNIT OPERAT I O N OFF Ti m e r P R O C E D U R E 1 OFF TIMER button Press this button. On start up, the time is set at 2:00 A.M.. A 2 HOUR, MINUTE buttons Press these buttons to set the stop time desired while the OFF Timer symbol is flashing. ON/OFF SLEEP TEMP. MODE FAN FLAP CLOCK EVERYDAY HOUR MINUTE TIMER RESERV. CANCEL ON OFF 3 R E S E RV. button Press this button by pointing the remote control towards the receiver of the indoor unit. A receiving beep is heard. TIMER lamp of the indoor unit illuminates.
18 O W N E R S MANUAL UNIT OPERAT I O N Combination of ON, OFF and EVERY D AY Ti m e r P R O C E D U R E For example, when you want the operation to start at 5:30 P.M. and stop at 10:30 P.M Reserve the ON Timer at 5:30 P.M.. Reserve the OFF Timer at 10:30 P.M.. Set the operation mode as desired. Or when you want to stop the operation at 10:30 P.M. and start again at 7:30A.M. with the same condition. 1 2 Reserve the OFF Timer at 10:30 P.M. during operation. Reserve the ON Timer at 7:30 A.M.. When you want to start operation at 5:30 P.M. and stop at 10:30 P.M. everyday with the same operating condition Reserve the ON Timer at 5:30 P.M.. Reserve the OFF Timer at 10:30 P.M.. Press the EVERYDAY button and RESERV. button. NOTE Refer to pp for the setting method and refer to p.17 for the canceling method of the ON, OFF and EVERYDAY Timers. In the ON and OFF Timer operation, the earlier setting compared to the current time will be applied first. The EVERYDAY Timer can be selected in case of a combination of the ON and OFF Timer reservation or ON and SLEEP Timer reservation. You can change the ON/OFF reservation time when the EVERYDAY Timer reserved.
19 O W N E R S MANUAL UNIT OPERAT I O N Cancellation of ON, OFF and EVERY D AY Ti m e r P R O C E D U R E ON/OFF A SLEEP 1 2 Press the ONTIMER button to cancel the ON Timer or press OFF TIMER button to cancel the OFF Timer. To cancel the EVERYDAY Timer reservation, press the EVERYDAY, ON TIMER or OFF TIMER button. Press the CANCEL button by pointing the remote control towards the receiver of the indoor unit. A receiving beep is heard. TIMER lamp of the indoor unit lights off. TEMP. MODE FAN FLAP CLOCK EVERYDAY HOUR MINUTE TIMER ON OFF RESERV. CANCEL NOTE If you cancel the ON Timer or OFF Timer reservation while EVERYDAY Timer is reserved, EVERYDAY Timer will be automatically canceled. When the electricity fails while EVERYDAY Timer is reserved, EVERYDAY Timer reservation will be canceled. Reserve the EVERYDAY Timer again after the electricity comes on. The current time will not be indicated and the TIMER lamp of the indoor unit will be on if either the ON Timer or the OFF Timer is reserved.
20 O W N E R S MANUAL UNIT OPERAT I O N Sleep Ti m e r This function enables the user to automatically switch off the unit. P R O C E D U R E If you want to stop the operation after 3 hours from now, ON/OFF A TEMP. SLEEP 1 Press the SLEEP button 3 times 3:hr will be displayed and the SLEEP signal will be f l a s h i n g. After 5 seconds, the stopping time will be displayed. The unit operates in sleep mode for 3 hours and will switch off at the end of the 3 hours. To change the reserved time or to cancel, press the SLEEP Button again. 1:hr 2:hr 3:hr 7:hr 9:hr C a n c e l 2When the SLEEP Timer is set, the unit will control the set temperature to avoid overcooling in Cool or Dry operation. Set temperature is changed as shown below. SLEEP SLEEP S E T T E M P T I M E ( M I N.) SET TIME ( For Cooling or Dry mode ) N O T E When the SLEEP timer is set, the luminosity of the unit lamps will be dimmed so as not to interrupt the sleep. The SLEEP timer can be combined with the ON timer. ( Refer to p.16 for combination )
21 O W N E R S MANUAL UNIT OPERAT I O N DISCHARGE AIR LOUVER CONTRO L Up and Down Contro l The air discharge direction can be controlled to swing up and down and can be fixed at a preferred position or at automatic position by the remote control. AUTO SWING Remote Control Swing Range Auto Position If you select the Flap position using the FLAP button in the remote control, the flap in the unit will move to that position automatically. Once you select the position, the unit remembers that position and whenever you turn on the unit, the flap will be positioned to that position. If you select SWING, the flap will swing up and down. If you select AUTO, the flap will position itself to the preset position according to the operation mode. NOTE Always use the remote control to adjust the flap position, otherwise it may cause abnormal operation. Please turn off the unit and turn it on again when you manually adjust the flap out of range. Left and Right Contro l If you want to adjust the direction of the discharge air left or right, adjust the vertical louver with the handle after opening the flap. HANDLE NOTE Please do not fix the flap at position for a long time, as this position minimizes air circulation resulting in uneven room temperature. Avoid the discharge air being directed towards the occupants for a long period of time. Do not adjust the flap by the hand during SWING operation because it may damage the air swing mechanism.
22 O W N E R S MANUAL - 20 UNIT OPERAT I O N EMERGENCY AND TEST OPERAT I O N EMERGENCY TEST Emergency Operation When the remote control is lost, damaged or the battery is discharged, the EMERGENCY button can be used to run the unit. Press the EMERGENCY button at the off mode condition. - The unit operates automatically according to the room temperature the cooling operation. If you want to stop the emergency operation, push the EMERGENCY button again or operate the remote c o n t r o l. The setting conditions of emergency operation are as follows: - Operation mode : COOL - Preset temperature : 24 - Fan speed : AUTO - Timer mode : Disable - Discharge air direction : Horizontal position Test Operation This operation is used for checking after unit installation. Press the TEST button. Press the TEST button once more after checking to activate the remote control. If there is any input signal ( remote control signal or EMERGENCY button press ) during test operation, the TEST mode will change to the input signal mode. The setting conditions of the test operation are as follows : - Operation mode : COOL - Fan speed : HIGH - Timer mode : Disable - Discharge air direction : SWING
23 O W N E R S MANUAL UNIT OPERAT I O N AIR CLEANING OPERATION Information for filters Filters Air filters O p t i o n1:active carbon filter/photo-catalyst filter Option 2:Active carbon filter/electrostatic filter Air filters eliminate dust and lint Optional Active carbon filter/photo-catalyst filter effectively eliminates odor and cigarette smoke in the room air. Optional Active carbon filter/electrostatic filter is particularly effective in eliminating odor and micro scopic dust. ACTIVE CARBON FILTER (Black color, OPTIONAL) PHOTO-CATALYST FILTER (Blue color, OPTIONAL) or ELECTROSTATIC FILTER (White color, OPTIONAL) STANDARD AIR FILTER Life time of filters The life of above filters varies according to the amount of cigarette smoke, room size and the operating time. Air filters can be cleaned with a vacuum cleaner or rinsed under running water after using a month. (Refer to CLEANING THE FILTERS AND FRONT PANEL,p.23.) The life time of optional Active carbon filter is about 2 years and that of optional Electrostatic filter is about 3 months. These filters cannot be recycled. The life time of optional Photo-catalyst filter is about 2 years. This filter can be washed under running water and can be refreshed by exposing under direct sun light. Exposed time is 6 hours after using 3 months. (Refer to CLEANING THE FILTERS AND FRONT PANEL,p.23)
24 O W N E R S MANUAL - 22 POINTS TO NOTE M O D E I N D O O R O U T D O O R C O O L 21 ~ 32 c 21 ~ 43 c D RY Time Delay CARE AND MAINTENANCE Operating Condition Temperature ranges which are suitable for unit operation are as follows: 17 ~ 32 c 12 ~ 43 c When the unit operates above or below these conditions for a long time, system diagnostics may detect a malfunction and the unit will not operate properly. If the unit operates for a long time under abnormal situation of extremely high humidity, condensed water may drip from the unit. In normal operation, there is a time delay of three minutes between compressor turning off and turning back on including initial power up. Minimum Operation Time After compressor turns on, it will operate for 3 minutes regardless of temperature condition. Auto Recovery When the electricity fails while the unit is operating, the unit memorizes the operating condition, and it will start operation automatically when the electricity is restored. When you leave home during an electricity failure, please unplug the power cord, or the unit will automatically restart in your absence. F rost Prevention of Indoor Unit When the unit is operates at a low ambient temperature, frost may appear on the indoor coil. When the indoor coil temperature is below 0, the microcomputer makes the compressor stop to protect the unit from frost. Normal Operation Any of the following can occur during normal operation: A sound like a GURGLE can sometimes be heard during operation or when the unit stops. - It is the sound of the refrigerant flowing through the unit. Bad smells can come from the unit. - Smells such as smoke or cosmetics can accumulate while room air circulates through the unit. - Cleaning the filters will reduce this problem. UNIT ON lamp on the indoor unit displays flashes and no air comes from the unit. - It indicates malfunction of the unit and the compressor will stop operating. A BAK-BAK sounding noise can sometimes be heard during operation or when the unit turns on. - It is the sound of plastic expanding due to an abrupt temperature change.
25 O W N E R S MANUAL CARE AND MAINTENANCE CLEANING THE FILTERS AND FRONT PANEL Cleaning the Air Filter Turn off the unit and pull out the power plug. Clean the air filters once a month. 1 Lift the front panel and pull the air filters downward. 2 Clean NOTE the filters with a vacuum cleaner. 3 Rinse the filters under running water, and dry them completely, and then refit them correctly into their guides. R e f reshing the optional Photo-catalyst filter 1 2 Lift the front panel and pull the Blow off the dust from the filter optional Photo-catalyst filter with fresh air or wash the filter downward. under running water. 3 Expose under direct sun light for 6 hours and refit it correctly into its guide. Washing the Front Panel Turn off the unit and pull out the power plug. Clean the front panel if it becomes dirty and spotted. Front panel is removable. 1 Lift the front panel up to the top of the unit. Then separate the front panel from the unit. 2 Rinse NOTE the panel under running water, and dry it completely in a shaded area. 3 Refit it correctly. Installation procedure is reverse to the removal procedure.
26 O W N E R S MANUAL CARE AND MAINTENANCE CLEANING THE MAIN UNIT Use only a damp soapy towel. Do not pour water onto the unit, and do not use petrol, solvents or abrasive powder which may result in damage of the unit. ;; ; ; NOTE When cleaning the unit, first turn it off and pull out the power plug. AFTER-SEASON CARE 1 Clean the filters and refit them into the unit. 2 If the unit is to be switched off for an extended period, run the unit on FAN only for two hours to dry inside of the unit. 3 Clean the indoor and outdoor unit, and wrap the outdoor unit with a protection cover.
27 OWNER fls MANUAL - 25 TROUBLESHOOTING Trouble Check Points Action Check that the power cord is plugged into the wall outlet. Insert the power cord into the wall outlet. Unit does not Has the circuit breaker tripped or has the Reset the circuit breaker or replace the operate fuse blown? fuse with the specified replacement fuse. Has there been a power failure? Does the UNIT ON lamp flash on and off? Is the voltage too low? Is the filter blocked with dust? Has the temperature been set properly? Restart operation when power is resumed. Call your service representative. Confirm the available voltage. Clean the air filter. Check and reset it if necessary. Cooling is Are the windows or doors open? Close the windows and doors. abnormally low. Is anything obstructing the outdoor unit? Remove the obstruction. Unit stops during operation. Is the fan speed too low? Is the operation mode FAN or DRY? Is the OFF timer operating? Has passed the set time of sleep timer? Change the fan speed selection. Change to cooling operation or reset the temperature. Restart the unit operation. Restart the unit operation. If the above actions do not correct the operation, consult the dealer from whom you bought the unit.
OWNER S MANUAL Split Type Room Air Conditioner KSWM units Please read the operating instructions and safety precautions carefully and thoroughly before installing and operating your room air conditioner.
R-410A Duct Free Split System Air Conditioner and Heat Pump Product Family: DFS4(A/H)-System, DFC4(A/H)3-Outdoor, DFF4(A/H)H-Indoor Please read the operating instructions and safety precautions carefully
ENGLISH INSTRUCTION & INSTALLATION MANUAL DUCTLESS MINI SPLIT AIR CONDITIONING SYSTEMS Céliera Corporation. All rights reserved. Unauthorized duplication, reproduction prohibited. CONTENTS SAFETY PRECAUTIONS...
Before using your air conditioner, please read this manual carefully and keep it for future reference. SPLIT- TYPE ROOM AIR CONDITIONER Read This Manual Inside you will find many helpful hints on how to
Table of Contents Important Safeguards...2 Product Layout...3 Preparing for Use...4 Air-conditioning without installation...4 Air-conditioning with installation...5 Control Panel...6 Operating from the
SPLIT TYPE AIR CONDITIONER INDOOR UNIT/OUTDOOR UNIT MODEL RAS-60YHA/RAC-60YHA OUTDOOR UNIT INDOOR UNIT RAC-60YHA RAS-60YHA Instruction manual Page 1~26 To obtain the best performance and ensure years of
Portable Air Conditioner Owner's Manual Model:3 in 1 12,000 Btu/h Series 3 Please read this owner s manual carefully before operation and retain it for future reference. CONTENTS 1. SUMMARY...1 2. PORTABLE
SPLIT WALL MOUNTED TYPE AIR CONDITIONERS OWNER'S MANUAL Thank you for choosing our Air Conditioner. Please read this OWNER'S MANUAL carefully prior to use and keep it for further reference. CONTENTS Contents
User Manual Room Air Conditioners R410A Split Type Y Series DC INVERTER ECO940SD ECO120SD ECO1840SD Please read this installation manual completely before installing the product. When the power cord is
Please read this owner s Manual carefully before operating the unit. - Cooling - Heating - Dehumidifying - Fan TABLE OF CONTENTS INTRODUCTION 2 IMPORTANT SAFEGUARDS...2 PACKAGE CONTAINS..2 NAMES OF PARTS.3
NewAir AC-10100E / AC-10100H Portable Air Conditioner Owner s Manual PLEASE READ AND SAVE THESE INSTRUCTIONS ELECTRICAL SAFETY This appliance is for indoor use only. Always turn off the unit and unplug
WNER S MANUAL Inverter Single Zone Ductless Mini Split Heat Pump VMH 30/36 Series Version C Heat Controller, Inc. 1900 Wellworth Ave. Jackson, MI 49203 (517)787-2100 www.heatcontroller.com wner s Manual
REMOTE CONTROL MANUAL ENGLISH CONTENT PRECAUTIONS...1-2 USING THE REMOTE CONTROL UNIT...3 OPERATION...4-9 Thank you for purchasing our Room Air Conditioner. Before using your air-conditioner, please read
AIRREX AIR CONDITIONER USER S MANUAL HSC-24A Thank you for purchasing an AIRREX AIR CONDITIONER. BEFORE operation please read this user s manual carefully. Keep this manual readily available. It is ESSENTIAL
OWNER S MANUAL AIR CONDITIONER (SPLIT TYPE) For general public use ENGLISH EN Indoor Unit RAS-07PKVP-E RAS-10PKVP-E RAS-13PKVP-E RAS-16PKVP-E RAS-18PKVP-E RAS-07PKVP-ND RAS-10PKVP-ND RAS-13PKVP-ND RAS-16PKVP-ND
OWNER S MANUAL VMH 09/12/18/27/36 InverterFlex Version C Single, Dual, Tri or Quad Zone Ductless Mini-Split System Heat Controller, Inc. 1900 Wellworth Ave. Jackson, MI 49203 (517)787-2100 www.heatcontroller.com
DAIKIN ROOM AIR CONDITIONER Operation Manual OPTIONAL SLENDER REMOTE CONTROL BRC944A2B READ BEFORE OPERATION Safety Precautions...2 Names of Functions of Parts...4 Preparation before Operation...5 OPERATION
R40A SPLIT SERIES DC INVERTER Models ECO905SINV ECO205SINV ECO805SINV Read This Manual Inside you will find many helpful hints on how to use and maintain your air conditioner properly. Just a little preventative
Air Conditioner Water Heater - A Product of HotSpot Energy LLC PLEASE READ THIS BEFORE YOU INSTALL THE UNIT 1. This air conditioner must be installed and/or repaired by a qualified technician. If you perform
USER S MANUAL Duct Type Series MH MH FEEA Series FUEA Series ENGLISH ESPAÑOL PORTUGUÊS E HNIKA DEUTSCH ITALIANO FRANÇAIS Free Joint Multi Air Conditioner (Cooling and Heating) E S F I P D G DB98-29565A(1)
Use and Care Manual Model CPA12KH AIR CONDITIONER Introduction Thank you for choosing this air conditioner to provide you and your family with all of the "Home Comfort" requirements for your home, cottage
OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. TYPE : WALL MOUNTED P/NO : MFL67657205 www.lg.com ITALIANO ESPAÑOL FRANÇAIS
DAIKIN ROOM AIR CONDITIONER Operation Manual MODELS FT50GAVEA FT60GAVEA FTY50GAVA FTY60GAVA ENGLISH ESPAÑOL TURKISH CONTENTS READ BEFORE OPERATION Safety Precautions... Names of Parts Indoor unit, Opening
HIGH-WALL DUCTLESS AIR CONDITIONING SYSTEM Models: GWC09MA-A3DNA3A GWC12MB-A3DNA3A GWC09MB-D3DNA3D GWC12MB-D3DNA3D GWC18MC-D3DNA3D GWC24MD-D3DNA3D GWC30LB-D3DNA3E GWC36LB-D3DNA3A Thank you for choosing
F566272 Operating Instructions Air Conditioner CS-C18FFH CS-C28FFH CU-C18FFH CU-C28FFH ENGLISH Before operating the unit, read these operating instructions thoroughly and keep them for future reference.
DAIKIN ROOM AIR CONDITIONER Operation Manual MODELS FT50BSG FT60BSG CONTENTS READ BEFORE OPERATION Safety Precautions... 2 Names of Parts Indoor unit, Opening the front grille... 5 Remote controller, Outdoor
NewAir AC-10000E, AC-10000H Portable Air Conditioner Owner s Manual PLEASE READ AND SAVE THESE INSTRUCTIONS BEFORE USE GENERAL SAFETY INSTRUCTIONS: ALWAYS OPERATE THE UNIT IN AN UPRIGHT POSITION AND PLACE
Multi System 16 SEER, Inverter System 9,000 to 18,000 BTU/Hr Single Split 4MXW8-A 4TXM6-A March2013 42 Warnings and Cautions Warnings and Cautions. Notice that warnings and cautions appear at appropriate
ENGLISH FRANÇAIS ESPAÑOL OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. TYPE : Room Air Conditioner P/NO : 3828A20434H www.lg.com
OPERATION MANUAL Split System Ducted Air Conditioner To suit Daikin FDY "F" Series and FD "F" Series AIR CONDITIONER A hr o C (and other models incorporating BRC1B62/52 Remote Controller) Dear Owner, Thank
TWD-0813-033 Neo Manual REV:Layout 1 9/27/13 11:13 AM Page 1 GREE ELECTRIC APPLIANCES, INC. www.greecomfort.com LIMITED WARRANTY GREE distributor (hereinafter Company ) warrants this product against failure
LG Multi Type Air Conditioner OWNER'S MANUAL LG Prior to installation, this airconditioning unit must be submitted for approval by the utility service which provides electricity (EN 61000-2, EN 61000-3
NewAir AC-14100E / AC-14100H Portable Air Conditioner Owner s Manual PLEASE READ AND SAVE THESE INSTRUCTIONS PARTS LIST Front Back FIG.5 FIG.6 1. Control panel 2. Carrying handle 3. Water tank 4. Casters
Website: www.andico.com.au Service manual CAUTION - BEFORE SERVICING THE UNIT, READ THE SAFETY - PRECAUTIONS IN THIS MANUAL. - ONLY FOR AUTHORISED SERVICE PERSONNEL. MODELS: MPK1-09CR-QB8 MPK1-12ER-QB6
USER INSTRUCTIONS FOR GET PORTABLE 12k BTU AIR CONDITIONER MODEL No. GPACU12HR CONTENTS Introduction Safety Notes Identification of parts Installation instructions Operation instructions Maintenance Troubleshooting
HIGH-WALL DUCTLESS AIR CONDITIONING & HEATING SYSTEM Models: GWH09MA-A3DNA3A GWH12MB-A3DNA3A GWH09MB-D3DNA3D GWH12MB- D3DNA3D GWH18MC-D3DNA3D GWH24MD-D3DNA3D GWH30LB-D3DNA3E GWH36LB-D3DNA3E Thank you for
PORTABLE AIR CONDITIONER MAC 7500 Owner s Manual Air Conditioner Dehumidifier Oscillating Fan Please read this owner s manual carefully before operating the unit. POWERED BY 66126113.p65 17 INTRODUCTION
All about the Use &Care of your Split Type Room Air Conditioner Refer to Page 2 for table of contents. www.frigidaire.com USA 1-800-944-9044 www.frigidaire.ca Canada 1-800-265-8352 66129904886 (June 2009)
MODE ALARM Portable Air Conditioner OWNER S MANUAL Read these instructions before use 8 Model: MF08CESWW Voltage rating: 115V~60Hz Power rating : 800W Customer Support : 1-800-474-2147 For product inquiries
Pocket Manual Service Diagnosis SPLIT & MULTI Service Diagnosis SPLIT & MULTI 1. Troubleshooting with LED...5 1.1 Indoor Unit... 5 1.2 Outdoor Unit... 10 2. Troubleshooting by Symptoms...11 2.1 Air conditioner
Fan Cool Furnace *Heat Pump or Heat Strip On/Off F Single Zone LCD Thermostat Operating Instructions MODEL 3313192.XXX Cool/Furnace 3313193.XXX Cool/Furnace/Heat Pump 3313194.XXX Cool/Furnace/Heat Strip
Portable Air Conditioner OWNER S MANUAL Read these instructions before use 8 Model: MN12CES / MN10CESWW Voltage rating: 120V~60Hz Power rating : 1100W (MN12CES) Power rating : 900W (MN10CESWW) Customer
USER INSTRUCTIONS FOR 10 LITRE PORTABLE DEHUMIDIFIER MODEL NO. DHMD102 THANK YOU FOR CHOOSING YOUR NEW DEHUMIDIFIER. BEFORE USING THE UNIT READ THESE INSTRUCTIONS FULLY AND RETAIN THEM FOR FUTURE REFERENCE
Portable Air Conditioner OWNER S MANUAL Read these instructions before use Model: MM14CCS Customer Support : 1-800-474-2147 Voltage rating: 115V~60Hz Power rating : 1400W For product inquiries or support
TEMPORARY SWITCH SPLIT TYPE AIR CONDITIONER INDOOR UNIT/OUTDOOR UNIT MODEL RAS-50FH7/RAC-50YH7 ENGLISH DEUTSCH FRANÇAIS INDOOR UNIT ITALIANO HITACHI RAS-50FH7 OUTDOOR UNIT DC INVERTER ESPAÑOL PORTUGUÊS
Portable Evaporative Air Cooler OWNER S MANUAL Read and save these instructions before use Model: CL30XC Power rating: 250 Watts Voltage rating: 230 Volt, 50Hz Made in P.R.C. QUICK START GUIDE Fill with
SERVICE INSTRUCTION SPLIT TYPE ROOM AIR CONDITIONER Universal Floor / Ceiling Duct / Cassette Wall Mounted / Floor type INVERTER MULTI R410A Models Indoor unit Outdoor unit AB*14LBAJ AB*18LBAJ AB*F14LAT
Before using your air conditioner, please read this manual carefully and keep it for future reference. SPLIT - TYPE RM AIR CNDITINER Read This Manual Inside you will find many helpful hints on how to use
DAIKIN ROOM AIR CONDITIONER Operation Manual MODELS FTKD50BSG FTKD60BSG FTKD7BSG CONTENTS READ BEFORE OPERATION Safety Precautions... Not for multi System... 4 Names of Parts Indoor unit, Opening the front
FRANCAIS ESPAÑOL OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. TYPE : WALL MOUNTED LSN-LSU-90-120HYV Applied Models : AS-W093MMM9
AIR CONDITIONER Duct Type OPERATING MANUAL KEEP THIS MANUAL FOR FUTURE REFERENCE P/N9374379460 CONTENTS SAFETY PRECAUTIONS... 1 FEATURES AND FUNCTIONS... 3 NAME OF PARTS... 4 PREPARATORY OPERATION... 5
Comfort Control Center 2 Thermostat Operating Instructions Programmable Thermostat MODEL 3312026.XXX With Dehumidify 3312024.XXX With Out Dehumidify TABLE OF CONTENTS About your new thermostat Features...2
Visit us at : http://www.lgservice.com LG Wireless Remote Controller Owner's & Installation Manual Models: PQWRHSF0 PQWRCSF0 LG ENGLISH ITALIANO ESPAÑOL FRANÇAIS DEUTSCH IMPORTANT Please read this installation
SERVICE & MAINTENANCE MANUAL Specifications are subject to change without notice according to Carrier Policy of continuous development. 03502566 Revision : (0) - 2009 TABLE OF CONTENTS PAGE NO. 1. Precautions
Visit us at http://www.lgservice.com LG Room Air Conditioner OWNER'S MANUAL Dear Owner Thank you for installing LG air conditioner. Your best choice guarantees you a great performance and service to make
SAFETY PRECAUTIONS Do not install the appliance if it is connected to the power supply. The Installation and service/repair must be performed by a qualified technician, in compliance with the producer's
SVENSKA NORSK SUOMI DANSK OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. TYPE : WALL MOUNTED P/NO : MFL67641301 www.lg.com
Troubleshooting Your Refrigerator With conscientious care, a refrigerator will perform for years with little or no repairs. Refrigerators are categorized according to the way frost is removed from them.
WHYNTER ECO-FRIENDLY 14,000 BTU PORTABLE AIR CONDITIONER WITH HEATER o MODEL#: ARC-14SH Instruction Manual Congratulations on your new WHYNTER product. To ensure proper operation, please read this Instruction
Contents PREPARING YOUR AIR CONDITIONER Safety Precautions..................................................... 3 View of the Indoor unit................................................ 8 RECOMMENDATIONS
AIR CONDITIONER REMOTE CONTROLLER ILLUSTRATION AM-6CPR(N) The design and specifications are subject to change without prior notice for product improvement. Consult with the sales agency or manufacturer
SPLIT TYPE AIR CONDITIONER INDOOR UNIT MODEL RAK-18QH8(W) RAK-25QH8(W) RAK-35QH8(W) RAK-50QH8(W) RAK-18QH8(B) RAK-25QH8(B) RAK-35QH8(B) RAK-50QH8(B) INDOOR UNIT ESPAÑOL ITALIANO FRANÇAIS DEUTSCH ENGLISH
OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. Type : Floor Standing Type(Console) www.lg.com ENGLISH ITALIANO ESPAÑOL FRANÇAIS
JH026EAV Series JH035EAV Series Air Conditioner user manual imagine the possibilities Thank you for purchasing this Samsung product. To receive more complete service, please register your product at www.samsung.com/global/register
ENGLISH FRANÇAIS ESPAÑOL OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. TYPE : WALL MOUNTED P/NO : MFL67502019 http://www.lghvac.com
Portable Air Conditioner OWNER S MANUAL Read these instructions before use Model: MM14CHCSCS Voltage rating: 120V~60Hz Power rating : 1400W(Cooling) Power rating : 1350W(Heating) Customer Support : 1-800-474-21477
Taurus Series YORK Window Air Conditioners IOM IOWRCAG50220711A1 Warning 1. Before using the Air conditioner please read the instructions carefully. They contain important advise about the installation,
CONTENTS Operation and maintenance Notices for operation Notices for use Names and functions of each part Operation of wireless remote control Emergency operation Clean and care Troubleshooting Installation
ENGLISH FRANÇAIS ESPAÑOL OWNER S MANUAL AIR CONDITIONER Please read this manual carefully before operating your set and retain it for future reference. TYPE : WALL MOUNTED P/NO : MFL63288101 www.lge.com
DC Inverter Portable Air Conditioner Model VS12 12,000 BTU Introducing The World s Most Efficient Portable Air Conditioner VS12 User & Installation Manual Version 1.0 1 Read This Manual Inside you will
AIR CONDITIONER (SPLIT TYPE) Indoor Unit Not accessible to the general public Model name: 4-way Air Discharge Cassette Type RAV-SM564UT-E RAV-SM804UT-E RAV-SM1104UT-E RAV-SM1404UT-E Air conditioner (Split
AIR CDITIER REMOTE CTROLLER ILLUSTRATI CS5-RA 005500 005 Thank you very much for purchasing our air conditioner Please read this owner's manual carefully before using your air conditioner CTENTS Handling
AIR CONDITIONER (SPLIT TYPE) Owner s Manual Indoor Unit Model name: High Wall Type RAV-SM07KRTP-E RAV-SM407KRTP-E For commercial use Owner s Manual English Original instruction ADOPTION OF NEW REFRIGERANT
SPLIT-TYPE AIR CONDITIONERS OPERATING INSTRUCTIONS INDOOR UNIT MSZ-A18YV MSZ-A24YV MSZ-A26YV MSZ-A30YV For customers Thank you very much for purchasing this Mitsubishi room air conditioner. To use this
VERY IMPORTANT! MODEL: GDC-AC9RW / GDC-AC9RCS GDC-AC9RCW / GDC-AC12RW GDC-AC12RB / GDC-AC12RCB GDC-AC12RCW INSTRUCTIONS FOR USE PORTABLE AIR CONDITIONER Do not install and use your portable air conditioner
Operating Instructions Split System Air Conditioner * Shows U1 type Model No. Indoor Units Type Indoor Unit Type 26 36 42 Remarks U1 4-Way Cassette S-26PU1U6 S-36PU1U6 S-42PU1U6 with Wired Remote Controller: