3 3 Content Technical specification.. 4 Performance curve.5 Outline & dimension of indoor unit..10 Outline & dimension of outdoor unit 11 Exploded view of indoor unit 12 Spare parts list of indoor unit 13 Exploded view of outdoor unit.. 14 Spare parts list of outdoor unit. 15 Circuit Diagram..16 PCB Function Manual 17 TECHNICAL SPECIFICATION Content AC-S13CG
4 4 Function Cooling Power supply 1Ph 220~230V-50Hz Capacity (BTU/h) Rated input (W) 1195 Rated current (A) 5.33 Air flow (m 3 /h) 480 Dehumidifying volume (L/h) 1.4 EER(W/W) 2.5 Motor fan speed(r/min) 1190/1090/990 Output power(w) 14 Fan type/piece Cross flow fan-1 Diameter-length(mm) 97mm x 583 Evaporator Aluminum fin-copper tube Row-fin distance(mm) Working area(m 2 ) 0.14 Indoor unit Swing motor MP24GA Input/Power(W) 2 Fuse(A) Controller 3.15A Transformer 0.2A Working capacitor(uf) 1 Noise(dB(A)) < 40 / = 40 Dimension (width-height-depth)(mm) 770 x 250 x 180 Net weight(kg) 8.5 Input power W 1179 Current A 5.33 L.R.A. A 29 Throttling method Capillary Compressor RH207VHKC Starting method Capacitor Starting Working temp. <115 o C / =115 o C Condenser Aluminum fan-copper tube Pipe-diameter 9.52 Outdoor unit Row-fin distance (mm) Working area 0.4 Fan motor speed(rpm) 48/880 Type-piece Axial fan-1 Diameter(mm) 400 Defrosting method Auto defrost Noise(dB(A)) 56 Dimension (width-height-depth) 848 x 540 x 320 (mm) Net weight(kg) 40 Refrigerant charge(kg) R22/0.8 Length (m) 4 Liquid pipe 6(1/4 ) Connecting Outer diameter Gas pipe 12(1/2 ) pipe Height(m) 5 Max distance Length(m) 10 PERFORMANCE CURVE The change relation between low pressure, operation current and temp.
5 5 Cooling operation condition: In testing, indoor and outdoor have same work condition. Heating operation Indoor work condition: dry bulb temp.21, wet bulb temp o C.
10 10 OUTLINES AND DIMENSIONS OF INDOOR UNIT
11 11 OUTLINES AND DIMENSIONS OF OUTDOOR UNIT EXPLODED VIEW OF INDOOR UNIT
13 13 PARTS LIST OF INDOOR UNIT No Description Part No Qty 1 Wall-Mounting Frame Rear Case Cross Flow Fan Fan Bearing Ring of Bearing Water Tray Assy Swing Louver Connecting Lever Connecting Lever Manual Lever Drainage Pipe Evaporator Gate Evaporator Supporter Evaporator Assy Front Case Assy Screw Cover Front Panel Filter Air Cleaner holder Air Cleaner A Guide Louver Remote Controller Guide Louver Bearing Air Cleaner B Evaporator Pipe Cover Sensor Insert Stepping Motor MP24GA Motor FN14A Motor Clamp Wire Clamp Pipe Clamp PCB 5K Tube Sensor Room Sensor Fuse 3.15A 250VAC Electric Box Cover Electric Box Cover Transformer Electric Box Cable Clamp Terminal Board T4A3A Wire Clip LED Holder LED Board Connection Cable Power Cord EXPLODED VIEW OF OUTDOOR UNIT
14 14 PARTS LIST OF OUTDOOR UNIT
15 15 No Description Part No Qty 1 Front Grill Nut M Washer Axial Flow Fan Front Plate Metal Base way Valve Capillary Assy Compressor RH207VHKC Nut with Washer M Handle Valve 1/2" Valve 1/4" Valve Support Right Side Plate Assy Wire Clamp Insulation Gasket Terminal Board T386A Electric Plate Comp Capacitor 30uF/450V Capacitor clamp Fan Capacitor 3uF/450V Terminal Board Isolation Sheet Assy Tube Sensor Condenser Assy Rear grill Assy Top cover Assy Motor Support Self-tapping Screw Motor FW48A CIRCUIT DIAGRAM These circuit diagrams are subject to change without notice. Please refer to the ones stuck on the machines.
16 16 PCB FUNCTION MANUAL 3 In 1 PCB Function manual A. Running mode
17 17 1. Cooling 2. Dehumidifying 3. Heating 4. Auto B. Input parameters 1. Indoor ambient temp. T in 2. Evaporator tube temp. T eva 3. Setting temp. T set 4. Condenser tube temp. T con C. Targets 1. Indoor motor (motor) 2. Swing motor 3. Outdoor motor (single speed motor) 4. Compressor 5. Four-way reversing valve 6. Cooling, dehumidifying indicator; running indicator 7. Digital tube setting temp. indicator or timer indicator D. Fundamental functions Cooling mode 1 The running conditions and control measures a. If T in > or = T set + 1 o C, the machine runs at the cooling mode. Compressor runs, outdoor motor runs at low speed, indoor fan runs at the set fan speed. b. If T in < or = T set 1 o C, the machine stops. Compressor stops first, outdoor motor stops after 15 seconds, indoor motor runs at the set fan speed. c. If T set 1 o C < T in < T set +1 o C,keep the previous state. 2 In this mode, the reversing valve is inactive, the temp. setting range is from 16~30 o C. 3 Protect function a. Anti-freezing function. i. If compressor have run 6 minutes, and detect T eva < 0 o C for continuous 3 minutes, then the compressor, outdoor fan stopped, indoor fan run at the set fan speed. After 3 minutes later, it will run at the original state if T eva > or = 10 o C. b. Compressor protection i. Compressor s starting interval should be more than 3 minutes no matter in whatever modes and conditions. If it s plugged in first time, the compressor does not have 3 minutes delay. When compressor is started, it will not stop within 5 minutes unless it is plugged out. c. Overload protection i. If it detect the system current surpass the designed 13 A for continuous 3 minutes, the machine go into fan mode, when 3 minutes passed and it detect the current no more than 13 A, it will back to original state. If it detects overloading states for 6 consecutive times, the machine stops, and must be restarted by remote controller. Dehumidifying mode 1 The working conditions and control measures a. If T in > T set + 2 o C, it is in cooling running, the indoor motor speed can be selected, and outdoor motor run at low speed.
18 18 b. If T set 2 o C < or = T in < or = T set + 2 o C,it goes into dehumidifying running,the indoor motor run at the low speed, 6 minutes later the compressor stops, another 15 seconds later the outdoor fan stops and another 30 seconds later, the indoor motor stops, 3 and a half minutes later, compressor and outdoor fan run again, indoor motor runs at the low speed, then the machine cycle the above procedures repeatedly. outdoor motor runs at the low speed. c. If T in > T set 2 o C, compressor,outdoor motor and indoor motor stop. 2 In this mode, the reversing valve is inactive, the temp. setting range is 16~30 o C. 3 Anti-freezing protection. a. If T indoor > T set + 2 o C, it goes into cooling running, anti-freezing function is same with cooling mode, but the compressor must stops for 4 minutes when it goes into dehumidifying mode, compressor runs 6 minutes, if it detects T eva < 0 o C, compressor and outdoor motor stop, indoor motor runs at low speed, after 3 minutes delay, and T eva > or = 10 o C, it will be back to its original state. Heating mode 1 The working conditions and control measures a. If T in < or = T set + 2 o C, it goes into heating mode, reversing valve, compressor and outdoor motor all work in the same time, indoor fan will run at the same procedures with anti cool air function. b. If T in > or = T set + 4 o C, compressor stops first, 15 seconds late, outdoor motor stops, but reversing valve keeps working, indoor motor run at the procedures of blowing surplus heat. c. If T set + 2 o C < T indoor < T set + 4 o C, keep the previous running state. 2 In this mode, the temperature setting range is 16~30 o C. 3 The working conditions of auxiliary electric heater. a. In heating mode, when compressor is working, indoor motor runs at high speed and middle speed. If it detect T eva < 50 o C for continuous 8 seconds and T indoor < or = 25 o C, electric heater will work, if compressor stop or indoor motor runs at low speed or T eva 54 o C or T indoor 28 o C or 10 seconds before defrosting, the electric heater will stop. 4 Protections a. Anti cool air i. When the machine starts heating and T eva > or = 22 o C, indoor motor runs at low speed, and swing motor makes the louver at the horizontal position, if T eva > or = 40 o C or compressor have run 2 minutes,indoor motor and swing motor will run at the set speed. b. Anti high temp. i. In heating mode, if it detect T eva 56 o C (58 can be selected), outdoor motor will stop (in this period it will not detect the defrosting temp.). If T eva 52 o C, outdoor motor will be back running (it will not detect defrosting temp. in the first 5 seconds). c. Blowing surplus heat i. In heating mode, when set temp is reached, comp. stops first, 15 seconds later outdoor fan stops, Indoor motor blows 90 seconds (60 seconds can be selected) at low speed,swing motor makes the louver at the horizontal position. d. Compressor s protection is same with the one in cooling mode. e. Overload protection i. If it detects that the system current surpassed the designed 13 A for continuous 3 seconds, compressor, electric heater and outdoor motor stop, indoor motor runs the same procedures as the blowing surplus heat condition. After 3 minutes and current no more than 13 A, the machine will be back to its original state, indoor motor runs as the anti cool air condition. If it detects overloading state for 3 con-
19 19 secutive times within 30 minutes, the machine stops, and it must be restarted by remote controller. f. Defrosting conditions and procedures i. In heating mode, if compressor has run 44 minutes ( in its first 6 minutes it will not detect defrosting temp.), and it has detected T con < or = -4 o C for continuous 1 minutes, it begins to defrost, electric heater will stop for 10 seconds ( even if electric heater is not working), then indoor motor stops, reversing valve becomes inactive in another 2 seconds, another 2 seconds later, outdoor motor stops, when T con > or = 10 o C or defrosting lasts for 10 minutes, outdoor motor and reversing valve becomes active, indoor motor will run as the anti cool air condition, then it cycles again, recalculates the compressor s running time again. (In this period, if any protection works, and after the machine is back to work, it will re-start defrosting state. it will not detect outdoor tube temp when compressor s in its first 6 minutes running) g. Noise eliminated protection i. When you use RUN/STOP button to switch off the machine, reversing valve will become inactive in 2 minutes. AUTO mode 1 In AUTO mode, standard cooling T set = 25 o C, standard heating T set = 20 o C. 2 Working procedures a. If T indoor > or = T set + 1 o C, select cooling mode, from this time, the set temp. is 25 o C. If T indoor < or = T set 1 o C, compressor and outdoor motor stop, indoor motor runs at the set speed, if T set -1 < T indoor < T set + 1 o C, keep the original state. b. If T indoor < or = T set + 2 o C, select heating mode, from this time, the set temp. is 20 o C, if T indoor > or = T set + 4 o C, compressor stops first, outdoor motor stops 15 seconds later, reversing valve is always active, indoor motor runs as the blowing surplus heat condition. If T set +2 o C < T indoor < T set +4 o C, keeps the original state. Cooling only AUTO mode: there is no heating function in this mode. 3 Protections a. It is same as the one in cooling or heating mode. 4 Other controls 1 SWING mode a. When it is active, the louver returns to position O, close the air outlet. b. When machine works, it turns to the max. Air output position D, then returns back to position L to stand by (position L is the horizontal place mentioned before). c. In swing state, the louver swings between position L and position D. d. When the machine is switched off, it is back to position O. e. When the machine is running and the swing is off, the louver stops at position E. O
20 20 L D E 2 Beeper a. When PCB becomes active or receives the signal from the remote controller, the beeper will beep. 3 Indication lamps a. It flashes when defrosting begin. 4 Press the AUTO button a time, the machine runs in AUTO mode, indoor motor runs in low speed, fresh air function is not active, press again the machine stops. 5 Fresh air function. a. There are two fresh air modes. Fresh air 2 i. Fresh air motor will work 1 hour, then rest 1 hour, then cycle again. Fresh air 1 ii. Press the button AIR on the remote controller to select fresh air 1 function, the swing motor keeps running till you give a signal to change it. 6 Automatic fan speed. a. In cooling mode, if T indoor > T set + 5 o C high speed T indoor > or = T set +3 o C middle speed T indoor > or = T set + 1 o C low speed b. In dehumidify mode, if T indoor > or = T set + 5 o C high speed T indoor > or = T set + 2 o C low speed SLEEP mode 1 In cooling or dehumidifying mode, 1 hour after you set the sleep timer,t set will add 1 o C automatically, another 1 hour, another 1 will be added. 2 In heating mode, 1 hour after you preset the sleep timer, T set will lower 1 o C automatically, another 1 hour, another 1 o C will be lowered.
2 Model Function Rated Voltage Rated Frequency Total Capacity (W) Power Input (W) Rated Input (W) Rated Current (A) Air Flow Volume (m 3 /h) Dehumidifying Volume (l/h) C.O.P / EER (W/W) Indoor unit Model
HUMMER GWHN07EANK3AA GWHN09EANK3AA GWHN07EANK3A2A GWHN09EANK3A2A HUMMER GWHN2EBNK3AA/I GWHN2EBNK3A2A/I GWHN2EBNK3AA GWHN2EBNK3A2A HUMMER Model Remarks 2 Model Function Rated Voltage Rated Frequency Total
SERVICE MANUAL SPLIT SYSTEM ROOM AIR CONDITIONER INDOOR UNIT AH-129 AH-MP14 OUTDOOR UNIT AU-129 AU-MP14 CONTENTS SPECIFICATIONS...2 EXTERNAL DIMENSIONS...4 WIRING DIAGRAMS...5 ELECTRICAL PARTS...6 MICROCOMPUTER
Website: www.andico.com.au Service manual CAUTION - BEFORE SERVICING THE UNIT, READ THE SAFETY - PRECAUTIONS IN THIS MANUAL. - ONLY FOR AUTHORISED SERVICE PERSONNEL. MODELS: MPK1-09CR-QB8 MPK1-12ER-QB6
Portable Air Conditioner Owner's Manual Model:3 in 1 12,000 Btu/h Series 3 Please read this owner s manual carefully before operation and retain it for future reference. CONTENTS 1. SUMMARY...1 2. PORTABLE
MULTI SPLIT TYPE, HEAT PUMP AIR CONDITIONERS Technical service manual 2009 KSIM MULTI ZONE SERIES R410A DC Inverter multi Series Models KSIM20912-H216 KSIM30912-H216 KSIM40912-H216 CONTENT 1. Product features
Failure code manual content 一 wall split AC series 2 二 floor standing AC series. 4 三 portable AC series.. 5 四 dehumidifer 6 五 DC inverter single split series...7 六 DC inverter multi-split series 10 1 一
HYUNDAI WALL MOUNTED SPLIT-TYPE AIR CONDITIONERS SERVICE MANUAL No.TE121023 Models HSH-I073NBE HSH-I123NBE HSH-I243NBE HSH-I093NBE HSH-I183NBE IMPORTANT NOTICE This service manual is intended for use by
SERVICE INSTRUCTION SPLIT TYPE ROOM AIR CONDITIONER WALL MOUNTEDtype INVERTER Models Indoor unit Outdoor unit ASYG07LECA ASYG09LECA ASYG12LECA ASYG14LECA AOYG07LEC AOYG09LEC AOYG12LEC AOYG14LEC R410A CONTENTS
[Gree Central Air Conditioner] Technical Service Manual Ducted type unit 2.3KW-16KW Version One GREE ELECTRIC APPLIANCES.INC.OF ZHUHAI - 1 - FG Series wind pipe blowing air-conditioning unit Section One:
SERVICE MANUAL Room Air Conditioner Multi Split type Outdoor unit /R410A DC Inverter/ FS2MI-147HFD FS2MI-187HFD FS3MI-217HFD FS3MI-277HFD FS4MI-277HFD FS4MI-367HFD FS5MI-367HFD NOTE: Before servicing the
Split Type Inverter Room Air Conditioner OPERATION MANUAL MODELS AY-X24LCJ AE-X24LCJ Thank you for choosing a SHARP air conditioner. Please read this manual thoroughly before using your air conditioner
AIRREX AIR CONDITIONER USER S MANUAL HSC-24A Thank you for purchasing an AIRREX AIR CONDITIONER. BEFORE operation please read this user s manual carefully. Keep this manual readily available. It is ESSENTIAL
Comfortstar Plus Introduction and features Technical Service Manual for 13SEER Comfortstar Plus Air Conditioners Model Remarks CHH024CD-13 Models & specifications Model CHH024CD-13 Function Cooling & Heating
SERVICE INSTRUCTION SPLIT TYPE ROOM AIR CONDITIONER Universal Floor / Ceiling Duct / Cassette Wall Mounted / Floor type INVERTER MULTI R410A Models Indoor unit Outdoor unit AB*14LBAJ AB*18LBAJ AB*F14LAT
SERVICE INSTRUCTION SPLIT TYPE ROOM AIR CONDITIONER WALL MOUNTEDtype INVERTER Models Indoor unit Outdoor unit ASU 9RLF ASURLF ASU5RLS AOU 9RLFW AOURLFW AOU5RLS R40A CONTENTS. DESCRIPTION OF EACH CONTROL
TECHNICAL DATA & SERVICE MANUAL INDOOR UNIT: AW52AL AW64AL SPLIT SYSTEM AIR CONDITIONER Model No. Product Code No. AW52AL 387030095 AW64AL 387030096 0.8180.463.0 07/05 IMPORTANT! Please read before installation
SPLIT WALL MOUNTED TYPE AIR CONDITIONERS OWNER'S MANUAL Thank you for choosing our Air Conditioner. Please read this OWNER'S MANUAL carefully prior to use and keep it for further reference. CONTENTS Contents
NewAir AC-10100E / AC-10100H Portable Air Conditioner Owner s Manual PLEASE READ AND SAVE THESE INSTRUCTIONS ELECTRICAL SAFETY This appliance is for indoor use only. Always turn off the unit and unplug
Internal Use Only http://biz.lgservice.com Room Air Conditioner SVC MANUAL(Exploded View) MODEL : LSN092CE(ASNC0914DH0)/LSN092HE(ASNH091E1H0) LSU092CE(ASUC0914DH0)/LSU092HE(ASUH091E1H0) LSN122CE(ASNC121E1H0)/LSN122HE(ASNH121E1H0)
GREE COMMERCIAL AIR CONDITION MARINE AIR CONDITIONERS Marine Air Conditioners Service Manual GREE ELECTRIC APPLIANCES INC. OF ZHUHAI 1 GREE COMMERCIAL AIR CONDITION MARINE AIR CONDITIONERS CONTENTS PRODUCT...2
14. Guide 14.1 Refrigeration Cycle System In order to diagnose malfunctions, ensure the air conditioner is free from electrical problems before inspecting the refrigeration cycle. Such problems include
OWNER S MANUAL Split Type Room Air Conditioner KSWM units Please read the operating instructions and safety precautions carefully and thoroughly before installing and operating your room air conditioner.
Pocket Manual Service Diagnosis SPLIT & MULTI Service Diagnosis SPLIT & MULTI 1. Troubleshooting with LED...5 1.1 Indoor Unit... 5 1.2 Outdoor Unit... 10 2. Troubleshooting by Symptoms...11 2.1 Air conditioner
REMOTE CONTROL MANUAL ENGLISH CONTENT PRECAUTIONS...1-2 USING THE REMOTE CONTROL UNIT...3 OPERATION...4-9 Thank you for purchasing our Room Air Conditioner. Before using your air-conditioner, please read
OWNER S MANUAL VMH 09/12/18/27/36 InverterFlex Version C Single, Dual, Tri or Quad Zone Ductless Mini-Split System Heat Controller, Inc. 1900 Wellworth Ave. Jackson, MI 49203 (517)787-2100 www.heatcontroller.com
ENGLISH INSTRUCTION & INSTALLATION MANUAL DUCTLESS MINI SPLIT AIR CONDITIONING SYSTEMS Céliera Corporation. All rights reserved. Unauthorized duplication, reproduction prohibited. CONTENTS SAFETY PRECAUTIONS...
Gree Solar Hybrid Hi Wall Inverter Air Conditioner Utilize the natural power of the sun to heat or cool your home. Find out more at www.greeonline.com Why Choose a Solar Hybrid Inverter? The new Gree Solar
PORTABLE AIR CONDITIONER MAC 7500 Owner s Manual Air Conditioner Dehumidifier Oscillating Fan Please read this owner s manual carefully before operating the unit. POWERED BY 66126113.p65 17 INTRODUCTION
DUCTLESS MINI-SPLITS SINGLE & MULTI-ZONE HORIZONTAL AIR CONDITIONERS PORTABLE UNITS FREE MATCH COMPONENTS AN EXCELLENT CHOICE IN COOLING, COMFORT AND CONVENIENCE Why choose a Mini-Split system? Installing
\ INSTALLATION INSTRUCTIONS AIRCOMMAND IBIS ROOFTOP AIRCONDITIONER Suitability: The IBIS caravan rooftop aircondioner is suitable for installation on caravans and motorhomes provided the roof structure
AI RCONDI TI ONI NG SYSTEMS Model s : UMATCH I NVERTER Ser vi cemanual Ser vi cemanual ChapterⅠ Introduction to Products 1. Kinds of Products Universal outdoor unit Duct type Floor ceiling type Cassette
New Deluxe Wall Mounted Heat Pump Series EXTERIOS May 2013 New Deluxe Wall Mounted Heat Pump Series Panasonic Adding New Air Conditioner Lineup Setting Another Mile Stone in the US Ductless Split History
HF/HFR Series Service Manual Wall split type Table of Contents 2. Model explaining....4 3. Installation.....4 4. Exploded view and part list.... 8 5. Operation principle.... 58 6. Parameter.... 59 7. Wiring
Air Conditioner Water Heater - A Product of HotSpot Energy LLC PLEASE READ THIS BEFORE YOU INSTALL THE UNIT 1. This air conditioner must be installed and/or repaired by a qualified technician. If you perform
Taurus Series YORK Window Air Conditioners IOM IOWRCAG50220711A1 Warning 1. Before using the Air conditioner please read the instructions carefully. They contain important advise about the installation,
ALL IN ONE Heat Pump Water Heater INSTALLATION AND OPERATION INSTRUCTIONS Please read this user s manual carefully before operate the unit. www.airtradecentre.com CONTENTS A. IMPORTANT REMARKS ------------------------------------------------------------------------------------------------
SPLIT TYPE ROO AIR CONDITIONER CEILING WALL TYPE INVERTER Indoor unit AWYZLBC AWYZLBC AWYZLBC AWYZLBC Outdoor unit AOYZLBC AOYZLBL AOYZLBC AOYZLBL CONTENTS SPECIFICATIONS................... OUTLINE AND
MDTN & MTDN0 SERVICE PARTS This parts list contains the service parts and wiring diagrams for this model. Check the model number of the machine requiring the parts to be sure that this is the correct parts
OVEN PARTS 30" BUILT IN ELECTRIC COMBO SENSOR/SC (GOLD LINE) 3 05 Litho In U.S.A. (cre) 1 Part No. Rev.A OVEN PARTS 1 Literature Parts 4455994 Installation Instructions Use & Care Guide 8300346 Microwave
Description Compact air/water heat pump for outside installation. With suction gas cooled rotary compressor. With extensive aluminium/cu lamellar tube evaporator and PVC Titanium condenser. Axial fan Refrigerant
Pioneer in sustainability Over 100 years ago Carrier helped pioneer a new industry, and in the last two decades we have pioneered environmentally sensitive products with a reduced impact on the environment.
TECHNICAL & SERVICE MANUAL SA 79G SA 99G FILE NO. WINDOW TYPE AIR CONDITIONER Model No. Product Code No. Destination SA-79G-A 1 851 005 18 General (50Hz) & Europe SA-99G-A 1 851 005 19 SA 79G SA 99G REFERENCE
F566272 Operating Instructions Air Conditioner CS-C18FFH CS-C28FFH CU-C18FFH CU-C28FFH ENGLISH Before operating the unit, read these operating instructions thoroughly and keep them for future reference.
Heat Pump Water Heater IOM Manual Installation Operation & Maintenance This manual is intended as an aid to qualified service personnel for proper installation, operation and maintenance of the heat pump
Please read this owner s Manual carefully before operating the unit. - Cooling - Heating - Dehumidifying - Fan TABLE OF CONTENTS INTRODUCTION 2 IMPORTANT SAFEGUARDS...2 PACKAGE CONTAINS..2 NAMES OF PARTS.3
A General Guide To Room Style Products Pipework Pipe sizes and lengths should be as the relevant Technical Guide Both lines should be insulated No line accessories or oil traps should be fitted In cooling
SERVICE & MAINTENANCE MANUAL Specifications are subject to change without notice according to Carrier Policy of continuous development. 03502566 Revision : (0) - 2009 TABLE OF CONTENTS PAGE NO. 1. Precautions
VERY IMPORTANT! MODEL: GDC-AC9RW / GDC-AC9RCS GDC-AC9RCW / GDC-AC12RW GDC-AC12RB / GDC-AC12RCB GDC-AC12RCW INSTRUCTIONS FOR USE PORTABLE AIR CONDITIONER Do not install and use your portable air conditioner
ENGLISH INSTRUCTION & INSTALLATION MANUAL DUCTLESS MINI SPLIT AIR CONDITIONING SYSTEMS Ramsond Corporation. All rights reserved. Unauthorized duplication, reproduction prohibited. CONTENTS SAFETY PRECAUTIONS...
SWIMMING POOL HEAT PUMP Owners Manual This manual refers to the 17.0kw and 21.0kw models only. The heat pump unit is sold with a 1 year warranty. In addition there is a 2 year parts warranty on the compressor
This is the parts list for the AFE. When looking up part numbers, always check the complete model and serial numbers to be certain of ordering the correct parts. The Air Cooled model has also been manufactured
SERVICE MANUAL AIRCONDITIONER DC INVERTER MULTI TYPE TAS-18MVHN/O TAS-27MVHN/O TAS-36MVHN/O DC MULTI OUTDOOR UNITS CONTENTS 1. General information of Outdoor Units... 3 2. Dimensions... 4 3. Wiring Diagram...
R-410A Duct Free Split System Air Conditioner and Heat Pump Product Family: DFS4(A/H)-System, DFC4(A/H)3-Outdoor, DFF4(A/H)H-Indoor Please read the operating instructions and safety precautions carefully
REPLACEMENT PARTS MANUAL WALL MOUNTED PACKAGE HEAT PUMPS Models: WH301 WH361 General Notes! Revised and/or additional pages may be issued from time to time.! A complete and current manual consists of pages
Wall Mounted Mini Split Heat Pump Air Conditioner OPERATING AND INSTALLATION MANUAL Model: KFHHP-18-ID / KFHHP-18-OD Indoor Unit. Outdoor Unit. Thank you for selecting Soleus Air. To ensure proper operation,
SPLIT-TYPE AIR CONDITIONERS Revision B: Descriptions regarding the outdoor fan motor have been corrected. Please void OBH549 REVISED EDITION-A. OUTDOOR UNIT SERVICE MANUAL HFC utilized R410A. OBH549 REVISED
INFORMATION INFORMATION ON THE TECHNOLOGY The -Frost refrigerators are different from the other static refrigerators in terms of their operational system. In normal refrigerators, in the freezing section,the
INSTALLATION MANUAL AIR CONDITIONER Please read this installation manual completely before installing the product. Installation work must be performed in accordance with the national wiring standards by
Internal Use nly http://biz.lgservice.com Multi Air Conditioner SVC MANUAL(Exploded View) MDEL : A5UW306FA3 CAUTIN Before Servicing the unit, read the safety precautions in Standard SVC manual. nly for
USER INSTRUCTIONS FOR GET PORTABLE 12k BTU AIR CONDITIONER MODEL No. GPACU12HR CONTENTS Introduction Safety Notes Identification of parts Installation instructions Operation instructions Maintenance Troubleshooting
Warranty Arlec guarantees this product in accordance with the Australian Consumer Law. Arlec also warrants to the original first purchaser of this product ( you ) from a retailer that this product will
SERVICE MANUAL FOR 6535 SERIES TWO TON HIGH EFFICIENCY PACKAGED HEAT PUMPS TABLE OF CONTENTS 1. Warnings...2 2. Accessibility Of Appliance...3 3. Unit Dimensions And Specifications...3 4. Unit Specifications
Fan Cool Furnace *Heat Pump or Heat Strip On/Off F Single Zone LCD Thermostat Operating Instructions MODEL 3313192.XXX Cool/Furnace 3313193.XXX Cool/Furnace/Heat Pump 3313194.XXX Cool/Furnace/Heat Strip
THERMO KING TRUCK & TRAILER UNIT ALARM CODES THIS DOCUMENT SHOWS ALL CURRENT ALARM CODES FOR THERMO KING TRUCK AND TRAILER UNITS. NOT ALL CODES ARE POSSIBLE ON ANY INDIVIDUAL UNIT. IF THE ALARM APPLIES
Structure & Features Air duct Type Air Conditioner Service Manual JIANGSU CHUNLAN REFRIGERATING EQUIPMENT Co., Ltd. AUGUST 2004 Structure & Features Contents Chapter I Structure & features... 1 Chapter
RMI-1103-A SERVICE MANUAL MIDEA AIRCONDITIONER EUROPE MARKET DC INVERTER MULTI TYPE R DC INVERTER MULTI SERIES CONTENTS 1. Precaution... 1 1.1 Safety Precaution... 1 1.2 Warning... 1 2. Function... 6 3.
REMOTE CONTROL MANUAL ENGLISH CONTENT PRECAUTIONS...1-2 ROOM IFEEL MODE TIMER TEMP USING THE REMOTE CONTROL UNIT...3 SLEEP SET CLEAR HOUR OPERATION...4-8 Thank you for purchasing our Room Air Conditioner.
NewAir AC-10000E, AC-10000H Portable Air Conditioner Owner s Manual PLEASE READ AND SAVE THESE INSTRUCTIONS BEFORE USE GENERAL SAFETY INSTRUCTIONS: ALWAYS OPERATE THE UNIT IN AN UPRIGHT POSITION AND PLACE
Your consent to our cookies if you continue to use this website.