DOWEC Blade pitch control algorithms for blade optimisation purposes


 Preston Wilkins
 3 years ago
 Views:
Transcription
1 DOWEC Blade pitch control algorithms for blade optimisation purposes E.L. van der Hooft 28th February 2001
2 Abstract As part of the first stage of the DOWEC project, a base control structure for a 3MW HAWT has been developed to support the evaluation of different rotor designs by means of load set calculations with PHATAS. During full load operation the rotorspeed is controlled by blade pitch speed adjustments towards feathering position to limit aerodynamic power. The basic controller consists of a rotorspeed feedback structure using a scheduled linear PDcompensator with nonlinear extensions. At partial load operation, the blade pitch angle is simply set to a constant value at which optimal tipspeed occurs. The report describes the structure and stability of the basic control algorithm, used for each rotor concept, and emphasizes the used assumptions and limitations. Rotor specific tuned parameter sets have been calculated. Time domain simulations driven by rotor effective windspeed, results in comparable control performance and energy yield of the FORTRAN algorithm for each proposed rotor design. As soon as a final rotor design has been defined, additional features to the basic control structure and detailed analysis are recommended. Energy yield improvements will be possible by feedforward control based on wind speed estimation and more extended controller scheduling. Active damping of tower and drive train resonances will be important to reduce fatigue. Acknowledgement The reported work is carried out within the scope of the DOWEC research and development project, partly funded by the Dutch EET program. Tim van Engelen (ECN) is acknowledged for helpfull development support and his pleasant commitment. Thanks to Frank Goezinne (NEGMICON Holland), Rene van den Berg (LM Glasfiber Holland) Koert Lindenburg (ECN) and Edwin Bot (ECN) for good cooperation and handing turbine data. Finally, Ben Hendriks is acknowledged for project management. 2 ECNCX
3 Distribution NEGMICON Holland 12 LM Glasfiber Holland 3 F.W. Saris 4 W. Schatborn 5 H.J.M. Beurskens 6 L.W.M.M Rademakers 7 H.B. Hendriks 8 T.G. van Engelen 9 J.T.G. Pierik 10 P. Schaak 11 C. Lindenburg 12 E.L. van der Hooft M.S.J. Bruin 15 ECN Centraal Archief 16 ECNDE Archief ECNCX
4 CONTENTS 1. INTRODUCTION 5 2. POINTS OF DEPARTURE Control objective and restrictions Turbine constants Rotor aerodynamic characteristics Generator characteristics Pitch actuation system and control equipment CONTROLLER DESIGN Control structure Linear PD compensator Parameters and setpoints Time domain simulation CONCLUSIONS 19 REFERENCES 21 APPENDIX A. CONTROL ALGORITHM (LMH95) 23 A.1 Parameters and setpoints: DATBLOK1.fi A.2 Control code: SBAGPRD1.f APPENDIX B. CONTROL ALGORITHM (LMH465X00) 37 B.1 Modification with respect to LMH B.2 Parameters and setpoints: DATBLOK3.fi APPENDIX C. CONTROL ALGORITHM (LMH465X01) 41 C.1 Modification with respect to LMH465X C.2 Parameters and setpoints: DATBLOK4.fi APPENDIX D. CONTROL ALGORITHM (LMH465X02) 45 D.1 Modification with respect to LMH465X D.2 Parameters and setpoints: DATBLOK5.fi APPENDIX E. CONTROL ALGORITHM (LMH465X00A) 49 E.1 Modification with respect to LMH465X E.2 Parameters and setpoints: DATBLOK6.fi APPENDIX F. CONTROL ALGORITHM (LMH465X00B) 53 F.1 Modification with respect to LMH465X F.2 Parameters and setpoints: DATBLOK7.fi APPENDIX G. CONTROL ALGORITHM (LMH465X01HI) 57 G.1 Modification with respect to LMH465X G.2 Parameters and setpoints: DATBLOK8.fi ECNCX
5 1. INTRODUCTION In favour of the DOWEC project 1 blade pitch algorithms has to be designed. Stage I of the DOWEC project implies development of a 3MW prototype windturbine (NM3000), initially for onshore operation and later (stage II) for offshore operation. The concept of the NM3000 is determined as a 3bladed horizontal axis wind turbine (HAWT) with a variable speed driven 3MW double fed generator and an active pitch system. As part of stage I, different blade designs have been defined. To evaluate these designs, load set calculations with PHATAS [14] have to prove both the aerodynamic and structural properties of each rotor design 2. To take realistic blade pitching actions into account, for each blade design a basic blade pitch algorithm has to be designed to control the rotor speed in full operation by means of pitch angle adjustments. As soon as a final rotor design is defined and turbine data is more valid, additional features (reducing resonance effects, improvements of energy yield) will be added to the basic blade pitch algorithm. This report describes briefly the points of departure (chapter 2), the controller design (chapter 3) and FORTRAN algorithm (Appendix A) of the basic blade pitch controller (Appendix A) based on a rotor (95m) having three LMH95X00 blades. Afterwards, a so called new baseline rotor (96m) has been defined by using LMH465X00 blades and changing rated speed from 15.1rpm to 14.9rpm. Because the structure of the controller remains similar, only relevant modifications and a modified (control)parameter set are listed in (Appendix B). With respect to the baseline (LMH465X00) the load consequenses of 10% slender blades (LMH465X01) and 10% wider blades (LMH465X02) were investigated by the PHATAS. The adapted (control)parameter sets are respectively listed in Appendix C and Appendix D. Another change with respect to the baseline is based on reducing the rotor speed. PHATAS calculations have to prove whether the loss of 2% and 4% energy yield will fulfill the expected reduction of fatique ( Low Lambda approach ). The (control)parameter sets are respectively listed in Appendix E and Appendix F. Finally, the rotor speed of the rotor with twist optimised LMH465X01 blades (LMH465X01Hi) has been increased to a rated tipspeed of 79m/s (rated rotor speed 15.9 rpm). The adapted (control)parameter set is listed in Appendix G. 1 DOWEC means Dutch Offshore Wind Energy Converter and implies development of a 56MW offshore turbine by the DOWEC consortium in in [14], the term configuration instead of design is used ECNCX
6 Blade pitch control algorithms DOWEC 6 ECNCX
7 2. POINTS OF DEPARTURE 2.1 Control objective and restrictions The control objective is defined as: Rotor speed regulation at rated rotor speed during full load operation (3MW electric power) by controlling the blade pitch angle in such a manner, that the lift coefficient lowers by decreasing the angle of attack and oppositely ( pitch angle control to vane ). The amount of crossing the rated rotor speed is restricted by the maximum speed of the generator. Above cutin and below rated rotor speed (partial load) the energy yield is maximised by an optimal tip speed ratio. In this region the blade pitch angle is forced to a constant value, (1 o, see figure 2.1) without further optimisation to improve energy yield or to lower noise. For convenience startup has been carried out by controlling the blade pitch angle from feathering position to working position with (relative slow) constant blade angular velocity (0.5 o /s). In this stage of the DOWEC project (with objective blade optimisation ) the following additional control features and enhancements have NOT been incorporated 3 : Scheduling of controller gains based on rotor and windspeed; Feed forward control based on rotor effective wind speed estimation [4]; Active damping of in plane tower resonances [6]; Active damping of foreaft tower resonances [9]; Active damping of drive train resonances [15]; Facility to avoid tower resonances in first bending mode during partial load. Fractional loss of energy yield or material fatique damage due to these assumptions are taken for granted in the concept stage of the DOWEC project. If required, these features will be added or developed in a next stage. 2.2 Turbine constants Design of the blade pitch controller is based on the following turbine data and constants [7], [2], [4]. Vcutin = 3.5; % Cutin windvelocity [m/s] Vcutout = 25.0; % Cutout windvelocity [m/s] VwAnnual = 10; % Annual windvelocity [m/s] RpmDsgn = 13.7; % Synchronous speed of generator [rpm] RpmMin = 0.7*RpmDsgn; % Lowest partial load rotor speed of generator RpmMax = 1.3*RpmDsgn; % Highest rotor speed of generator RpmPartin = 9.6; % Cutin rotor speed [rpm] RpmOptout = 14.5; % End of optimal lambda control (partial load operation) RpmRat = 15.1; % Rated rotor speed [rpm] Pelrat = 3e6; % Rated electric power [W] LAMBDA1 = 21; % Turbulence scale parameter (because hubheight >30m) L1 = 8.1*LAMBDA1; % Integral scale parameter in longitudinal direction 3 Research and concepts of these listed items are part of the ECNproject [5], funded by Dutch Ministery of Economic Affairs. ECNCX
8 Blade pitch control algorithms DOWEC aib = 3; % WTGS class (turbulence) I15IB = 0.16; % Turbulence intensity by 15m/s windvelocity at hubheight Etarat = ; % Gearbox and generator efficiency at rated conditions Rbs = 47.5; % Rotor radius (to rotorcenter) [m] Rhub = 1.2; % Hub radius [m] rho = 1.225; % Air density [kg/m^3] B = 3; % Number of blades Jrs = ; % Rotor inertia [kg*m^2] Jg = 200; % Generator inertia related HSS [kg*m^2] itran = 109.5; % Gear box ratio [] Zt = 100; % Hub Height [m] w0t = 2*pi*0.2; % Natural frequency of 1st bending mode of tower [rad/s] mt = ; % Tower top equivalent mass of 1st bending mode [kg] betat = 0.005; % Damping rate 1st bending mode of tower [] alphac = 0; % Cone angle [dg] alphan = 5; % Tilt angle [dg] alphashear = 0.2; % Shearcoefficient [] dtowtop = 3.5;, % Towertop diameter [m] dtowbase = 4.2; % Torenbase diameter [m] dn = 5.6; % Distance between rotorcenter and torenaxis [m] TdelCtrl = 0.1; % Sample time control equipment [s] TdelNrpm = 0.5*TdelCtrl; % Measurementdelay rotor speed samples [s] TdelPtLoad = 0.1; % Extra delay pitchactuator during speed reversal [s] TdelPtTrans = 0.0; % Representative delay pitch dynamics [s] TdelPtBase = 0.04; % Delay pitch actuator during normal operation [s] MaxRandNrpm = 0.05; % Amplitude random uniform speed measurement noise Tgen = 0.3; % Generator time constant [s] grav = 9.83; % Gravity constant [m/s^2] 2.3 Rotor aerodynamic characteristics Power coefficient and thrust coefficient characteristics of the turbine rotor with three LMH95 blades are shown as function of tipspeed ratio for different blade pitch angles in figure 2.1 and 2.2 (dashed lines respresents zero pitch angle). 0.7 power coefficient curves for pitch angles from 2 o, step 2 o, to 30 o power coefficient [ ] tip to wind speed ratio [ ] file C:\vdhooft\nm3000ct\DATA\PS\rot1\cpcurves.ps 30 Jun 2000 by C:\vdhooft\nm3000ct\DATA\M\modpar.m Figure 2.1 Power coefficient curves at different pitch angles Both power and thrust coefficient data are based on profile calculations obtained with Blade Optimisation Tool (BOT) [1]. 8 ECNCX
9 POINTS OF DEPARTURE 1 thrust coefficient curves for pitch angles from 2 o, step 2 o, to 30 o thrust coefficient [ ] tip to wind speed ratio [ ] file C:\vdhooft\nm3000ct\DATA\PS\rot1\ctcurves.ps 30 Jun 2000 by C:\vdhooft\nm3000ct\DATA\M\modpar.m Figure 2.2 Thrust coefficient curves at different pitch angles 2.4 Generator characteristics The steady state behaviour of the double fed induction generator is calculated in accordance with the values of RpmDsgn, RpmMin, RpmMax, RpmPartin, RpmOptout, RpmRat, Pelrat as given in section 2.2. Five ranges are distinguished and shown in figure 2.3, viz. no production below Vcutin; transition from startup to optimal tipspeed ratio control; optimal tipspeed ratio control during partial load (variable speed control); transition from optimal tipspeed ratio control to rated speed; constant power control from rated load up to Vcutout ( constant speed control ). and shown in figure 2.3. generator torque (slow shaft equiv) [knm] torque rotorspeed curve electric power [kw] power windspeed curve power rotorspeed curve 18 rotorspeed windspeed curve electric power [kw] rotor speed [rpm] rotorspeed [rpm] file C:\vdhooft\nm3000ct\DATA\PS\rot1\TPNVCurv.ps 30 Jun 2000 by C:\vdhooft\nm3000ct\DATA\M\modpar.m wind speed [m/s] Figure 2.3 Steady state figures of generator torque, power and speed ECNCX
10 Blade pitch control algorithms DOWEC Generator dynamics have been included with a conservative first order approximation. To achieve maximum energy yield it seems to be attractive to minimise the transition range from optimal speedtip control to constant power control (steep slope). However, to ensure sufficient suppression of undesirable 3p wind excitation noise in the electric power, this is limited. The 3p reduction is determined by this slope (gain), the effective inertia and the generator time constant. In a later stage of the DOWEC project (when more detailed generator data is available) more analysis will be carried out to specify possible restrictions due to this phenomenon. In the concept stage the transisition range is defined between 14.5rpm (1198kNm) and 15.1rpm (1898kNm) or a stiffness of 1170kNm/rpm related to slow shaft equivalent 4, and the first order time constant is set to Tgen= 0.3s. In the region of optimum tipspeed (between 9.6 and 14.5 rpm) a tipspeed ratio of 7.0 is calculated. 2.5 Pitch actuation system and control equipment For lack of detailed data of the pitch system in this stage of DOWEC, it was supposed to be valid to assume a pitchactuating system with similar performance as used in the NW62 [3] and NM2000 turbine, [4]: a double acting hydraulic actuator with proportional servo. It seemed realistic to model the pitching system as a pure delay amounted to 0.04s for speed setpoint changes in the same direction of pitching. Additionally a delay of 0.1s has been applied to setpoint changes in reverse pitching direction. For the development of the controller, only the expected measurement noise on the rotor speed was considered to be relevant, because of the differentiating action (Daction). Therefore a uniformly distributed random error of ± 0.05 rpm on the turbine rotor shaft was assumed. Measurement of blade angle was not corrupted with noise. 4 for comparison, this corresponds with a virtual slip of 11% 10 ECNCX
11 3. CONTROLLER DESIGN 3.1 Control structure The structure of the blade pitch angle controller is shown in figure 3.1. In full load Θ meas gain scheduler partial load pitch control Ω r nom setpoint adaptor Ω ref r PD +  linear PD controller + + Θ full Θ lim ( Ω r ) part Θ part full partial/full load selector dead zone & pitching bounds Θ set Rotorspeed limiter Ω meas r Ω r 3pfilt LPF lowpass ` 3p' filter Figure 3.1 Structure blade pitch angle controller NM3000 operation, a linear PD controller (Kprop,Kdiff) 5 sets the pitch speed dependent on the error between rotor speed setpoint and the actual rotor speed. Due to the heavily non linear character of the windturbine dynamics, some non linear extensions were necessary to meet satisfied performance: Linear controller gains have been scheduled (pinvschfac) dependent on the actual blade angle; with gain scheduling the linear controller is adapted to the operation envelope of the windturbine. A dead zone to avoid undesired pitch angle adjustments due to small controller corrections caused by noise, tower pass influences etc. The dead zone (dthdtsetinacbase) has also been scheduled by the actual pitch angle to achieve a relative equal pitch speed inactivation zone over the whole operation range. Additional magnification of linear controller gains below rated rotor speed (MuKsubNom) because of the stabilizing generator properties in this range. rotor speed setpoint adaptation proportionally with pitch angle (NrpmRatOff Max, WeightNrpmRefOld, ThLLAdapNref, ThULAdapNref), which supports the linear controller to avoid energy yield loss in case of falling wind gusts (storing kinetic energy in rotor). rotor speed limitation which forces the pitch angle with maximum pitch speed in feathering direction as soon as the actual rotor speed exceeds a certain 5 Terms between brackets refer to names of variables as used in the algorithm code Appendix A through Appendix D ECNCX
12 Blade pitch control algorithms DOWEC safety level and is still accellerating (NrpmLimFuz, NrpmDdtLimFuz, DeltaThFuz, dthdtfuztarg). A low pass filter to reduce measurement noise and 3p components (tower shadow, rotational sampling) of the measured rotor speed. To achieve sufficient suppression at least phase shift (delay), a fourth order invers Chebychev filter was used (alo3p, blo3p, clo3p, dlo3p, glo3p). Pitching bounds were incorporated to limit the calculated pitch speed values at the minimum and maximum pitch speed boundaries of the actuator and pitch mechanism (Thmax, Thmin, dthdtmax, dthdtmin). Dependent on the rotor speed value, a selector switches between full load operation or partial load operation. A transition from full load to partial load is based on first order filtered rotor speed and a transition from partial to full load (NrpmToFull) is based on the actual rotor speed value. A switching hysteresis (NrpmToPartial, NrpmToFull) is incorporated to avoid repeatable transitions between full and partial load. Partial load pitch control is simply implemented by setting the pitch angle to a constant value (ThetaPartConstant) with a certain pitch speed (dthdtsetpart) and an allowable error (ThSetPartDev). 3.2 Linear PD compensator As mentioned before in full load operation, a linear proportional/differential feedback structure (PD) sets the pitch speed dependent on the error between rotor speed setpoint and the actual filtered rotor speed. The linear PD compensator is dimensioned by phase and amplitude margin criteria of Bode to ensure sufficient stability and robustness [5]. The linear design has been based on the following assumptions and restrictions: Operation envelope defined as: aerodynamic torque between 90% and 140% with respect to rated torque rotor speed range between 14.1rpm and 17.1rpm windspeed range between 10.3m/s and 26m/s Phase margin of 45 o and amplitude margin of 0.5 Proces transfer function (pitch speed vs rotor speed) has been simplified to maximum value of aerodynamic torque to pitch angle sensitivity 6 overall delay which represents worst case pitch dynamics, computer calculation and measurement delays and rotor speed filter delay (phase shift) integrator incorporating the effective rotor inertia Stability analysis of the designed PD compensator and accompanying schedulefactor incorporates the following additional turbine modelling aspects (which were not taken into account during linear controller design): rotor speed influences caused by indirect foreaft tower deformation including aerodynamic rotor damping 7 Pitch angle influences caused by indirect foreaft tower deformation including aerodynamic rotor damping 7 Natural rotor speed feedback (aerodynamic torque to rotor speed sensitivity) Electric torque influence by generator through speed curve rotor speed low pass filter dynamics (3p filtering). 6 the schedulefactor is a non linear extension which achieve a suitable magnification of the PD gains over the whole operation envelope 7 aerodynamic damping is here defined as thrustforce to windspeed sensitivity 12 ECNCX
13 CONTROLLER DESIGN For clarity, in plane tower movement influences to electric torque were NOT taken into account. In figure 3.2, the Nyquist stability diagrams are shown for four classified blade angles areas centered around 5 o,10 o,15 o and 20 o m toren; Th = 5.00dg m toren; Th = 10.00dg 1 1 Im(Hrond) 0 Im(Hrond) Re(Hrond) Re(Hrond) m toren; Th = 15.00dg m toren; Th = 20.00dg 1 1 Im(Hrond) 0 Im(Hrond) re(hrond) file C:\vdhooft\nm3000ct\DESIGN\PS\rot1\DFNyqB1a.ps 23 Jun Re(Hrond) Figure 3.2 Nyquist diagrams for the windturbine with scheduled PDfeedback and lowpass 3p filter; aerodynamic torquelevels between 90% and 140% of the rated value; wind speed range [10.3m/s  26m/s]; rotor speed range [14.1rpm rpm] According to figure 3.2 there s no danger of closed loop instability (no curve is passing the instability point (1,0) from the wrong side and sufficient margins are guaranteed). The encirceling of the (0,0) point visualises the indirect torque influences by pitching in and around the tower eigenfrequency. 3.3 Parameters and setpoints The control structure as described in section 3.1 has tuned to match with typical turbine characterstics. The parameters as given in table 3.1 corresponds with the parameters and setpoints as used in the control algorithm (Appendix A) 8. Tuning of the nonlinear parameters and setpoints was done by running time domain simulations at different windspeeds (see section 3.4). The rotor speed limitation has been set to the maximum allowable generatorspeed (17.8rpm). A hysteresis of 0.75 rpm between full load and partial load operations has been used to avoid too many transitions. 8 Note that both the proportional and differential gain of the PD controller have been designed in dimensions [( o /s)/(rad/s)], [( o /s)/(rad/s 2 )] respectively. In the control algorithm the dimensions [( o /s)/(rpm/s)][( o /s)/(rpm/s 2 )] are used! ECNCX
14 Blade pitch control algorithms DOWEC Table 3.1 Parameters and setpoints in control algorithm item symbol meaning valuespecification Lowpass 3p filter alo3p(4,4) A State transition matrix e e e e e e e e e e e e e e e e 1 blo3p(4,1) B Inputcolumnvector e e e e 002 clo3p(1,4) C Outputrowvector e e e e 2 dlo3p D Throughputscalar e 1 glo3p(1,4) (I A) 1 B Initialisation vector e e e e+0 PDcompensator Kprop Kp dsgn Design value proportional gain ( o /s)/(rad/s) Kdiff K dsgn d Design value differential gain ( o /s)/(rad/s 2 ) pinvschfac(2) µ PD Coefficients schedule factor ( e2/ o ), e1 rotor speed setpoint adaptation RpmRat Ω nom Rated rotor speed 15.1 rpm RpmRatOffMax Ω r Maximum offset on Ω offmax nom 2 rpm WeightNrpmRefOld w Ω r old Weightfactor of 1 st order LPF ThLLAdapNref ThULAdapNref θ min Ω r off θ max Ω r off Min. pitchangle for adap.ω r Max. pitchangle for adap.ω r PD magnification factor below rated operation MuKsubnom µ k Gain factor for Ω<Ω nom 1.75 rotor speed limiting control NrpmLimFuz Ω max r Rotor speed limit 17.8 rpm NrpmDdtLimFuz lim Ω r Accelerationlimit constraint 0 rpm/s DeltaThFuz θ off Target pitch angle increase 3 o dthdtfuztarg θtarg Pitching speed during limiting 5 o /s 5 o 12 o Inactivity zone dthdtsetinacbase θinac Basic zone ampitude 0.12 o /s Partial load pitch setting table NrpmList(10,1) rotor speed values [rpm] ThdgList(10,1) Pitch angle values dthdtsetpart θr part Pitching speed 1.0 o /s ThSetPartDev θpart off Allowed pitch angle deviation 0.2 o Transition between partial and full load RpmToPartial Ω topart r Transient full partial load rpm RpmToFull Ω tofull r Transient partial full load rpm WeightNrpmSwitchOld weightfactor 1 st order LPF Pitching limits Thmax θ max Max. pitch angle +90 o Thmin θ min Min. pitch angle 1 o dthdtmax θmax Max. pitching speed +5 o /s dthdtmin θmin Min. pitching speed 5 o /s [ o ] 14 ECNCX
15 CONTROLLER DESIGN 3.4 Time domain simulation Rotor effective windspeed To verify the performance of the control algorithm as depicted in figure 3.1 with parameters and setpoints as defined in table 3.1, simulations in time domain are necessary. The simulations were driven by so called rotor effective windspeed. Rotoreffective windspeed is described as: a single point windsignal which causes wind torque variations through power and thrustcoefficient, that are stochasticly equivalent to those calculated through blade element theory in a turbulent windfield [5]. The stochastic signal is constructed from the autopower spectrum of the (longitudinal) windspeed variations and the lateral coherence, according to IECclass IB and turbulence intensity 16% [2]. The rotor effective windspeed signal has been normalised by the meanvalue of windspeed and consists of: 0p mode of the turbulent windfield 3p and 6p effects of the rotationally sampled windfield tower shadow influences wind shear variations Figure 3.3 shows these components in detail. tower+shear infl. [m/s] turb.mode 3 6 [m/s] wind speed variations at 1.76 r/s (16.8rpm) rotor speed and 11.3 m/s mean wind turb.mode 0 [m/s] time [s] file C:\vdhooft\nm3000ct\SCOPE\PS\vwexcitm.ps 09 May 2000 by C:\vdhooft\nm3000ct\SCOPE\M\scsmlvwe.m Figure 3.3 Details of contributions to rotor effective windspeed; tower and shear, rotational sampling, 0p mode Turbine model The turbine model [5] [3] used for time domain simulations is based on the following assumptions and restrictions: quasi stationary aerodynamic conversion (without dynamic stall) rigid rotor blades (no flapwise, no leadlag movements) stiff drive train (no torsion) first order generator dynamics and quasi stationary torque speed curve foreaft tower deformation in only the first bending mode neglection of influences on electric power due to lateral tower deformation constant torque losses simplified pitch system approached ( 2.5) ECNCX
16 Blade pitch control algorithms DOWEC The turbine model has been dimensioned using turbine constants as defined in 2.2, generator characteristics in 2.4 and aerodynamic characteristics in 2.3. Simulation results Several time simulations at different mean windspeed values, were calculated with the proposed control structure ( 3.1) using parameters and setpoints as defined in table 3.1 and the rotor effective windspeed and turbine model as described before in this section. In figure 3.4 the overall results (400s) of a time simulations at mean windspeed of 12.3 m/s are shown. The simulation shows both partial load operation (for example between 120s and 160s, the pitch angle is set to 1 o ) and full load operation. The overall performance of the controller and the energy yield is quite satisfying. There are no undesired pitch speed control actions because rotor speed filtering and dead zone are working properly. However the rotor speed setpoint is raised by the setpoint adaptation mechanism of the controller, some energy yield is lost in case of falling windgusts at 75s, 100s and 350s. In [4] is proved that an additional feedforward control based on windspeed estimation will improve this performance. In figure 3.5 a detail (50s) at mean windspeed of 13.3 m/s is shown. This detail shows both rotor speed setpoint adaptation and rotor speed limitation. The rotor speed setpoint is being increased to 17.1 rpm ( rpm) as soon as the pitch angle crosses 12 o. At 334s the rotor speed exceeds, due to an increasing windgust, the safetylevel of 17.8rpm. Additional kinetic energy has stored in the turbine rotor. The rotor speed limitation forces with maximum pitch speed (5 o /s) the blade angle in feathering direction, until the rotor accelleration has been decreased to zero value. Despite of the fact that aerodynamic power is strongly reduced by this forced action, no loss of electric power is caused because the stored kinetic rotor energy is adopted to prevent this. After the rotor speed limitation the transition to the linear controller is smoothly. Remark that the dead zone prevents small undesired pitch speed changes in the first part of the detail. The FORTRAN code of the blade pitch control algorithm is added in Appendix A. For convenience, parameters and setpoints were separated in an includable file:../datblok1.fi. The control code is called:../sbagprd1.f. Index 1 refers to the LMH95 blades and turbine constants as defined in [7] (dated 03/05/2000). Both FORTRANfiles are stored on PCplatform P2352 in directory c:/vdhooft/nm3000ct/algo/src. All development data (including source codes) and results are also stored on CDROM. 16 ECNCX
17 CONTROLLER DESIGN 16 NM3000 bij V w =12.3m/s; η regeling 99.1% (src: dssimp12.mat) Vw effectief [m/s] P (el; ae) [kw] file C:\vdhooft\nm3000ct\DESIGN\PS\rot1\dssp12a0.ps 06 Jun 2000 by C:\vdhooft\nm3000ct\DESIGN\M\dssimprd.m 18 Ω r (:smp; lo3p; ref) [rpm] dω r /dt (lo3p) [rpm/s] file C:\vdhooft\nm3000ct\DESIGN\PS\rot1\dssp12b0.ps 06 Jun 2000 by C:\vdhooft\nm3000ct\DESIGN\M\dssimprd.m Θ [ o ] dθ/dt [ o /s] tijd [s] file C:\vdhooft\nm3000ct\DESIGN\PS\rot1\dssp12c0.ps 06 Jun 2000 by C:\vdhooft\nm3000ct\DESIGN\M\dssimprd.m Figure 3.4 Turbineperformance at mean windspeed of 12.4 m/s; overall figure ECNCX
18 Blade pitch control algorithms DOWEC 20 NM3000 bij V w =14.3m/s; η regeling 98.8% (src: dssimp13.mat) 18 Vw effectief [m/s] P (el; ae) [kw] file C:\vdhooft\nm3000ct\DESIGN\PS\rot1\dssp13a2.ps 06 Jun 2000 by C:\vdhooft\nm3000ct\DESIGN\M\dssimprd.m 18 Ω r (:smp; lo3p; ref) [rpm] dω r /dt (lo3p) [rpm/s] file C:\vdhooft\nm3000ct\DESIGN\PS\rot1\dssp13b2.ps 06 Jun 2000 by C:\vdhooft\nm3000ct\DESIGN\M\dssimprd.m Θ [ o ] dθ/dt [ o /s] tijd [s] file C:\vdhooft\nm3000ct\DESIGN\PS\rot1\dssp13c2.ps 06 Jun 2000 by C:\vdhooft\nm3000ct\DESIGN\M\dssimprd.m Figure 3.5 Turbineperformance at mean windspeed of 13.4 m/s; detail figure 18 ECNCX
19 4. CONCLUSIONS A basic blade pitch control algorithm for full load operation of the DOWEC 3MW turbine, has been designed for making aerodynamic and structural comparisons [14] between different rotor designs (LMH95, LMH465X00/X01/X02, 24% speed reduction,lmh465x01hi). The control structure for all rotor designs are similar, however for each rotor design a specific parameterset is determined (Appendix A through Appendix G). The basic blade pitch control algorithm consists of a rotor speed feedback structure with a linear PDcompensator which sets the pitch speed dependent on the error between rotor speed setpoint and the actual rotor speed. Stability and robustness is guaranteed by Bode s amplitude and phasemargins and proved by Nyquist diagrams and time domain simulations with representative rotor effective windspeed. Non linear extensions have been added to meet better energy yield and to improve control performance. For each rotor, specific tuned parametersets have been calculated. Time domain simulations driven by rotor effective windspeed, result in comparable control performance and energy yield of the FORTRAN algorithm for each rotor design. The basic blade pitch control algorithm doesn t provide: a feed forward control based on windspeed estimation to achieve improved energy yield in case of falling windgusts a more dimensional, and therefore more effective scheduling of controller gains active damping facilities to reduce inplane and foreaft tower resonances or to reduce drive train dynamics More detailed analysis and research is recommended to implement these features in the final control structure. Some feasibility studies on these subjects have already be done [5], [6], [9], [15]. During partial load operation the blade pitch angle is simply set to a constant value (maximum power coefficient) and startup is integrated by increasing the pitch angle from feathering position to working position by a constant speed (0.5 o /s). In a more definite stage, it s also recommended to look at a facility which avoid tower resonances in first bending mode during partial load operation and/or a more advanced startup algorithm to ensure a smooth rotor accelleration [5]. When more detailed generator data is available, it will be needed to consider the influence of a stiff transition from optimal speedtip control to constant power control and generator dynamics with respect to energy yield and 3p wind excitation reduction in the electric power. Stability analysis of the control algorithm dimensioned for use at reduced rotor speed ( Low Lambda approach, see Appendix E and Appendix F), shows worrying operating points at small pitch angles due to destabilising effects of both natural and electric rotor speed feedback. If the Low Lambda approach fulfills fatigue reduction (PHATAS calculations [14] ) this phenomenon needs more attention for controller design. ECNCX
20 Blade pitch control algorithms DOWEC 20 ECNCX
Cost Optimization of Wind Turbines for Largescale Offshore Wind Farms
RisøR1000(EN) Cost Optimization of Wind Turbines for Largescale Offshore Wind Farms Peter Fuglsang, Kenneth Thomsen Risø National Laboratory, Roskilde February 1998 Abstract This report contains a
More informationUpwind 20MW Wind Turbine Pre Design
Upwind 20MW Wind Turbine Pre Design Blade design and control Johan Peeringa, Remco Brood(WMC), Ozlem Ceyhan, Wouter Engels, Gerben de Winkel(WMC) ECNE11017 December 2011 Acknowledgement This project
More informationWIND ENERGY  BASIC PRINCIPLES
Module.1 WIND ENERGY  BASIC PRINCIPLES Gerhard J. Gerdes Workshop on Renewable Energies November 145, 005 Nadi, Republic of the Fiji Islands Contents calculate the power in the wind power coefficient
More informationResponse to Harmonic Excitation Part 2: Damped Systems
Response to Harmonic Excitation Part 2: Damped Systems Part 1 covered the response of a single degree of freedom system to harmonic excitation without considering the effects of damping. However, almost
More informationWind Turbine Generator System. General Specification for HQ1650
Wind Turbine Generator System General Specification for HQ1650 3 Dec 2010 Hyundai Heavy Industries Co., Ltd Electro Electric Systems http://www.hyundaielec.co.kr Table of Contents 1. General description...
More informationIndustrial drive based wind simulator for small wind turbine optimisation
Industrial drive based wind simulator for small wind turbine optimisation S. Paepen MSc*, K. De Koker MSc*, P. Adams MSc* and P. Coussens PhD* * KAHO SintLieven, Department Gent, G. Desmetstraat, 9000
More informationLecture 4 Energy Conversion in Wind Turbine
Tuuli ja aurinkovoimateknologia ja liiketoiminta Wind and Solar Energy Technology and Business BL20A1200 Lecture 4 Energy Conversion in Wind Turbine LUT Energia, Olli Pyrhönen Equations for energy conversion
More informationSimulation of wind power with frontend converter into interconnected grid system
Simulation of wind power with frontend converter into interconnected grid system Sharad W. Mohod 1 ; Mohan V. Aware 2 1 Meghe Institute of Technology & Research, Badnera(INDIA); 2 Visvesvaraya National
More informationManufacturing Equipment Modeling
QUESTION 1 For a linear axis actuated by an electric motor complete the following: a. Derive a differential equation for the linear axis velocity assuming viscous friction acts on the DC motor shaft, leadscrew,
More informationENERCON WIND TURBINES
Sales ENERCON GmbH Dreekamp 5 2665 Aurich Germany Phone +49 494192 7 Fax +49 4941 92 71 9 vertrieb@enercon.de E33 E44 E48 E53 E7 E82 ENERCON WIND TURBINES PRODUCT OVERVIEW ENERCON GmbH Dreekamp 5
More informationIntroduction. Chapter 1. 1.1 The Motivation
Chapter 1 Introduction 1.1 The Motivation Hydroelectric power plants, like real systems, have nonlinear behaviour. In order to design turbine controllers, it was normal practice in the past, when computer
More information1. The prime mover which extracts the energy from the flow  a rotor of some sort;
Operational Principles Description of the WavetoWire Chain Tidal stream current turbines use similar principles to wind turbines in order to harness the kinetic energy in moving water. Accordingly, the
More informationWindsim manual. function [Cdax,Cp, a] = cplambda(windturbine, lambda, theta)
Contents: 1 General 1 1.1 Call.m files 1 1.2 Trics 2 2 Survey MATLAB programs 4 2.1 Run files 4 2.2 Subroutines 5 2.3 Applied MATLAB subroutines 6 2.4 Graphical overview 7 3. Some examples 8 1 General
More informationEE 402 RECITATION #13 REPORT
MIDDLE EAST TECHNICAL UNIVERSITY EE 402 RECITATION #13 REPORT LEADLAG COMPENSATOR DESIGN F. Kağan İPEK Utku KIRAN Ç. Berkan Şahin 5/16/2013 Contents INTRODUCTION... 3 MODELLING... 3 OBTAINING PTF of OPEN
More informationV52850 kw The turbine that goes anywhere
V28 kw The turbine that goes anywhere Versatile, efficient, dependable and popular The highly efficient operation and flexible configuration of the V2 make this turbine an excellent choice for all kinds
More informationEstimating Dynamics for (DCmotor)+(1st Link) of the Furuta Pendulum
Estimating Dynamics for (DCmotor)+(1st Link) of the Furuta Pendulum 1 Anton and Pedro Abstract Here the steps done for identification of dynamics for (DCmotor)+(1st Link) of the Furuta Pendulum are described.
More informationWind turbine database: Modelling and analysis with focus on upscaling. Master s thesis in the Master programme Applied Mechanics
Wind turbine database: Modelling and analysis with focus on upscaling Master s thesis in the Master programme Applied Mechanics JUAN PABLO SÁNCHEZ DE LARA GARCÍA Department of Applied Mechanics Division
More informationIntroduction to the IEC standard. Peter Hauge Madsen Risø DTU
Introduction to the IEC 614001 standard Peter Hauge Madsen Risø DTU IEC or ISO? (Electric component, machine or building or a wind turbine) Wind turbine generator system ~ Wind turbine structure 2 The
More informationTHE COMPOSITE DISC  A NEW JOINT FOR HIGH POWER DRIVESHAFTS
THE COMPOSITE DISC  A NEW JOINT FOR HIGH POWER DRIVESHAFTS Dr Andrew Pollard Principal Engineer GKN Technology UK INTRODUCTION There is a wide choice of flexible couplings for power transmission applications,
More informationELG4126 Wind Turbine Generators for Wind Power Plants
ELG4126 Wind Turbine Generators for Wind Power Plants The application of WTGs in modern wind power plants (WPPs) requires an understanding of a number of different aspects related to the design and capabilities
More informationTurbine Description REpower MM 92
Turbine Description REpower MM 92 Table of Contents 1 MM 92  Technical Description and Data... 3 1.1 Concept... 3 1.2 Rotor... 3 1.3 Drive Train... 4 1.4 Gear Box... 4 1.5 Electrical System... 4 1.6 Brake
More informationUnderstanding Inertia Ratio in Synchronous Motor Control
Understanding Inertia Ratio in Synchronous otor Control Executive summary When sizing a motor for a particular application, the general rule of thumb is to keep the inertia ration below : meaning the motor
More information300 MW Variable Speed Drives for PumpStorage Plant Application Goldisthal
May 24 MW Variable Speed Drives for Aurélie Bocquel APCG / 4BOC4 (MWGoldisthal 1524).PPT MW Variable Speed Drives for Content Major benefits of the cycloconverter driven doublyfed induction machines
More informationPower Electronics. Prof. K. Gopakumar. Centre for Electronics Design and Technology. Indian Institute of Science, Bangalore.
Power Electronics Prof. K. Gopakumar Centre for Electronics Design and Technology Indian Institute of Science, Bangalore Lecture  1 Electric Drive Today, we will start with the topic on industrial drive
More informationAERODYNAMIC ANALYSIS OF BLADE 1.5 KW OF DUAL ROTOR HORIZONTAL AXIS WIND TURBINE
AERODYNAMIC ANALYSIS OF BLADE 1.5 KW OF DUAL ROTOR HORIZONTAL AXIS WIND TURBINE HITENDRA KURMI Research scholar, School of Energy and Environmental Managment,UTD, RGPV Bhopal,MP,INDIA htr.ptl@gmail.com
More informationFAILURE OF A CONTROLLABLE PITCH PROPELLER SYSTEM AT NO LOAD OPERATION
FAILURE OF A CONTROLLABLE PITCH PROPELLER SYSTEM AT NO LOAD OPERATION ~ Herbert Roeser TransMarine Propulsion Systems, Inc. It is often assumed that failure of a mechanical system can occur only under
More informationIPNBM. Copyright Capgemini 2012. All Rights Reserved
IPNBM 1 De bescheidenheid van een schaker 2 Maar wat betekent dat nu 3 De drie elementen richting onsterfelijkheid Genomics Artifical Intelligence (nano)robotics 4 De impact van automatisering en robotisering
More informationAeroelastic models for wind turbines
Aeroelastic models for wind turbines how accurate does the flow model have to be? Helge Aagaard Madsen Georg Pirrung Torben J. Larsen Section Aeroelastic Design Department of Wind Energy hama@dtu.dk How
More informationUnit  6 Vibrations of Two Degree of Freedom Systems
Unit  6 Vibrations of Two Degree of Freedom Systems Dr. T. Jagadish. Professor for Post Graduation, Department of Mechanical Engineering, Bangalore Institute of Technology, Bangalore Introduction A two
More informationWIND TURBINE TECHNOLOGY
Module 2.22 WIND TURBINE TECHNOLOGY Electrical System Gerhard J. Gerdes Workshop on Renewable Energies November 1425, 2005 Nadi, Republic of the Fiji Islands Contents Module 2.2 Types of generator systems
More informationCOBRANDING RICHTLIJNEN
A minimum margin surrounding the logo keeps COBRANDING RICHTLIJNEN 22 Last mei revised, 2013 30 April 2013 The preferred version of the cobranding logo is white on a Magenta background. Depending on
More informationEDUMECH Mechatronic Instructional Systems. Ball on Beam System
EDUMECH Mechatronic Instructional Systems Ball on Beam System Product of Shandor Motion Systems Written by Robert Hirsch Ph.D. 9989 All Rights Reserved. 999 Shandor Motion Systems, Ball on Beam Instructional
More informationDevelopment of 2MW Downwind Wind Power Generation System
Hitachi Review Vol. 62 (23), No. 6 Development of 2MW Downwind Power Generation System Shingo Inamura, Dr. Eng. Yasushi Shigenaga Soichiro Kiyoki Shigeo Yoshida, Dr. Eng. OVERVIEW: Renewable energy is
More informationDNVGLCG0039 Edition December 2015
CLASS GUIDELINE DNVGLCG0039 Edition December 2015 The electronic pdf version of this document, available free of charge from http://www.dnvgl.com, is the officially binding version. FOREWORD DNV GL class
More informationOPTIMAL ROTOR TIP SPEED RATIO
OPTIMAL ROTOR TIP SPEED RATIO M. Ragheb 3/11/2014 INTRODUCTION A rotor that rotates slowly will allow the wind to pass unperturbed through the gaps between the blades. A rotor rotating rapidly will appear
More informationNOMENCLATURE Ω V. ρ P s =P +ρgh. Turbine Output Power Rotor Radius Rotational Speed Free Stream Velocity. Maximum Airfoil Lift Coefficient.
Owemes 6,  April. Civitavecchia, Italy. Horizontal Axis Tidal Current Turbine: Numerical and Experimental Investigations D.P. Coiro, U. Maisto, F. Scherillo, S. Melone, F. Grasso Department of Aeronautical
More informationTurbines and speed governors
ELEC0047  Power system dynamics, control and stability Turbines and speed governors Thierry Van Cutsem t.vancutsem@ulg.ac.be www.montefiore.ulg.ac.be/~vct November 2015 1 / 36 Steam turbines Turbines
More informationRelevance of Modern Optimization Methods in Turbo Machinery Applications
Relevance of Modern Optimization Methods in Turbo Machinery Applications  From Analytical Models via Three Dimensional Multidisciplinary Approaches to the Optimization of a Wind Turbine  Prof. Dr. Ing.
More informationGMPZ Annex 15: Kwalificatie en validatie
Z Annex 15: Kwalificatie en validatie item Gewijzigd richtsnoer Z Toelichting Principle 1. This Annex describes the principles of qualification and validation which are applicable to the manufacture
More informationDynamics of Offshore Wind Turbines
Proceedings of the Twentyfirst (2011) International Offshore and Polar Engineering Conference Maui, Hawaii, USA, June 1924, 2011 Copyright 2011 by the International Society of Offshore and Polar Engineers
More informationMobile field balancing reduces vibrations in energy and power plants. Published in VGB PowerTech 07/2012
Mobile field balancing reduces vibrations in energy and power plants Published in VGB PowerTech 07/2012 Dr. Edwin Becker PRÜFTECHNIK Condition Monitoring PRÜFTECHNIK Condition Monitoring GmbH 85737 Ismaning
More informationMATHEMATICAL MODEL OF PROPELLER CONTROL SYSTEM
18 Proceedings of the International Scientific Conference Modern Safety Technologies in Transportation 2015 MATHEMATICAL MODEL OF PROPELLER CONTROL SYSTEM Jaroslav BRAŤKA 1 Jozef ZAKUCIA 2 Abstract: This
More informationME 343: Mechanical Design3
ME 343: Mechanical Design3 Design of Shaft (continue) Dr. Aly Mousaad Aly Department of Mechanical Engineering Faculty of Engineering, Alexandria University Objectives At the end of this lesson, we should
More informationAeroelastic Investigation of the Sandia 100m Blade Using Computational Fluid Dynamics
Aeroelastic Investigation of the Sandia 100m Blade Using Computational Fluid Dynamics David Corson Altair Engineering, Inc. Todd Griffith Sandia National Laboratories Tom Ashwill (Retired) Sandia National
More informationUser orientated simulation strategy to analyse large drive trains in SIMPACK
User orientated simulation strategy to analyse large drive trains in SIMPACK SIMPACK User Meeting / Dipl.Ing. Thomas Hähnel / Dipl.Ing. Mathias Höfgen 21. / 22. November 2007 Content Motivation, state
More informationSYNCHRONOUS MACHINES
SYNCHRONOUS MACHINES The geometry of a synchronous machine is quite similar to that of the induction machine. The stator core and windings of a threephase synchronous machine are practically identical
More informationDesign and Characterization of a Small Wind Turbine Model equipped with a Pitching System
Design and Characterization of a Small Wind Turbine Model equipped with a Pitching System In Partial Fulfilment of the Requirements for the degree Master of Science in Engineering Renewable Energy and
More informationActive Vibration Isolation of an Unbalanced Machine Spindle
UCRLCONF206108 Active Vibration Isolation of an Unbalanced Machine Spindle D. J. Hopkins, P. Geraghty August 18, 2004 American Society of Precision Engineering Annual Conference Orlando, FL, United States
More informationDefinition of a 5MW Reference Wind Turbine for Offshore System Development
Definition of a 5MW Reference Wind Turbine for Offshore System Development Technical Report NREL/TP50038060 February 2009 J. Jonkman, S. Butterfield, W. Musial, and G. Scott Definition of a 5MW Reference
More informationPrecise Modelling of a Gantry Crane System Including Friction, 3D Angular Swing and Hoisting Cable Flexibility
Precise Modelling of a Gantry Crane System Including Friction, 3D Angular Swing and Hoisting Cable Flexibility Renuka V. S. & Abraham T Mathew Electrical Engineering Department, NIT Calicut Email : renuka_mee@nitc.ac.in,
More informationWINDER SYSTEMS GE Industrial Control Systems
WINDER SYSTEMS Systems Concepts Terminology GE Industrial Control Systems APPLICATION TECHNIQUES With a smooth metal surface material, a paper liner is sometimes wound with a coil. The paper is lightweight
More informationController Design in Frequency Domain
ECSE 4440 Control System Engineering Fall 2001 Project 3 Controller Design in Frequency Domain TA 1. Abstract 2. Introduction 3. Controller design in Frequency domain 4. Experiment 5. Colclusion 1. Abstract
More informationWind Turbine Power Calculations
Wind Turbine Power Calculations RWE npower renewables Mechanical and Electrical Engineering Power Industry INTRODUCTION RWE npower is a leading integrated UK energy company and is part of the RWE Group,
More informationPython s wind turbine design package manual
Python s wind turbine design package manual Author: Dennis van Dommelen September 2013 Supervisor: Dr. ir. W.A.A.M Bierbooms Contents Nomenclature iv 1 Introduction 1 2 Descriptions 2 2.1 Description
More informationMajor motion control features
Digital servo motor controller PM1000 (Provisional Data) A fundamental feature of the PM1000 controller is the motion control algorithm developed to meet the most demanding accuracy requirements enabling
More informationParameter identification of a linear single track vehicle model
Parameter identification of a linear single track vehicle model Edouard Davin D&C 2011.004 Traineeship report Coach: dr. Ir. I.J.M. Besselink Supervisors: prof. dr. H. Nijmeijer Eindhoven University of
More informationThe DTU 10MW Reference Wind Turbine
Downloaded from orbit.dtu.dk on: Nov 22, 2015 The DTU 10MW Reference Wind Turbine Bak, Christian; Zahle, Frederik; Bitsche, Robert; Kim, Taeseong; Yde, Anders; Henriksen, Lars Christian; Hansen, Morten
More informationSIMULATION OF WALKING HUMANOID ROBOT BASED ON MATLAB/SIMMECHANICS. Sébastien Corner
SIMULATION OF WALKING HUMANOID ROBOT BASED ON MATLAB/SIMMECHANICS Sébastien Corner scorner@vt.edu The Robotics & Mechanisms Laboratory, RoMeLa Department of Mechanical Engineering of the University of
More informationMachine Design II Prof. K.Gopinath & Prof. M.M.Mayuram. Module 2  GEARS. Lecture 17 DESIGN OF GEARBOX
Module 2  GEARS Lecture 17 DESIGN OF GEARBOX Contents 17.1 Commercial gearboxes 17.2 Gearbox design. 17.1 COMMERCIAL GEARBOXES Various commercial gearbox designs are depicted in Fig. 17.1 to 17.10. These
More informationWind Turbine Blade Aerodynamics
Wind Turbine Blade Aerodynamics Wind turbine blades are shaped to generate the maximum power from the wind at the minimum cost. Primarily the design is driven by the aerodynamic requirements, but economics
More informationA preliminary comparison on the dyna mics of a VAW T on three different support structures 23 rd January, 2014 Mic ha el Borg
A preliminary comparison on the dyna mics of a VAW T on three different support structures 23 rd January, 2014 Mic ha el Borg Outline Context Floating Wind Turbines studied Degrees of Freedom Loading Conditions
More informationResponse to Harmonic Excitation
Response to Harmonic Excitation Part 1 : Undamped Systems Harmonic excitation refers to a sinusoidal external force of a certain frequency applied to a system. The response of a system to harmonic excitation
More informationWind energy extraction and conversion: optimization through variable speed generators and non linear fuzzy control
Wind energy extraction and conversion: optimization through variable speed generators and non linear fuzzy control Paulo Costa Instituto Politécnico de Viana do Castelo, Avenida do Atlântico, 4900 Viana
More informationVariable Speed Drives for Combined Cycle Power Plants
Variable Speed Drives for Combined Cycle Power Plants Voith Turbo s proven technology in combined cycle plants Speed variation produces significant energy savings and efficiency improvement in combined
More informationFull Scale Testing Facilities. Stuart Herbert Business Development Manager, Engineering and Drive Train EWEC 2010
Full Scale Testing Facilities Ensuring Reliability for Offshore Wind Stuart Herbert Business Development Manager, Engineering and Drive Train EWEC 2010 Narec UK operational locations Head Office Wind,
More informationGE s Haliade * 1506MW
GE Renewable Energy GE s Haliade * 1506MW High yield offshore wind turbine GE Renewable Energy Since entering the wind industry in 2002, GE Renewable Energy has invested more than $2 billion in next generation
More informationGuidelines to engine dynamics and vibration
The Ship Power Supplier Guidelines to engine dynamics and vibration by Hannu Tienhaara Technology Wärtsilä Corporation In recent years shipyards and shipowners have increasingly tuned in to the negative
More informationModeling and Study of a Standalone PMSG Wind Generation System Using MATLAB/SIMULINK
Universal Journal of Electrical and Electronic Engineering 2(7): 270277, 2014 DOI: 10.13189/ ujeee.2014.020702 http://www.hrpub.org Modeling and Study of a Standalone PMSG Wind Generation System Using
More information1.0 Background 1.1 Historical background 1.2 Cost of wind turbines
1.0 Background 1.1 Historical background Wind energy has been used for thousands of years for milling grain, pumping water and other mechanical power applications. Wind power is not a new concept. The
More informationModeling Mechanical Systems
chp3 1 Modeling Mechanical Systems Dr. Nhut Ho ME584 chp3 2 Agenda Idealized Modeling Elements Modeling Method and Examples Lagrange s Equation Case study: Feasibility Study of a Mobile Robot Design Matlab
More informationTechnical Guide No. 100. High Performance Drives  speed and torque regulation
Technical Guide No. 100 High Performance Drives  speed and torque regulation Process Regulator Speed Regulator Torque Regulator Process Technical Guide: The illustrations, charts and examples given in
More informationGeneration of design knowledge from the development of a theoretically idealized wind turbine. Z. H. Zamora Guevara
Generation of design knowledge from the development of a theoretically idealized wind turbine Z. H. Zamora Guevara Generation of design knowledge from the development of a theoretically idealized wind
More informationCurrent Loop Tuning Procedure. Servo Drive Current Loop Tuning Procedure (intended for Analog input PWM output servo drives) General Procedure AN015
Servo Drive Current Loop Tuning Procedure (intended for Analog input PWM output servo drives) The standard tuning values used in ADVANCED Motion Controls drives are conservative and work well in over 90%
More informationSwitched Reluctance Machine (SRM)
Switched Reluctance Machine (SRM) 3D FEA Analysis using MagNet Jerry Foshage  RCT Systems 1 Wind and Water Power Technologies Office eere.energy.gov Acknowledgment & Disclaimer Acknowledgment This material
More informationOnshore Wind Services
GE Renewable Energy Onshore Wind Services www.ge.com/wind PITCH TABLE OF CONTENTS: 3 Operate and Maintain 3 Asset and Park Management 5 Turbine Maintenance 8 Enhance and Optimize 8 Wind PowerUp * Services
More informationSeries 6000 Torque measured metal bellow coupling
Properties Free of float metal bellow coupling with integrated torque measurement Noncontact measurement system, high robustness High torsional stiffness Limited torque of inertia Performance Measurement
More informationPitch systems of the future under all climatic conditions. Wind Power Works
Pitch systems of the future under all climatic conditions Pitch Systems of the Future Pitch systems for wind turbines Pitch Systems of the Future Hydraulic Electric The Fail Safe Principle Hydraulic Pitch
More informationIf we let the vertical tail lift coefficient depend on a vertical tail lift curve slope and a rudder deflection we can write it as:
Roll and Yaw Moments and Stability Yaw Moment Equation The yaw moment is the moment about the z body axis and is positive if it moves the nose of the plane to the right. The big contributor to the yaw
More informationDually Fed Permanent Magnet Synchronous Generator Condition Monitoring Using Stator Current
Summary Dually Fed Permanent Magnet Synchronous Generator Condition Monitoring Using Stator Current Joachim Härsjö, Massimo Bongiorno and Ola Carlson Chalmers University of Technology Energi och Miljö,
More informationGE Renewable Energy. GE s 3 MW Platform POWERFUL AND EFFICIENT. www.ge.com/wind
GE Renewable Energy GE s 3 MW Platform POWERFUL AND EFFICIENT www.ge.com/wind GE S 3 MW PLATFORM PITCH Since entering the wind industry in 2002, GE Renewable Energy has invested more CONTROLS than $2 billion
More informationDIRECT MATCHING TO GRID WITHOUT INVERTER VARIABLE PITCH. 20/24/30 mt TOWER WITH HYDRAULIC SYSTEM YAWING SYSTEM SAFETY LEVELS PLC CONTROL
Wind turbine EW 50 Ergo Wind srl can boast of thirty years experience in the field of renewable energies as a producer of low environmental impact systems. The core business is represented by small wind
More informationABSTRACT. Wang Yao, M.S. Mentor: Kwang Y. Lee, Ph.D. power control strategy named loadfollowing has been given attention recently.
ABSTRACT WindTurbine Generator for LoadFollowing and Its Applications to Primary Frequency Support and SmallSignal Stability Improvement Wang Yao, M.S. Mentor: Kwang Y. Lee, Ph.D. In today s power grid,
More informationPhysics 1A Lecture 10C
Physics 1A Lecture 10C "If you neglect to recharge a battery, it dies. And if you run full speed ahead without stopping for water, you lose momentum to finish the race. Oprah Winfrey Static Equilibrium
More informationControl of Rotor Geometry and Aerodynamics: Retractable Blades and Advanced Concepts
WIND ENGINEERING VOLUME 32, NO. 1, 2008 PP 13 26 13 Control of Rotor Geometry and Aerodynamics: Retractable Blades and Advanced Concepts Timothy J. McCoy and Dayton A. Griffin Global Energy Concepts, LLC,
More informationGE Power & Water Renewable Energy. Digital Wind Farm THE NEXT EVOLUTION OF WIND ENERGY. www.ge.com/wind
GE Power & Water Renewable Energy Digital Wind Farm THE NEXT EVOLUTION OF WIND ENERGY www.ge.com/wind GE S DIGITAL WIND FARM PITCH Since entering the wind industry in 2002, GE Power & Water s Renewable
More informationGE Renewable Energy. GE s 2MW Platform A CUSTOMIZABLE PLATFORM TO ENHANCE SITING EFFICIENCY.
GE Renewable Energy GE s 2MW Platform A CUSTOMIZABLE PLATFORM TO ENHANCE SITING EFFICIENCY www.ge.com/wind GE S 2MW PLATFORM PITCH Since entering the wind industry in 2002, GE Renewable Energy has invested
More informationControl Concepts to Enable Increased Wind Power Penetration
Control Concepts to Enable Increased Wind Power Penetration Magni Þ. Pálsson, Trond Toftevaag, Member IEEE, Kjetil Uhlen, Member IEEE, John Olav Giæver Tande Abstract This paper addresses problems encountered
More informationEðlisfræði 2, vor 2007
[ Assignment View ] [ Pri Eðlisfræði 2, vor 2007 31. Alternating Current Circuits Assignment is due at 2:00am on Wednesday, March 21, 2007 Credit for problems submitted late will decrease to 0% after the
More informationFAN PROTECTION AGAINST STALLING PHENOMENON
FAN PROTECTION AGAINST STALLING PHENOMENON Roberto Arias Álvarez 1 Javier Fernández López 2 2 1 ZITRON Technical Director roberto@zitron.com ZITRON Technical Pre Sales Management jfernandez@zitron.com
More informationFMV New Vestas products. vestas.com
FMV 20100128 New Vestas products vestas.com V1123.0 MW Approved for IECII and IECS Suitable up to 9,5 m/s depending on turbulence intensity Nominal rating 3.0 MW Tower range 84119 m Tip height range
More informationTwinCAT NC Configuration
TwinCAT NC Configuration NC Tasks The NCSystem (Numeric Control) has 2 tasks 1 is the SVB task and the SAF task. The SVB task is the setpoint generator and generates the velocity and position control
More informationPOTENTIAL OF STATEFEEDBACK CONTROL FOR MACHINE TOOLS DRIVES
POTENTIAL OF STATEFEEDBACK CONTROL FOR MACHINE TOOLS DRIVES L. Novotny 1, P. Strakos 1, J. Vesely 1, A. Dietmair 2 1 Research Center of Manufacturing Technology, CTU in Prague, Czech Republic 2 SW, Universität
More informationRotation: Moment of Inertia and Torque
Rotation: Moment of Inertia and Torque Every time we push a door open or tighten a bolt using a wrench, we apply a force that results in a rotational motion about a fixed axis. Through experience we learn
More informationAn Experimental Study on Power Quality of Wind Turbines
An Experimental Study on Power Quality of Wind Turbines Joaquín Mur Ángel Antonio Bayod Roberto Zapata Samuel Ortiz Universidad de Zaragoza Dpto. Ingeniería Eléctrica CIRCE joako@posta.unizar.es Abstract
More informationV1123.0 MW. Your best option for low cost energy production at low and medium wind sites. Federico Gonzalez Vives. Director Technology.
V1123.0 MW Your best option for low cost energy production at low and medium wind sites Federico Gonzalez Vives. Director Technology. Vestas MED REOLTEC. Jornadas tecnicas 17 de junio de 2010 vestas.com
More informationEVALUATION OF FLICKER LEVEL IN A T&D NETWORK WITH A LARGE AMOUNT OF DISPERSED WINDMILLS
EVALUATION OF FLICKER LEVEL IN A T&D NETWORK WITH A LARGE AMOUNT OF DISPERSED WINDMILLS H. Knudsen V. Akhmatov The amount of installed wind power capacity in Denmark is very large, when seen relatively
More information1 Theoretical Background of PELTON Turbine
c [m/s] linear velocity of water jet u [m/s) runner speed at PCD P jet [W] power in the jet de kin P T [W] power of turbine F [N] force F = dj Q [m 3 /s] discharge, volume flow ρ [kg/m 3 ] density of water
More informationControl design for a pitchregulated, variable speed wind turbine
RisøR1500(EN) Control design for a pitchregulated, variable speed wind turbine Morten H. Hansen, Anca Hansen, Torben J. Larsen, Stig Øye, Poul Sørensen and Peter Fuglsang Risø National Laboratory Roskilde
More informationThe Reliance on Wind Energy Depends on Advancements in Blade Pitch Control
INSIGHT# 201023MPH JULY 6, 2010 The Reliance on Wind Energy Depends on Advancements in Blade Pitch Control By Sal Spada Overview Source: GWEC Many nations are in the process of making wind power an integral
More informationWind Energy What is Wind Energy?
Wind Energy What is Wind Energy? People have known how to make use of energy from the wind for centuries. The kinetic energy of the wind can be changed into other forms of energy, either mechanical energy
More information