1 Page 1 of 60 NFPA 70E Electrical Safety Presentation (updated for 2012) By Bruce Bowman, P.E.
2 OSHA and the IEC Alliance Page 2 of 60 Through the OSHA and Independent Electrical Contractors (IEC) Alliance, IEC developed this presentation ti for informational purposes only. It does not necessarily reflect the official views of OSHA or the U.S. Department of Labor.
3 What is the best way to prevent the hazards of electricity? Page 3 of 60 Stop Think Options Protection - Before Action - Risks/Hazards - LOTO - Proper PPE Avoiding energized circuits is the safest way!
4 Electrical Safety Page 4 of 60 Why Electrical l Safety Practices and Procedures? 1. An estimated 30,000 non-fatal electrical shock accidents occur each year 2. Over 600 people die from electrocution ti each year 3. Electrocution remains the fourth (4 th ) highest cause of industrial fatalities 4. Approximately 3000 flash burn incidents reported annually along with approximately 350 deaths
5 Electrical Safety Page 5 of 60 NFPA 70 E Standard for Electrical Safety in the Workplace Formally Standard for Electrical Safety Requirements for Employee Workplaces Began in 1976 by NFPA to assist OSHA
6 Electrical Hazards Page 6 of 60 Shock Arc Flash & Arc Blast Fire Ignition
7 The Effects of Shock Page 7 of 60 Immediate Long Term - Muscle contraction - Memory Loss - Vital organs (heart, lungs, etc.) - Nervous disorders - Tingling - Chemical imbalances - Pain - Damage to vital organs - Breathing - Sometimes fatal - Disorientation - Dizziness - Death
8 Men Perception Threshold Amps (1 ma) Effects of Current on the Body Women Perception Threshold Amps (0.7 ma) Page 8 of 60 Painful Shock Amps (9 ma) Cannot Let-Go Level Amps (10 ma) Ventricular Fibrillation Amps (100 ma) for 3 seconds Amps (200 ma) for 1 second Heart Failure Amps (500 ma) Painful Shock Amps (6 ma) Cannot Let-Go Level Amps (10 ma) Ventricular Fibrillation Amps (100 ma) for 3 seconds Amps (200 ma) for 1 second Heart Failure -0.5 Amps Organ Burn and Cell Breakdown Organ Burn and Cell Breakdown -1.5 Amps (1500 ma) -1.5 Amps (1500 ma) Electrical Safety in the Workplace by Ray A. Jones, PE 2001
9 Resistance and the Body Page 9 of 60 The body has a natural defense system to shock (skin) Why y50 v0lts? As you can see from the calculation below, a 50 volt exposure would not cause muscles to lock and is insufficient to cause physical harm. The key to survival is to decrease our exposure to energized circuits. Ohm s Law for electric current (amps), voltage and body resistance The typical body has a contact resistance of approximately 500 ohms at the point of contact with the electrical source. The body has an internal resistance of approximately 100 ohms. There is another ac resistance or impedance to ground of approximately 5000 ohms v / (500Ω + 100Ω Ω) = 21mA - 50v / (500Ω + 100Ω Ω) = 8.9 ma It is around 10 ma that the cannot let go level is reached.
10 Two Types of Burns from Shock Page 10 of 60 Surface Burns Internal Tissue Burns Caused by entrance and Caused by current exit of electrical currents flowing through organs through the body of the body Can be caused by a very Caused by currents in small amount of current excess of 1.5 amps 1 st degree to 3 rd degree 4 th degree Internal organs Typically y fatal
11 One Type of Burn from Arc Flash Page 11 of 60 Surface Burns Caused by exposure to the arc flash Can cause more surface burns if the initial arc flash ignites it other material such as clothing 1 st degree to 3 rd degree It has and may cause death!
12 Electrical Safety Page 12 of 60 How to prevent shock? 1. Place circuits in electrically safe working conditions by locking out and tagging out all sources Chapter 1, Section of NFPA 70E Verifying that no electrical energy is present Chapter 1, Section of NFPA 70E-2012
13 Fire Ignition from Arc Flash Page 13 of 60 The original and primary mission of the NFPA - Primarily covered by installation standards contained in the National Electric Code NFPA 70 - The incidence of fire ignition has dropped dramatically since the advent of the NEC and the acceptance of installation requirements within the industry Th NFPA 0 NEC d t dd th th h d f The NFPA 70 NEC does not address the other hazards of electricity
14 Exposure to Danger Page 14 of 60 The National Electric Code protects individuals from shock hazards under normal conditions. It is not designed to protect us from abnormal conditions. We need additional policies to protect from abnormal conditions.
15 Conditions Page 15 of 60 Normal Conditions Abnormal Conditions Panel covers in place. Panel covers removed. Equipment plugged in normally. Normal, designed d protection in place. Equipment temporarily wired. Normal, designed d protection such as guards, limits switches, etc. not in place. Faulty or Damaged Equipment.
16 Protection from Abnormal Conditions Page 16 of 60 The Company You NFPA 70E The first line of defense OSHA Electrical Safety Procedures Manual Electrical Safety Training Only you can truly keep you safe Implement safety procedures outlined in Safety Manual Only you can implement the procedures that may save your life
17 Page 17 of 60 Old School Electricians have always recognized the shock hazards of electricity. We are taught: - To consider circuits to be energized - To insulate and protect ourselves - Stand to one side if an arc flash/blast is suspected
18 New School Page 18 of 60 Arc Flash and Blast hazards were not formally studied until 1993 (IEEE 1584 began study). Electricians have not experienced arc flash and blasts to the same frequency as electrical shock. We have not been trained how to avoid and minimize arc flash and blasts in the past. The Electrical Energized Work Practices outlined in NFPA 70E e ect ca e g ed Wo act ces out ed N 70 incorporates measures to help avoid or minimize damage from arc flash.
19 Pictures from ESA Book Practical Solution Guide to Arc Flash Hazards Page 19 of 60
20 Page 20 of 60 Electric arcs produce the highest h temperatures on earth up to 35,000 degrees Fahrenheit (4 x temp of the sun)! The intense heat from arc causes the sudden expansion of air that t results in a blast with very strong air pressure (Lightning is a natural arc). All known materials are vaporized at this temperature. (Copper expands 67,000 times, Water 1,670 times). Notes are from Practical Solution Guide to Arc Flash Hazards, by Chet Davis, P.E.; Conrad St. Pierre; David Castor, P.E.; Robert Luo, PhD; and Satish Shrestha.
21 Page 21 of 60 Arcs in enclosures, such as a Motor Control Centers (MCCs) or switchgear, magnify blast and energy transmitted as the blast is forced to the open side of the enclosure. Arcs spray droplets of molten metal at high-speed pressure. Blast shrapnel can penetrate the body. Blast pressure waves have thrown workers across rooms and knocked them off ladders. Pressure on the chest can be higher than 2000 lbs/sq. ft. Notes are from Practical Solution Guide to Arc Flash Hazards, by Chet Davis, P.E.; Conrad St. Pierre; David Castor, P.E.; Robert Luo, PhD; and Satish Shrestha.
22 Page 22 of 60 Clothing can be ignited from several feet away. Clothed areas can be burned more severely than exposed skin. Hearing loss from sound blast. The sound can have a magnitude as high as 140dB at a distance of 2 feet from the arc. Energy released is a function of: System voltage Fault current magnitude Fault duration f i l l i id l h d b Notes are from Practical Solution Guide to Arc Flash Hazards, by Chet Davis, P.E.; Conrad St. Pierre; David Castor, P.E.; Robert Luo, PhD; and Satish Shrestha.
23 Page 23 of 60 How to Protect Against Shock and Arc Flash/Blast? Chapter 1, Section 130 of NFPA 70E Justification for Live Work 2. Work Permits Secured if Applicable 3. Approach Boundaries Established A. Shock Protection ti 1. Limited Boundary 2. Restricted Boundary 3. Prohibited Boundary B. Flash Protection ONE BOUNDARY
24 Pictures from ESA Book Practical Solution Guide to Arc Flash Hazards Page 24 of 60
25 Approach Boundaries NFPA 70E-2012 Ch. 1, Section 130 Limited Approach Boundary Entered only by qualified persons or unqualified persons that have been advised and are escorted by a qualified person Restricted Approach Boundary Entered only by qualified persons required to use shock protection techniques and PPE Prohibited Approach Boundary Entered only by qualified persons requiring same protection as if direct contact with live part Flash Protection Boundary Linear distance to prevent any more than 2 nd degree burns from a potential arc-flash (typically 4 feet) Page 25 of 60
26 Page 26 of 60 SHOCK Hazard Analysis Ch. 1, Sec. 130 Shock Hazard Analysis. Shock hazard analysis shall determine the voltage to which personnel will be exposed, boundary requirements, and the PPE necessary in order to minimize the possibility of electric shock to personnel. What is required? 1. Determine the Operating Voltage of the System 2. Determine Shock Protection Boundaries 3. Determine the Personnel Protective Equipment
27 Page 27 of 60 How to comply with NFPA 70E? SHOCK Hazard Analysis 1. Determine the Operating Voltage. 2. Determine the Three Shock Protection Boundaries by using Table 130.4(c)(a) of NFPA 70E-2012 A. Limited Approach Boundary 10 ft for 480 V for movable energized object 3 ft 6 in. for fixed energized object B. Restricted Approach Boundary 12 in. for 480 V C. Prohibited Approach Boundary 1 in. for 480 V
28 Page 28 of 60 SHOCK Hazard How to comply with NFPA 70E? 3. Determine the Personnel Protective Equipment: NOTE: Short-Circuit Current and Clearing Time Limitations Apply for use of tables! a. Determine risk category from Table (c)(15)(a) on NFPA 70E-2012 b. Determine specific PPE & clothing from Table 130.7(c)(16) of NFPA 70E-2012
29 Flash Hazard Page 29 of 60 Ch. 1, Sec Arc Flash Hazard Analysis. An arc flash hazard analysis shall determine the arc flash boundary, the incident id energy at the working distance, and the personal protective equipment that people within the arc flash boundary shall use. How to comply with NFPA 70E for Flash Protection? 1. Determine the flash protection boundary 2. Determine the incident energy exposure level 3. Determine the protective clothing and PPE
30 Page 30 of 60 Flash Hazard How to Comply with NFPA 70E for FLASH Protection? ti 1. Determine Flash Protection Boundary: Calculate using the I Short-Circuit Amperes & the clearing time for the overcurrent protection (see Formula below & Annex D of NFPA 70E-2012 or default to the distances listed in the Table 130.7(C)(15)(a) if the I Short-Circuit Amperes & the clearing time are not exceeded! Flash Protection Boundary Formula (600 V or less) D C = [53 x MVA x t] 1/2 where Dc = Arc Flash Boundary (AFB) in Feet MVA = Transformer capacity in MVA t = clearing time in seconds Second Degree Burn Threshold h 1.2 cal/cm 2
31 Page 31 of 60 Flash Hazard Analysis 2. Determine the Incident Energy Level: Calculate incident energy exposure level for the distance between worker s face & chest from the potential arc source (18 typical) OR use 130.7(C)(15)(a) and 130.7(C)(16) Incident energy formula for Arc in a Cubic Box: E MB = D A t A [0.0093F F ] Where E MB = cal/cm 2 in 20 inch Cubic Box D A = distance from electrode in inches (typically this value would be 18 ) t A = clearing time F = I short-circuit Amperes available (range of 16 ka to 50 ka)
32 Page 32 of 60 Flash Hazard Analysis 3. Determine the Proper PPE: Once the incident id energy is determined, d the PPE has to have a rating equal to or greater than the incident energy available. Or, if the alternate method of using 130.7(C)(15)(a), then the proper PPE is selected from 130.7(C)(16) of NFPA 70E-2012 if the I Short- Circuit Amperes & the clearing time limitations are not exceeded.
33 Flash Hazard Analysis Page 33 of 60 Example 1 An electrician is to remove the covers to measure the voltage on a panelboard operating at 480 V with no arc flash analysis labels to indicate the incident energy and the I Short-Circuit Amperes & the clearing time exceeds the limitations in the Table 130.7(C)(15)(a). Table 130.7(C)(15)(a) > Hazard Risk Category (HRC) = 2 cannot be used because the I Short-Circuit Amperes & the clearing time limitations have been exceeded! d In this situation Table 130.7(C)(15)(a) could not be used to determine the HRC and would require an incident id energy analysis to be performed in accordance with Article of the 2012 NFPA 70E prior to starting any work.
34 Flash Hazard Analysis Page 34 of 60 Example 2 - An electrician is to operate a circuit breaker in the main switchgear (with all of the covers on the switchgear) to de-energize a circuit it that t is operating at 480 V for lock-out tagout and the I Short-Circuit Amperes & the clearing time limitations are not exceeded. Table 130.7(C)(15)(a) > Hazard Risk Category (HRC) = 0 (No V-Rated Gloves & No V-Rated Tools Required ) Table 130.7(C)(16) specifies the following required: Untreated Natural Fiber long-sleeve shirt & pants Safety Glasses & Hearing Protection NEXT STEP IS TO VERIFY VOLTAGE IS OFF! Electrician goes to machine disconnect to open and test for presence of voltage What is the HRC level? (Ans: 2) ELECTRICAL HOT WORK PERMIT REQUIRED? (Ans: NO)
35 Flash Hazard Analysis Page 35 of 60 Example 3 - An electrician is to operate a circuit breaker in the main switchgear (with some of the covers removed from the switchgear) to de-energize a circuit that is operating at 480 V for lock-out tagout and the I Short-Circuit Amperes & the clearing time limitations are not exceeded. d Table 130.7(C)(15)(a) > Hazard Risk Category (HRC) = 1 (No V-Rated Gloves & No V-Rated Tools Required ) Table 130.7(C)(16) specifies the following required: AR Pants & Shirt or Coveralls of at least 4 cal/cm 2 Hard Hat Arc Rated Face Shield Safety Glasses or Goggles Hearing Protection Leather Shoes Leather Gloves NEXT STEP IS TO VERIFY VOLTAGE IS OFF! Electrician goes to machine disconnect to open and test for presence of voltage What is the HRC level? (Ans: 2)
36 Flash Hazard Analysis Page 36 of 60 Example 4 - An electrician is to remove the covers on a panelboard to troubleshoot a 20 A lighting circuit that is not working. The circuit is operating at 208/120 V and the I Short-Circuit Amperes & the clearing time limitations are not exceeded. Table 130.7(C)(15)(a) > Hazard Risk Category (HRC) = 1 (V-Rated Gloves & V-Rated Tools Required ) Table 130.7(C)(10) specifies the following required: AR Pants & Shirt or Coveralls of at least 4 cal/cm 2 Hard Hat Arc Rated Face Shield Safety Glasses or Goggles Hearing Protection Leather Shoes Leather Gloves ELECTRICAL HOT WORK PERMIT REQUIRED? (Ans: NO)
37 Page 37 of 60 Flash Hazard Analysis Example 5 - An electrician i is to install a 100 A, 480 V I-Line circuit it breaker on a panelboard for a new bailer machine. If the panel is shutdown, all the lines will stop and the warehouse will be without lighting and the I Short-Circuit Amperes & the clearing time limitations are not exceeded. Table 130.7(C)(9) > Hazard Risk Category (HRC) = 2 (V-Rated Gloves & V-Rated Tools Required ) Table 130.7(C)(10) specifies the following required: AR (8 cal/cm2) Long Sleeve Shirt & Pants or AR Coveralls Hard Hat Safety Glasses or Safety Goggles Arc-Rated Face Shield w/ Flash Hood or AR Balaclava Hearing Protection Leather Gloves Leather Work Shoes ELECTRICAL HOT WORK PERMIT REQUIRED? (Ans: YES)
38 Page 38 of 60 Flash Hazard Analysis Notes are from Practical Solution Guide to Arc Flash Hazards, by Chet Davis, P.E.; Conrad St. Pierre; David Castor, P.E.; Robert Luo, PhD; and Satish Shrestha.
39 Page 39 of 60 Flash Hazard Analysis Example 2 Flash Protection Boundary Calculation Circuit using non current limiting circuit breaker Overcurrent protective device with clearing time of 6 cycles Amperes Available 480 Volt, 3 phase Main Lug Only Panel Answer D C = 10 ft This example provided by Bussmann
40 Page 40 of 60 Flash Hazard Analysis Example 2 Flash Protection Boundary Calculation Circuit using current limiting fuses 480 Volt, 3 phase Main Lug Only Panel Class J, 200 A fuse clearing time of 1/4 cycle under short circuit conditions Amperes Available 6000 Equivalent RMS Let Through Answer D C =.23 ft This example provided by Bussmann
41 Flash Hazard Analysis Page 41 of 60 Incident Energy Calculation Formula: Based on CUBIC BOX E F 2-2 MB = D B t A [0.0093F.3453F ] cal/cm E MB = Incident Energy (cal/cm 2 ) D B = Distance, (in.) [for Distances > 18 inches] A = Arc Duration,,(sec.) t A F = Bolted Fault Short Circuit Current [16KA to 50kA] This example provided by Bussmann
42 Flash Hazard Analysis Example 2 Incident Energy 18 Circuit using non current limiting circuit breaker Overcurrent protective device with clearing time of 6 cycles Page 42 of Amperes Available 480 Volt, 3 phase Main Lug Only Panel Answer E MB = cal/cm 2 This example provided by Bussmann
43 Flash Hazard Analysis Page 43 of 60 Incident Energy 18 Example 2: amps of available fault current, 480 volt 3 phase system, Non-current limiting overcurrent device 6 cycle (0.1 sec) opening time. E = MB D B t A [0.0093F F ] E MB = (18) (.1) [0.0093(41) (41) ] E MB = cal/cm 2 This example provided by Bussmann
44 Flash Hazard Analysis Example 2 Incident Energy 18 Circuit using current limiting fuses Class J, 200 A fuse clearing time of 1/4 cycle undershort circuit conditions. Page 44 of Volt, 3 phase Main Lug Only Panel Amperes Available 6000Equivalent RMSLet Through Answer E MB <.17 cal/cm 2 This example provided by Bussmann
45 Section of the 2011 NEC Requires Arc Flash Hazards Labels Page 45 of 60
46 Arc Flash Labeling Required by NEC Page 46 of Arc-Flash Hazard Warning. Electrical equipment, such as switchboards, panelboards, industrial control panels, meter socket enclosures, and motor control centers, that are in other than dwelling units, and are likely to require examination, adjustment, servicing, or maintenance while energized shall be field marked to warn qualified persons of potential electric arc flash hazards. The marking shall be located so as to be clearly l visible ibl to qualified persons before examination, adjustment, servicing, or maintenance of the equipment. Also see Informational Notes 1 and 2 for additional information. Reprinted from NEC 2011
47 Page 47 of 60 Arc Flash Labeling by NEC & NFPA 70E Minimum Requirement! WARNING Arc Flash Hazard & 480 V Shock Hazard: 1) PPE/HRC Level 2 Required 2) Arc Flash Boundary is 30 Generic labels prior to September 30, 2011 are acceptable if they at least have the incident energy or required PPE/HRC level.
48 Page 48 of 60 Arc Flash Labeling Required by NEC & NFPA 70E! WARNING Arc Flash and Shock Hazard Appropriate PPE Required 24 inch Flash Hazard Boundary 3 cal/cm 2 Flash Hazard at 18 inches HRC 1 PPE Level, AR Pants & Shirt or Coveralls (4 cal/cm 2 ) Hearing) Protection Hard Hat Safety Glasses Face Shield 480 VAC Shock Hazard when 42 inch Limited Approach 12 inch Restricted Approach V Class 00 Gloves 1 inch Prohibited Approach V Class 00 Gloves Equipment Name: Pump # 1 Starter
49 Page 49 of 60 What are the OSHA Regulations and NFPA 70E Requirements for Working on Live Equipment?
50 NFPA 70 E: Safety in Workplace OSHA 29CFR & 29CFR Page 50 of 60 These two paragraphs are very similar, but apply differently. It is important that you realize that Electrical Safety applies wherever you are working. 29CFR 1910 applies to the General Industry and 29CFR 1926 applies to the Construction Industry. We may quote an article from 29CFR 1910 but due to the parallel article in 29CFR 1926 the information presented still applies to the Construction Industry.
51 NFPA 70E: Safety in Workplace OSHA 29CFR 1910 Subpart S & 29CFR 1926 Subpart K Page 51 of 60 Before we go any further, it is important for you to understand a few important definitions: - Qualified Worker One who has received training in and has demonstrated skills and knowledge in the construction and operation of electric equipment and installations and the hazards involved. (Qualification is dependent on several factors, such as different equipment, systems and/or voltages qualified to work on. A qualified worker could be qualified at a certain level or on a certain voltage, etc. While working under the direct supervision of a qualified worker, and would be considered qualified). -- Unqualified Worker One who is not qualified, has not had training, or does not possess the experience with the equipment, systems, and/or voltage to be worked on.
52 Page 52 of 60 NFPA 70E: Safety in Workplace OSHA 29CFR 1910 Subpart S & 29CFR 1926 Subpart K Before we go any further, it is important for you to understand a few important definitions: - Guarded Covered, fenced, enclosed, or otherwise protected by means of suitable covers or casings, barrier rails or screens, mates or platforms designed to minimize the possibility, under normal conditions, of dangerous approach or accidental contact by persons or objects. Note: Wires which are insulated, but not otherwise protected are not considered as guarded.
53 NFPA 70 E: Safety in Workplace OSHA 29CFR & NFPA 70E Page 53 of 60 Qualified electrical workers shall not be asked to work on equipment that is hot or live except for these demonstrable reasons: 1. Deenergizing introduces additional or increased hazards Interruption of life support equipment Deactivation of emergency alarm systems Cutting ventilation to a hazardous location Or 2. Infeasible due to equipment design or operational limitations Voltage testing for diagnostics Start up testing Or 3. Live parts that operate at less than 50 volts to ground need not be deenergized if there will be no increased exposure to electrical burns or to explosion due to electric arcs.
54 NFPA 70 E: Safety in Workplace OSHA 29 CFR (a)(1) & NFPA 70E Page 54 of 60 This article disallows work in such close proximity to any part of an energized electrical power circuit that the employee could contact in the course of their work, unless the employee is protected against electric shock by deenergizing and grounding the circuit, or guarding g it effectively by insulation or other means.
55 Safety-Related Work Practices Selection & use of work practices Page 55 of 60 (a) General. Safety-related work practices shall be employed to prevent electric shock or other injuries resulting from either direct or indirect electrical contact, when work is performed near or on equipment or circuits which are or may be energized. The specific safety-related work practices shall be consistent with the nature and extent of the associated electrical hazards.
56 Safety-Related Work Practices Safe guards for personnel protection Page 56 of 60 (a) (2) (ii) Protective shields, protective barriers, or insulating materials shall be used to protect each employee from shock, burns, or other electrically related injuries while that employee is working near exposed energized parts which might be accidentally contacted or where dangerous electric heating or arcing might occur. When normally enclosed live parts are exposed for maintenance or repair, they shall be guarded to protect unqualified persons from contact with live parts.
57 Who is Responsible for Safety? Page 57 of 60 The Employer is responsible for OSHA requirements Electrical Safety Program Safety Policies and Procedures Safety Training and Retraining The Employee is responsible for Implementing employer s safety procedures The Owner and Contractors are both responsible to coordinate and document hazards and safety procedures Contractors on site with Owner
58 Page 58 of 60 Response to an Electrical Accident Personnel that are trained in CPR & AEDs should be identified and available when work near or on energized parts is being performed and they shall be trained annually.
59 Responses to an Electrical Accident Page 59 of 60 The FIRST step must be to: TURN OFF THE POWER and/or attempt to remove the victim from the power with dry wood or other insulating type of materials to remove the hazard! SECOND step: CALL 911 or the local emergency number THIRD step: Administer CPR & First Aid if needed Note: 29CFR (c) requires that in the absence of a reasonably accessible medical professional, that someone with valid CPR/First-aid training be on site.
60 What is the best way to prevent the hazards of electricity? Page 60 of 60 Stop Think Options Protection - Before Action - Risks/Hazards - LOTO - Proper PPE Avoiding energized circuits is the safest way!
Understanding Arc Flash Presented by Eddie F. Jones, PE 1 2 3 4 5 Five to 10 arc flash explosions occur in electric equipment every day in the United States. This number does not include cases in which
The Other Hazard of Electricity Larren Elliott Ph.D. Lindsay Polic, CSP, REHS Presenters Larren Elliott Ph.D. EORM Electrical Safety Service Partner 45 years practical and hands-on industrial experience
BRANDON AND CLARK INC. // SCOTT W. CLARK, P.E. ELECTRICAL CONTINUING EDUCATION ARC FLASH - NFPA 70E Training is not a substitute for following corporate safety guidelines. Always refer to the latest safety
2012 NFPA 70E Ten Most Important Changes John A. DeDad GE Energy Management 41 Woodford Avenue Plainville, CT 06062 USA 860-747-7344 John.firstname.lastname@example.org Abstract The 2012 Edition of NFPA 70E, Standard for
What s up with Arc Flash? Presented by Mark Haskins, CSP Practical Safety Solutions, LLC CONN OSHA Breakfast Roundtable February 18, 2014 2014 Practical Safety Solutions, LLC What is Arc Flash? Definition
misconceptions about arc-flash hazard assessments There are some common misconceptions about Arc-Flash Hazard Assessments which reduce the effectiveness of the Assessments and can increase electrical hazards.
Arc Flash Avoidance and its Application to Overhead Traveling Cranes Whitepaper August 2012 Jason Wellnitz, Controls Product Manager Material Handling Numerous technical papers, bulletins, magazine articles
SAFE ELECTRICAL WORK PRACTICES & 2015 NFPA 70E This easy-to-use Leader s Guide is provided to assist in conducting a successful presentation. Featured are: INTRODUCTION: A brief description of the program
NFPA 70E Updates Affect Your Most Valuable Assets EXECUTIVE SUMMARY Electrocution is a well-known hazard associated with direct contact with electrical energy. According to the U.S. Department of Labor,
NFPA 70E 2012 Rolls Out New Electrical Safety Requirements Affecting Data Centers A market position paper from the experts in Business-Critical Continuity TM Executive Summary Electrocutions are the fourth
ARC FLASH HAZARD OVERVIEW Presented August 13, 2015 WWOA Lake Michigan District by Mead & Hunt, Inc. ARC FLASH EXPERIENCE Christopher J. DeWaal, MS, MEM, PE, LEED AP, HACCP How did I get involved? A client
IMPLEMENTING THE NEW ELECTRICAL SAFETY REQUIREMENTS Paul A Zoubek, CSP, CIH Occupational Services, Inc. San Diego, CA 619-861 861-0612 email@example.com OCCUPATIONAL SERVICES, INC. BACKGROUND Update Update
Introduction to Arc Flash Worker Training of Electrical Hazards Including Arc Flash SH-16614-7 This material was produced under grant number SH-16614-7 from the Occupational Safety and Health Administration,
Roadmap to Compliance with NFPA 70E Arc Flash Requirements TAHFM Interlink 2015 March 30, 2015 Antony Parsons, Ph.D., P.E. Schneider Electric Engineering Services 1 2 How do we get to Reliable Power? >
California State University-Fullerton 800 N. State College Blvd. Fullerton, CA 92831 Prepared by: Paul A Zoubek, CSP, CIH President/Principal Consultant Zoubek Consulting, LLC 3737 Granada Ave. San Diego,
Analyzing Electrical Hazards in the Workplace By Dennis K. Neitzel, CPE AVO Training Institute, Inc. The need for analyzing electrical hazards in the workplace has been recognized by a small segment of
Common Electrical Hazards in the Workplace Including Arc Flash Presented by Ken Cohen, PhD, PE & CIH (Ret.) 1 What s New In February 1972, OSHA incorporated the 1971 edition of the National Fire Protection
2013WWOA Conference Technical Conference Program Understanding Arc-Flash Hazards, Its Implications on Operations and Solutions that Mitigate Such Exposure Presented by Jerry Baskin Senior Product Manager
Electrical Safety - Construction OSHA Office of Training & Education 1 Electricity - The Dangers About 5 workers are electrocuted every week Causes 12% of young worker workplace deaths Takes very little
Arc Flash Mitigation Remote Racking and Switching for Arc Flash danger mitigation in distribution class switchgear. Distance is Safety We will discuss through examples of actual occurrences and possible
Written Program ELECTRICAL SAFETY Based on OSHA Subpart S and NFPA 70E Standards Revised November 2012 Disclaimer The presentations and program provided by Workplace Safety Solutions, Inc. are based on
3053 Electrical Safety Training Program Course Outline The following outline summarizes the major points of information presented in the program. The outline can be used to review the program before conducting
Learning Objectives After reviewing this material, the student will be able to: 1. Identify the installations that fall under the scope of the 2015 edition of NFPA 70E. 2. Identify the assessments required
INTRODUCTION TO ELECTRICAL SAFETY At the end of this module, you will be able to Recognize key statistics relating to electrical injuries. Recognize OSHA regulations and other standards relating to electrical
May 2013 NFPA 70E 2012 20 Most Frequently Asked Questions By Michael Fontaine Copyright 2013 National Fire Protection Association. All rights reserved. Ask an NFPA Expert The Technical Questions Service
provided by: Any work conducted near live electrical circuits poses its share of risk and electrical measurement jobs are no exception. In commercial and industrial settings today, electricians commonly
Department of the Air Force HQ AEDC (AFMC) Arnold AFB, TN 37389 Safety, Health, and Environmental Standard Title: Standard.: Low-Voltage Electrical Safety-Related Work Practices B6 Effective Date: 03/30/2015
CALIFORNIA STATE UNIVERSITY, STANISLAUS Electrical Safety Program LAST UPDATED 6/2/11 CALIFORNIA STATE UNIVERSITY, STANISLAUS ELECTRICAL SAFETY PROGRAM TABLE OF CONTENTS 1.0 Purpose......2 2.0 Scope......2
Florida State University - Center for Advanced Power Systems Electrical Safety Policy for Researchers Revision 1 STATEMENT: The purpose of this policy is to provide a safe work environment for personnel,
An Overview of Arc Flash Risk Assessments Randy Heard, PE, Larson Design Group Abstract Recently, arc flash risk assessments have become more challenging as a result of additional researching and modelling
SALISBURY ASSESSMENT SOLUTIONS Electrical engineering services for a safe and compliant workplace Electrical Safety Program Assessments - Electrical Safety Training Arc Flash Risk Assessments - Power Systems
Definitions 100% Rule Work on or near energized parts must be performed only after all participating qualified electrical workers are in 100% agreement on the work to be completed, on the sequence in which
PLANT OPERATIONS ELECTRICAL SAFETY PROGRAM Prepared by the Department of Occupational Safety & Environmental Health PLANT ELECTRICAL SAFETY PROGRAM TABLE OF CONTENTS Page I. Purpose and Scope 1 II. Definitions
OSHA and NFPA 70 Understanding NFPA 70 and its Implications in Electrical Inspections 2010 By: Martin Robinson, Level III Thermographer 18-1030-0005 Rev. A The National Fire Protection Association (NFPA)
FlashGard TM Motor Control Center Electrical Safety Hazards Design Philosophy The Product 2008 Eaton Corporation. All rights reserved. Research studies say. Five to 10 arc flash explosions occur in electrical
High Voltage Electric Safety Safety Precautions for Working on or near High Voltage Power Lines Introduction Pam Tompkins, CSP, CUSA President, SET Solutions, LLC Ballentine, SC Many employees are exposed
Integrating SPDs in Switchgear & Switchboards Causes More Problems than it Solves White Paper July 2010 Integrating surge protective devices (SPD) into distribution equipment (i.e. switchgear, switchboards,
Electrical Safety Solutions: CSA Z462 2012 Edition from Schneider Electric Canada Services & Projects Make the most of your energy SM Shock and electrocution have long been recognized as a serious workplace
NOT MEASUREMENT SENSITIVE DOE-HDBK-1092-2009 DOE HANDBOOK ELECTRICAL SAFETY U.S. Department of Energy Washington, D.C. 20585 AREA SAFT DISTRIBUTION STATEMENT A. Approved for public release; distribution
A USERS GUIDE TO ARC RESISTANT LOW VOLTAGE SWITCHGEAR & MOTOR CONTROL ANALYTICAL COMPARISON VS ARC FLASH TEST RESULTS By: Gabriel Arce, ABB, San Luis Potosi, Mexico Casey McCollum, ABB, Houston, TX John
Part 1 System Modeling & Studies for Existing Systems Operation Technology, Inc. Copyright 2009 Result of rapid release of energy due to an arcing fault between two conductors. Bus voltages > 208V Temperatures
ABB Arc Flash Protection Portfolio - Features and Applications Karl Smith M.S.E.E, P.E Product Application Specialist Overview Introduction to ABB arc flash products highlighting new features and innovations
Common Arc Flash Hazard Myths Over the last five years, the arc flash hazard (AFH) phenomenon has taken industry by storm. It is hoped that the positive result of this exposure will be increased accuracy
Understanding 2015 Changes to NFPA 70E Safety-related work practices and maintenance requirements mandate more robust electrical safety programs for commercial and industrial facilities Executive Summary
Disclaimer Electrical Safety Training for the Manufacturing Industry This material was produced under grant number SH 20999 10 60 F 21 from the Occupational Safety and Health Administration, U.S. Department
Understanding 2015 Changes to NFPA 70E Safety-related work practices and maintenance requirements mandate more robust electrical safety programs for data centers Executive Summary Every three years, the
FACILITIES ELECTRIC SUBCONTRACTORS SAFETY MANUAL GENERAL DYNAMICS ELECTRIC BOAT CORPORATION June 28, 2011* *All changes as of this date are noted in red. 1 of 9 Table of Contents 1. Requirements 2. Tools
Why Construction Workers are Getting Electrocuted Michael McCann, PhD, CIH Director of Safety and Ergonomics The Center to Protect Workers Rights firstname.lastname@example.org Causes of Death in Construction, 1992-98
ELECTRICAL SAFETY RISK ASSESSMENT The intent of this procedure is to perform a risk assessment, which includes a review of the electrical hazards, the associated foreseeable tasks, and the protective measures
INDUSTRY WIDE LABOR-MANAGEMENT SAFETY COMMITTEE SAFETY BULLETIN #23 GUIDELINES FOR WORKING WITH PORTABLE POWER DISTRIBUTION SYSTEMS AND OTHER ELECTRICAL EQUIPMENT "ADDENDUM C" WORKING WITH 480 VOLT SYSTEMS
Electrical Safety in the Workplace NFPA 70 E Presented by Sabine Mueller What Made Sabine Choose Such a DRY Topic? Ulterior Motive Metso Mueller Engineering has been visiting many scrap yards two or more
Arc Flash Energy Mitigation Techniques When short circuits occur on an electrical distribution system, an arc flash event usually forms. These arc flash events can cause dangerous and potentially fatal
Midwest Healthcare Engineering Conference and Trade Show 2012 Indianapolis, Indiana Arc Flash Overview An engineering solutions company November 7, 2012 Agenda Introductions Arc Flash defined History and
January 3, 2001 TEHNIAL BULLETIN 010 Electrical Safety in the Marine Environment Approach Boundaries Electrical Safety in the Marine Environment presented by adick orporation 1 Overview Electrical power
A Guide to Performing An Arc Flash Hazard Assessment Using Power Analysis Software Abstract: The nature of explosive equipment failures, and the rate of serious burn injuries in the electrical industry
Dielectric Withstand Testing in a Production Environment Performing a routine product safety test should not in itself represent a shock hazard to the operator who is conducting the test, yet anytime you
Appendix B-2 - Electrical Safety In Design Final Report TECHNOLOGIES THAT REDUCE LIKELIHOOD OF INJURY FROM ELECTRICAL HAZARDS, INCLUDING SHOCK, ARC FLASH AND FIRE The following are technologies that reduce
RISK MITIGATION for ELECTRICAL WORK Feb 2013 San Diego CA Agenda I. RISK Define the Risks Arc Flash Review II. MITIGATION 3 Easy Steps New Designs Vs. Existing Systems III. DUKE UNIVERSITY EXAMPLE I. Risk
Understanding GFCIs Developed by the NEMA 5PP Personnel Protection Technical Committee The Association of Electrical and What Is to Be Covered? Electrical Shock - Why Have GFCIs? How GFCI s Operate Proper
Job Site Electrical Safety A Matter of Life and Death Scott Forsyth, PE Senior Engineer Johnson Controls Performing the Job Right and on Time is Top Priority!!!! Right? Wrong!!!! Performing the Job Safely
INTRODUCTION ELECTRICAL SAFETY / ARC FLASH PROGRAM This program establishes minimum standards to prevent hazardous electrical exposures to personnel and ensure compliance with regulatory requirements applicable
CONVENTION SESSION HANDOUT Choosing the Best Solution for Reducing Arc Energy Terry L. Schiazza, Business Development Manager Square D / Schneider Electric SESSION #11 Independent Electrical Contractors
Types of electrical injuries Electrical injury is a term for all injuries caused by contact with electrical energy. Electrical contact can cause a wide variety of injuries involving most organ systems.
Arc Flash Hazard Labeling Do s and Don ts! WARNING Arc Flash and Shock Hazard Appropriate PPE Required 11' - 3" Flash Hazard Boundary 9 cal/cm2 Flash Hazard at 18 inches #3 PPE Level Cotton underwear plus
ARTICLE 110 Requirements for Electrical Installations INTRODUCTION TO ARTICLE 110 REQUIREMENTS FOR ELECTRICAL INSTALLATIONS Article 110 sets the stage for how you ll implement the rest of the NEC. This
Safety By Design Strategies for Electrical Contractors Introduction Engineering and system design significantly impact worker safety System design provides opportunity to eliminate/minimize workers exposure
Instruction Sheet 07-2013 Installation Instructions for Alarm Module Kit A043F059 1 Introduction The information contained within is based on information available at the time of going to print. In line
**Printed copies of this document are uncontrolled, visit the EHS website at http://www.wright.edu/admin/ehs/ for the latest revision** I. Purpose Ensure the safety of employees who may work on or near
ELECTRICAL SAFETY Introduction The following sections provide general safety guidelines and procedures for electrical safety. This chapter covers the following topics: TOPIC PAGE General Electrical Safety
Low Voltage Circuit Breakers Arc flash hazards Index Low voltage selectivity with ABB circuit breakers Introduction... 2 Definitions, acronyms and terms used... 3 Electrical arcs and their dangerous effects
ELECTRICAL & ARC FLASH SAFETY PROGRAM ADOPTED VERSIO 2, SEPTEMBER 26, 2012 Supercedes all prior versions A. COMMITTEE OVERSIGHT OF PROGRAM The University of Montana ( University ) recognizes the importance
Electrical Safety Health Worker Safety Training Module 6 Topics Introduction Key definitions Causes of electric shock Dangers of electric shock Electrical burns The Electrical Safety Model Introduction
ARC Flash Boundary & NFPA-70E Requirements PPE Program 1. Purpose and Scope The Arc Flash Boundary - PPE Program was developed to minimize the risk to AMS employees from safety and health hazards in the
Campus Safety Procedure Electrical Safety Electrical Safety Procedures 1.0 Purpose The purpose of this procedure is to provide guidance in the performance of work on electrical systems, wiring, and equipment
Cal/OSHA Guide to Electrical Safety Research and Education Division of Occupational Safety and Health This guide is not meant to be either a substitute for or a legal interpretation of the occupational
Electrical Safety of Medical Equipment Hasan Al-Nashash School of Engineering American University of Sharjah (AUS) 1 Are you aware Electrocutions are the 5th leading cause of accidental death in the U.S.
The Three A s of Arc Flash Gary H. Fox, PE Senior Specification Engineer In 2007 GE conducted a survey of industry professionals working in facilities related to the oil and gas industry, pulp and paper
Flame Resistance and Arc Flash Review of Industry Consensus Standards for Personal Protective Equipment Gary S. Kephart Environment, Safety & Health Supervisor Bechtel Jacobs Co LLC Genesis of the Presentation
How to Build a Safe and Effective Electrical Maintenance Program The Business Case Ask Yourself the Following Questions: What is your dependence on electrical energy and control systems? What are the consequences
What are the basic electrical safety issues and remedies in solar photovoltaic installations? Presented by: Behzad Eghtesady City of Los Angeles Department of Building and Safety Topics Covered Photovoltaic
SKM Arc Flash Line vs. Load The option of choosing the line-side or the load-side arc flash incident energy for arc flash labels is an important decision when performing an arc flash hazard analysis. When
BWC Division of Safety and Hygiene A SAMPLE LOCKOUT/TAGOUT PROCEDURE A good Lockout/Tagout Procedure, at a minimum, should contain the following elements: 1. All maintenance personnel shall be provided
Understanding the Standards Surrounding Arc Flash Hazards and Arc Resistant Equipment 1 Rev 5058-CO900E This presentation contains many hidden slides that are provided for the presenters information and/or