1 N8MXL Product Specifications 80% ECM Single Stage Heating Furnace EASIER TO SELL 80% AFUE Flame roll out sensors standard Category I venting Blocked vent switch 24 VAC humidifier terminal Electronic air cleaner terminal N8MXL model California NOx approved Certified to leak 2 percent or less of nominal air conditioning CFM delivered when pressurized to 1-inch Water Gauge with all present air inlets, air outlets, and condensate drain port(s) sealed TOUGHER ECM blower motor Adjustable heating blower OFF delay Factory set blower ON delay RPJ aluminized steel heat exchanger High temperature limit control prevents overheating Direct ignition with Silicon Nitride ignitor One piece prepainted steel cabinet QUIETER In shot burners Insulated blower compartment EASIER TO INSTALL AND SERVICE 33 1/3 (847mm) high, for ease of installation Innovative knobs for easy door removal and secure attachment Factory shipped for natural gas, with propane gas conversion kits available Four position upflow/downflow/horizontal (left/right) installation Three position vent elbow capability Through the casing flue pipe for counterflow applications Common venting with other Category I appliances Masonry chimney adapter available Self diagnostics Slide out blower assembly WARRANTY * 20 year heat exchanger limited warranty 10 year parts limited warranty with timely registration 5 year parts limited warranty if not registered within 90 days of original installation * For residential applications only. See warranty certificate for complete details and restrictions, including warranty coverage for other applications. Model Input (MBTUH) Efficiency AFUE Cooling Capacity CFM in. w.c. (125 Pa) Illustrations and photographs are only representative. Some product models may vary.! WARNING This furnace is not designed for use in mobile homes, trailers, or recreational vehicles. Such use could result in property damage and/or death. Dimensions H x W x D Inches (Millimeters) Use of the AHRI Certified TM Mark indicates a manufacturer s participation in the program. For verification of certification for individual products, go to Shipping Wt. Lbs (Kg) N8MXL ,000 80% /3 x 14 3/16 x 29 (847 x 360 x 737) 104 (47) N8MXL ,000 80% /3 x 17 1/2 x 29 (847 x 445 x 737) 126 (57) N8MXL ,000 80% /3 x 17 1/2 x 29 (847 x 445 x 737) 126 (57) N8MXL ,000 80% /3 x 17 1/2 x 29 (847 x 445 x 737) 127 (58) N8MXL ,000 80% /3 x 21 x 29 (847 x 533 x 737) 140 (64) N8MXL ,000 80% /3 x 21 x 29 (847 x 533 x 737) 152 (69) N8MXL ,000 80% /3 x 24 1/2 x 29 (847 x 622 x 737) 163 (74) Specifications are subject to change without notice. 6/18/15
2 MODEL NUMBER IDENTIFICATION GUIDE DIGIT POSITION ,7,8 9,10 11, N 8 M X L A 1 N = Entry 8 = 80% AFUE EFFICIENCY M = Multiposition POSITION V = Variable Speed Blower Motor ECM X = ECM Blower Motor S = Single stage T = Two stage TYPE N = Standard L = Low NOx FEATURE 045 = 44,000 BTU/hr 070 = 66,000 BTU/hr 090 = 88,000 BTU/hr 110 = 110,000 BTU/hr 135 = 132,000 BTU/hr HEAT INPUT 14 = 14 3/16 17 = 17 1/2 21 = = 24 1/2 CABINET WIDTH 12 = 1200 CFM 14 = 1400 CFM 16 = 1600 CFM 20 = 2000 CFM 22 = 2200 CFM NOMINAL MAXIMUM COOLING IN. W.C. SALES (MAJOR) REVISION DIGIT ENGINEERING (MINOR) REVISION DIGIT ECM-Electronically Commutated Motor ACCESSORIES PART NUMBER IDENTIFICATION GUIDE DIGIT POSITION , 6, 7 8, 9 10, 11 N A H A DH N = Non Branded BRANDING A = Accessory H = Heating A = Original B = 2nd Generation Product Identifier Number Package Quantity Type of Kit (Example: DH = Draft Hood Chimney Adapter) PRODUCT GROUP KIT USAGE MAJOR SERIES 2 Specifications subject to change without notice.
3 PHYSICAL DATA NATURAL GAS A A A A A A A INPUT BTUH* OUTPUT CAPACITY BTUH* (Nonweatherized ICS) AFUE * Upflow 44,000 66,000 66,000 88,000 88, , ,000 Hz/Downflow 42,000 63,000 63,000 84,000 84, , ,000 Upflow 36,000 54,000 54,000 71,000 72,000 90, ,000 Hz/Downflow 34,000 51,000 51,000 68,000 68,000 85, ,000 Nonweatherized ICS TRANSFORMER (24 volt) 40 VA CERTIFIED TEMP RISE RANGE F ( C) (17 33) (19 36) (14 31) (22 39) (19 36) (17 33) (22 39) CERTIFIED EXT Heating STATIC PRESSURE Cooling AIRFLOW CFM Heating Cooling LIMIT CONTROL SPST HEATING BLOWER CONTROL Solid State Time Operation BURNERS (Monoport) GAS CONNECTION SIZE Minimum Inlet Pressure (in. w.c.) Maximum Inlet Pressure (in. w.c.) IGNITION DEVICE COOLING CAPACITY CFM range (.5 in. w.c.) 1/2 inch NPT White Rodgers 4.5 (Natural Gas) 13.6 (Natural Gas) Hot Surface * Gas input ratings are certified for elevations to 2000 ft. (610 M). In USA, for elevations above 2000 ft. (610 M), reduce ratings 4 percent for each 1000 ft. (305 M) above sea level. Refer to National Fuel Gas Code NFPA 54/ANSI Z Table F.4 or furnace Installation Instructions. Capacity in accordance with U.S. Government DOE test procedures. Airflow shown is for bottom only return-air supply in comfort mode (as shipped). For air delivery above 1800 CFM, see Air Delivery Table for other options. A filter is required for each return air supply. ICS Isolated Combustion System GAS VALVE (Redundant) Manufacturer ELECTRICAL DATA Volts Operating Voltage* Range Minimum Maximum Maximum FURNACE MODEL Hertz Phase Maximum Minimum Maximum Unit Amps Unit Ampacity# Wire Size AWG Wire Length ft (m) Fuse or CKT BKR Amps (14.3) (14.3) (8.2) (10.1) (10.1) (10.1) (7.9) 15.0 * Permissible limits of the voltage range at which the unit operates satisfactorily. Time delay type is recommended. Length shown is as measured 1 way along wire path between unit and service panel for maximum 2 percent voltage drop. Specifications subject to change without notice. 3
4 SCALE 3: 16 PRODUCT SPECIFICATIONS UNIT DIMENSIONS 5 15/16 [150.7] 1 15/16 [49.2] ACCESSORY 1/2 [12.7] THERMOSTAT WIRE ENTRY ACCESSORY 21 5/8 [549.5] BOTTOM INLET 33 1/4 [843.9] 28 3/8 [721.2] 29 [736.9] 9 [250.7] 8 7/16 [213.5] 5 1/2 [140.3] 26 1/8 [663.6] SECTION Z-Z TOP VIEW AIR FLOW 5 1/8 [130.5] 6 1/8 [155.7] C 2 1/16 [51.6] 1 11/16 [43.5] C ACCESSORY (2) 3 7/16 [86.8] 5 [148.5] JUNCTION BOX LOCATION 1 3/4 [44.5] GAS ENTRY 2 5/16  NOTES: 1. Doors may vary by model. 2. Two additional -in. (22 mm) diameter holes are located in the top plate. 3. Minimum return-air openings at furnace, based on metal duct. If flex duct is used, see flex duct manufacturer's recommendations for equivalent diameters. a. For 800 CFM-16-in. (406 mm) round or 14 1/2 x 12-in. (368 x 305 mm) rectangle. b. For 1200 CFM-20-in. (508 mm) round or 14 1/2 x 19 1/2-in. (368 x 495 mm) rectangle. c. For 1600 CFM-22-in. (559 mm) round or 14 1/2 x 22 1/16-in. (368 x 560mm) rectangle. d. Return air above 1800 CFM may require one of the following configurations: 2 sides, 1 side and a bottom or bottom only for return air. See Air Delivery table in this document for specific use to allow for sufficient airflow to the furnace. AIR FLOW 19 [481.7] OUTLET 22 15/16 [582.6] 22 3/4 [577.8] 22 9/16 [573.1] 21 5/8 [549.3] 19 3/4 [501.6] A B 9 9/16 [243.3] 4 13/16 [122.2] 1/2 [12.7] THERMOSTAT WIRE ENTRY 1 3/4 [44.5] GAS ENTRY 7 13/16 [197.8] 9 11/16 [245.4] 11 7/16 [290.7] 29 9/16 [750.7] 27 3/4 [704.7] ALTERNATE JUNCTION BOX LOCATION 27 3/4 [704.7] ACCESSORY Z ACCESSORY Z 14 [337.3] (BOTH SIDES) D BOTTOM RETURN WIDTH NOTE: ALL DIMENSIONS IN INCH [MM] 3/4 [19.1] KNOCK OUTS FOR VENTING (5 PLACES) 22 1/16  SIDE INLET (BOTH SIDES) 26 1/16 [662.0] 26 7/16 [671.5] 1 [25.4] 1 1/4 [31.8] SD A B C D TOP AND BOTTOM OUTLET WIDTH OUTLET IN (MM) IN (MM) CABINET WIDTH IN (MM) BOTTOM INLET WIDTH IN (MM) VENT CONNECTION SIZE SHIP WT N8MXL LB (KG) A 14 3/16 (360) 12 9/16 (319) 9 5/16 (237) 12 11/16 (322) (47) A 17 1/2 (445) 15 (403) 11 9/16 (294) 16 1/8 (410) (57) A 17 1/2 (445) 15 (403) 11 9/16 (294) 16 1/8 (410) (57) A 17 1/2 (445) 15 (403) 11 9/16 (294) 16 1/8 (410) (58) A 21 (533) 19 3/8 (492) 13 5/16 (338) 19 1/2 (495) (64) A 21 (533) 19 3/8 (492) 13 5/16 (338) 19 1/2 (495) (69) A 24 1/2 (622) 22 (581) 15 1/16 (383) 23 (584) (74) 135 Btu/h size furnaces require 5 inch (127 mm) vents. Use a 4-5 inch ( mm) vent adaptor between furnace and vent stack. See installation instructions for complete installation requirements. 4 Specifications subject to change without notice.
5 DOWNFLOW VENT CONFIGURATIONS SEE NOTES: 1,2,4,5,7,8,9 DOWNFLOW CONTINUTED A02061 SEE NOTES: 1,2,4,5,6,7,8,9 A02062 SEE NOTES: 1,2,3,4,5,7,8,9 A02063 UPFLOW VENT CONFIGURATIONS SEE NOTES:1,2,3,4,5,7,8,9 A02060 SEE NOTES: 1,2,4,7,8,9 A02058 SEE NOTES: 1,2,3,4,7,8,9 A02059 HORIZONTAL RIGHT VENT CONFIGURATIONS SEE NOTES: 1,2,4,5,7,8,9 A02070 HORIZONTAL LEFT VENT CONFIGURATIONS SEE NOTES: 1,2,4,5,7,8,9 A02068 SEE NOTES: 1,2,4,7,8,9 A02069 SEE NOTES: 1,2,4,7,8,9 A02064 HORIZONTAL LEFT VENT CONFIGURATIONS SEE NOTES: 1,2,4,5,7,8,9 A02065 SEE NOTES: 1,2,4,5,7,8,9 A02066 SEE NOTES: 1,2,4,5,7,8,9 A02067 Specifications subject to change without notice. 5
6 Venting Notes 1. For common vent, vent connector sizing and vent material: United States use the NFGC. 2. Immediately increase to 5 inch (127 mm) or 6 inch (152 mm) vent connector outside furnace casing when 5 inch (127 mm) vent connector is required, refer to Note 1 above. 3. Side outlet vent for upflow and downflow installations must use Type B vent immediately after exiting the furnace, except when Downflow Vent Guard Kit, is used in the downflow position. 4. Type B vent where required, refer to Note 1 above inch single wall (26 ga. min.) vent must be used inside furnace casing and when the Downflow Vent Guard Kit is used external to the furnace. 6. Accessory Downflow Vent Guard Kit, required in downflow installations with lower vent configuration. 7. Chimney Adapter Kit may be required for exterior masonry chimney applications. Refer to Chimney Adapter Kit, for sizing and complete application details. 8. Secure vent connector to furnace elbow with (2) corrosion resistant sheet metal screws, spaced approximately 180 apart. 9. Secure all other single wall vent connector joints with (3) corrosion resistant screws spaced approximately 120 apart. Secure Type B vent connectors per vent connector manufacturer s recommendations. MINIMUM CLEARANCES TO COMBUSTIBLE MATERIALS FOR ALL UNITS This forced air furnace is equipped for use with natural gas at altitudes 0 10,000 ft (0 3,050m). An accessory kit, supplied by the manufacturer, shall be used to convert to propane gas use or may be required for some natural gas applications. This furnace is for indoor installation in a building constructed on site. The furnace may be installed on combustible flooring in alcove or closet at minimum clearance as indicated by the diagram from combustible material. This furnace may be used with a Type B 1 Vent and may be vented in common with other gas fired appliances. This furnace is approved for UPFLOW, DOWNFLOW, and HORIZONTAL installations. Downflow Positions: Installation on non combustible floors only. For Installation on combustible flooring only when installed on special base or coil assembly. 18 inch front clearance required for alcove. * Indicate supply or return sides when furnace is in the horizontal position. Line contact only permissible between lines formed by intersections of the Top and two Sides of the furnace jacket, and building joists, studs or framing. BLOWER PERFORMANCE DATA N8MXL DIRECT-DRIVE MOTOR Hp (ECM) 1/3 1/3 3/4 1/2 1/2 1 3/4 MOTOR FULL LOAD AMPS RPM (Nominal) Speeds BLOWER WHEEL DIAMETER WIDTHS in (mm) 10 x 6 ( ) 11 x 8 (279 x 203) 11 x 8 (279 x 203) 11 x 8 (279 x 203) 10 x 10 (254 x x 11 (279 x x 11 (279 x Specifications subject to change without notice.
7 UNIT SIZE WIRE- LEAD COLOR SPEED AIR DELIVERY CFM (with filter)* Test Airflow Various External Static Pressures (in. w.c.) Gray Yellow Orange Blue Red Gray Yellow Blue Orange Red Gray Yellow Blue Orange Red Gray Yellow Blue Orange Red Gray Blue Yellow Orange Red Gray Yellow Blue Orange Red Gray Blue Yellow Orange Red NOTES: 1. A filter is required for each return air inlet. Airflow performance includes a 3/4 in. (19 mm) washable filter media such as contained in factory authorized accessory filter rack. See accessory list. To determine airflow performance without this filter, assume an additional 0.1 in. W.C. available external static pressure. 2. ADJUST THE BLOWER SPEED TAPS AS NECESSARY FOR THE PROPER AIR TEMPERATURE RISE FOR EACH INSTALLATION. 3. Highlighted areas indicate airflow range is beyond the range allowed for heating. THESE AIRFLOW RANGES MAY ONLY BE USED FOR COOLING. Indicates unstable operating conditions. Specifications subject to change without notice. 7
8 ACCESSORIES PART NUMBER DESCRIPTION NAHB00501FF External Bottom Filter Rack, 14 inch (14 x 25 inch washable filter included) X NAHB00601FF External Bottom Filter Rack, 17 inch (16 x 25 inch washable filter included) X X X NAHB00701FF External Bottom Filter Rack, 21 inch (20 x 25 inch washable filter included) X X NAHB00801FF External Bottom Filter Rack, 24 inch (24 x 25 inch washable filter included X NAHA00506FB Washable filter, 1 inch 16 x 25 (6 pack) X X X X NAHA00706FB Washable filter, 1 inch 24 x 25 (6 pack) X X X NAHA01001FF Side Filter Rack 16 x 25 (not adjustable) X X X X X X X NAHA01006FF Side Filter Racks 16 x 25 (6 pack) X X X X X X X NAHA01101SB Combustible Floor Base (Not required when evaporator coil case is X X X X X X X used for downflow) NAHB00301VC Downflow Vent Guard (Not required when vent is routed through cabinet) X X X X X X X NAHA00401DH Chimney Adapter Kit 4 in. vent X X X X X X NAHA00301DH Chimney Adapter Kit 5 in. vent X NAHD00901LP* Natural to Propane Conversion Kit X X X X X X X NAHD00901NG* Propane to Natural Conversion Kit X X X X X X X X Accessory available Suitable for side return filter rack and 17 inch external bottom filter rack. * Factory authorized and field installed. Gas conversion kits are CSA recognized. 8 Copyright 2015 International Comfort Products Lewisburg, Tennessee USA
96% AFUE, Two Stage ECM Gas Furnace EASIER TO SELL 96% AFUE, all models, all positions Two stage heating operation Xtra SEER ECM blower motor Supports two stage cooling units Dehumidification feature in
TECHNICAL SPECIFICATIONS M7RL Series High Efficiency / Direct Vent Condensing Downflow Gas Furnace Induced Draft - 9%+ AFUE Input 4,000 thru 7,000 Btuh The high efficiency downflow gas furnace is especially
TECHNICAL GUIDE 95.5% SINGLE STAGE GAS-FIRED RESIDENTIAL MULTI-POSITION GAS FURNACES MODELS: TG9S NATURAL GAS 40-130 MBH INPUT Due to continuous product improvement, specifications are subject to change
Service Literature G26 SERIES UNITS G26 series units are high-efficiency upflow gas furnaces manufactured with DuralokPlust aluminized steel clamshell-type heat exchangers. G26 units are available in heating
TECHNICAL GUIDE SINGLE PIECE AIR HANDLERS FOR USE WITH SPLIT-SYSTEM COOLING & HEAT PUMPS MODELS: AHR18 THRU 60* DESCRIPTION This fan coil line offers the ultimate in application flexibility. The AHR (non-variable
LF Standard Features Horizontal unit heaters are compact in design and easy to install. Steady State Efficiencies of up to 80.%. Ideal for economical commercial heating systems. Shipped completely assembled
Indoor Coils Cased/Uncased Coils For Gas And Oil Furnaces RCFL- Series featuring Industry Standard R-410A Refrigerant Airflow Capacity 600-1,900 CFM [283-897 L/s] Rheem Indoor Coils are designed for use
FORM NO. C11-211 REV. 7 Supersedes Form No. C11-211 Rev. 6 INDOOR COILS RCFL- featuring Industry Standard R-410A Refrigerant CASED/UNCASED COILS FOR GAS AND OIL FURNACES AIRFLOW CAPACITIES 600-1,900 CFM
FORM NO. O11-608 REV. 2 Supersedes Form No. O11-608 Rev. 1 OIL FURNACES CLASSIC PREMIUM CLASS UPF OIL FURNACES ROBD- SERIES Heating Capacities 56,000 to 151,200 BTU/HR [16.41 to 44.30 kw] The Rheem Classic
FORM NO. C11-213 REV. 4 Supersedes Form No. C11-213 Rev. 3 INDOOR COILS RCFN- featuring Industry Standard R-410A Refrigerant CASED/UNCASED COILS FOR GAS AND OIL FURNACES AIRFLOW CAPACITIES 600-1,900 CFM
NATURAL GAS TO PROPANE CONVERSION KIT 090 INSTALLATION INSTRUCTIONS FOR ALTITUDES 0 -,00 FT. ONLY PROPANE CONVERSION KIT SAFETY... INSTALLATION REQUIREMENTS... Tools and Parts... LP Gas Requirements...
Residential/Commercial Gas Condensing High Efficiency Tankless Water Heaters FEATURES ULTRA-LOW NOx CONDENSING TECHNOLOGY PROVIDES UNPRECEDENTED 0.95 ENERGY FACTOR DURABLE HEAT EXCHANGER Primary Heat Exchanger
Engineering Submittal Sheet Boiler Overview C US Engineering Specifications There shall be provided and installed a quantity of Buderus G234X-55 fl oor standing hot water boiler(s), suitable with natural
POWERED BURNER MODELS LARGE-VOLUME POWERED BURNER FEATURES The large-volume powered burner line includes the largest, most powerful A. O. Smith tanktype gas water heaters. With tank capacities up to 600
Diagnostics for Mobile Homes: HVAC Adam Harris NYSWDA Wade Thompson - IWTC Objectives Identify different types of HVAC used in mobile homes Provide an overview of duct systems Demonstrate various tests
E2 Series Electric Furnaces Service Manual Table of Contents Electrical Requirements... 10 Codes, Specifications Requirements... 10 Connection Supply Service Wires... 10 Furnace Sequence of Operation...
2 THRU 5 TONS SPLIT SYSTEM FCP / FCX Series FEATURES Air Conditioning or Heat Pump ready Prepainted galvanized steel cabinet Internally lined with R3.2, 3/4 Tuf--Skin II insulation Electronic control board
This document was created with FrameMaker 4.0.4 PAYNE Heating & Cooling HEATING/COOLING FAN-COIL UNITS Model Sizes 018, 024 and 030 Model Heating/Cooling Fan-Coil Units are specifically designed for installation
H5HK Series Installation Instructions 3 Phase Electric Heater Kits 7.5 and 0 TON Package A/C Systems Description Installation of 08/40V and 480V H5HK 3 Phase Heater Kits in 7.5 and 0 TON Packaged Air Conditioners.
SECTION 23 81 03 - PACKAGED ROOFTOP AIR CONDITIONING UNITS NON-CUSTOM PART 1 - GENERAL 1.1 SUMMARY A. Section Includes: 1. Packaged rooftop air conditioning unit (5 tons and smaller). 2. Roof curb. 1.2
Roof Top Air Conditioner INSTALLATION AND OPERATING INSTRUCTIONS Ducted System RECORD THIS UNIT INFORMATION FOR FUTURE REFERENCE: Model Number: Serial Number: Date Purchased: This manual must be read and
Local Dealer: C.E. LLC - Miami, FL USA www.cebrands.com Res2012-Rev2 QUALITY YOU CAN FEEL Residential Product Line >TCA7,9 Tempstar SmartComfort TXT + Air Conditioner Featuring The Observer Communication
Bulletin 20-20.2 / July 2012 M SERIES REFRIGERANT COIL MODULE REFRIGERANT COILS for R-22, R-407C, R-410A ➀ ➁ ➂ Model Number Key M 2430 C L 1 - A - ➀ Unit Type M=Modular Nominal Capacity 2430=24000 to 30000
Commercial Gas Water Heater 3-Year Limited Tank/1-Year Limited Parts Warranty* The Polaris has a high grade 444 stainless steel tank with brass connections for years of dependable, trouble-free service
USER S INFORMATION MANUAL UPFLOW, DOWNFLOW, UPFLOW/HORIZONTAL & HORIZONTAL ONLY INDUCED DRAFT GAS FURNACES Recognize this symbol as an indication of Important Safety Information If the information in this
INDEX ELECTRIC FURNACE MODULAR AIR SYSTEM EFC/EFV... 5-10 electric Heat Kits... 5-11 evaporator coils EC1P / EM1P UPFLOW / COUNTERFLOW APPLICATIONS and upflow / horizontal applications (CASED)... 5-6 5-7
SENTRY High efficiency, cast-iron gas boiler LOWER PROFILE MAKES PROBLEM INSTALLATIONS EASY SENTRY High efficiency, cast-iron gas boiler A smarter choice for informed The boiler you choose for your home
Replacement parts DO NOT SERVICE THE BOILER WITHOUT A WM97+ MAINTENANCE KIT AVAILABLE Failure to adhere to these guidelines can result in severe personal injury, death or substantial property damage. The
Cooling/Heat Pump Convertible Air Handlers 2/4TEC3F18-60A1000A 1½ 5 Ton PUB. NO. 22-1774-01-0905 (EN) Features and Benefits 13.0 SEER Ships horizontal converts to vertical by standing unit on end. Six-way
INSTALL INSTRUCTIONS KK-C-HVAC-1 HVAC UNIT 2003-2014 CHEVROLET/GMC VANS FOR (For NEW 2007 ALL WHITE KWIK-KITS ONLY) Warning do not attempt to install A/C units unless you are experienced with servicing
Split System Cooling Product XL16i 1½ 5 Tons PUB. NO. 22-1890-01 Features and Benefits Climatuff compressor Efficiency up to 16.0 SEER and 9.0 HSPF All aluminum Spine Fin coil WeatherGuard fasteners Quick-Sess
Glossary of Heating, Ventilation and Air Conditioning Terms Air Change: Unlike re-circulated air, this is the total air required to completely replace the air in a room or building. Air Conditioner: Equipment
PSD-3-148 WIRING/HARNESS & PROBES See page 8 PROPANE GAS TRAIN ASSEMBLY See page 6 COMMERCIAL POWER BURNER BOILER REPLACEMENT PARTS LIST COPPER BOILERS FOR HYDRONIC HEATING & HOT WATER SUPPLY LEGEND MODELS
18-AH39D1-13 Cased Aluminum "Convertible" Coils 4TXCA018BC3HC** 4TXCA024BC3HC** 4TXCB025BC3HC** 4TXCB026BC3HC** 4TXCB031BC3HC** 4TXCB032BC3HC** ALL phases of this installation must comply with NATIONAL,
2010 Residential Water Heater Replacement Check List The intent of this check list is to provide installers a general reference for the enforcement of code requirements in the Greater San Diego Area. This
INSTALLATION INSTRUCTIONS COMMERCIAL ROOM VENTILATORS WITH EXHAUST MODEL CHCRV-5 For Use with Bard CH Series 3, 4 & 5 Ton 2-Stage Wall Mount Heat Pumps AND W38H, W43H, W49H and W61H Single Stage Wall Mount
IQAir Perfect 16 ID-Series MERV16 Micro-Particle Filtration System Perfect 16 Installation Manual Product Data High-Performance Medical-Grade Residential/Commercial Air Filtration System Application The
Evaporator Coil Slab Coil --- Cased Horizontal Product Data irflow direction for heat pump application irflow direction for heat pump application the environmentally sound refrigerant Use of the HRI Certified
G S F U R N C E S G50UHi ELITE SERIES Up Flow / Horizontal Precision Speed Blower E N G I N E E R I N G D T Bulletin No. 210380 ugust 2005 Supersedes May 2004 FUE 80% Input 66,000 to 132,000 Btuh Nominal
Air Volume Requirement Air conditioning systems are engineered with a specific amount of indoor air passing across the surface of the evaporator coil. The amount of air is measured in cubic feet per minute.
INSTALLATION INSTRUCTIONS FOR HIGH ALTITUDE KITS: RXGY-F04, F05, F06 & F07 FOR MOST 90 PLUS GAS FURNACE MODELS (NOT FOR USE WITH (-)GRK AND (-)GGD MODELS) Recognize this symbol as an indication of Important
Modular Blower (115 Volt) MB08B1500B, MB12F1900B, MB16J2200B, MB20L2400B These instructions must be read and understood completely before attempting installation. Improper installation, adjustment, alteration,
DIESEL-FUELED, BLOWN AIR, DUCTABLE HEATERS Electronic thermostatically controlled Low power consumption Compact space saving size Short heat-up times Dehumidification of the cabin Quiet when running Combustion
Evaluate, Clean, and Tune Guidance The Evaluate, Clean and Tune (ECT) process serves three essential purposes in the Weatherization Assistance Program (WAP). The first is to evaluate the existing system
TECHNICAL DATA & SERVICE MANUAL INDOOR UNIT: AW52AL AW64AL SPLIT SYSTEM AIR CONDITIONER Model No. Product Code No. AW52AL 387030095 AW64AL 387030096 0.8180.463.0 07/05 IMPORTANT! Please read before installation
Compare These Side Wall Venting Means No Chimney/Chase More Living Space Increased Safety & Efficiency Lower Installation Costs Venting for heating appliances doesn t have to go through the roof, either
Multi-Fin flue technology Flue damper saves energy Electronic controls HEAVY DUTY STORAGE GAS Dependability The Rheem heavy duty gas range is the work horse of the industry having proved itself over many
DRYER VENTING SPECIFICATIONS Table of Contents DRYER SAFETY...1 INSTALLATION REQUIREMENTS...4 Venting Requirements...5 DRYER INSPECTION AND CLEANING...7 Frequency of Exhaust System Cleaning...7 Inspecting
INSTALLATION INSTRUCTIONS 4" COMBUSTION AIR INLET KIT TUBULAR GAS FIRED DIRECT SPARK PROPELLER UNIT HEATERS UNIT CONVERSION & CATEGORY III VENTING FOR SEPARATED COMBUSTION For 30,000 to 75,000 BTU/HR SUPPLEMENT
TM Automatic Humidifier Control SEH-7100-000 by Skuttle Indoor Air Quality Products Safety and Installation Instructions* INSTALLER: READ COMPLETE INSTALLATION INSTRUCTIONS BEFORE BEGINNING INSTALLATION.
One Year Warranty ELECTRIC Stock U.S. # of Volts Weight CONN. Height Dia. Watts # GAL. Elements INS. Inches Fused Ceramic Shield tank lining is corrosion-resistant for years of dependability. Adjustable
High Efficiency Copper Finned Tube Boilers 750,000-2,000,000 BTU/HR The heat transfer innovators. THE RELIANCE COPPER FINNED TUBE HYDRONIC BOILER FEATURES Copper Fin-Tube Heat Exchanger Up to 88% Thermal
GIAC-7 HVAC INDOOR MAKE-UP AIR HANDLERS Application Manual PACKAGED INDOOR ARRANGEMENTS FOR MAKE-UP AIR, HEATING AND COOLING Contents 2 PAGE GENERAL INFORMATION 2, 3 MODEL NUMBER DESCRIPTION 4 INDOOR DUCT
EFFECTIVE OCTOBER 2005 Atwood Furnaces and Digital Thermostats Unique 2-Stage System Set the temperature, turn the thermostat on automatic and let the furnace take over! During cold start-ups, the furnace
Operation and Installation Manual Max Series Models 95MAX 155MAX 155ECM 155MAXRX 200MAX 200MAXRX MAXTOP 195DCS 300DCS 200ERV 200ERVD New Auto Dehumidistat Function prevents unwanted use of the dehumidistat
MCR1900 Media Converter 19-Slot Chassis Installation Guide Part #5500304-11 Copyright Statement This document must not be reproduced in any way whatsoever, either printed or electronically, without the
http://waterheatertimer.org/how-to-troubleshoot-gas-water-heater.html APPLY POWER TO APPLIANCE FIELD WIRING CORRECT? DPLAY ERROR CODE 1 OR 2 Intelli-Vent TM Sequence of Operation REQUEST FOR HEAT PRESENT?
Skypak Model RGAD/SGAD Self Contained Cooling/ Gas Heating Units Supersedes: 145.25-IOM1 (708) Form 145.25-IOM1 (908) RGAD AND SGAD INSTALLATION AND OPERATION INSTRUCTIONS Models RGAD & SGAD-R410A Category
Type FX4 FX4 Explosion-Proof Electric Air Heaters FX4 heaters are UL listed and/or CSA certified for use in hazardous locations. They are designed for dry indoor industrial applications such as oil refineries,
Excerpts from the Canadian National Building Code (NBC) Reproduced here with Permission of the Copyright Owner, the National Research Council of Canada, Institute for Research in Construction. For more
Portable Air Conditioner Owner's Manual Model:3 in 1 12,000 Btu/h Series 3 Please read this owner s manual carefully before operation and retain it for future reference. CONTENTS 1. SUMMARY...1 2. PORTABLE
ENGINEERING DT MTCHED REMOTE SYSTEMS 50hz S LOWER UNITS 50hz ELITE 10 MULTI POSITION LOWER UNITS 20 100 to 49 00 tuh (5.9 to 14.4 kw) Cooling Capacity 19 700 to 49 100 tuh (5.8 to 14.4 kw) Heat Pump Heating
Dehumidification Basics Why do you want to keep indoor Rh between 30-60%? ASHRAE recommends keeping the relative humidity in a home between 30-60% to limit the effects of many unwanted conditions and harmful
APPLICATIONS Heating >> FACTORIES >> WAREHOUSES >> HALLS >> SHOWROOMS >> GREENHOUSES >> RETAIL >>... UDSA - UDSBD unit heater www.reznor.eu V3 gas fired unit heater Reznor V3 unit heaters are one of the
Propane Conversion Kit Supersedes: 145.25-IOM2 (708) Form 145.25-IOM2 (908) PROPANE CONVERSION KIT INSTALLATION MANUAL "LPKIT " - PROPANE CONVERSION KIT Kits are available for field conversion from natural