1 Introduction to DEAP for Professionals Introduction to DEAP for Professionals 1 DWELLING ENERGY ASSESSMENT PROCEDURE (DEAP)
2 2 Introduction to DEAP for Professionals Introduction to DEAP for Professionals Introduction The Dwelling Energy Assessment Procedure (DEAP) is the official Irish methodology for calculating the energy performance and associated carbon dioxide emissions for the provision of space heating, ventilation, water heating and lighting in dwellings. DEAP consists of a software tool and an associated guidance manual and is a key component of the Irish Building Energy Rating (BER) scheme. DEAP is also the compliance tool specified in Part L of the Irish Building Regulations. The software and manual are freely available on DEAP is published by the Sustainable Energy Authority of Ireland (SEAI). Our mission is to play a leading role in transforming Ireland into a society based on sustainable energy structures, technologies and practices. This document provides an introduction to the principles of DEAP for anyone involved in building research or the design, construction or retrofit of dwellings. It is also useful for anyone wishing to understand the technical basis for BER certificates. DEAP Functionality: The key functions of DEAP are as follows: 1 DEAP models expected energy consumption and associated CO 2 emissions for the dwelling under standardised operating conditions. 2 DEAP enables publication of a BER certificate as shown in Figure 1. The BER cert shows a rating scale based on the dwelling s energy consumption per unit area. The published BER certificate is accompanied by an advisory report outlining relevant improvements for the dwelling. 3 All BER certificates are stored on SEAI s National Administration System (NAS). Summary information from published BER certificates is accessible from using the dwelling s BER number or MPRN number. The MPRN for the home is printed on the electricity bill. 4 Aggregated data for all BERs can be downloaded from the SEAI National BER Research Tool Tool on
3 Introduction to DEAP for Professionals 3 Figure 1: The BER Certificate Actual Building Energy Rating for this home Version of software used to rate this home Home Address Official BER Number - this is unique to this home BER Assessor Number - This is the registration number for the assessor who carried out this assessment Assessor Company Number - This is the registration number for the aseessor company who carried out this assesment BER Rating A-G A= Most Efficient G= Least Efficient CO 2 emissions for your home. Less is best and it s an indication of how green your home is
4 4 Introduction to DEAP for Professionals 5 DEAP allows prospective buyers or tenants to objectively compare the energy performance of different dwellings on a like for like basis. DEAP is an asset (calculated) energy rating rather than an operational (measured consumption) rating. The key differences between calculated energy consumption and measured energy consumption are as follows: Figure 2: Calculated vs. Measured Energy Consumption Calculated Energy Consumption Key features: Calculate energy usage based on the dwelling NOT the occupants like MPG rating for cars the actual driving style, terrain and conditions not accounted for Consistent assumptions made for all dwellings such as: Same level of lighting required in all dwellings Number of occupants and hot water demand based on floor area Fixed length heating season and fixed heating periods per day Dwelling heated to fixed temperatures Climate Some pros: Allows all dwellings to be compared on like for like basis The prospective buyer or tenant is not dependant on current occupier behaviour Ideal for dwellings being sold or rented Ideal for evaluating the building for regulatory purposes Some cons: If the occupant is frugal or wasteful in their energy usage, their energy bills could be much smaller or larger than the asset rating would indicate Requires detailed survey of dwelling fabric and heating system Measured Energy Consumption Key features: Measures actual energy usage Can be based on bills and/or monitored data No need to identify building components Standardised assumptions not relevant Some pros: Reflects actual energy usage Does not require detailed survey of dwelling fabric and heating system Some cons: Difficult for prospective buyer or tenant to compare on like for like basis Highly dependent on behaviour of occupants Not suitable for demonstrating compliance with regulatory requirements as home must be occupied to enable measurement of energy consumption
5 Introduction to DEAP for Professionals 5 6 DEAP performs compliance checking calculations for Part L of the Building Regulations and generates a conformance report summarising the relevant information for the purposes of building control. The calculation checks that the primary energy consumption associated with the operation of the dwelling and the related CO 2 emissions do not exceed the Maximum Permitted Energy Performance Coefficient (MPEPC) and the Maximum Permitted Carbon Performance Coefficient (MPCPC) when compared to a reference dwelling defined in the Building Regulations Part L Technical Guidance Document (TGD L). In addition to checking compliance with the above target values DEAP also performs the following checks as specified in TGD L: level of installed renewable energy per unit area; heat losses through the building fabric; 7 DEAP enables the dwelling designer to identify likely areas of high energy usage in the dwelling. The designer can determine the relative impacts of various design changes using DEAP.
6 6 Introduction to DEAP for Professionals Legislative Background Figure 3: Legislation and the BER Programme European Union EPBD EU Energy Performance of Buildings Directive Ireland Irish Building Regulations TGD Part L Irish legislation S.I. 243 of 2012 SEAI SEAI Domestic BER Programme including: DEAP Methodology Software Manual Survey Guide FAQs Technical Bulletins BER Helpdesk Quality Assurance Programme National Administration System (NAS) database Code of Practice Registered BER Assessors TGD L Compliance Checking BER Cert and Advisory Report The Energy Performance of Buildings Directive (EPBD Recast Directive 2010/31/EU) Article 3 requires that each member state adopts a methodology for the calculation of building energy usage. Article 12 of EPBD Recast requires that energy performance certificates are made available by building owners when the building is constructed, sold or rented. S.I. 243 of 2012 transposes EPBD Recast into Irish Legislation, specifically referencing the requirement for a calculation methodology and software from the Issuing Authority (SEAI). This is illustrated in Figure 3. The original EPBD (2002) was first transposed into Irish legislation through S.I.666 of 2006 and introduced the mandatory requirement for BERs in Ireland. DEAP was first developed to meet this requirement and has evolved through a number of revisions since then.
7 Introduction to DEAP for Professionals 7 DEAP Development Figure 4: The evolution of DEAP DEAP v2.1.2: First release based on EN13790 and SAP New dwellings only Part L 2005 compliance checking Detailed report output showing DEAP entries DEAP v3.1: Major usability improvements Expanded use of webservices Added report output for Part L compliance checking DEAP v DEAP v DEAP v DEAP v DEAP v3.0: Cater for existing dwellings: Survey guide Default values Add Part L 2008 checking Improved usability DEAP v3.2: Add Part L 2011 checking Further improved usability DEAP manual guidance expanded More detail on heat pumps, wind power, lighting and CHP Facilitate automatic upgrade of electricity factors to reflect grid efficiency changes DEAP was first introduced in 2006, and, as shown in Figure 4, it has been regularly updated and refined to meet the needs of regulation, users, consumers and industry. DEAP is the national tool for BER calculation and Building Regulations Part L compliance checking. It is compliant with the methodology framework as detailed in Annex I of the EU Energy Performance of Buildings Directive (EPBD). The DEAP methodology is primarily based on the following: IS EN 13790: Energy performance of buildings -- Calculation of energy use for space heating and cooling. Other relevant European and international standards as detailed in the DEAP manual. The Standard Assessment Procedure (SAP) for energy rating of dwellings in the UK. The original DEAP methodology was based on research work by University College Dublin s Energy Research Group, National Energy Services (UK) and Rickaby Thomson Associates (UK). Ongoing development, maintenance and support is carried out by SEAI as required. Major revisions to DEAP follow a process of design, public consultation, development and software testing. The DEAP software and manual are freely available on the SEAI website and are supplemented by guidance publications and SEAI s BER Helpdesk. The SEAI website provides a register of BER assessors. These assessors are trained in the use of DEAP to produce BER certificates as required by the legislation. Many construction professionals such as Architects and Engineers have also attended DEAP training, enabling them to check compliance with Part L of the Building Regulations during dwelling design. As DEAP evolves, it will continue to maintain alignment with forthcoming Irish policies and Building Regulations, particularly Irish transposition of EPBD Recast, associated IS and EN standards and Part L of the Building Regulations.
8 8 Introduction to DEAP for Professionals DEAP and the EPBD Requirements The Energy Performance of Buildings Directive (Recast Annex I) requires that a number of building categories are catered for via a national methodology. DEAP is the methodology for single family houses of different types and also assesses individual apartments. EPBD Annex I Requirement Summary of implementation in DEAP The methodology of calculation of energy performances of buildings shall include at least the following aspects: (a) thermal characteristics of the building (b) heating installation and hot water supply, including their insulation characteristics (c) air-conditioning installation (d) ventilation (e) built-in lighting installation (mainly the non-residential sector) (f) position and orientation of buildings, including outdoor climate (g) passive solar systems and solar protection (h) indoor climatic conditions, including the designed indoor climate (h) internal loads DEAP calculates ventilation/air leakage and external fabric heat loss along with the impacts of thermal mass and thermal bridging at junctions. Passive internal and solar gains are also calculated. DEAP evaluates the heating system type and controls along with insulation on hot water storage and pipe work. DEAP accounts for heating from air conditioning systems, but does not yet account for the cooling from these systems. To date, cooling calculations have not been deemed necessary for dwellings in the Irish climate. This is partially due to low market penetration of these systems and also the low cooling energy demand expected in Irish dwellings. DEAP accounts for ventilation losses (natural and mechanical) and electrical fan power required for mechanical ventilation systems. Structural air tightness is also accounted for. DEAP calculates the dwelling lighting demand and associated electricity requirement. Reduced lighting energy requirement is calculated based on installed low energy lighting. DEAP accounts for orientation of openings and solar collectors and calculates resulting solar gain. It also considers typical Irish monthly temperatures, and shelter impact on ventilation losses. DEAP accounts for passive solar heat and light gains. The level of overshading on openings and solar collectors is evaluated. DEAP assumes that an adequate level of ventilation and air temperature are maintained in the dwelling. Standard temperature levels are assumed during heating periods: 21 o C in living areas and 18 o C in the remainder of the dwelling. DEAP calculates the heat load based on the above climatic conditions. It also calculates the dwelling hot water demand based on the assumed number of occupants (which is in turn based on floor area). The positive influence of the following aspects shall, where relevant in the calculation, be taken into account: (a) local solar exposure conditions, active solar systems and other heating and electricity systems based on energy from renewable sources (b) electricity produced by cogeneration (c) district or block heating and cooling systems (d) natural lighting DEAP accounts for a multitude of conventional and renewable heat sources (active solar, passive solar, boiler, heat pump, wood, electric etc). PV and onsite wind turbines are also accounted for. DEAP accounts for CHP systems in group (district) and individual heating systems DEAP accounts for thermal energy supplied by group heating systems allowing for various types of systems and distribution networks. DEAP does not yet calculate cooling requirement. DEAP accounts for natural lighting depending on the window size, type, shading and orientation. This can reduce the dwelling heat and lighting demand.
9 Introduction to DEAP for Professionals 9 Technical Outline of the DEAP Software Figure 5 shows the key considerations in the DEAP calculation to derive the total primary energy and CO 2 results. The diagram summarises the calculation process to derive the total energy usage for space heating, water heating, lighting, pumps and fans. Figure 5: DEAP Calculation Summary Space heating Heat loss via walls /windows/floors/ doors/roofs Ventilation heat loss via openings and structural air permeability Internal gains (lighting, metabolic, appliance, cooking) Internal and external temperatures Space heating controls and heat emitters (e.g. radiators) Total envelope heat loss Total heat demand Net space heat demand Heat from space heater(s) Space heater(s) e.g. boiler, heat pump, electric heaters etc Solar gain through windows Useful heat gain (accounts for thermal mass) Energy delivered as fuel for space heating Space heating primary energy and CO 2 Water heating Lighting Pumps/Fans Total primary energy per m 2 per year and total CO 2 per m 2 per year as shown on BER cert Total floor area Hot water demand Total floor area Pumps for central heating and solar hot water Ventilation fans Solar water heating system Net hot water demand Hot water storage and controls Net lighting requirement (Allows for light gain through windows) Heat from water heater(s) Water heater(s) e.g. boilers, heat pumps, immersion etc. Energy delivered as fuel for water heating Primary energy and CO 2 factors for fuel (eg. oil/gas/wood/electricity) Water heating primary energy and CO 2 Electrical energy delivered for lighting Primary energy and CO 2 factors for electricity Lighting primary energy and CO 2 Electrical energy delivered for pumps/fans Primary energy and CO 2 factors for electricity Pumps and fans primary energy and CO 2
10 10 Introduction to DEAP for Professionals The DEAP software brings the user through a number of windows or tabs to calculate the BER result. The red arrow in Figure 6 follows through the list of tabs from Start to Results, with the Energy Rating shown on the left hand side of the screen. Most of the DEAP entries must be completed, although some of the optional entries provide useful ancillary information relating the dwelling. There are strict conventions and guidelines relating to each field set out in the DEAP Manual and survey guide to avoid incorrect entry of data. The DEAP guidance documents, available on provide full detail on all of the DEAP entries and tabs. The BER technical bulletins provide further detail and worked examples on various sections of DEAP, and users may obtain guidance from the BER helpdesk where further assistance is needed. Figure 6: DEAP software screenshot The DEAP Manual provides a significant level of detail on the data entries in the software. The tables in the DEAP Manual provide conservative defaults and assumed values for the various DEAP fields in the absence of actual data. The DEAP Survey Guide and Survey Form are used by BER assessors when carrying out a BER survey. The Survey Guide provides useful guidance on how to complete a survey correctly and details how evidence supporting each DEAP field is obtained on site or from the dwelling owner. The DEAP calculation is also available in Microsoft Excel format at the website above for those who wish to gain further insight into the calculation equations. The Excel version of DEAP cannot be used to publish a BER on the SEAI National Administration System (NAS) or to generate BER certs.
11 Introduction to DEAP for Professionals 11 Figure 7: DEAP tab outline General data relating to the assessment Total floor area Number of storeys Storey heights Dwelling volume Living room area Area*U value of floors, doors, windows, roofs, walls Thermal bridging losses Solar and light gains through windows Calculation of total heat losses (including fabric and ventilation losses) Check of fabric insulation against TGD L Start Property and assessor details Dimensions Ventilation Building elements Water heating Lighting and internal gains Dist. system losses and gains Energy requirements Summer internal temperature Dwelling, client and BER assessor details and addresses Openings (e.g. chimneys) Structural leakage Shelter from wind Natural and mechanical ventilation details Calculation of water heating demand Account for distribution and piping losses Combi boilers Summer immersion heating Hot water storage insulation Water heating controls Solar water heating Determine energy demand for lighting Calculate heat gains from Net space heat internal sources demand (e.g. occupants and appliances) Account for dwelling Determine annual space heating demand to be supplied by heat source. This is based on net space heat use whilst accounting for heat emitter type (e.g. radiators) and heating system controls (e.g. room thermostats). Calculate electrical energy needed for heating system pumps and fans thermal mass Determine useful heat gains Calculate net space heat use to maintain set temperatures during 8 months of space heating season Net space heat use is total heat loss minus (useful internal gains and solar gains) Optional assessment of internal temperature in summer Calculate primary energy and CO 2 emissions based on fuel type and delivered energy. Calculate Building Energy Rating Based on primary energy total divided by floor area. Summarise all TGD L compliance checking results. Results Main and secondary space heating efficiency, make, model and fuel Main water heating efficiency, make, model and fuel Account for heating system efficiency adjustments (e.g. weather compensation installed) Allow for group heating systems Determine delivered energy to each heating system The DEAP tabs are summarised in Figure 7. The table below provides further detail on the key data to be entered in DEAP. The table also shows the main outputs from each tab and identifies some of the parameters most likely to have a large bearing on the BER result. When designing a dwelling, or considering potential improvements to an existing dwelling, consider all areas of the BER for potential improvements. Entries on most of the DEAP screens can impact the BER, allowing flexibility in choosing the most effective upgrade.
12 12 Introduction to DEAP for Professionals Tab Main user entry actions Visible calculated outcome and other comments Start Property and assessor details Dimensions Ventilation Building elements: Floors Walls Roofs Doors Building elements: Windows Administrative details of the dwelling and BER assessment including electricity Meter Point Reference Number (MPRN), new/existing dwelling, TGD L version, construction date and dwelling type. Details of property, client and Assessor Area and height of each storey, area of living room, number of storeys. Openings (e.g. chimneys), structural leakage and mechanical ventilation systems. Heat loss building element dimensions and U-values. Default U-values may be used for existing dwellings. Window and glazed door dimensions, orientations, U-values and shading characteristics. Defaults may be used for new or existing dwellings. As entered As entered Total floor area, dwelling volume and living area fraction. Total energy usage is divided by the dwelling floor area to determine the Building Energy Rating. All dimensions in DEAP are internal this is a standard convention in UK and other EU member states. Irish Building Regulations Part L work to internal dimensions. Ventilation heat loss (components and total), electricity for fans, heat gain from fans. Air permeability compliance check with Building Regulations 2008 and 2011 TGD L requirements. Number of openings (such as chimneys, permanently open wall/window vents) is likely to have a significant bearing on the BER. If using mechanical ventilation, it is best to use test data from SAP Appendix Q rather than default data. Total Area*U-value for each element type. U-value is the rate of heat loss per m 2 surface area per degree. E.g. a U-value of 1, with a temperature inside of 21 and outside of 11 on a 1m 2 wall area has a rate of heat loss of 10W. Best to use actual calculated U-values instead of defaults, but supporting evidence must be acquired from survey or dwelling specifications (such as insulation type, thickness, area, certified test data). Certified data from Agrement certs or accredited data gives insulation thermal conductivity. The DEAP Manual details the applicable European U-value calculation standards (such as EN6946 for walls and roofs). Adding insulation to a poorly insulated building element will have a significant bearing on the BER. Glazed area, heat loss, effective area for solar gain, glazing ratio for daylight gain, summer heat gain. Window orientation is important. Actual U-values and solar transmittance should be used where available from certified data (to relevant European standards such as EN ;2).
13 Introduction to DEAP for Professionals 13 Tab Main user entry actions Visible calculated outcome and other comments Building elements: Heat loss results Thermal bridging factor Tab calculates fabric heat loss, total heat loss coefficient and heat loss parameter for the dwelling. Compliance check with Building Regulations fabric insulation requirements (for Building Regulations TGD L as appropriate for the dwelling) is also carried out. Obtain more beneficial thermal bridging factor from certified calculations or use of Acceptable Construction Details for new dwellings as published by DECLG. Dimensions are internal as per TGD L. Thermal bridging heat losses are added to the fabric plane elements heat losses. A supporting spreadsheet to calculate actual Thermal Bridging heat loss as per TGD L 2011 is available on Water heating Lighting and internal gains Water heating system characteristics, including supplementary electric water heating in summer and solar water heating Proportion of fixed lighting outlets which are low energy Tab calculates the hot water heating demand, solar hot water output, solar hot water pump consumption, primary circuit loss, internal heat gains from hot water, distribution losses. Hot water storage insulation and improved hot water storage controls (time and thermostatic) are commonly used to improve the BER. Annual energy use for lighting, internal seasonal heat gains from lighting and other internal heat gains. Installation of low energy light bulbs (CFLs, LEDs and fluorescent tubes) is a cost effective way to improve the BER. Net space heat demand Thermal mass category Mean internal temperature, annual useful space heat demand from monthly calculations allowing for intermittency, solar gains and internal heat gain utilisation. Distribution system losses and gains Heating system control category, responsiveness category, heat emission characteristics, pumps and fans Annual space heat demand allowing for control, responsiveness, heat emission and equipment heat gain characteristics. Electrical power consumed by pumps (e.g. central heating pumps) calculated. Use of thermostats, zoning, TRVs and programmers along with other control improvements can have a significant bearing on the BER. Central heating pumps with high efficiency labels will also decrease energy consumption in DEAP.
14 14 Introduction to DEAP for Professionals Tab Main user entry actions Visible calculated outcome and other comments Energy requirements: Individual heating system Energy requirements: Group heating Individual heating systems: Space and water heating appliance efficiency and fuel characteristics. Combined heat and power plant characteristics. Secondary heating (e.g. fireplace) is also considered. Community/ group heating schemes: Space and water heating appliance efficiency and fuel characteristics. Combined heat and power plant characteristics. Annual delivered fuel consumption for space and water heating, CO 2 emissions. Improved heat source efficiency is critical to obtaining a better BER. Data is preferably taken from The Home-heating Appliance Register of Performance (HARP) lists efficiencies based on accredited test data to the standards and calculation methods specified in DEAP. Replacing an open fire with a stove and flue will reduce ventilation losses and improve the secondary heating system efficiency. Heating system efficiencies are based on Gross Calorific Values and generally are a seasonal value as calculated in the DEAP Appendices. The test data are derived from European standards (e.g. EN14511 for heat pumps). Annual fuel consumption for space and water heating, CO 2 emissions. Heating system efficiency, controls and pipework should all be considered to reduce energy consumption for all dwellings heated by the group system. Summer internal temperature Effective air change rate of dwelling Optional tab Calculates threshold internal temperature and provides approximate indication of overheating risk Results None Annual delivered energy Annual primary energy and CO 2 emissions. DEAP derives these values by multiplying the delivered energy for each fuel by the associated primary energy and CO 2 factors for those fuels. The BER grade ranging between A1 and G. Building Regulations Compliance checking for new dwellings: Energy and CO 2 emissions compared to TGD L reference dwelling. Renewables conformance requirements checking as per TGD L Fabric insulation levels as per TGD L Air tightness checking against TGD L performance levels
15 Introduction to DEAP for Professionals 15 Figure 8: DEAP Electricity Factors since Year Electrical Primary energy factor CO 2 emissions (kg/kwh) The primary energy and CO 2 factors for electricity are shown in Figure 8. The electricity factors are higher than other fuels as there are inherent inefficiencies involved in electricity generation and transmission. However, this figure is updated annually as the electricity generation fuel mix changes. In earlier versions of DEAP, the primary energy factor for electricity meant that for every unit of electricity delivered to the dwelling, 2.7 units of primary energy were assumed by DEAP. This value is now much lower at DEAP allows for automatic update of the electricity factors - the update is carried out annually by SEAI.
16 16 Introduction to DEAP for Professionals Graphical Energy Representation DEAP has a number of features to ensure ease of use. For example, it provides graphical representation of the data on the results tab (shown in Figure 9) and the net space heat demand tab to help users quickly identify where most energy savings can be made. The sample graph below clearly shows that the space heating demand should be addressed if this BER grade is to be improved. This indicates that one or both of the building fabric and heating system should be examined more closely for inefficiencies. Figure 9: DEAP results tab graph Renewable 3 Renewable 2 Renewable 1 CHP Elec Output CHP Input Energy for Lighting Pumps, Fans, etc Water Heating Sec Water Heating Main Space Heating - Sec Space Heating - Main kwh/y Figure 10 shows the graphical information provided in DEAP s net space heat demand tab. In this case, the dwelling is well insulated and is capitalising on solar heat gains to reduce the space heat loss. As it is well insulated, the heat use is minimal in Spring and Autumn. While DEAP is not a building design tool, this graph does indicate that space heat demand will be very low, particularly in Spring and Autumn. As always, Building Regulations should be followed when designing the building (e.g. ensure there is adequate ventilation). The building designed should also ensure best practice is followed to avoid unwanted overheating in summer.
17 Introduction to DEAP for Professionals 17 Figure 10: Net space heat demand W Jan Feb Mar Apr May Jun Jul Aug Sep Oct Nov Dec Heat Use Useful Internal Gains Useful Solar Gains
18 18 Introduction to DEAP for Professionals References: DEAP Methodology guidance and software: BER Helpdesk: HARP database: National BER database: https://ndber.seai.ie/pass/ber/search.aspx National BER Research Tool: DEAP FAQ (including thermal bridging calculation tool): Legislation from Department of Environment, Community and Local Government (DECLG): : Building Regulations (Part L Amendment) Regulations 2011 (S.I. No. 259 of 2011) Technical Guidance Document to Part L 2011 and Acceptable Construction Details Statutory Instrument 243 of 2012 Statutory Instrument 666 of 2006 EPBD Recast Directive 2010/31/EU: SAP Appendix Q Database:
19 Introduction to DEAP for Professionals 19
20 V 1.0_0413 The Sustainable Energy Authority of Ireland is partly financed by Ireland s EU Structural Funds Programme co-funded by the Irish Government and the European Union. This document is printed on environmentally friendly paper stock
BER Assessors Dwellings Technical Bulletin Issue No. 3/11 May 2011 Contents: 1 Window defaults in DEAP and use of DEAP Table 6a... 2 2 Solar Space Heating Systems in DEAP... 4 3 Storage and direct electric
SAP 2012 IN A NUTSHELL The consultation version of the SAP 2012 methodology was published by the Department of Energy and Climate Change (DECC) on January 4th 2012. This article from Dyfrig Hughes of National
Topic 3 Understanding the Energy Requirements Planning for Climate Change - Delivering Sustainable Buildings & Quality Design Learning Objectives By the end of this session, you should have a basic understanding
Report Date: 04/03/2014 Assessor: John Doyle Address: BLOCK K APT 108 SANDYFORD VIEW DUBLIN 18 BER: 106178106 MPRN: 10301589669 About this Advisory Report Energy use in our homes is responsible for almost
Dwelling Energy Assessment Procedure (DEAP) VERSION 3.2.1 Irish official method for calculating and rating the energy performance of dwellings This document describes DEAP 2012, Version 3.2.1, dated June
Energy Performance Certificate 0 Raleigh Drive CULLOMPTON EX15 1FZ Dwelling type: Date of assessment: Date of certificate: Reference number: Type of assessment: Total floor area: Semi detached house 09
3/12/10 User Guide isbem An Interface for SBEM (Simplified Building Energy Model) Part of the National Calculation Methodology : SBEM for assessing the Energy Performance of Buildings A User Guide to isbem
Improving comfort and energy efficiency in a nursery school design process S. Ferrari, G. Masera, D. Dell Oro Dept. Building Environment Science &Technologies Politecnico di Milano Italy Research funded
Energy Performance Certificate 35, Chapman Way HAYWARDS HEATH RH16 4UL Dwelling type: Date of assessment: Date of certificate: Reference number: Type of assessment: Total floor area: Top floor flat 8 June
Energy Performance Certificate 68, Burlton Road CAMBRIDGE CB3 0GS Dwelling type: Date of assessment: Date of certificate: Reference number: Type of assessment: Total floor area: Top floor flat 7 May 011
Full text Executive Order amending the Executive Order on the Publication of the Danish Building Regulations 2010 (BR10) 1) 1. The following amendments shall be made to Executive Order no. 810 of 28 June
- Energy Certification, Information And Communication Technologies For User Satisfaction D5.1 National reports on energy certification of buildings PORTUGAL 1 2 Statement of originality This deliverable
THE EUROPEAN GREEN BUILDING PROGRAMME Technical Module on Combined Heat and Power Contents Foreword...1 1. Introduction...2 2. Inventory of the CHP system...3 3. Assessment of technical energy saving measures...5
Module 3.8 Window U-value Learning Outcomes On successful completion of this module learners will be able to - Describe the concept of U-values and alternative energy rating system for windows. 2 Calculation
Water heating systems Module 6 Contents Introduction Module 6.1 Water Heating Systems Module 6.2 Water Heating System Fuel Types Module 6.3 Standardised Operation Conditions Module 6.4 Water Heating Systems
Energy Performance Certificate 1 Mornington Mews COWES PO31 8AU Dwelling type: Date of assessment: Date of certificate: Reference number: Total floor area: Ground floor flat 9947-2885-6228-0998-1541 84
Heating and cooling challenge in nzeb Experiences from built houses and detailed building simulations calls for a careful and integrated approach when designing heating and cooling systems for nearly zero
Methodology for the production of Display Energy Certificates (DEC) February 2013 2 Contents Summary 3 Section 1 Introduction 4 Section 2 Scope 6 Section 3 Applicable Conventions 8 3.1 Basis for the DEC
Recognised energy Dynamic Simulation Modelling (DSM) software DesignBuilder is a user interface to the EnergyPlus DSM. EnergyPlus builds on the most popular features and capabilities of BLAST and DOE-2
L Conservation of Fuel and Energy - Dwellings Building Regulations 2011 Te c h n i c a l G u i d a n c e D o c u m e n t Building Regulations 2011 Technical Guidance Document L Conservation of Fuel and
your comfort. our world. Daikin Altherma Hybrid Heat Pump Smart heating technology for the best of both worlds Heating Integrated Solutions Ventilation Air Conditioning Refrigeration Forward thinking About
PROTOCOL FOR BUILDING ENERGY ANALYSIS SOFTWARE For Class 3, 5, 6, 7, 8 and 9 buildings Version 2006.1 AUSTRALIAN BUILDING CODES BOARD JANUARY 2006 TABLE OF CONTENTS Foreword 1. Scope 2. Purpose and context
Improving thermal insulation of concrete sandwich panel buildings Jørgen Munch-Andersen Danish Building Research Institute, Aalborg University LCUBE conference, Vienna 17-18 April 2007 Outline A general
Non Domestic BER Assessors Technical Bulletin Issue No. 1/11 October 2011 * Contents: 1 Introduction... 2 2 Quality Assurance programme... 2 3 Building Energy Rating requirement... 3 4 Data integrity...
Energy Efficiency in Buildings Supplemental Guide to SANS 10400-XA & SANS 204 V. 3.0 Registered to: The Drawing Studio Image: digitalart / FreeDigitalPhotos.net Report Date: 26 August 2014 Practice Name:
THE NATIONAL BUILDING REGULATIONS PART XA: ENERGY EFFICIENCY. Presentation by Peter Henshall-Howard: HEAD: BUILDING DEVELOPMENT MANAGEMENT. A Diagrammatic representation of the relationship between the
Archetype: 3250330 Archetype Description: 1965-1975, semi / end terraced dwelling, timber frame walls, oil / gas / electric warm air heating, E This archetype represents 823 dwellings, which accounts for
Kent County Council Energy and emissions information Kent KCC Area Energy and emissions information Energy Performance Certificates and Domestic Energy Rating (SAP) 2009/10 Published January 2011 Research
RESNET National Rater Test Study Guide Outline The RESNET national home energy rating standard spells out a listing of the knowledge base and skills set for Home Energy Ratings. Trainers and Rating Quality
CE291 Energy efficiency and the Code for Sustainable Homes Level 4 Also available: Energy efficiency guidance for level 3 Energy efficiency guidance for levels 5 and 6 Contents 1. Introduction 3 1.1 Energy
PASSIVE Solar Design Solar Homes Catch the Sun Are you planning a new house? Discover how you can apply solar architecture principles to: keep your heating bills to a minimum enjoy the comfort of a warm
Daikin Altherma Hybrid Heat Pump Smart technology for the best of both worlds NATIONAL HEAT PUMP 19 JUNE 2014 ICC BIRMINGHAM WINNER Forward thinking Now is the time to rethink the way we heat our homes
Energy Performance Certificate North Cottage Dwelling type: End-terrace house Middlebere Farm Date of assessment: 03 May 011 Arne Date of certificate: 04 May 011 WAREHAM Reference number: 0584-867-655-9309-4361
ZERO CARBON HOMES AND NEARLY ZERO ENERGY BUILDINGS UK Building Regulations and EU Directives This leaflet summarises the UK s proposed Zero Carbon Standard for Homes, and the EU s new Nearly Zero- Buildings
A guide to energy performance certificates for the Construction, sale and let of non-dwellings Preface This document is intended to give a simplified overview of Commercial Property Energy Certification.
Setting the Scene Fuelling the Future, Heat Pumps and more Ireland s Import Dependence in 2013 was 89% Energy Flow Thermal Uses 2013 Oil is the dominant fuel accounting for 44% of fuel inputs Renewable
Energy Efficiency and Renewable Energy For Schools Jesse Putzel & David Pitcher (energy conservation and solar centre) ecsc - who we are Environmental Charity involved in both energy efficiency and renewable
Continuous flow direct water heating for potable hot water An independently produced White Paper for Rinnai UK 2013 www.rinnaiuk.com In the 35 years since direct hot water systems entered the UK commercial
CO2 Emissions Direct Emissions AFOLU 24 % Buildings 6,4 % Transport 14 % 49 Gt CO2 eq (2010) Indirect CO 2 Emissions Electricity and Heat Production 25 % Energy 1,4% Industry 11 % Transport 0,3 % Industry
Directorate for the Built Environment Building Standards Division Energy Management Solutions Ltd Investigation of measures to improve the energy performance of a existing building: Retail JUNE 2009 Report
Energy audit in Finland NorTech Oulu Lauri Mikkonen Energy Audit in Finland An energy audit tells about the energy efficiency and total energy consumption in a building, including all consumed heating,
Energy Performance Certificate 10, Northfleet Road Eccles MANCHESTER M30 7PQ Dwelling type: Semi-detached house Date of assessment: 11 February 009 Date of certificate: 1 February 009 Reference number:
Assessment Methods 15 th November 2010 Huw Jenkins Simon Lannon Assessment Methods Program Country Year Program Country Year 1 R-2000 Canada 1982 12 LEED US 2000 2 P-mark Sweden 1989 13 ECO-Quantum Netherlands
Technical Papers supporting SAP 2009 Boiler efficiency for community heating in SAP Reference no. STP09/B06 Date last amended 26 March 2009 Date originated 28 May 2008 Author(s) John Hayton and Alan Shiret,
Energy Performance Certificate Rhanleta Cottage Woolsery BIDEFORD EX39 5QP Dwelling type: Detached bungalow Date of assessment: 15 July 2009 Date of certificate: 17 July 2009 Reference number: 0347-2845-6036-0991-7175
Rainwater Harvesting With climate change now a reality rather than a speculated possibility, the demand on water resources has gone up, whilst the amount of water available for supply has gone down. Forth
HOMEOWNER STANDALONE Homeowner Information SEPTEMBER 2011 Ecodan Air Source Heat Pump and Flow Temperature Controller 2 Ecodan Air Source Heat Pump Model Number PUHZ-W50VHA(2)-BS PUHZ-W85VHA(2)-BS PUHZ-HW140VHA(2)-BS
Energy Performance Certificate 7, Northfield Road SHEFFIELD S10 1QP Dwelling type: End-terrace house Date of assessment: 3 August 2009 Date of certificate: 3 August 2009 Reference number: 8311-6628-6400-5587-2002
The DART Energy Research Programme Recognising that the programme should be as much about people and changing cultures while delivering service the approach was developed initially through the four different
Is an air source heat pump the right choice for my home? Important information and key things to consider before installing an air source heat pump The basics... This guide can help you make an informed
Subtropical Cities September 2006 Design for Energy Efficiency in Commercial Buildings in Queensland Contents Typical Building Constraints & Requirements Understanding Energy Consumption in Buildings HVAC
DISTRIBUTED GENERATION AND ENERGY EFFICIENCY FOR ACHIEVING ENERGY SELF-SUSTAINING INDUSTRIAL AREAS Ing. Maria-Anna Segreto LAERTE Laboratory - 1 EUROPEAN DIRECTIVE 2010/31/UE It 's well known that higher
1. INTRODUCTION Norwegian Tax Authority - Oslo Norway PROJECT SUMMARY Year of construction - 1980 No previous energy renovations SPECIAL FEATURES Main topics in the renovation are: High insulated pre fabricated
Energy Performance Certificate Georgia House Stud Bradley Road Burrough Green NEWMARKET CB8 9NH Dwelling type: Detached house Date of assessment: 17 August 2011 Date of certificate: 17 August 2011 Reference
Information Guide Domestic Air Source Heat Pumps Issue 41 Domestic Air Source Heat Pumps This is an independent guide produced by Mitsubishi Electric to enhance the knowledge of its customers and provide
Land East of Clitheroe Road Renewable Energy Statement Commercial Estates Group 6th December 2010 WSP Document Reference Renewable Energy Assessment QM Issue/revision Issue 1 Revision 1 Revision 2 Revision
Energy Performance Certificate Flat 45 Ashton House 53, Cottington Street LONDON SE11 4BN Dwelling type: Mid-floor flat Date of assessment: 21 March 2012 Date of certificate: 21 March 2012 Reference number:
ENPER-EXIST WP3 Building stock knowledge Brussels, 27 June 2007 Kirsten Engelund Thomsen Danish Building Research Institute, SBi Aalborg University Main objectives in WP3 To conduct a survey of the level
Par Hill Research Reducing air pollution from your building - a series of manuals for operators, designers & developers Manual A - Minimising air pollution during building use Factsheet A1 - Laws & Regulations
Dr. Vahik Enjily International Director Building Research Establishment (BRE) Watford, England Environmental drivers & opportunities:- Impacts on housing sector in UK Die britische Bauwirtschaft und ihre
Energy Performance Certificate Non-Domestic buildings and buildings other than dwellings St Kessogs Church, 27 Ancaster Square, Callander, Stirling FK17 8DZ Date of assessment: 04 February 2013 Date of
MOST Ministry of Science and Technology Republic of China Sino-Italian Environment & Energy Building S I E E B Concept The Sino-Italy Environment & Energy Building (SIEEB) is an intelligent, ecological
2012 Ontario Building Code Requirements for New Construction Bradford West Gwillimbury Building Division March 5, 2012 1 Ontario Building Code changes Applicable to permits applied for after December 31,
Connolly Hospital Blanchardstown makes rapid recovery on energy technology investment Connolly Hospital, Blanchardstown (CHB) is a major teaching hospital and provides medical, surgical and support services
M. and W. Saman Sustainable Energy Centre University of South Australia Mawson Lakes Boulevard, Mawson Lakes, SA 5095, Australia E-mail: firstname.lastname@example.org Abstract A prototype of a roof integrated
Implementation of the EPBD in Cyprus Status in November 2010 Constantinos Xichilos Energy Service Ministry of Commerce, Industry and Tourism Nicos Hadjinicolaou Energy Service Ministry of Commerce, Industry
Energy Performance Certificate 14, Clifton Road, Anfield, LIVERPOOL, L6 4BQ Dwelling type: Groundfloor flat Date of assessment: 27 January 2009 Date of certificate: 27 January 2009 Reference number: 21389078626951619080
Energy Performance Certificate Flat 307 Windsor House Cumberland Market LONDON NW1 4DE Dwelling type: Date of assessment: Date of certificate: Reference number: Total floor area: Mid-floor flat 8361-6824-6900-7049-8026
Energy Performance Certificate 42 Cedar House Lucas Court LEAMINGTON SPA CV32 5JL Dwelling type: Mid floor flat Date of assessment: 12 November 2008 Date of certificate: 12 November 2008 Reference number:
Greenhouse Gas Implications of HVAC Upgrades in Multi-Unit Residential Buildings J A NUARY 2015 INTRODUCTION This Research Report explores best practices and approaches for reducing greenhouse gas (GHG)
GUIDANCE SHEET FOR CONSERVATORIES, SUNROOMS AND EXTENSIONS TO DWELLINGS. This leaflet provides guidance on how to attain compliance with The Building (Amendment) Regulations (Northern Ireland) 2006, Part
HOW TO CONDUCT ENERGY SAVINGS ANALYSIS IN A FACILITY VALUE ENGINEERING STUDY Benson Kwong, CVS, PE, CEM, LEED AP, CCE envergie consulting, LLC Biography Benson Kwong is an independent consultant providing
Part L1B & What you need to know to get your building to pass. Mike Andrews DipNDEA, DipDEC, DipOCDEA, DipHI The Building Regulations Part L1B what they are, how they affect your building design, and what
Energy Performance Certificate Flat 3 Dwelling type: Mid-floor flat 30, Brunswick Square Date of assessment: 23 September 2008 HOVE Date of certificate: 23 September 2008 BN3 1ED Reference number: 8398-6021-5510-4127-8022
your comfort. our world. Daikin Altherma Hybrid Heat Pump The natural combination Heating Integrated Solutions Ventilation Air Conditioning Refrigeration About Daikin Forward thinking... Daikin has a worldwide
Energy Performance Certificate (EPC) INGAGARTH, LOWER HILLSIDE, GULBERWICK, SHETLAND, ZE2 9FG Dwelling type: Detached house Date of assessment: 21 August 2013 Date of certificate: 03 September 2013 Total
Case Studies: Infrared Heating in Industrial Applications Chao Chen, Puget Sound Energy ABSTRACT Puget Sound Energy (PSE) is a utility which serves more than one million electric customers and over 700,000
CASE STUDY: Russia's First LEED Certified Commercial Office Building Renaissance Pravda Business Center, St. Petersburg LEED Consultants: ALAN Project Management and Architecture / Mimta EkoYapı http://www.leedcertification.ru/
Residential HVAC System Sizing William P. Goss University of Massachusetts, Amherst, Massachusetts, USA Corresponding email: email@example.com SUMMARY Heating, ventilating and air-conditioning (HVAC)
Data Collection Summary Report Asilo Cologno Monzese Polo Territoriale per la Prima Infanzia con Asilo Nido 22/09/2011 The sole responsibility for the content of this report lies with the authors. It does
www.asiabusinesscouncil.org Energy efficiency building standards in Japan Japan s regulation of building energy efficiency falls under the Energy Conservation Law that was first adopted in 1979. Subsequently
Sea Water Heat Pump Project Alaska SeaLife Center, Seward, AK Presenter: Andy Baker, PE, YourCleanEnergy LLC Also Present is ASLC Operations Manager: Darryl Schaefermeyer ACEP Rural Energy Conference Forum
You can use this document to: Energy Performance Certificate (EPC) Dwellings Scotland 17 WOODLANDS CRESCENT, WESTHILL, INVERNESS, IV2 5DY Dwelling type: Detached house Date of assessment: 22 December 2015
Efficiency for the Homeowner How to Reduce Your Home s Bills October 2009 National Mall Washington, DC A Quick Test Using Efficient Products and Practices Can: A. Make your home more affordable B. Make
Your consent to our cookies if you continue to use this website.