1 CIPHI s 75 th Annual conference Safe Drinking Water Course Cross Connection Control and Backflow Prevention Presented By: Roland Tomuschat Plumbing and Gas Safety Codes Officer May 3, 2009
2 Cross Connection Control and Backflow Protection OBJECTIVES: What is a Cross Connection? Why is a Cross Connection Control program necessary? What are the Legal Implications? Who is the Authority Having Jurisdiction? What type and where should backflow preventers be used? Examples. 2-5/15/2009
3 What is a Cross Connection? An actual or potential connection between the potable water distribution system and any source of pollution or contamination. 3-5/15/2009 Bypass arrangements, jumper connections, or any temporary or permanent connection through which backflow may occur are considered cross connections.
4 Contaminants Contaminates found in potable water due to cross connections. Chemical Fertilizers Pesticides Herbicides Ethylene glycol Chromates Detergents Biological E. coli Salmonella Shigella Norwalk Virus Giardia Cryptosporidium 4-5/15/2009 These are but a few of the serious contaminates found in the potable water supply after a cross connection incident.
5 Back-Siphonage Backflow caused by pressure below atmospheric in the supply system. Back Pressure Pressure higher than the water supply pressure. 5-5/15/2009 The piping in green shows a container/fixture on 4 th flr that has a hose in it. When the water main breaks and the water to the main is turned off and the water drains out of the system, a negative pressure is created that siphons the contents of the fixture back into the building water system and all the way to the municipal distribution mains. This container could contain contaminates that are toxic. Regardless of whether it is highly toxic or drinkable water it is still considered used water and must not be allowed to enter the potable water system. Toilet tank water could also be siphoned if the ballcock does not have an anti-siphon feature built into it or if it isn t installed properly. The ballcock s critical level must be installed 25 mm above the top of the overflow tube. It has been demonstrated when a toilet plunger is used to unclog a plugged bowel contents of the bowel can be forced up into the tank. The hot water heating system, that may have chemicals added, could also be drawn back into the potable water lines under a back-siphonage condition. The heating system water could also be forced back into the potable water system if the pressure in the heating system is higher than the potable water system pressure. This is a back pressure condition. A backflow preventer must be installed on the water line to the heating system. In addition, individual backflow preventers must be installed at each fixture, whether it s a bathtub, lavatory, toilet, or other piece of equipment.
6 High Risk Facilities Hospitals Laboratories Wastewater Treatment Plants Funeral Homes Morgues Battery Shops Plating plants Greenhouses Refineries Car washes Dry cleaner Laundries Many Others 6-5/15/2009 These are a few of the high risk facilities that require a high level of backflow prevention.
7 Moderate to Low Risk Facilities Apartments Condominium Complexes Hotels Elementary Schools Restaurants Hardware Stores Super Markets Small Shopping Centres Office Towers Many Others 7-5/15/2009 Moderate to minor risk facilities require less stringent backflow prevention. However, after an inspection of the facility it maybe determined that a higher level of protection is required as in a high risk facility.
8 Degrees of Hazard MINOR Low probability of becoming a health hazard (water aesthetically displeasing). MODERATE Low probability of becoming a severe hazard. SEVERE Could cause illness or death. 8-5/15/2009 The degree of hazard associated with a contaminated source must also be taken into account. For instance, a fixture or piece of equipment that is classified as a minor hazard would not have the same type of backflow preventer that a moderate or severe hazard require. A minor hazard may cause the water to look, smell or taste bad but it is not considered a health risk. A moderate hazard is not a health hazard but has the potential to become one. A severe hazard could cause injury if someone consumed or came in contact with the contaminated water.
9 Why is a Cross Connection Control Program Necessary? Compliance with National & Provincial Codes, Standards, Acts and Regulations. Eliminate backflow of contaminants into the water distribution system. Provide & maintain safe drinking water. Due diligence requirement. Mitigate liability. 9-5/15/2009 There are many Codes, Acts etc, that address protection of the potable water system. Health, Environment, Municipalities, Water Purveyors, and anyone involved in potable water must adhere to these documents. Parties that could administer a CCC Program include the Water Purveyor, the Municipality or the Health Department. Generally it is the water purveyor who implements the program, as they have a vested interest in supplying safe potable water to their customers. Backflow preventers must be installed and maintained to ensure contaminants do not enter the potable water system. Due diligence is the level of judgment, care, prudence, determination, and activity that a person would reasonably be expected to do under particular circumstances. Due diligence is measured by 3-factors 1. Foreseeability could a reasonable person have foreseen that something could go wrong? 2. Preventability was there an opportunity to prevent the injury of accident? 3. Control who was the responsible person who could have prevented the accident or incident? Failure to prove that you have been diligent in complying with safety legislation can result in significant penalties.
10 Acts, Regulations Alberta Safety Codes Act adopted the National Plumbing Code of Canada with some amendments. National Plumbing Code of Canada Protection of potable water from Contamination 10-5/15/2009 National Plumbing Code of Canada 2005 was adopted in Alberta on September 2, Section of this code refers to the protection from contamination. This section also states the backflow prevention devices must be installed and maintained in accordance with the CSA B64.10, Manual for the Selection and Installation of Backflow Prevention Devices.
11 Standards National Plumbing Code requires backflow preventers follow the Canadian Standards Association B64.10 Manual for the Selection and Installation of Backflow Prevention devices. 11-5/15/2009 The CSA B64.10 Standard provides detailed information on the type of backflow prevention devices that must be used on various fixtures, processes and equipment. It also indicates when devices must be tested and how to test them.
12 Standards CSA B64 Standard & AWWA Canadian CCC Manual Selection of Backflow preventers Installation of backflow preventers Testing of backflow preventers CCC Specialists/ Testers Course 12-5/15/2009 The Standard not only identifies the type of devices that must be used it also describes how they must be installed. Testable backflow preventers must be tested by properly trained and certified testers. AWWA s Cross Connection Control Committee have developed courses for testers. An individual successfully completing the course receives a CCC specialist certificate that is recognized by communities that have CCC programs.
13 Testing of Cross Connection Control Devices All devices must be tested when installed. All devices must be tested annually or more often when required by the AHJ. 13-5/15/2009 Even though new backflow preventers are installed they must be tested. New water lines must be cleaned before they are put into service. Debris in the cleaning process could become lodged in the backflow preventer s check valve causing it to not seat properly allowing contaminates to enter the potable water supply. Annual tests are required to ensure they are working properly. If a backflow preventer is placed in a line that is known to cause a backflow preventer to fail the AHJ may require more frequent tests.
14 CCC Testers / Specialists Training Supported by WCS AWWA CCC Committee City - Institute Edmonton - NAIT Calgary - SAIT Red Deer - College Medicine Hat - College 14-5/15/2009 Courses are available at these Alberta Institutes. There are similar courses offered in provinces across Canada.
15 Standards Alberta Municipal Standards & Guidelines (2006) Section When an existing crossconnection poses a potential health or system hazard, the owner shall shut off water service until the cross-connection has been eliminated or controlled by the installation of a proper backflow prevention assembly. 15-5/15/2009 Alberta Environment is responsible for the Drinking Water and Wastewater Programs for large public systems in Alberta. AENV considers the establishment of standards and guidelines for municipal waterworks, wastewater and storm drainage facilities an integral part of our regulatory program directed at ensuring public health and environmental protection. This document sets out the regulated minimum standards and requirements for municipal waterworks in Alberta.
16 Standards Alberta Municipal Standards & Guidelines Section Cross-Connection Control There shall be no physical connection between any waterworks systems and a sanitary or storm sewer that may allow the passage of wastewater into the potable water supply. Further, to prevent potential contamination, and avoid re-growths, no cooling water shall be returned into the potable water system. 16-5/15/2009 The recirculation of potable water, used for cooling purposes, back into the municipal mains is not addressed in the plumbing code but is in this standard. Alberta Municipal Affairs has received calls asking about this piping arrangement and have told the individual it is not allowed.
17 Standards Alberta Municipal Standards & Guidelines Section Backflow Preventers shall be installed in accordance with the latest edition of the WCS AWWA CCC Manual. 17-5/15/2009 The Standard refers to the Western Canada Section of The American Water Works Association Cross Connection Control Manual for the installation of backflow preventers. This manual is now a Canadian manual used by all technical institutes and colleges providing CCC courses. The manual provides additional information not found in the CSA B64.10 standard.
18 Bylaws Local/Municipal Water Bylaws generally regulates Cross Connection Control. Presently: Calgary, Camrose, Canmore, Edmonton, Red Deer, Lethbridge, Medicine Hat, Okotoks and Redcliff are some places that have CCC in their Bylaw. 18-5/15/2009 Provinces have given municipalities the power to adopt bylaws. Unless a bylaw is passed to adopt a cross connection control program they could not enforce it. Bylaws generally identify where backflow preventers must be installed, when they must be tested and penalties for not installing or testing devices. CCC Programs, in a lot of instances, are adopted after there have been incidents of municipal water main contamination.
19 CCC Responsibilities Engineer/designer Backflow preventers required in design. Plumber Installation & testing of backflow preventers. Safety Codes Officer/CCC Inspector Ensure proper devices installed and tested. Owner Responsible for having the device tested and maintained. Health Inspector Identify contamination incidents. 19-5/15/2009 Every one from the designer, to the owner and various inspectors must play a role in ensuring potable water does not become contaminated.
20 Backflow Preventers? There are 2 types of Backflow Preventers: Non-Testable Devices Testable Devices 20-5/15/2009 Non-testable devices are generally used to protect the potable water system from minor and moderate hazards. Some non-testable devices can be used in a severe hazard situation but they are backed up by an additional backflow preventer that can be used to protect against severe hazards. Not all testable backflow preventers can be used in severe hazard condition
21 Non-Testable Backflow Preventers Air Gap (AG) Dual Check (DuC) Hose Connection Vacuum Breaker (HCVB) Atmospheric Vacuum Breaker (AVB) 21-5/15/2009 An air gap, although not a device, is one of the best and most inexpensive means of protecting the potable water supply. There is a physical air break of at least one inch or twice the diameter of the supply pipe from the flood level rim of the fixture or equipment. It can be used to protect against all hazards. However, if the an air gap is installed in an atmosphere that may become toxic such as in a laboratory fume hood it would have to be backed up by another device out side the fume hood. It has its shortfalls if water pressure is needed downstream of the air gap in which case a pump would have to be installed. Air gaps are seen on basins bathtubs and other fixtures where the tap is above the flood level rim of the fixture. Dual check valves have two check valves built into them and can be used to isolate a house from the municipal water supply. HCVB s must be installed on all Hose bibs. If installed outdoors they should automatically drain the water to avoid freezing and ultimate breakage of the device. AVB s are installed on mop sinks, lab sinks, toilets etc. to prevent contaminates being siphoned back into the potable water supply. A HCVB and an AVB cannot have pressure on the device for more then 8 hours and are only used in back-siphonage conditions.
22 Testable Backflow Preventers RP - Severe DCVA - Moderate PVB Severe 22-5/15/2009 A reduced pressure principle backflow prevention device (RP) can be used on all types of hazards. This device is used extensively on severe hazard. An example of where an RP is used is on a heating system that has chemicals added to the heating media. A double check valve assembly (DCVA) is used on moderate hazards such as a fire sprinkler system that has no chemicals added. A pressure vacuum breaker (PVB) is a device that is not widely used. It is mostly used to protect an irrigation system. That being said it is used sparingly in other applications. An ordinary PVB requires a drain nearby to catch any spillage from the relief ports. If spillage is a problem a spill resistant PVB must be installed. PVB s can be used on a severe hazard but are generally backed up by another device at the water service entrance.
23 Back Pressure & Siphonage Device Application RP DCVA DCAP DuC 23-5/15/2009 These are some of the more popular devices used when a back pressure is a possibility or when continuous pressure is placed on the device. They can also be used when a back siphonage condition is a possibility. Soft drink carbonators have a Dual Check Valve with Atmospheric Port (DCAP) that is specially designed for this purpose. Copper or brass DCAP devices should not be used in this application as the carbonic acid created attacks the copper and brass parts.
24 Back-Siphonage Device Application Air Gap (AG) Hose Connection Vacuum Breaker (HCVB) Pressure Vacuum Breaker (PVB) Atmospheric Vacuum Breaker (AVB) 24-5/15/2009 These devices cannot be used where there is back pressure on the device.
25 Protection Locations INDIVIDUAL At location of hazard. ZONE/AREA Isolation of area within a building. PREMISE Isolation from the water distribution system. 25-5/15/2009 One or all of these methods maybe used to protect a water supply from becoming contaminated. A typical example of all three is in a hospital. Individual backflow preventers are required at the fixture or equipment. Zone or area isolation is used to isolate a section of the hospital such as the morgue or operating rooms. Premise isolation is immediately after the water meter. Backflow preventers must be tested annually and repaired as needed. Where 24 hr water service is necessary, such as in a hospital, a bypass line is required around the backflow preventer. This bypass also requires the same type of backflow preventer.
26 Examples of Premise Isolation DCVA on Fire DCVA on Irrigation RP on Premise 26-5/15/2009 This piping arrangement is typical for many residential, commercial and industrial facilities. Along with the devices shown additional devices are required at each fixture or piece of equipment.
27 Implications of Premise Isolation Impact on system performance. Pressure/Flow Restriction Excessive pressure lose Thermal Expansion 27-5/15/2009 All backflow preventers impact water pressure and performance of the system. Some devices can reduce the pressure as much as 20 psi. The installation of a device could seriously impact a fire protection system if the water pressure is reduced. When a backflow preventer is installed, especially in an existing fire protection system, the entire system must be checked by a professional engineer to ensure the fire system is still capable of performing properly. If premise isolation is part of the water system, equipment must be added to compensate for the excess pressure created by a hot water heater, i.e. an expansion tank. Hot water expands creating excessive pressure in the piping system.
28 How many Cross Connections in a Potable Water System? Depends on the number of total connections to the water system. Fire, domestic, irrigation, sinks, basins toilets, aspirators, carbonators, hose bibs etc. 28-5/15/2009 The list above are a few examples of where cross connections could contaminate the potable water. In an average home there are over a dozen potential cross connections. In hospitals and other commercial and industrial facilities there could be thousands. Due diligence by all parties involved in the design, installation and inspection of these facilities is essential to keep our potable water safe.
29 Cross Connection Instances Winnipeg 2006 Cooling system water enters Health Care facility potable water. A bypass valve left open. Edmonton High Rise experiences brackish water from taps after a water main break. Fire system water siphoned through a single check valve separating the potable water from the fire system. Blue caustic water from heating system enters potable water system. 29-5/15/2009 Residents of a major health care facility in Winnipeg noticed a sweet smell coming from a tap. Staff found a ball valve had been mistakenly opened that allowed cooling system water to enter the potable water system. No illnesses were reported but the incident impacted the facilities operation for several days while the system was flushed. Residents of an Edmonton high rise noticed brackish water coming out of their taps after a water main break. Apparently, a single check valve separating the fire system and the potable water failed. There were no reported illnesses. An Edmonton high rise required repairs to the domestic water lines. When the valve at the meter was turned off and the water piping drained, caustic water from the heating system back flowed into the potable water system. When the water was turned on blue caustic water came from the taps. Fortunately, no one was injured, but it took 1-2 weeks to clear the potable system as the caustic embedded itself in the calcium and magnesium deposits in the water lines.
30 Cross Connection Instances Regina 1997 Meter reader notices meter turning backwards in major production facility. Redcliff 1989/ 1990 Carwash, soapy water in main. Greenhouse fertilizer, repairs, 1 ill for 1 wk. 30-5/15/2009 A meter reader noticed that the meter was turning backwards. The reversed flow occurred during annual maintenance of the plant. The plants process water consisted of well water supplemented by city water. No process water was required during maintenance but the well pump continued to operate overcoming the city s water pressure forcing well water into the city mains. The existing single check valve failed. A proper backflow preventer was installed. Note: A private water system cannot be connected with a municipal water system; an air gap separation is required. A failed backflow preventer, together with a drop in Redcliff s water main pressure allowed soapy water to enter the public water supply. Residents in the area complained about soapy water after the water pressure was restored. Water was turned off and drained to make repairs to a water main in Redcliff. The lack of a backflow preventer in the water line serving a green house allowed fertilizer to back siphon into the distribution pipe. When the water to the main was restored some of the fertilizer remaining in the municipal system mixed with the water and was delivered to other customers. An individual drinking the contaminated water became violently ill and missed a week of work.
31 Cross Connection Instances Medicine Hat 1989 Large Comm. Building combined back pressure & back siphonage of glycol into City Main, wrong device, 2 people sent to hospital. Calgary 1987 Main break, back siphoned chemicals, into water main and elementary school, no injury. 31-5/15/2009 Single check valves were used to separate the potable water piping from a boiler heating system which had ethylene glycol in it. The single non-testable check valves failed allowing the glycol to enter the potable water piping and Medicine Hat s water mains. Several surrounding residents complained about the water quality and two people inside the building were sent to hospital. Fortunately, no one was serious hurt. An elementary school in Calgary experienced a backflow condition during a water main break. The schools chemically treated water in the heating system was forced into the potable water system. After the repairs were made to the water mains and the water turned on, contaminates made their way to drinking fountains and washrooms. These contaminates contained chromates, a highly toxic substance. Fortunately, the students were sent home when the water main break occurred and no one was hurt. The school remained closed for several days while the system was repeatedly flushed.
32 Could this happen to you? 32-5/15/2009 Guelph s population in 1996 was about 96,000. A town which had 48,000 residents without water were bound to have a lot of complaints.
33 Who do you call? Water Purveyor Health Inspector Accredited Municipality s Plumbing Inspector Non-Accredited Municipality - Alberta Municipal Affairs Municipal Affairs Web Site /15/2009 When a contamination occurs in a building the water purveyor should be called immediately if there is a possibility that the contaminate could backflow into the municipal distribution system. The Health Inspector may have to be called. In an accredited municipality the municipal office should be called to have their plumbing inspector investigate the incident if warranted. In non-accredited municipalities Alberta Municipal Affairs (AMA) should be contacted so that either one of AMA s inspectors or an agency contracted to do inspections for AMA could investigate the incident. To determine whether a municipality is accredited go to the AMA s web site. There is a drop down menu that lists all the municipalities in Alberta. Select the municipality to determine its accreditation status. If it is accredited call the municipal office; if not contact AMA.
34 CCC Summary To eliminate contaminants back flowing into the potable water system through a cross connection. Provide & maintain safe drinking water. Comply with National & Provincial codes, standards, acts & regulations. Due diligence requirement. Mitigate liability. Type of devices required for the hazard. Examples 34-5/15/2009
What Is a Cross-Connection? A cross-connection is a direct arrangement of piping that allows the potable (safe drinking) water pipe to be connected to a pipe supply that contains a contaminant or pollutant.
Cross Connection Control and Backflow Prevention Program Guidelines February 2010 EPB #422 Note: As of October 1, 2012 The Water Security Agency and Saskatchewan Ministry of Environment share responsibility
Backflow Bulletin #1 FIRE PROTECTION SYSTEMS Chemicals in the System Anti-Freeze, Foam, Corrosion Inhibitors, etc. Chemicals in the System Glycerin Glycerin or similar food-grade non-toxic additive Siamese
PROTECT YOUR WATER FROM CONTAMINATION Normally, your water supply is under 40 to 80 pounds of pressure when it enters your home or business. On rare occasions, this pressure is interrupted perhaps by a
Guide to Backflow Prevention, Cross-Connection Control, Auxiliary Water Systems and Booster Pumps Why be concerned? It can be a health hazard for you, your family and others if contaminated water enters
CROSS-CONNECTION CONTROL and BACKFLOW PREVENTION Les O Brien, UF/TREEO Center CROSS-CONNECTION is any connection between a potable water system and any source of contamination through which contaminated
Plumbing Installations A homeowner guide to the City of Winnipeg plumbing requirements for a single-family dwelling February 2001 contents General Information 3 Inspection 4 New Drain and Vent Installations
Section 19.0 Cross Connection Control Policy 19.1 Responsibility 19.1.1 The Elkhart Water Utility has the responsibility to supply safe, potable water from the source to the point of delivery defined as
CHAPTER 26 PLUMBING CODE 26.01 PLUMBING CODE The Illinois Plumbing Code as promulgated by the Illinois Department of Public Health at 77 Illinois Administrative Code, Part 890, is hereby adopted as the
CITY OF BAY CITY ORDINANCE NO. 628 AN ORDINANCE FOR THE CONTROL OF BACKFLOW AND CROSS- CONNECTIONS, REPEALING ORDINANCE NO. 560 AND DECLARING AN EMERGENCY. THE CITY COUNCIL OF THE CITY OF BAY CITY, OREGON
PLANNING, PROPERTY AND DEVELOPMENT DEPARTMENT Plumbing Installations A homeowner guide to the City of Winnipeg plumbing requirements for a single-family dwelling October 2014 contents General Information
Cross-Connection Control Protecting the potable water supply from contamination. CROSS-CONNECTIONS What is a cross-connection? A physical or POTENTIAL connection between a drinking water system and any
ALBUQUERQUE BERNALILLO COUNTY WATER UTILITY AUTHORITY CROSS CONNECTION PREVENTION AND CONTROL ORDINANCE 8-1-2. SHORT TITLE. This Ordinance shall be known and may be cited as The Cross Connection Prevention
ORDINANCE NO. 1125 AN ORDINANCE OF THE CITY COUNCIL OF THE CITY OF NORTH LAS VEGAS TO CREATE A NEW CHAPTER 4.17 OF THE MUNICIPAL CODE ENTITLED BACKFLOW AND CROSS- CONNECTIONS; PROVIDING PENALTIES FOR VIOLATIONS
Plumbing Code in Commercial Kitchens City of Concord Code Administration 225-8580 Dan Clark Plumbing Inspector Tedd Evans, Chief Building Inspector Code References from the 2009 edition of the International
Chapter 8 Water and Sewage Systems Proper sanitary controls pertaining to the water supply system and sewage and liquid waste disposal systems are necessary in all types of food establishments to prevent
SUBPART I: WATER SUPPLY AND DISTRIBUTION Section 890.1110 Quality of Water Supply All premises intended for human habitation or occupancy shall be provided with a potable water supply. The potable water
12.33 - CROSS-CONNECTION CONTROL. (a) Purpose. The purpose is to safeguard potable water supplies by preventing backflow into public water systems. (b) Definitions. The following definitions shall apply
Metropolitan Domestic Water Improvement District Backflow Prevention Control Ordinance Ordinance No. 1993-01 September 23, 1993 Metropolitan Domestic Water Improvement District Backflow Prevention Control
Effective Cross-Connection: Why & How Judson Smith Water Supply Division Public Drinking Water Section Technical Review & Oversight Team MC -155 TCEQ Requirements 1. Service Agreement, Plumbing Ordinance
Minimum Standards for a Cross-Connection Control Program Arkansas Department of Health Bureau of Environmental Health Services Division of Engineering 4815 West Markham Street Little Rock, Arkansas 72205
UTILITIES DEPARTMENT Dear Business Owner, As a Business owner or manager you know how important it is to provide a safe and reliable service or product. Similarly, the City of Brighton Utilities Department
The Plumbing Pipeline A Newsletter for licensed Plumbers and Drainlayers November 2015, Issue 28 Please copy this bulletin and distribute to your staff. The Plumbing Pipeline is a semi-annual information
8 90 2010 PulteGroup, Inc. All Rights Reserved. drains All the water you use leaves the home through a drain. Maintaining drains prevents clogging, overflows, water damage, and other problems. care and
CROSS-CONNECTIONS AND BACKFLOW PREVENTION MANUAL Governor Secretary Department of Health and Human Resources Chris H. Curtis, M. P. H Acting Commissioner Bureau for Public Health Department of Health and
Cross Connection Control Policy Date of Last Revision: March 19, 2015 Policy on Cross-Connections OUC agrees with the American Water Works Association s (AWWA) statement issued on cross connection as follows:
City of West Chicago Community Development Department 475 Main Street, West Chicago, IL 60185 Phone: (630) 293-2200 x 131 / Fax: (630) 293-1257 APPLICATION FOR DEMOLITION PERMIT Permit Number: Date Received:
STATE OF CONNECTICUT CROSS CONNECTION CONTROL MANUAL Prepared by: The State of Connecticut Department of Public Health Drinking Water Division 410 Capitol Avenue, MS #51 WAT P.O. Box 340308 Hartford, Connecticut
Texas State Board of Plumbing Examiners Plumbing Inspector Examination Review Course The following Examination Review Course is designed to assist an applicant in preparing for the Plumbing Inspector examination.
Presented by: Jeremy Harris, E.I. Department of Health & Hospitals/ Office of Public Health Engineering Services Causes of Backflow & Examples of Cross Connections Documented Backflow Incidents Backflow
PUBLIC WORKS TECHNICAL BULLETIN 420-49-16 16 July 2001 CROSS-CONNECTION CONTROL AT ARMY INSTALLATIONS Public Works Technical Bulletins are published by the U.S. Army, Corps of Engineers Washington, DC.
PLUMBING & CROSS-CONNECTION CONTROL. MODULE 4 VII. Typical Retail Food Service Cross-Connections VIII. Air Gaps and Air Breaks for Drains and Waste IX. Grease Interceptors VII. TYPICAL RETAIL FOOD SERVICE
PART 1 - GENERAL 1.01 OVERVIEW A. This section addresses domestic cold, hot and hot water return distribution systems within and to five feet beyond building perimeter. PART 2 - DESIGN CRITERIA 2.01 GENERAL
MassDEP Cross Connection Control Program Regulations - 310 CMR 22.22 Definitions as Related to Cross Connections. As used in 310 CMR 22.22, unless the context indicates otherwise, the following words shall
Georgia State Amendments to the International Plumbing Code (2006 Edition) Georgia Department of Community Affairs Local Government Assistance Division 60 Executive Park South, N.E. Atlanta, Georgia 30329-2231
The Plumbing Pipeline A Newsletter for licensed Plumbers and Drainlayers May 2016, Issue 29 Please copy this bulletin and distribute to your staff. The Plumbing Pipeline is a semi-annual information newsletter
This Program is made Possible through the Code Officials Education & Training Fund. Revenue for the Fund comes from Assessments on Building Permits. Please turn down cell phones and put pagers on vibrate.
SECTION 11 PLUMBING AND CROSS CONNECTION CONTROL DRAINS INDEX I. Plumbing Systems 11-1 II. Cross-Connections: Direct & Indirect 11-1 Ill. Forces Acting on Cross-Connections, 11-4 Backflow: Backpressure
Backflow Preventer Presentation ASSE/ASPE Conference New York City May 2015 What is Backflow? Backflow is the undesirable reversal of flow of water or mixture of water and / or other substances into the
Indirect-Fired Storage Water Heater Models WH-30 through WH-80 INSTALLATION AND OPERATING INSTRUCTIONS Contents Page Ratings and Specifications..................... 2 Installation Requirements......................
THE CORPORATION OF THE CITY OF COURTENAY BYLAW NO. 2182 A bylaw to amend Storm Sewer Bylaw No. 1402, 1986 The Council of the Corporation of the City of Courtenay in open meeting assembled enacts as follows:
INDIANA DEPARTMENT OF ENVIRONMENTAL MANAGEMENT 2013 Edition Bulletin PWS 1 December 1987 Revised February 1996 Reprinted June 1997 Revised 2001 & 2009 & 2013 CROSS CONNECTION CONTROL & BACKFLOW PREVENTION
Do-It-Yourself (DIY): How to Winterize Underground Sprinkler/Irrigation System by Blow-out Method Using an Air Compressor Water expands as it turns into ice, resulting in a volumetric expansion sufficient
CALIFORNIA PLUMBING CODE MATRIX ADOPTION TABLE CHAPTER 17 - NONPOTABLE RAINWATER CATCHMENT SYSTEMS (Matrix Adoption Tables are non-regulatory, intended only as an aid to the user. See Chapter 1 for state
Amendments to the 2012 International Plumbing Code North Central Texas Council of Governments region The following sections, paragraphs, and sentences of the 2012 International Plumbing Code are hereby
TITLE 22 PART 17 CHAPTER 363 RULE 363.11 EXAMINING BOARDS TEXAS STATE BOARD OF PLUMBING EXAMINERS EXAMINATION AND REGISTRATION Endorsement Training Programs (a) General requirements for Course Providers
www.garyklinka.com Page 1 of 51 Exterior Plumbing Quiz Part 1 Instructions: $60 1. Print these pages..all reference materials are included. 2. Review and answer the simple questions in each mini section.
3940-W 2998-W A. General 1. Utility s Responsibility a. (1) In urban areas with dedicated front streets, rear service roads, or public utility easements the utility will furnish and install the service
Plumbing Helpful Hints Residential Construction Bert Polk Plumbing Inspector Lincoln County 2015 Waste and vent fittings Vent 90 medium 90 long 90 1/16 bend,1/8 bend,1/6 bend, medium 90 san tee combination
Indiana Department of Environmental Management www.in.gov/idem Well Disinfection Why Disinfect? Well disinfection can eliminate or reduce many different kinds harmful bacteria and viruses as well as harmless
Preventing water damage caused by plumbing fixtures Thousands of home insurance claims are filed every year. Some losses are major, others aren t, but they re always inconvenient and usually avoidable!
The Plumbing Pipeline Lond A on DA The Plumbing Pipeline is a semi-annual information newsletter publíshed by the City of London, Building Division, for the plumbíng and drainlaying industry. City of London
2010 Residential Water Heater Replacement Check List The intent of this check list is to provide installers a general reference for the enforcement of code requirements in the Greater San Diego Area. This
Preventing Overheated Boiler Incidents PSE&G Appliance Service October 2012 Runaway Boiler Explosion Review Items Hazard Background Past Incidents PSE&G Emergency Response Future Process Improvements What
Only RAIN down the Storm Drain... DRAFT Guidelines for Manually Diverting Outdoor Wastewater to the Sanitary Sewer This publication applies to you if: You generate wastewater outdoors, and The wastewater
DISSCUSSION ITEM 3 ATTACHMENT E Chapter 16.130 PLUMBING CODE 16.130.100 Plumbing Code - Incorporation. There is incorporated by reference, for purpose of adopting regulations, provisions, conditions, terms,
PRIVATE WELL SEPARATION This is an explanation to explain what you have to do with your well, and/or the other sources of water that you may have, in order to receive public water. The term well includes
Ohio Department of Commerce Division of Industrial Compliance, Construction Compliance 6606 Tussing Road P. O. Box 4009 Reynoldsburg, Ohio 43068-9009 (614) 644-3153 FAX (614) 995-1146 Backflow Prevention
later damage - Loss ControL axisinsurance.ca Table of Contents EXECUTIVE SUMMARY... 1 FACILITY SYSTEMS WATER DAMAGE... 2 Frozen Pipes.....................................................................................
Plumbing Apprenticeship Program Curriculum Plumbing Level One 02101-05 Introduction to the Plumbing Profession (5 Hours) Introduces the trainee to plumbing, starting with the history of plumbing from ancient
RIVERGROVE WATER DISTRICT FREQUENTLY ASKED QUESTIONS 1. WHERE DOES THE WATER COME FROM? Rivergrove Water District s water source is groundwater and comes from wells that we have drilled into the Columbia
Title 15 - Mississippi Department of Health Part 20: Bureau of Public Water Supply Subpart 72: Public Water Supply CHAPTER 1. MISSISSIPPI PRIMARY DRINKING WATER REGULATION Subchapter 1. General Provisions:
Province of Alberta SAFETY CODES ACT PLUMBING CODE REGULATION Alberta Regulation 119/2007 With amendments up to and including Alberta Regulation 227/2012 Office Consolidation Published by Alberta Queen
Fats, Oil and Grease Best Management Practices Manual Information, Pollution Prevention, and Compliance Information For Food Service Facilities Pinellas County Utilities Water Quality Management Division
LITHGOW CITY COUNCIL A GUIDE TO RAINWATER TANKS A Guide to Rainwater Tanks This kit aims to assist you to maximise the benefits from the use of rainwater tanks. Water use depends on its availability and
A cure for water damage in real estate Presented for BC Non-Profit Housing Association by Jeff Shearman, Zurich Services Corporation 2010 Zurich Canada Focused on our customer Reduce overall risk by reducing:
PROTECTIVE PLUMBING - WHAT IS IT? TABLE OF CONTENTS Protective Plumbing What is it?...page 1 What is Foundation Drainage?...Page 2 What is a Sump Pumping System?...Page 4 Does Part of My Basement Floor
YOUR HOME S PLUMBING SYSTEM By Tim Oglesby, Home Check America Plumbing has changed significantly since the days when American s lived in little houses on the prairie. Unfortunately, many homeowners don
Reference Guide for Obtaining Permits and Utility Services For New Construction (Revised 04-2012) Table of Contents City Offices Telephone Numbers...1 Application for Utilities...2 Building Permits New
Chapter 851 WATER SUPPLY 851-1. Definitions. 851-2. Administration. 851-3. Use and receipt of water. 851-4. Water service connections. 851-5. Metering of water. 851-6. Water meter inspection. 851-7. Maintenance.
COMPREHENSIVE DRINKING WATER SOURCE-TO-TAP ASSESSMENT GUIDELINE MODULE 4 EVALUATE WATER SYSTEM MANAGEMENT, OPERATION AND MAINTENANCE PRACTICES Source Protection Emergency Response Training Treatment Multiple
Sample Exam Questions and Recommended References for ABC s Backflow Prevention Assembly Tester Exam The following questions are provided as examples of the types of questions that will be covered on the
BULK WATER HAULING GUIDELINES Under The Public Health Act regulations, Bulk Water Haulers must obtain a permit to sell or convey water for sale for domestic purposes. For the purposes of this guideline,
WHITE OAK BEND MUD 12841 Jones Rd, Suite 120, Houston, Texas 77070 Phone Number (281) 897-9100 Welcome to your Water District, White Oak Bend Municipal Utility District, The District. You may request water
VILLAGE OF GRANVILLE SEWER BACK-UP and WATER LEAK POLICIES SEWER BACK-UP POLICY General Sewer back-ups are an unfortunate, but common problem in older communities. A sewer back-up can create a health or
TOWN OF WRENTHAM EMERGENCY RESPONSE PLAN Cross Connection 3/7/2014 This Emergency Response Plan was created in the event that there was a cross connection or backflow incident to the town s water distribution
PREVENTING WET OR FLO ODED BASEMENTS TABLE OF CONTENTS Prevention Tips...Page 1 Why is there Water in my Basement?...Page 2 City of Saskatoon Sewer Systems...Page 3 Why Does Saskatoon Have Two Separate
UPPER MOHAWK VALLEY REGIONAL WATER BOARD The following Rules and Regulations and the fees rates and charges incorporated herein are to be considered as a part of the contract between the Upper Mohawk Valley
ToTo Protect and Promote the Health and the Environment of the People of Kittitas County New or Remodeled Food Service Establishment Checklist** **Some items may not be required for limited food service
WHITE PLAINS PLUMBING CODE PART 1. GENERAL REQUIREMENTS a. New Plumbing and Gas Piping Systems. This code in conjunction with the Plumbing and Fuel Gas Codes of the State of New York shall apply to plumbing
SECTION 5 - COMMERCIAL CONSTRUCTION MECHANICAL, ELECTRICAL, PLUMBING AND SOLAR OTHER TECHNICAL CODES 5.1.0 GENERAL Section five reviews consolidates the various local amendments technical code information
Texas State Board of Plumbing Examiners Tradesman Plumber-Limited Licensee Examination Review Course The following Examination Review Course is designed to assist a registered Plumber s Apprentice in preparing