1 World Class Water Chemistry By Accident? BRO Chemistry Session 8/5/2014
2 From Safe by Accident? by Judy Agnew & Aubrey Daniels Despite decades of reduction in safety related deaths and injuries on the job, catastrophic accidents appear to be on the rise. In the last ten years, there have been at least nine industrial accidents that resulted in more than 125 deaths.
3 From Safe by Accident? by Judy Agnew & Aubrey Daniels BP s Deepwater Horizon offshore oil rig operated for seven consecutive years without a single lost time incident or major environmental event. By these measures they were safe. Safe by Accident?
4 Supposedly World Class Stuff? We benchmark numbers going down each year No blade failures due to water chemistry No single phase FAC catastrophic failures Water Chemistry Related Boiler tube failures trending downward We have required cycle chemistry instrumentation We have training We have management support We measure carryover quarterly We conduct complete cation and anion analysis of cycle, stator systems, water plant quarterly We have boiler water chloride analyzers etc., etc., etc.
5 Last 36 months Operator not tripping unit when ph was below 7.0 Operator not tripping unit when boiler water chlorides were 30,000 ppb Open turbines and see deposition. Post chemical cleaning tube samples indicate unit not successfully chemical cleaned. Operator not tripping unit when boiler water chlorides were 15,000 ppb Tube deposit weight of over 70 g/ft2 Replacement of approximately 120 tubes due to severe pitting.
6 Assessment Is AEP s cycle water chemistry program world class by accident? We have everything we need to be successful so how does events like this occur at AEP? Should we accept these events as unavoidable events that just periodically happen?
7 A New Concept Repeat Situations Cycle Chemistry Influenced BTF and HTF Can Be Directly Related to Repeat Situations in Cycle Chemistry 2010 Paper Authored by Dr. Barry Dooley, Kevin Shields, Steve Shulder Structural Integrity Associates Inc.
9 Unintended Messages Is your cycle water instrumentation all in alarm on startup? Do you tell operators to ignore because it is due to CO2? What is the unintended message you send operators with this approach? Starting up unit more important than chemistry? Don t believe online instrumentation?
10 The Reality of Life One Ahh (bleep) wipes out all Atta boys This concept is AEP s attempt to eliminate the Ahh (bleep) that we have every 5 to 7 years. You will leave this years BRO Forum with the tools you need to use this concept.
11 Breakdown of Repeat Situations World Class Water Chemistry By Accident?
12 High Levels of Corrosion Product Corrosion product indicates a non optimized corrosion program. It can indicate flow accelerated corrosion is occurring. Very small increases in corrosion product transport can be significant Water chemistry influenced boiler tube failures start with tube deposition.
13 Where Do You Think All This Corrosion Product Went?
14 Severe FAC
15 High Levels of Corrosion Product (Subcritical/HRSG) Are you running Millipore's on your unit? Are your Millipore's snow white? Are you maintaining proper cycle ph per your unit specific chemical operating specification? Are your Dolan Lab feedwater total irons less than 5 ppb (dissolved iron <0.5 ppb) for subcritical/hrsg units? Are your Dolan Lab steam drum total iron less than 5 ppb (dissolved iron <0.5 ppb)? Are dissolved iron results samples at same conditions?
16 High Levels of Corrosion Product (Supercritical ) Are you running Millipore's on your deaerator inlet, deaerator outlet, economizer inlet, and hp heater drain? Are your Millipore's on your deaerator inlet, deaerator outlet, economizer inlet, and hp heater drain snow white? Are you maintaining proper cycle ph per your unit specific chemical operating specification? Are your Dolan Lab deaerator inlet, deaerator outlet, economizer inlet and hp heater drain sample total iron less then 3 ppb and/or dissolved iron less than 0.5 ppb? Are dissolved iron samples at same conditions?
17 High Boiler /HP Evaporator Deposition Is an indication of non optimized corrosion control of the condensate/feedwater cycle. For a subcritical unit is part of the mechanism for underdeposit corrosion tube failures (hydrogen damage, caustic gouging, acid phosphate attack)
18 >70 g/ft2 deposits
19 >100 g/ft2 deposits
20 High Boiler /HP Evaporator Deposition Are you experiencing phosphate hideout? Do you have piles of iron in your steam drum when you inspect steam drum? Are you experiencing any active underdeposit corrosion tube failures?
21 High Steam Generator Deposition Are chemical cleaning tube samples deposit thickness less then 40 micron (1.57 mils) Are prechemical cleaning samples taken from recommended locations per circular letter CH-O-Cl-010B Chemical Cleaning of Supercritical Units Is depoit thickness being used to determine need to chemical clean instead of deposit weight? Are you experiencing any supercritical waterwall cracking tube failures driven by ID deposits? Is dissolved oxygen detected at the hp heaters, economizer inlet cation conductivity below 0.15 mmhos, and the unit pressurized for a minimum of 2 hours before booster pump ph is allowed to be lowered during OT conversion during startup? Is booster pump specific conductivity increased and deaerator vents opened prior to removal of unit from service?
22 Non-Optimum Chemical Cleaning Chemical cleaning is the method used to remove deposition in our boilers and steam generators. This is a key tool in reducing the risk of underdeposit boiler tube failures on subcritical units AEP has recently had chemical cleans recently that have not removed all deposition.
23 Over 100 Waterwall Tube Leaks
24 Non-Optimum Chemical Cleaning Has it been more than 5 years for a subcritical or combined cycle unit since your last chemical cleaning? Are you using the proper chemical cleaning solvent for the deposits needing to be removed and the metallurgy of the unit? Are you maintaining proper temperatures during circulation? Are you ensuring proper circulation during chemical cleaning? Are you circulating chemicals for the required time?
25 Contaminant Ingress The introduction of sodium, chlorides and sulfates into the cycle from various sources, the most common being condenser leaks is also key in all water chemistry related boiler tube and turbine blade failures. These contaminants damage the protective passive layer and initiates damage mechanism.
26 SCC - Chlorides
28 Contaminant Ingress Subcritical/HRSG Are you experiencing hydrogen damage tube failures? Are you seeing turbine deposition due to chlorides, sodium, sulfate or silica during turbine outages? Are you exceeding action levels during contaminant ingress events? Are you operating with a condenser leak? Are you operating with attemperation sprays during condenser leaks? Do you track the amount of time core cycle chemistry parameters are within or outside of limits?
29 Contaminant Ingress - Supercritical Are you seeing turbine deposition due to chlorides, sodium, sulfate or silica during turbine outages? Are you exceeding action levels during contaminant ingress events? Are you operating with a condenser leak? At anytime including during resin transfer during regeneration, are you unable to maintain 100 % cleanup when operating with a condenser leak? Do you track the amount of time core cycle chemistry parameters are within or outside of limits?
30 Drum Carryover For subcritical & combined cycle units, drum carryover due to mechanical issues inside the steam drum or drum level control problems allows for chlorides, sulfates, and sodium to enter the steam circuits. These contaminants can initiate pitting and stress corrosion cracking (stainless material) in reheaters and superheaters. They can also initiate pitting of turbine blades that can lead to stress corrosion cracking and corrosion fatigue turbine blade failures
32 Drum Carryover Are you participating in the Dolan Lab Sampling Program? Do you know your % drum carryover? Do you have a sodium or cation conductivity spike on your saturated steam sample when you start your phosphate or caustic pump? Do you have phosphate or caustic on turbine when you perform inspection? Are you experiencing significant drum level swings during operation?
33 High Levels of Air in Leakage For subcritical units that have copper or copper alloy metallurgy in the condensate and feedwater cycle, the copper corrosion rate of this material is orders of magnitude higher when dissolved oxygen is present. Copper corrosion will redeposit in the boiler, superheat and more troubling on the HP turbine blades.
34 Copper Deposition on HP Turbine
35 High Levels of Air in Leakage Do you know what your air in leakage rate is? Are air in leakage tests performed? Does air in leakage change when equipment (FW heaters, condensate pumps, etc.) is placed into or removed from service?
36 Lack of Shutdown Protection All water chemistry related boiler tube and turbine blade failures start with the damaging of the protective passive layer. This layer needs to be protected 24/7 365 days/year when the unit is operating and also when the unit is out of service. If the protective layer is not damaged water chemistry related equipment failures will not occur. Failure mechanisms like pitting, stress corrosion cracking, and corrosion fatigue start with pits forming. These pits form when the unit is out of service. So if 99.99% of water chemistry related boiler tube and turbine blade issues are associate with condenser leaks, why do we not have a layup plan for the condenser?
37 Inadequate Shutdown Protection
38 Inadequate Shutdown Protection
39 Inadequate Shutdown Protection
40 Pitting and Stress Corrosion Cracking
42 Lack of Shutdown Protection Does a procedure exist that describes plant shutdown practices for layup protection of the unit? This includes condensate, feedwater, boiler, turbine, LP and HP drains. Is this procedure followed? Is dehumidification of the LP turbine being used on shutdown?
43 Inadequate On-Line and Alarmed Chemistry Instrumentation On-line instrumentation are our tools to inform operations that damaging conditions are present.
44 AEP Hydrogen Damage
45 Inadequate On-Line and Alarmed Chemistry Instrumentation Are required cycle chemistry instruments installed, trended and alarmed in control room? Do operators know how to respond to cycle chemistry alarms that initiate in control room? Are operators told to ignore certain alarms on startup? Is there a pm schedule to service and calibrate the instruments? Is the pm and calibration schedule being performed? Are operators decommissioning audible alarms because of unrealistic or unobtainable limits? Are cycle chemistry instruments removed from service because they are not working without another plan in place to monitor the parameter that is being compromised with the analyzer out of service?
46 Not Challenging the Status Quo One of the most damaging cultures to a water chemistry program is the that is the way we always have done it Or that plant is really screwed up that would never happen on my unit. Or repeat situations another Columbus boondoggle. They need to get a clue!!
47 If You Don t Look, This is What You Have
48 Not Challenging the Status Quo Subcritical/HRSG Will operators trip a unit on high steam sodium >24 ppb? Will operators trip unit on low boiler ph? Will operators remove subcritical from service when boiler water chlorides exceed 1000 ppb? Do we have a chemistry inspection plan during major outages to assess chemistry program success? Is the correct cycle chemistry being used? Do operators and/or chemists monitor unit chemistry and make changes prior to action levels Do chemist review and track Dolan Lab data? Are cycle samples taken and forwarded to Dolan Lab during upset conditions?
49 Not Challenging the Status Quo Supercritical Will operators trip a unit on high steam sodium >24 ppb? Will operators trip unit on low economizer inlet ph? Will operators remove unit from service when economizer inlet cation conductivity is 2 mmho for 5 minutes? Will operators remove unit from service when economizer inlet cation conductivity is 5 mmho for 2 minutes? Do we have a chemistry inspection plan during major outages to assess chemistry program success? Is the correct cycle chemistry being used? Do operators and/or chemists monitor unit chemistry and make changes prior to action levels Do chemist review and track Dolan Lab data? Are cycle samples taken and forwarded to Dolan Lab during upset conditions? Does the plant have a forum for communication with operators, maintenance, and performance on chemistry issues?
50 No Action Plan For the Above Repeat Situations Each repeat situation needs a tracking mechanism and action plan developed to remedy repeat situation. Are you operating with more than three repeat situations at the same time?
51 How Does Concept Work A 4 hour presentation is given to plant to introduce this concept. It is up to the plant to decide who attends this presentation, but it is recommended that it be a cross section of leadership, maintenance, operators and technicians (very similar to the BRO Team concept) After presentation, the lab team breaks away with the regional or central engineer and completes the repeat situation assessment.
52 How Does Concept Work There are two parts to the concept: Repeat Situation Assessment Daily Repeat Situation
53 Repeat Situation Assessment There are approximately 47 questions on the subcritical repeat situation checklist. There are approximately 43 questions on the supercritical repeat situation checklist. The assessment is completed by the lab (with help from central or regional engineering if required.)
54 Hoe Does Concept Work After assessment is complete and the ongoing repeat situations determined, the lab team presents the findings to the group that underwent the training. The group then votes on the on going repeat situations (similar to Lean) to determine which repeat situations will be addressed first. Team leads are assigned
55 How Does the Concept Work The daily repeat situations are the repeat situations that can change day to day. For instance you may not have a condenser leak today but you may have one tomorrow. When the leak occurs a repeat situation occurs Contaminant Ingress The lab team should be keeping track of the daily repeat situations. The goal is to keep from having three or more of the daily repeat situations occurring at the same time.
56 Daily Repeat Situations Are your Millipore's showing any color on your deaerator inlet, deaerator outlet, economizer inlet, or hp heater drain? Is cycle water ph operating outside required limits as defined in unit specific chemical operating specification? Are Dolan Lab deaerator inlet, deaerator outlet, economizer inlet and hp heater drains total iron (hot acid digestion) greater than 3 ppb and/or dissolved iron (acid soluble) greater than 0.5 ppb? Are chemical cleaning tube samples deposit thickness greater than 40 microns (1.57 mils)? Is conversion to OT on startup not following these minimum requirements: 1.) dissolved oxygen detected at the hp heaters prior to lowering cycle ph, 2.) economizer inlet cation conductivity below 0.15 mmho prior to closing deaerator vent. 3.) The unit pressurized for a minimum of 2 hours prior to closing deaerator vent?
57 Daily Repeat Situations Has it been more than 15 years since the unit has been chemical cleaned? Are you exceeding action levels during contaminate ingress events? Are you operating with a condenser tube leak? At any time including during resin transfer during regeneration, are you unable to maintain 100 % cleanup when operating with a condenser leak? Is layup shutdown procedure not being followed? Is dehumidification of the LP turbine not being used on shutdown? Is the pm and calibration schedule not being performed?
58 Daily Repeat Situations Are cycle chemistry instruments removed from service because they are not working without another plan in place to monitor the parameter that is being compromised with the analyzer out of service? Are there any standing cycle chemistry alarms in control room? Are you operating with more than three daily repeat situations at the same time?
CYCLE CHEMISTRY COMMISSIONING Otakar Jonas, P.E., Ph.D. Lee Machemer, P.E. Jonas, Inc. 1113 Faun Road Wilmington, DE 19803 USA Abstract This paper presents an outline of cycle chemistry commissioning guidelines
The following article was published in ASHRAE Journal, December 2002. Copyright 2002 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. It is presented for educational purposes
Steam Turbine Operating Conditions, Chemistry of Condensates, and Environment Assisted Cracking A Critical Review Shengqi Zhou and Alan Turnbull May 2002 Date: May 2002 Steam Turbine Operating Conditions,
Essentials for a Sound Boiler Water Treatment Program Presented by Steve Connor & Debbie Bloom April 23, 2014 Today s Topics Chemical Aspects The Necessity of Water Treatment Mechanical Aspects Essentials
Application Data Sheet ADS 4900-87/rev.B January 2009 Power Industry Inferred ph in Steam Plant Water Chemistry Monitoring INTRODUCTION Inferred ph means ph calculated from straight and cation conductivity.
A DB RILEY TECHNICAL PUBLICATION CURRENT EXPERIENCE IN TYPICAL PROBLEMS AND FAILURES WITH BOILER PIPING COMPONENTS AND SUPPORTS by James P. King, Design Manager DB Riley, Inc. Presented at the 1998 ASME
BOILER WATER TREATMENT AND RELATED COSTS OF BOILER OPERATION: AN EVALUATION OF BOILERS IN THE LOUISIANA SUGAR INDUSTRY James A. Cuddihy, Jr., Walter J. Simoneaux, Robert N. Falgout, and James S. Rauh Midland
BOILER WATER TREATMENT FOR KILN DRY OPERATIONS Technical Presentation IMPORTANT TOPICS PRETREATMENT TEMPERATURE VS OXYGEN FEED WATER / DA BOILER WATER CONDENSATE 1 Boiler Water Pretreatment Purpose - Statistically
High-Pressure Steam Cycle and Boiler Water Treatment High Pressure Boilers Pressure range 60-84 bar Critical needs High quality makeup water External pre-treatment through distillation and mechanical deaeration
Case History Report The Dolphin Nonchemical Device Boilers and Cooling Tower Device Evaluated "The Dolphin HYTRONIC Series 1000" pulsed power water treatment device (Dolphin) manufactured by Clearwater
OPERATING EXPERIENCE OF LARGE REHEAT HRSGs in MERCHANT SERVICE Peter S. Jackson, PE David S. Moelling, PE Frederick C. Anderson, PE James W. Malloy TETRA ENGINEERING GROUP TETRA ENGINEERING GROUP TETRA
BASIC WATER TREATMENT OF STEAM BOILERS Steve Kenny and Dave Pope Chemco Water Technology Vancouver, WA This is a brief discussion on low-pressure steam boiler chemistry. It provides dry kiln boiler operators
Keeping corrosion at bay Analysis in ultra-supercritical power plants Corrosion is the natural enemy of steam-electric power plants, eating away at pipes, turbine blades, and rotors. The lack of a separation
IMPLEMENTATION OF BOILER BEST PRACTICES Natalie R. Blake Market Development Manager Nalco Chemical Company Naperville, IL ABSTRACT Boilers are an essential part of any industrial plant, and their efficient,
AMERICAN FOREST & PAPER ASSOCIATION AMERICAN FOREST & PAPER ASSOCIATION OPERATIONS & MAINTENANCE SUBCOMMITTEE RECOVERY BOILER SAFETY AUDIT GUIDELINES March 1990 Revised July 2004 Revised May 2012 893 McLean
Best Practices: The Engineering Approach for Industrial Boilers Natalie R. Blake, ONDEO Nalco ABSTRACT A plant s boilers represent a large capital investment, as well as a crucial portion of overall plant
P R E P R I N T ICPWS XV Berlin, September 8 11, 2008 The control of corrosive conditions caused by concentration of low-volatility solutes in boilers and steam generators Geoffrey J Bignold GJB Chemistry
Technical Paper Boiler Chemistry Management Using Coordinated Approach of Chemicals, Membranes and Online Monitoring Authors: Rajendra Prasad Kalakodimi, Lead Technologist, and Mel J. Esmacher, Engineering
Global Journal of Petroleum and Chemical Engineering ISSN: XXXX-XXXX Vol. 2 (1), pp. 1-1, January, 214. Global Science Research Journals Full Length Research Paper Corrosion-erosion on waste heat recovery
Boiler Preparation, Start-Up and Shutdown Learning Outcome When you complete this module you will be able to: Describe the basic preparation of a boiler for start-up, and the start-up and shutdown procedures.
Routine and Emergency Boiler Operation Learning Outcome When you complete this module you will be able to: Describe the routine safe and efficient operation of a packaged boiler. Learning Objectives Here
Recovery Boiler Research Needs An Industry Perspective Andrew Jones International Paper 7th International Colloquium on Black Liquor Combustion and Gasification International Paper Recovery Operation Goals
Sample Questions REVISED FIRST CLASS PARTS A1, A2, AND A3 (NOTE: these questions are intended as representations of the style of questions that may appear on examinations. They are not intended as study
TheNationalBoardofBoilerandPressureVesselInspectors 1055CrupperAvenue Columbus,Ohio43229 614.888.8320 NB-410, Revision 3 Sept, 2015 1 1.0 GENERAL The purpose of this document is to provide basic guidelines
Standard Recommendations for Pressure Part Inspection During a Boiler Life Extension Program M.N. Hovinga G.J. Nakoneczny Babcock & Wilcox Barberton, Ohio, U.S.A. Presented to: ICOLM (International Conference
SUGAR MILL BOILER CYCLE CHEMISTRY: AN UPDATE ON BEST PRACTICES By DAVID RODMAN Nalco Australia Pty Ltd, Townsville KEYWORDS: Sugar, Boiler, Water Chemistry, Deposit, Water Treatment. Abstract SUGAR mill
THE NEED FOR CONTROL Vecom Marine clean ships - clean seas BOILER WATER TREATMENT Whether distilled or raw (city) water is used for boiler make-up, chemical treatment is necessary to counteract harmful
HIGH PRESSURE FEEDWATER HEATER REPAIR B. W. Helton II Tennessee Valley Authority 1101 Market Street Chattanooga, Tennessee 37402 Peter Tallman CTI Industries Inc. 200 Benton Street Stratford, Connecticut
Operational Flexibility Enhancements of Combined Cycle Power Plants Dr. Norbert Henkel, Erich Schmid and Edwin Gobrecht Siemens AG, Energy Sector Germany POWER-GEN Asia 2008 Kuala Lumpur, Malaysia October
WATER WALL BOILER FOR AIR AND OXYGEN FIRED CLAUS SULPHUR RECOVERY UNITS Abstract Mahin RAMESHNI, P.E. Technical Director, Sulphur Technology Mahin.Rameshni@worleyparsons.com WorleyParsons 125 West Huntington
General Electric Systems Technology Manual Chapter 2.8 Reactor Water Cleanup System TABLE OF CONTENTS 2.8 REACTOR CLEANUP SYSTEM... 1 2.8.1 Introduction... 2 2.8.2 System Description... 2 2.8.3 Component
s/objectives Level F ADMN 6044: Post Job Management It is important to know the proper procedures for closing out a job so that rigging and equipment is maintained for future use and personnel are adequately
Page 1 Water Treatment, Cycle Chemistry, Boiler Operation and Related Problems/Failures on Steam Generator Systems > 30 bar By Mr. Ludwig Hoehenberger, TÜV SÜD, Munich,. Phone: +49 89 5791 1063; Telefax:
Portable leak detection instrument improves heat rate at electric power plant. By Terrence O'Hanlon, CMRP Reliabilityweb.com By using a ruggedized portable ultrasonic leak detector, Mr. Brian Thorp, PdM
PRODUCT NAME NALCO BT-25 Boiler Internal Treatment PRODUCT DESCRIPTION AND APPLICATION NALCO BT-25 is an innovative program that combines the use of polyphosphate and the most advanced synthetic organic
Common Problems with Online Water Quality Analyzers Greg Macy Director AquatiPro LLC Objectives Diagnosing Colorimetric Analyzers Identifying Common Problems with Sodium Analyzers Troubleshooting ph Analyzers
Troubleshooting: Condensate Contamination By James McDonald, PE, CWT Originally Published: Ultrapure Water, July/August 2003, Volume 20, Number 6 In a well maintained, properly operating boiler system,
Hartford Steam Boiler One State Street P.O. Box 5024 Hartford, CT 06102-5024 Tel: (800) 472-1866 www.hsb.com July 2014 Safety should only be inspected, tested and maintained by qualified trained personnel.
BOILER FEED AND CONDENSATE RECOVERY SYSTEMS Extend the life and efficiency of your boiler system INTEGRATE BOILER FEED AND RECOVERY TO GET THE MOST FROM YOUR BOILER SYSTEM. Increase the safety, reliability,
Technical Topic Technical Training Guide Turbine Oil Condition Monitoring Introduction Modern steam and gas turbines subject the turbine lubricant to ever greater demands. Higher temperatures are encountered
The International Association for the Properties of Water and Steam London, United Kingdom September 2013 Technical Guidance Document: Corrosion Product Sampling and Analysis for Fossil and Combined Cycle
CHALLENGES IN A DILUTION STEAM GENERATOR SYSTEM Lee Siang Hua Titan Petrochemicals (M) Sdn Bhd Cheah Phaik Sim Titan Petrochemicals (M) sdn Bhd firstname.lastname@example.org Karl Kolmetz Westlake Group, Lake Charles,
Technical Paper Effective Deoxygenation by a Hybrid Process Combining Gas Transfer Membranes with Catalytic Oxygen Reduction Authors: S. B. Gorry, GE, W. E. Haas, GE and J. W. Mahaffee, Baltimore Gas &
Increasing Natural Gas Boiler Efficiency by Capturing Waste Energy from Flue Gas Mark Schiffhauer, ATSI Engineering Services Cameron Veitch, Combustion and Energy Systems Scott Larsen, New York State Energy
CONTAMINANT REMOVAL FROM CENTRIFUGAL SYSTEMS BULLETIN 240-10-3 June 2004 Supersedes June 1983 Many centrifugal systems get little maintenance. As a result they operate with the refrigerant highly contaminated
Newsletter: Summer 2005 G.L.A. WATER, INC. Boiler Lay-up Procedures There are many reasons for laying up a boiler (i.e., placing it out of service.) A primary influence revolves around the actual demand
If you would like a more detailed version of this report, please request SOS from email@example.com along with your e-mail address. A. Introduction Sulfites for Oxygen Control Robert R. Cavano
Current state of plant Functioning as a peak and emergency centre Statistics Accumulated operating hours: D1-2-3-6-7: 43000 to 48000 hrs D4-5: 53000 to 57000 hrs D8: 33000 hrs Layout of the plant Index:
A Guide to Trouble-Free Cooling Towers A basic understanding of cooling tower operation and maintenance will help keep a cooling water system running in top condition, year after year By David M. Suptic
Committed to make a better world 1. Higher Availability & Reliability 2. Highest Plant efficiency 3. Lower Heat Rate 4. Minimum Auxiliary Power Consumption 5. Minimum Emission of Pollutants Committed to
Technical Service Bulletin July 2009 TSB102.06 RO Membrane Foulants and Their Removal from Polyvinyl Derivative (PVD) RO Membrane Elements This bulletin provides general information about the usual foulants
Tube Damage Mechanism and Analysis in Feed Water Heaters Asst. prof. Dr. Rafaa Abbas Al-Baldawi College of Engineering Al-Mustansirya University firstname.lastname@example.org Dr. Mohammed Najm Abdullah College of
Corrosion can be defined as the destructive attack of a metal by an electrochemical reaction with its environment. Steel exposed to moisture and oxygen will rust and corrode. Corrosion is defined as the
ABC CIRCUITS 10 Circuit Drive Circuit Town, IN 12345 SLUG CONTROL PLAN The purpose of this plan is to provide detailed instructions for slug prevention and control. A complete copy of this plan is maintained
Factory owners must ensure the boiler is: * Registered with the Boilers and Pressure Vessels Division, Labour Department * Examined by an appointed examiner and has a valid certificate of fitness * Supervised
7.0 Chemical Treatment 7.1 OVERVIEW This section deals with specific chemical treatments. Type, purpose, and application are all discussed. The treatments are divided along the lines of preboiler and condensate
9707 Key West Avenue, Suite 100 Rockville, MD 20850 Phone: 301-740-1421 Fax: 301-990-9771 E-Mail: email@example.com Part of the recertification process is to obtain Continuing Education Units (CEUs). One way
Chapter 2.2: Boilers Part I: Objective type Questions and Answers 1. The minimum capacity of any closed vessel which generates steam under Indian Boilers Regulation Act is. a) 2.275 liters b) 22.75 kilo
The Current State of Boiler Tube Failures in Fossil Plants Barry Dooley Peter S. Chang The Current State of Boiler Tube Failures in Fossil Plants INTRODUCTION At the last international boiler tube failure
ISRAEL ELECTRIC OROT RABIN POWER STATION UNITS 1-4 4 x 350 MW COAL BOILER CONVERSION TO LOW NO X NATURAL GAS AND COAL FIRING BY PRIMARY AND SECONDARY MEASURES INSTALLATION Replacing the Burner Management
I. STEAM GENERATION, BOILER TYPES and BOILER PLANT SYSTEMS 1 Steam Generation Water s Unique Properties: High Thermal Capacity (Specific Heat) High Critical Temperature Ideal Medium for Heat Delivery High
VACUUM REFRIGERATION SYSTEMS CHILL VACTOR The Croll-Reynolds CHILL-VACTOR is a chiller that uses a vapor flashing process. Water has a pressure-temperature relationship which is its boiling point. If its
Defining Quality. Building Comfort. Heating and Cooling Coils Heating and Cooling Coils Heating and Cooling Coils For over 20 years, AAON has supplied the coil needs of industrial and commercial HVAC customers.
Energy Efficient Operations and Maintenance Strategies for Boilers Large, complex and widely used, industrial boilers are major consumers of fuel. Proper operations and maintenance (O&M) procedures must
1 Index 1. Inspection and monitoring... 3 1.1 Handling of new elements... 3 1.1.1 Storage of original packaged RO elements... 3 1.1.2 Packing... 3 1.2 Initial start- up checks of a plant... 3 1.2.1 Preparation
Drying of Woody Biomass BioPro Expo & Marketplace / Atlanta, GA / March 14-16, 2011 Drying of Woody Biomass Conventional Direct Fired Dryer Technology Proprietary work of the Copyright Owner Issues with
12 Ways To Avoid Boiler Tube Corrosion By: H. F. Hinst Plant Metallurgist Tubular Products Division, Keystone Plant The Babcock & Wilcox Company Corrosion troubles in low pressure heating boilers -- which
HRSG - Heat Recovery Steam Generators Excellence in the making From the beginning, the goals of Victory Energy Operations, LLC have been to be a single-source solutions provider backed by worldclass service.
D a v i d E. H e n d r i x, P. E. RESUME 15823 N. Barkers Landing Houston, TX 77079 281/556 8774 firstname.lastname@example.org www.hghouston.com Experience: 2013 1990 President, The Hendrix Group Inc., A
PACIA Carbon Solutions Forum 3-29 September 20 Boiler and Steam Efficiency What does it mean? Andrew Hook - Area Manager, Nalco 1 Purpose, Process, Payoff Purpose: To explain boiler and steam efficiencies
www.alltemp.ca Introducing an All New Line of Cleaning Chemicals Coil Cleaners & Brighteners Metal Cleaning Detergents Ice Machine Cleaners Scale Removers Electronic Cell Cleaner Degreasing Solvent Leak
Reuse of Alternative Water Sources for Cooling Tower Systems Two Case Studies Using Non-Traditional Water Sources Matthew L. Haikalis Veolia Water Solutions & Technologies April 24, 2013 Operational Priorities
1/20/14 2014 Service Technician Training Program Closed Loop Systems Daniel S. Krack, CWT 2 Closed Loop Cooling and Heating The Closed Loop Cooling Advantages High Efficiency Chillers, Heat Exchangers,
Page 1 of 76 1.0 PURPOSE The purpose of the Wastewater Treatment System is to remove contaminates from plant wastewater so that it may be sent to the Final Plant Effluent Tank and eventually discharged
Steam End User Training Steam Generation Efficiency Module Blowdown Losses Section Slide 1 Blowdown Losses Module This section will discuss blowdown loss and its affect on boiler efficiency. [Slide Visual
Tankless Water Heater USER S INFORMATION MANUAL Models WGRTNG199 / WGRTLP199 WGRTCNG199 / WGRTCLP199 NOTICE: Westinghouse reserves the right to make product changes or updates without notice and will not
The Single Absorption Scrubbing Sulfuric Acid Process Leonard J. Friedman, Samantha J. Friedman Acid Engineering & Consulting, Inc. 17770 Deauville Lane, 33496, USA LJ.Friedman@Acideng.com Keywords: Sulfuric
Helsinki University of Technology Department of Mechanical Engineering Energy Engineering and Environmental Protection Publications Steam Boiler Technology ebook Espoo 2002 Boiler Calculations Sebastian
Technical Paper Industrial Water Reuse and Wastewater Minimization Author: James P. McIntyre, P.E. Abstract Many industrial users of fresh water are under increasing pressure to reuse water within their
IGEMA BOILER LEVEL & TDS CONTROLS IGEMA offers boiler level and TDS control products of the highest quality standard, being certified to ISO 9001. Made in Germany, IGEMA products are manufactured in compliance
The Relationship between ph and Deionized Water The basics of ph The topic of ph and water has been well documented over the years; however, there is still much confusion about its significance in high
Water Efficiency Water Management Options Boilers for Commercial, Industrial and Institutional Facilities Boiler Water Impurities All boiler make-up water contains impurities. As clean steam is released