# WTW SWANTM. Linear slot air diffusers of wall-to-wall design for ceilings

Save this PDF as:

Size: px
Start display at page:

Download "WTW SWANTM. Linear slot air diffusers of wall-to-wall design for ceilings"

## Transcription

1 SWANTM WTW Linear slot air diffusers of wall-to-wall design for ceilings Quick facts Wall-to-wall installation Diffuser face of light aluminium design 2, 3 or slots Horizontal/vertical air distribution Telescopic installation White-painted or natural anodized diffuser parts Black air deflectors made of ABS plastic Corner module, 90 Removable damper Quick selection A I R F L O W - S O U N D L E V E L Size 2 db(a) db(a) 3 db(a) Data specified in the table includes the SWAN T commissioning box and is applicable to 0 Pa total pressure. 1

3 x/2 x/ x/2 x/ x=97 x=97 Figure 1. Installation in blind rivet sockets. x/2 x/ x/2 x/ x=97 x=97 Figure 2. Installation in angle brackets. Wall-to-wall calculation before placing an order Example: Installation of m long linear slot diffusers which of three are active. Calculate the number of complete modules (118 mm). Recal culate m to millimetres and divide by the module length: x00/118 = = Check that the length of the SWAN END air diffusers will be sufficient, i.e. between 79 and 117 mm: 118 x = 736 mm 736 mm is left over, which is not enough for two SWAN END air diffusers. Recalculate: Add a whole module, which gives = 189 mm (= 2 x 97). Two end air diffusers, each 97 mm long. Seven 118 modules to be distributed as active SWAN ACT and passive SWAN PASS linear slot air diffusers. Order: Four SWAN PASS, length: 118 mm. Three are SWAN ACT, length: 118 mm. Three SWAN Ta commissioning boxes for active diffusers. Two SWAN END passive end modules, length: 97 mm (includes an end-piece, 16 mm). Calculation check: (7x118)+(97x2) = 000 mm Figure 3. Measurement tappings for commissioning. Swegon reserves the right to alter specifications

4 Figure a. Installing of the air deflectors. Figure b. Dismantle of the air deflectors. Figure a. 1-way air discharge. Figure b. 2-way air discharge. Figure c. Vertical air discharge. Figure d. Extract air. Swegon reserves the right to alter specifications. 18

5 Installation example: According to Figures 6a-6d 1. Measure the location of the commissioning boxes and the slot diffusers. 2. Start by mounting the commissioning boxes (the products are supplied without mounting accessories). 3. Then install the first slot diffuser, which is a SWAN END. (end- piece in the left end and jointing piece in the right end) Figure 6a. WTW installation, Step 1-3. Swegon reserves the right to alter specifications. 18

6 &. Remove the outer air deflectors from the next diffuser (which is an active slot diffuser) to enable you to access and tighten the locking screw against the jointing pieces. 6. Install the SWAN ACT active slot diffuser against the SWAN END s jointing piece and secure the diffuser against the commissioning box with screws. Figure 6b. WTW installation, Step Swegon reserves the right to alter specifications. 18

7 7. Adjust the slot diffuser ends against each other in order to obtain a good joint between the diffusers and lock the jointing pieces with a hexagon spanner (size: 2 mm). 8. Refit the air deflectors into the SWAN ACT slot diffuser and remove the outer air deflectors on the next slot diffuser, in this case: a SWAN PASS which will be located between two commissioning boxes. Figure 6c. WTW installation, Step 7 and 8. Swegon reserves the right to alter specifications

8 9 &. Install the SWAN PASS slot diffuser against the preceding slot diffuser and lock the jointing pieces as shown in Item Refit the air deflectors in the SWAN PASS slot diffuser. Then continue the installation with the next active slot diffuser, in the same way as in Steps -8. The last slot diffuser is a SWAN END which in this case should be installed against the other active slot diffuser. It might be necessary to remove the jointing pieces from this last SWAN END slot diffuser. Figure 6d. WTW installation, Step Swegon reserves the right to alter specifications. 18

9 Sizing The sound levels, db(a), are applicable to rooms with db room attenuation. The throw l 0.2 is measured under isothermal discharge conditions. The recommended max. permitted temperature below room temperature is 8 K. To calculate the air stream diffusion, air velocities in the occupied zone or sound levels in rooms with other dimensions, please refer to our ProAir web computer program at N.B.! Technical data applies for SWAN ACT active diffusers and are the same as for standard mm (118 mm + end-pieces). Acoustic data SWAN ACT + SWAN T Supply air 1-way and 2-way air discharge Sound power level L w (db) Table K ok Size Mid-frequency (Octave band) Hz SWAN ACT Tol. ± Sound attenuation DL (db), without sound absorber in the SWAN T Table DL, 1-way, 2-way and vertical Size Mid-frequency (Octave band) Hz SWAN ACT Tol. ± SWAN ACT + SWAN T Supply air Vertical air discharge Sound power level L w (db) Table K ok Size Mid-frequency (Octave band) Hz SWAN ACT Tol. ± Sound Attenuation DL (db), with sound absorber in the SWAN T Table DL, 1-way, 2-way and vertical Size Mid-frequency (Octave band) Hz SWAN ACT Tol. ± Swegon reserves the right to alter specifications

10 SWAN ACT + SWAN T Extract air Sound power level L w (db) Table K ok Size Mid-frequency (Octave band) Hz SWAN ACT Tol. ± Sound attenuation DL (db), without sound absorber in the SWAN T Table DL Size Mid-frequency (Octave band) Hz SWAN ACT Tol. ± Sound attenuation DL (db), with sound absorber in the SWAN T Table DL Size Mid-frequency (Octave band) Hz SWAN ACT Tol. ± Swegon reserves the right to alter specifications. 18

11 Sizing diagram SWAN ACT Supply air Airflow - Pressure drop - Sound level Throw The diagrams illustrate data for a SWAN ACT recessed in a ceiling. The diagrams should not be used for commissioning. The db(a) values are for rooms with normal acoustic absorption ( db room attenuation). The db(c) value is normally 6-9 db higher than the db(a) value. = Min. airflow required for obtaining sufficient commissioning pressure. SWAN ACT Supply air, 1-way and 2-way SWAN ACT SWAN T SWAN ACT SWAN T l/s m 3 /h 0 0 l/s m 3 /h 3 3 SWAN ACT SWAN T l/s m 3 /h Swegon reserves the right to alter specifications

12 SWAN ACT SWAN T SWAN ACT SWAN T l/s m 3 /h 0 0 l/s m 3 /h 3 3 SWAN ACT SWAN T 3-20 SWAN ACT SWAN T l/s 0 0 l/s m 3 /h m 3 /h SWAN ACT SWAN T -0 SWAN ACT SWAN T l/s l/s m 3 /h m 3 /h Swegon reserves the right to alter specifications. 18

13 SWAN ACT Supply air, vertical air discharge SWAN ACT SWAN T SWAN ACT SWAN T l/s m 3 /h 0 0 l/s m 3 /h SWAN ACT SWAN T 2-20 SWAN ACT SWAN T l/s m 3 /h 0 0 l/s m 3 /h l 0,2 m SWAN ACT SWAN T 3-0 SWAN ACT SWAN T l/s m 3 /h l/s m 3 /h Swegon reserves the right to alter specifications

14 SWAN ACT SWAN T -160 SWAN ACT SWAN T l/s l/s m 3 /h m 3 /h 0, l 0,2 m SWAN ACT SWAN T l/s m 3 /h 0, l 0,2 m 1 Swegon reserves the right to alter specifications. 18

15 Sizing diagram SWAN ACT Extract air Airflow - Pressure drop - Sound level The diagrams illustrate data for a SWAN ACT for flush installation. The diagrams should not be used for commissioning. The db(a) values are for rooms with normal acoustic absorption ( db room attenuation). The db(c) value is normally 6-9 db higher than the db(a) value. = Min. airflow required for obtaining sufficient commissioning pressure. SWAN ACT SWAN T SWAN ACT SWAN T l/s m 3 /h 0 0 l/s m 3 /h SWAN ACT SWAN T l/s m 3 /h Swegon reserves the right to alter specifications

16 SWAN ACT SWAN T SWAN ACT SWAN T l/s l/s m 3 /h m 3 /h SWAN ACT SWAN T 3-20 SWAN ACT SWAN T l/s m 3 /h 0 0 l/s m 3 /h SWAN ACT SWAN T -0 SWAN ACT SWAN T l/s m 3 /h l/s m 3 /h 16 Swegon reserves the right to alter specifications. 18

17 Dimensions and weights - Dimensions (mm) Size A A1 B B1 ØD H (H+2) J K L Holemaking size: length = X -32 mm. Width = B -12 mm. 1 2 Figure 7. SWAN ACT with SWAN T. 3 A1 A1 B1 B 90 B Figure 8., overview in a room Figure 9., parts included: 1) SWAN ACT 2) SWAN PASS 3) SWAN END ) SWAN CORN90 (accessory) Swegon reserves the right to alter specifications

18 SWAN T Location, duct connection (mm) SWAN T P R S Ø160 mm Ø0 mm Ø20 mm Weight, parts included (kg) Size SWAN ACT SWAN PASS SWAN END *) SWAN T ,6 2,8 1, - 2, ,6 2,8 1, - 2, ,6 2,8 1, - 2, ,6,0 2,0 -, ,6,0 2,0 -, ,6,0 2,0 -, ,6,3 2,7 -, ,6,3 2,7 -, ,6,3 2,7 -,3 7.7 *) SWAN END, min. weight for A=79 and max. weight for A=118 Z1 Z2 Figure 8. with SWAN T commissioning box. Z1 = False ceilings, Z2 = Plasterboard ceilings. 18 Swegon reserves the right to alter specifications. 18

19 Ordering key Product Active linear slot air diffuser SWAN a ACT -b d Version ACT = Active air diffuser installed with SWAN T commissioning box Number of slots: 2, 3, Length: 118 mm standard Version: W = white A = natural anodized Note in plain text whether the active slot diffuser should have an end-piece. Passive linear slot air diffuser SWAN a PASS -b d Version Passive air diffuser with cover plate Number of slots: 2, 3, Length: 118 mm standard Version: W = white A = natural anodized End linear slot air diffuser SWAN a END -b -cccc -d Version End, passive air diffuser with cover plate and one end-piece Number of slots: 2, 3, Length: 79-1,17 mm Version: W = white A = natural anodized Specification text Swegon s type linear slot diffuser for wallto-wall installation with commissioning boxes for active linear slot diffusers and in between them passive linear slot diffusers with the following features: Individually adjustable air deflectors made of ABS plastic. Natural anodized or white powder paint sprayed and baked white finish, RAL 9003/NCS S 000-N Cleanable commissioning box with removable commissioning damper with lockable flow adjustment cords, measuring method with low systematic error. Size SWAN a ACT W xx items SWAN a PASS W xx items SWAN a END 3-60-W xx items SWAN Ta 3-0 xx items SWAN a CORN90 3-W xx items Accessories *) Commissioning box, standard for active slot air diffusers SWAN T a -a -bbb Version Number of slots: 2, 3, (118 mm length) Connecting duct dimension Ø: 160, 0, 20 Without sound absorber in the standard version. With sound absorber; please specify this in plain text in the order. Corner module SWAN a CORN90 -b -c Version Corner module, 90, passive section with cover plate Number of slots: 2, 3, Version: W = white A = natural anodized *) The products are supplied without mounting accessories. Mounting strips, hanger brackets/rods, ceiling mounting brackets etc. can be purchased from local suppliers. Standard product range For the SWAN WTW W SWAN T W SWAN T W SWAN T Swegon reserves the right to alter specifications

### CONDOR. Supply air ceiling. Quick guide A I R F L O W - S O U N D L E V E L. Va r iz o n

Supply air ceiling General is a supply air ceiling system with adjustable discs. The spread pattern is infinitely flexible and can be adjusted as required without affecting the airflow, pressure drop or

### CGV/RGV. Sound attenuating transfer units QUICK FACTS

Sound attenuating transfer units QUICK FACTS For transfer air through walls Flow range < 80 l/s Circular or rectangular hole in wall Simple installation Available in alternative colours on special order

### Swirl diffuser VSKA. Product facts. Quick selection. Swirl diffuser VSKA. Connection box ATTB. Product code example:

VSKA are supply air diffusers designed for ceiling mounting. The design of the air deflectors and discharge outlets causes the air discharged by the diffuser to mix with the air in the premises (high induction

### CRM. Controllable measurement unit, Ductwork Leakage Class 0 or 4 QUICK FACTS

Controllable measurement unit, Ductwork Leakage Class 0 or 4 QUICK FACTS Type-approved method of measurement Pressure class A Ductwork leakage class 0 or 4 Leakage factor for housing according to tightness

### Supply air diffuser ROKA/RPKA

Supply air diffuser ROKA/RPKA The ROKA and RPKA are supply air diffusers designed for ceiling mounting. Diffuser ROKA has an unperforated diffuser plate and RPKA has a perforated diffuser plate. The diffusers

### CALMO. Sound attenuator with recessed connection for rectangular ducts QUICK FACTS

Sound attenuator with recessed connection for rectangular ducts QUICK FACTS Remarkably space-saving rectangular sound attenuator Excellent aerodynamic characteristics Extremely low pressure drop via tapered

### CONTROL/SLAVE Zone. Zone damper for Swegon s WISE System for demand-controlled ventilation

CONTROL/SLAVE Zone Zone damper for Swegon s WISE System for demand-controlled ventilation Quick facts Pressure regulation from -300 Pa Flow measurement or flow regulation Optimisation of supply- and extract

### CLA. Compact sound attenuator for circular ducts QUICK FACTS

Compact sound attenuator for circular ducts QUICK FACTS Extremely low installation height. Excellent sound attenuation Mineral wool covered with special polyester woven fabric. Tightness Class D Low pressure

### TSA - Swirl Diffuser. Halton TSA. Swirl Diffuser

Halton TSA Swirl Diffuser Horizontal radial or alternatively vertical compact swirl jet air supply, also suitable for heating applications Also well suited to large and high spaces Supply air pattern can

### HDA -----------------------------------------------------------

----------------------------------------------------------- Lightstrips ---------------------------------------------------------------------- Ceiling system for heating and cooling LIGHTSTRIPS LIGHTSTRIPS

### Laminar Flow Panel. Type LFP 2/2.4/B/2. Telephone +44(0) 1842 754545 Telefax +44(0) 1842 763051 e-mail trox@troxuk.co.uk www.troxuk.co.

2/2./B/2 Laminar Flow Panel Type LFP TROX UK Ltd Caxton Way Thetford Norfolk IP2 3SQ Telephone +(0) 182 7555 Telefax +(0) 182 763051 e-mail trox@troxuk.co.uk www.troxuk.co.uk Contents Description Description

### Grilles & Diffusers Series LFP Incorporating

Grilles & Diffusers Incorporating Series LFP Produce a stable linear throw, creating an area of clean air with minimal diffusion Perfect for areas like clean rooms and operating theatres Tile replacer

### INDEX. Chapter8. air master. Perforated Ceiling Diffusers

Chapter8 INDEX A. Perforated ceiling diffuser 1. Perforated ceiling diffuser with plenum box..: APCD+P...8.1. Perforated ceiling diffuser with damper....: APCD...8. Standard sizes...8. Fixing details...8.

### Under sill units. Type FSL-B-ZAS

.1 X X testregistrierung Under sill units Type, heat recovery Centrifugal fan Adaptive heat recovery damper HYGIENISCH GETESTET V DI 022 Tested to VDI 022 Secondary air unit for supply air and extract

### H45 LED - Direct and indirect pendant

RAL 01 10 00 IP 20 230V 50/60Hz Specifications Direct and indirect light pendant linear luminaire. Aluminium profile. Diffusers in frosted polycarbonate profile. Driver included. Supplied with clear base,

### High Static Pressure Ductable Fan Coil Unit Models 07 to 27

VH High Static Pressure Ductable Fan Coil Unit Models 07 to 27 5.3 to 26.9kW 4.1 to 22.6kW 800 to 4650 m 3 /h VH 1 General Characteristics Presentation The new ducted high static pressure fan coil units

### Incorporating V2.3. Product spec >>> > Series ECG - Egg Crate Grilles. > Series ECG45-45 Egg Crate Grilles

Incorporating V2.3 Product spec >>> > Series ECG - Egg Crate Grilles > Series ECG45-45 Egg Crate Grilles Grilles Egg crate Recommended for: Wall, ceiling & duct Extract Overview Industry standard extract

### Ecophon Focus Ds. System range. XL 1800x600. Size, mm. XL 2400x600 T24 Thickness (THK) XL 2000x600. 1200x600 1200x1200 1600x600 M206, M208, M238

Ecophon Focus Ds For applications where a suspended ceiling with a concealed grid is required, but individual tiles must be easily demountable. Ecophon Focus Ds has a concealed grid and syetrical edge

### SERVER ROOM CABINET INSTALLATION CONCEPTS

SERVER ROOM CABINET INSTALLATION CONCEPTS SERVER ROOM CABINET INSTALLATION CONCEPTS SERVER ROOM CABINET INSTALLATION CONCEPTS ZPAS 169 EXAMPLES OF SERVER ROOMS PROJECTS WITH ZPAS CABINETS Data Box in the

### Ecophon Focus A. System range. Size, mm. XL 2000x600. XL 1800x600. XL 2400x600 T15 T24 Thickness (THK) Inst. Diagr. 1200x600 1200x1200 1600x600

Ecophon Focus A For applications where a robust suspended ceiling system is required. Ecophon Focus A has an exposed grid system. Each tile is easily demountable. The systems consist of Ecophon Focus A

### TFSR & TFSK Roof Fans

Fans Air Handling Units Air Distribution Products Fire Safety Air Conditioning Air Curtains and Heating Products Tunnel Fans TFSR & TFSK Roof Fans With swing-out function 2 I TFSR/TFSK TFSR & TFSK Roof

### --- 1-1. STEREO PANELS

_Stereo acoustic panels and screens for architecture Texaa Stereo are rigid acoustic panels and screens designed to reduce reverberation inside a wide range of spaces. They are available in a multitude

### DSRQ - DSRSQ - DSRSQ-THERM

DSRQ - DSRSQ - DSRSQ-THERM Specification item: Variable geometry diffuser on 597x597 mm panel developed for rooms with high ceilings where a long throw and a high induction ratio are required. Made up

### CEILING SYSTEMS. CI/SfB (35) Xy April 2006. [Between us, ideas become reality.] ULTIMA CANOPY. Data sheet. Acoustic performance meets High Design

CEILING SYSTEMS [Between us, ideas become reality.] CI/SfB (35) Xy April 2006 ULTIMA CANOPY Data sheet Acoustic performance meets High Design ULTIMA CANOPY Installation Instructions I. GENERAL 1. Product

### Organisational Kitchen Fittings Kitchen Cabinet Fittings

Pull-out wire storage basket Finish: Chrome plated Load capacity: 30 kg Installation depth: 400 mm Version: Runners and baskets separated, designed for wardrobe interiors without doors Type of pull out:

87045 LIMOGES Cedex France Telephone: (+33) 05 55 06 87 87 - Fax: (+33) 05 55 06 88 88 Linkeo 19" freestanding cabinets Page 1. General characteristics....1 2. Range....2 3. Technical characteristics...3

### SOHOline and SOHO Slimline The SOHOline and SOHO Slimline offer a modular, sturdy and compact design

SOHOline and SOHO Slimline The SOHOline and SOHO Slimline offer a modular, sturdy and compact design Ideal installation for; Offices Branch Offices Schools Computer Aided Classes Government Offices Hotels

### Pendant Light Fitting IEC Series 6470

> Available light sources highpressure sodium lamps (HSE) metal halide lamps (HIE) mercury lamps (HME) blended lamps (LME) halogen lamps (QT) > Versatile mounting methods > Enclosure made of saltwaterresistant

### Mirage over door heater. Features: Electric and LPHW versions. Compact and Versatile. Suitable for mounting up to 3.0m high from finished floor level.

Features: Electric and LPHW versions. Compact and Versatile Suitable for mounting up to 3.0m high from finished floor level. Recessed or surface mounted. Energy saving controls option available. Available

### EX C E L L E N C E ISO 9001 CERTIFIED COMPANY SAND TRAP LOUVERS.

25 YEARS OF EX C E L L E N C E 13.0 13.0 index INDEX SECTION TOPIC PAGE 13.1 Sand Trap Louver with Bird screen ASTL 3 13.2 Sand Trap Louver with Filter ASTL+F 4 13.3 Sand Trap Louver with Damper ASTL+D

### SERIES L. Fineline & Broadline. Linear Strip Grilles GRILLES 12

Fineline & Broadline PUBLICATION Strip GRILLES JUNE 0 Features - Fineline or Broadline Appearances. - 6 Different Frame Options. - 0, or 0 Angles. - Single Units or Continuous Runs. - Multiple Fixing Options.

### Low and High Static Pressure Fan Coil Units. VH2N 03 to 27. Technical Brochure. TM VH2N-A.1GB Date : June 2006 Supersedes : None

Low and High Static Pressure Fan Coil Units VH2N 03 to 27 Technical Brochure TM VH2N-A.1GB Date : June 2006 Supersedes : None Design Features Presentation The VH2N fan coil units has been specially designed

### Knürr Smaract. Knürr Smaract. CompactRack

CompactRack Features Ample space for components and cabling provided in an efficient, compact design. The innovative frame concept with triangular extrusions ensures low weight while maintaining high stability.

### 64 Push-to-Close Latch

244 64 Push-to-Close Latch Pull-to-open Paddle latch Miniature Plastic slide 11 (.42) Stainless steel, passivated and brushed finish and glass-filled reinforced nylon, black working load: 90 N (20 lbf)

LightBaffle AcousticBaffle Spectral Blade Silent light. LED The acoustic BLADE range from Spectral combines a highly efficient LED luminaire, called LightBaffle, with a vertical acoustic panel system manufactured

### K17.11 DOOR BOLTS K17 DOORS 01.09.2013

K17 DOORS K17.11 01.09.2013 Waregemstraat 5-9870 Zulte - Belgium - T. +32 9 388 88 81 - F. +32 9 388 88 21 - commercial@sobinco.com - www.sobinco.com CONTENTS 1. Locking set series 86000...K17.11.03 2.

### Sliding and Folding Door Fittings Sliding Door Accessories

Sliding door lock Toplock For 1- and 2-leaf sliding doors Suitable for toughened safty glass and laminated sheet glass Suitable for DIN left and DIN right Max. weight per door leaf 120 kg For glass thickness:

### Plaster In Grilles 1/1.5/B/1. AHP Plaster-in Linear Bar Grille ADMP Plaster-in Linear Diffuser ALSP Plaster-in Linear Slot Diffuser

1/1.5/B/1 Plaster In Grilles AHP Plaster-in Linear Bar Grille ADMP Plaster-in Linear Diffuser ALSP Plaster-in Linear Slot Diffuser TROX UK Ltd Caxton Way Thetford Norfolk IP24 3SQ Telephone +44 (0) 1842

### AMF Line; wall absorbers Wall mounted acoustic designs PERFORMANCE CEILINGS. M ore s c op e f or i n n ovat i on MADE IN GERMANY

PERFORMANCE CEILINGS M ore s c op e f or i n n ovat i on AMF Line; wall absorbers Wall mounted acoustic designs MADE IN GERMANY 138568_Prospekt Wandabsorber_GB int.indd 1 Acoustic elements on the wall

### LindabAtriumPlana. Heating and cooling panels. lindab atrium plana. lindab we simplify construction

lindab we simplify construction LindabAtriumPlana Heating and cooling panels 052016 Lindab Ventilation All forms of reproduction without written permission are forbidden is the registered trademark of

### CELO5. User & Installation Manual. www.audac.eu

CELO5 User & Installation Manual www.audac.eu 2 Introduction 5 High-end Slim Ceiling Speaker The CELO5 is the 5 version of AUDAC s CELO High-end Slim ceiling speaker series with an RMS power of 50 Watt

### plenum slot diffusers

light powered Redefine your comfort zone. www.titus-hvac.com dual-function smart logic light powered energy solutions Table of Contents PLENUM SLOT IFFUSERS products Plenum Slot iffusers Products... 4

### PLASTIC VOLUME CONTROL DAMPERS OVERVIEW TYPE: GGB

OVERVIEW TYPE: GGB All composite construction Rigid extruded upvc aerofoil blade section Integral blade seals for low leakage operation Individual blades driven via reinforced styrene gear wheels in maintenance

### Door grilles. Door grilles for various applications. patented technology

Door grilles Door grilles for various applications patented technology Silendo type 461 AK Acoustic door grille for residential use The Renson grille Silendo 461 AK is an acoustically damping door grille

(for adjustable heads) Part. 209 40 ø,5 ø10,5 2 2,5 115 15 42 5 11 37 72 4 70 Code 209 / 0754 MATERIALS: Bracket made out of reinforced polyamide black colour. FEATURES: To be used with heads Part.221,

### 6/S1 SOUND ATTENUATORS PZ, PZC, PZM, PK. v 2.4 (en)

6/S1 v 2.4 (en) SOUND ATTENUATORS PZ, PZC, PZM, PK www.klimaoprema.hr 9 TABLE OF CONTENTS Rectangular attenuators - PZ... 3 Round sound attenuators - PZC... 16 Interspace sound attenuator - PZM... 18 Definition

### TECHNICAL MANUAL PIPECLAMP JULY 2013 ROHRVERBINDER ONLINESHOP.DE

TECHNICAL MANUAL PIPECLAMP JULY 2013 ROHRVERBINDER ONLINESHOP.DE Selecting a Fitting fittings are a blackheart malleable casting and are manufactured to BS EN 1562 1997 for the strength requirements. fittings

### RADIANT PANELS TRENCH PERIMETER GRILLES ELEMENTS

RADIANT PANELS TRENCH PERIMETER GRILLES ELEMENTS PIPER FARM, BROMLEY GREEN ROAD, ASHFORD, KENT. TN26 2EF TEL: 01233 733308 FAX: 01233 733883 E-MAIL: sales@feukltd.com RADIANT PANEL RANGE Solutions... brought

HEAT RECOVERY UNITS CADB and CADT-D / DI / DC Series NEW The CADB, CADT heat recovery range consists of: - Self-supporting casing with extruded aluminium profile structure and beige plastic coated galvanised

### TECNA Partition wall 10 TECNA is universal partition wall. Unique in richness and configuration possibilities, it can be enhanced with natural wood pa

tecna TECNA Partition wall 10 TECNA is universal partition wall. Unique in richness and configuration possibilities, it can be enhanced with natural wood panels and accessory components. Intrinsically

### Weather Resistant Louvres

L---e Weather Resistant Louvres Type WSL Untreated aluminium Contents Application Realisation Safety instructions Contents Application Realisation Safety instructions Dimensions Sizes Installation Accessories

### Halogen infrared heater IH Suitable for exposed outdoor environments with design demands

Halogen infrared heater 3 1000 1500 W Electrical heat 4 models Halogen infrared heater Suitable for exposed outdoor environments with design demands Application Halogen infrared heater is the perfect choice

### Basic Selection & Proper Application of Overhead Air Distribution Devices

Basic Selection & Proper Application of Overhead Air Distribution Devices GRD Selection & Application Terms Selection Throw Sound Installation Variations affect Performance Inlet Effects Basics Return

### CABINET ORGANIZERS. 2 V-WAX catalog 3. Pull-out wire basket 2 layers KITCHEN EQUIPMENT. Pull-out wire basket. Pull-out wire basket

CHAPTER 4 Cabinet organizers... p. 2 Wall hanging units and functional post system... p. 8 Plinths... p. 15 Drawer organizers... p. 18 Countertop supports... p. 22 Waste bins... p. 22 Stainless steel sinks...

### InForm Mobile Units. Selection. Equipment trolley, filing trolley Printer/PC trolley Overhead/demo trolley

Selection Equipment trolley, filing trolley Printer/PC trolley Overhead/demo trolley Basic mobile unit Basic mobile with vertical profiles Installation options Functional shelf, low Functional shelf, inclinable

### Wing Radiant Heating Wingline Range

Wing Radiant Heating Wingline Range 1 Wings Radiant Heating and Cooling Wingline Wings Radiant Ceiling Panel Wingline The Wingline Panels are lightweight radiant heating panels consisting of two types

### KIRÁLY TRADING KFT H-1151 Budapest Mogyoród útja 12-14 tel: 061307-3801 Email_pzoli@kiralytrading.hu. Clamps Clamping devices

04000 Clamps Clamping devices 23000 22000 21000 20000 09000 08000 07000 06000 05000 04000 03000 02000 01000 297 04010 Adjustable straps Tempered steel 1.1191 Black oxide finish nlm 04010-101 Suitable thrust

### Saferand easierinstallation

EN 85-07 Saferand easierinstallation IföSigninstallationsystem andifösignbuilt-incistern www.ifosanitar.com/sign Aneffectivesolution withmanyadvantages. Ifö Sign installation system makes life a little

### Technical Information

Technical Information This section of the catalogue provides technical information that will help specify, install and maintain Surelock McGill devices and components. The topics are listed below: Blast

### Flue Installation. High Efficiency Condensing Boilers

Flue Installation High Efficiency Condensing Boilers Table of contents INTRODUCTION 1 Instruction guidance...4 1.1 Product documentation...4 1.2 Explanation of symbols...4 1.3 Important Notes...4 INSTALLATION

### 06 / 2003. Optional components. MAXDATA PLATINUM Server-Rack PLATINUM. [Product Guide] www.maxdata.de

D Positioning Key-Features Specifications Optional components MAXDATA PLATINUM Server-Rack PLATINUM [Product Guide] www.maxdata.de Positioning Description Server-Racks with 41U, 37U and 23U Highlights

### Quality alu LED profiles

Quality alu LED LED PROFILES - PRODCUT CATALOGUE 2010 Quality Aluminum LED Manufacturer & Designer NEW RECESSED SLIM LINE 15mm Introduction: It is recessed type of the aluminum LED profile to build into

### ADAPT Parasol EX b Energy-saving, suspended comfort module for Swegon s WISE System for demand-controlled ventilation

Energy-saving, suspended comfort module for Swegon s WISE System for demand-controlled ventilation www.eurovent-certification.com www.certiflash.com Suspended comfort modules for demand-controlled ventilation

### Elztrip EZ 100 SINGLE PANEL RADIANT HEATER FOR HEIGHTS BETWEEN 2.5 AND 4 METRES

Electrical heat 600 1500 W Elztrip EZ 100 SINGLE PANEL RADIANT HEATER FOR HEIGHTS BETWEEN 2.5 AND 4 METRES 3 models Elztrip 00 has a single heating panel and is designed for ceiling heights between 2.5

### Re-board Accessories

Re-board Accessories Plastic Screws Plastic screws specially developed for 16 mm Re-board, but works with most thicknesses. A special version comes with a loop for hanging (only available in transparent

### Knürr Miracel. Knürr Miracel. 19 Network and Server Rack Platform 1.12 to 1.22 1.11

Knürr Miracel 19 Network and Server Rack Platform 1.12 to 1.22 1.11 19" Server Rack: Knürr Miracel Strong points 1.13 Knürr Miracel ASP ASP/Server Rack 1.16 Knürr Miracel Server Rack 1.18 Knürr Miracel

### Flexit S3 R. Air Handling Unit - rotor technology - flexible installation FOR FLATS AND SMALL DETACHED HOUSES

Flexit S3 R Air Handling Unit - rotor technology - flexible installation FOR FLATS AND SMALL DETACHED HOUSES F O R A H E A LT H Y I N D O O R E N V I R O N M E N T Flexit S3 R Air Handling Unit with Rotor

### Technical Concept. Filter Fan Unit COMPACT. Type COMPACT AC Type COMPACT EC

Technical Concept Filter Fan Unit COMPACT Type COMPACT AC Type COMPACT EC Ultra Filter Fan Unit COMPACT Technical Concept Product Description Filter Fan Units (FFUs) from M+W Products are designed to provide

### IT-SOLUTIONS.

IT-SOLUTIONS Well conceived Haewa Group has gained a strong profile as an innovative and competent supplier for the machinery, systems, electrical and electronic industries, well beyond European geographic

### 19" Data Racks. Adjustable feet To compensate for uneven floors and assure great stability all feet can be up to 20 mm adjusted.

19" Data Racks Attractive design and high quality are characteristic. Basic framework is welded from multiple bent metal plate, which assures great rigidity suitable for heavier equipment. All profile

### Lindab's recommendations

Mounting instruction Suspension of ventilation systems Lindab's recommendations Content General Examples of suspension Lower requirements of bearing capacity Suspension without requirements of fire class

### Machine devices, jig devices

Machine devices, jig devices 853 K0697 Rolled thread studs DIN 6379 Material: Tempered steel. KIPP Rolled thread studs DIN 6379 Order No. D L B1 B2 Approx. weight g Surface finish: Thread rolled. Class

### Ateo 4/6. User & Installation Manual.

Ateo 4/6 User & Installation Manual www.audac.eu 2 Introduction 2-Way speaker with Clevermount The ATEO is a series of extraordinary loudspeakers especially designed for fixed install in indoor applications,

### TD-SILENT Series (160 to 1000 models) TD-SILENT Series (1300 and 2000 models) NEW TD-SILENT. In-Line duct fans

IN-LINE MIXED LOW DUT ANS ultra-quiet Series (16 to 1 models) Low profile Mixed-flow fans with sound-absorbent insulation. Extremely quiet. ertified of Approval Noise Abatement Society (TD-35, TD-5, TD-8

### BOQ SPECIFICATIONS. The Blind system consist of a coated aluminium tube of 38 mm diameter with provision of fabric clamping.

BOQ SPECIFICATIONS VERTICAL BLINDS Vertical Blinds made of glass fibre fabrics in width 5 (or 4 ). Minimum overlapping of ¾ in fabric. Top aluminium anodized rail of 1.4 mm thickness. 2 inch wide channel

### sound reduction systems for commercial, educational and industrial environments

sound reduction systems for commercial, educational and industrial environments Tel: +44 ()14 3874 Fax: +44 ()14 38957 E-mail: info@soundreduction.co.uk Web: www.soundreduction.co.uk soundblocker Acoustic

### Zehnder FLATLINE Radiant Cooling and Heating Ceiling Panel

Zehnder FLATLINE Radiant Cooling and Heating Ceiling Panel Company profile: The Zehnder Group is a leading manufacturer in the indoor climate systems market. It began producing radiators in 930, and has

### Vertical Blind Systems

Vertical Blind Systems Tel: 0208 421 6605 sales@blindtrack.co.uk Application Chart Dimensions Operation Applications Profile Features / Options Fitting Options Fitting Surfaces Single Stack Pair Stack

### swimming pool accessories

76 swimming pool accessories 77 Dolphin pool cleaners Dolphin Plus Battery Cordless pool cleaner with lithium ion battery Cleans the pool in 1.5 hours Special programs Clogged filter bag indicator Incl.

### Worth noting. Use. Key figures. Installation. lindab atrium - loggia

Contact, Overview, Index Guideline heating and cooling Plexus Professor / Professor Plus Premum / Premax / Solus Architect Polaris I & S Plafond Podium Celo Cabinett Capella Carat Fasadium Atrium / Loggia

### pinta BALANCE [1/7] Service

[1/7] Flexible and elegant: The pinta BALANCE ceiling cloud combines optimum office acoustics with timeless design and is easy to install and remove. Service Call our telephone hotline for advice on your

### Portman Sliding Door Gear Timber/Frames Doors Frameless Glass Doors

Portman Sliding Door Gear Timber/Frames Doors Frameless Glass Doors Top track Portman top tracks are suitable for door leaves of up to 80kg as standard Material is 6063T6 aluminium alloy anodised to 15

### Halogen infrared heater IH Suitable for exposed outdoor environments with design demands

3 1000 2000 W Electrical heat 6 models Halogen infrared heater IH Suitable for exposed outdoor environments with design demands Application Halogeninfra IH is powerful with a high filament temperature

### IH 17025 E Sigma Island 90

INSTRUCTIONS FOR USE Kitchen extractor hood Type: IH 17025 E Sigma Island 90 Dear Customer!! You are now a user of the newest generation kitchen extractor hood type IH 17025 E Sigma Island 90. This hood

### Filter Fan Unit SILENT. Type SILENT AC Type SILENT EC

Technical Concept Filter Fan Unit SILENT Type SILENT AC Type SILENT EC Filter Fan Unit SILENT Technical Concept Product Description Filter Fan Units (FFUs) from M+W Products are designed to provide clean

### DOOR STOP SERIES. www.shengjiu.com LS531 LS532 ERP LS531F3A100001. Main material: Black PC ERP LS532N00000001. Accessories.

Accessories LS531 DOOR STOP SERIES Electronic Handle Cylinder Main material and finish: Bright chrome plated steel Panel LS5 Main material: Black PC LS531F3A100001 LS5N00000001 TX80 P245 TX0-3 P247 TX100-A

### HERZ-Thermal Actuators

HERZ-Thermal Actuators Data Sheet 7708-7990, Issue 1011 Dimensions in mm 1 7710 00 1 7710 01 1 7711 18 1 7710 80 1 7710 81 1 7711 80 1 7711 81 1 7990 00 1 7980 00 1 7708 11 1 7708 10 1 7708 23 1 7709 01

### lindab duct suspension & support system Duct suspensions & Support systems

lindab duct suspension & support Duct suspensions & Support s lindab duct suspension & support Content Duct suspensions & Support s Duct suspension Duct suspension FB... DRSN... 0 DRSNR... 0 Channels and

### Elztrip EZF Radiant heater for ceiling heights between 4 and 15 metres

Electrical heat 4200 W 1 model Elztrip EZF Radiant heater for ceiling heights between 4 and 15 metres Elztrip EZF42 has an option of two or three heating panels and is intended for ceiling heights between

### IT infrastructure Efficiency-boosting solutions. nextlevel. for data centre

IT infrastructure Efficiency-boosting solutions nextlevel for data centre 2 Rittal IT infrastructure The whole is more than the sum of its parts. The same is true of Rittal The System. With this in mind,

### K17.12 Door closers K17. Doors 01.09.2013

K17 Doors K17.12 01.09.2013 Waregemstraat 5-9870 Zulte - Belgium - T. +32 9 388 88 81 - F. +32 9 388 88 21 - commercial@sobinco.com - www.sobinco.com Contents 1. OPTIC door closer TS40(V) with scissor

### ErP ROOF UNITS - ROOFMASTER STOF SHUTTER FEATURES ELECTRICAL SUPPLY TEMPERATURE RANGE SIZES MATERIAL AND DESIGN PRODUCT CODE - STOF-190-SAC-102-0

151 ROOF UNITS - ROOFMASTER STOF SHUTTER FEATURES 8 sizes Volume flows up to 4.7 m 3 /s Static Pressures up to 950 Pa Both EC- and AC-versions available Low sound level High efficiency Speed controllable

### Optiffuser. High-performance, high bandwidth lightweight 1D diffuser.

Optiffuser High-performance, high bandwidth lightweight 1D diffuser. General product information The Optiffuser comes in packs of four panels. Two positives and two negatives (see page 5) per package.

### FLEXIT S3 X/TT A3 X/TT K3 X/TT S3 R S3 RK

944E-05 006-0 FLEXIT S X/TT A X/TT K X/TT S R S RK Installation Instructions Air Handling Unit/ Kitchen Model S X/TT K X/TT A X/TT S R S RK Air handling unit with cross heat exchangeror TT exchanger Air

### mechanics PP-Profiles Panel Profiles PT-Profiles T-Groove Plates RE-Profiles Rectangular Profiles PU-Profiles Universal Profiles

Overview PP-Profiles Panel Profiles PP 50 PP 100 PP 150 PP 200 PP 0 B 4 PT-Profiles T-Groove Plates B 5 PT PT 50 RE-Profiles Rectangular Profiles B 6 RE 15 RE 30 RE40 RE65 PU-Profiles Universal Profiles

### 2.8. Ex-Recess-mounted, ceiling emergency light fittings in compact metal design

.8 Ex-Recess-mounted, ceiling emergency light fittings in compact metal design RLF/RLF-INOX 50 18-58 W / RLF/RLF-INOX 50... N 18-36 W (Zone 1,, 1, ) The explosion-protected lighting concept for clean rooms

### Airline. small air handlers and extract fan units. VES Airline part of a complete range of innovative, flexible products from the HVAC experts

Lo w p r o f i l e small air handlers and extract fan units Duties to 0.55m 3 /sec Available with the Electroline fitted control panel Ceiling void friendly - unit heights from 190mm to 350mm Airline VES