1 Page 1 of 46 Inspection Report Stockbridge GA Property Address: Stockbridge GA South East Building Consultants Ray Thoroman Atlanta GA
2 Page 2 of Serving Atlanta GA and the Entire South East
3 Page 3 of 46 Table of Contents Cover Page Table of Contents Intro Page 1 General Physical Condition 2 Utilities 3 Structural Frame and Building Envelope 4 Mechanical and Electrical System 5 Interior Elements (Tenants) 6 Additional Considerations General Summary Invoice
4 Page 4 of 46 Date: 2/19/2013 Time: 09:00 AM Report ID: Property: Stockbridge GA Executive Summary: Customer: Stockbridge GA Commercial Strip Mall Real Estate Professional: This is a Property Condition Report "PCR" using the ASTM E2018 as a standard guideline to describe the condition of building or buildings for the property inspected. This process involves observation of the property by a person or entity. It can include interviews of sources, and reviews of available documentation for the purpose of developing an opinion and preparing a PCR of a commercial real estate's current physical condition. At the option of the user, a PCA may include a higher level of inquiry and due diligence than the baseline scope described within this guide or, at the users option, it may include a lower level of inquiry or due diligence than the baseline scope described in this guide. If there are such deviations from this guideã½s scope it should be disclosed here on this page. A PCR is a written report, prepared in accordance with the recommendations contained in this guide, that outlines the consultantã½s observations, opinions as to the subject property"s condition, and opinions of probable costs to remedy any material physical deficiencies observed. In defining good commercial and customary practice for conducting a baseline PCA, the goal is to identify and communicate physical deficiencies to a user. The term physical deficiencies means the presence of conspicuous defects or material deferred maintenance of a subject property material systems, components, or equipment as observed during the field observers walk-through survey. This definition specifically excludes deficiencies that may be remedied with routine maintenance, miscellaneous minor repairs, normal operating maintenance, etc., and excludes de minimis conditions that generally do not present material physical deficiencies of the subject property. A walk-through survey, conducted during the field observers site visit of the subject property, that consists of nonintrusive visual observations, survey of readily accessible, easily visible components and systems of the subject property. Concealed physical deficiencies are excluded. It is the intent of this guide that such a survey should not be considered technically exhaustive. It excludes the operation of equipment by the field observer and is to be conducted without the aid of special protective clothing, exploratory probing, removal of materials, testing, or the use of equipment, such as scaffolding, metering/testing equipment, or devices of any kind, etc. It is literally the field observers visual observations while walking through the subject property. The purpose of the PCA is to observe and report, to the extent feasible pursuant to the processes prescribed herein, on the physical condition of the subject property. Deviations from the Guide: Please refer to our signed agreement detailing the scope of this inspection and PCR. Recommendations: It is recommended that the user of this report review both summaries and the entire report. The complete report may include additional information of concern. This property and subsequent building (s) has been inspected by Ray Thoroman, South East Building Consultants. Comment Key and Definitions: The following definitions of comment descriptions represent this inspection report. All comments by the inspector should be considered before purchasing this home. Any recommendations by the inspector to repair, replace, or require immediate attention suggests a second opinion or further inspection by a qualified
5 Page 5 of 46 contractor. All costs associated with further inspection fees and repair or replacement of item, component or unit should be considered before you purchase the property. Inspected: This term means I visually observed the item, component or unit and if no other comments were made then it appeared to be functioning as intended allowing normal wear and tear. The notation does not mean that the item is perfect but does meet a reasonable standard on the day of inspection. : The item, component or unit is not functioning as intended or needs further inspection by a qualified contractor. Items, components or units that can be repaired to satisfactory condition may not need replacement. Requires Immediate Attention: The item, component or unit needs immediate attention by a qualified professional or contractor for the safety or health of the occupants of the building. Could cause further major deterioration, or complete failure of a system or component. Worsen appreciably, cause damage, or be a serious hazard. Not Inspected: I did inspect this item, component or unit and made no representations of whether or not it was functioning as intended and will state a reason for not testing or operating Building Use: Retail Construction Type: Masonary Number of floors/stories: 1- Story Approximate building size: square feet Age Of building: Approximately 5 years old Apparent occupancy status: 90% Client Is Present: No, Robert with Property Management was present Weather: Mostly sunny Temperature: Over 80 during inspection
6 Page 6 of General Physical Condition Items A. Basic Information Inspected Hello John, Thank you for allowing me to inspect your future building. During the time you own the building you may call me anytime for information about anything in this report, or anything else you need to know or understand. This Inspection Report will be uploaded to my web server for 2 years after I it to you, the report can be forwarded to anyone by simply forwarding the sent to view the report.if you have any questions please do not hesitate in calling or with any further help regarding the inspection. Thank You, Ray Thoroman South East Building Consultants B. Purpose and Scope Inspected You have contracted with us to through verbal communication and (s) to perform an inspection in accordance with ASTM industry standards for the commercial inspection profession. This is different from our technically exhaustive inspection which takes several days to complete, involves the use of specialized instruments, the dismantling of equipment, video scanning, destructive testing and laboratory analysis of possible contaminates. Our purpose is to identify defects or adverse conditions that need repair or replacement, are safety concerns or may lead to costs that would significantly affect your evaluation of the property at the time of this inspection. The purpose of the Inspection is to document in a narrative format the condition of the building at the time of the inspection. The inspection is a visual snapshot in time regarding the condition of the systems and components of the building at the time of the inspection and is not a warranty nor an insurance policy, but that should not deter you purchasing such a policy. The building has deferred maintenance, as with all building systems, components, items, etc; need to be maintained properly though the years. We do not document items which are cosmetic in nature or would be apparent to the average person or document items that pertain to an building of this age weather stripping on doors, rust staining, loose door knobs or items of that nature. Pictures are placed in the report as a courtesy to help you understand the reason for the narrative. There is an summary at the end of this report which you could use as a check-list if needed. Please read the entire report C. Topography Inspected The grounds are generally level to small slope around the building with positive drainage away from the structure. D. Paving, Curbing and Parking (1) Parking lot had one area rear left of building in front of dump that had some settlement occurring and cracking at concrete & asphalt. Recommend repairing to prevent further significant damage.
7 Page 7 of 46 D. Item 1(Picture) General parking lot views D. Item 2(Picture) General parking lot views D. Item 3(Picture) General parking lot views D. Item 4(Picture) Settlement and cracking
8 Page 8 of 46 D. Item 5(Picture) D. Item 6(Picture) D. Item 7(Picture) (2) One parking space barrier in front of 113-G was loose/damaged. Recommend repair. D. Item 8(Picture) E. Flatwork (sidewalks, plazas, patios) Inspected All sidewalks and patios appeared in good condition. No significant issues noted.
9 Page 9 of 46 E. Item 1(Picture) E. Item 2(Picture) E. Item 3(Picture) F. Landscaping, Appurtenances and Retaining walls Block paver retaining wall left side rear of building had evidence of erosion and soot travel occurring at uncovered ground. Recommend installing proper ground cover and drainage to prevent further issues. Also there was evidence of settlement at ground in front of retaining wall behind trash bin and small leaning at the retaining wall. I again, recommend installing proper ground cover and proper drainage to prevent further issues. Recommend evaluate the retaining wall to ensure reinforcement or repairs are not necessary at this time by retaining wall and landscape contractors.
10 Page 10 of 46 F. Item 1(Picture) F. Item 2(Picture) F. Item 3(Picture) F. Item 4(Picture) G. DECKS, BALCONIES, STOOPS, STEPS, AREAWAYS, PORCHES AND APPLICABLE RAILINGS Front right patio metal railing was rusting. Recommend sealant coat to prevent further damage. G. Item 1(Picture) Add sealant coat G. Item 2(Picture) Add sealant coat
11 Page 11 of 46 H. Signage and exterior lighting (1) Road signage was in good condition for age. Exterior lighting was in good condition. H. Item 1(Picture) (2) There was one stop or yield sign pole damaged at rear right of parking lot. One light pole right front corner was leaning/damaged. Front main signage had loose electrical J-box. Recommend repair issues to prevent further damage or injury.
12 Page 12 of 46 H. Item 2(Picture) H. Item 3(Picture) H. Item 4(Picture) Loose electric J-box I. Suite Numbers Inspected 10 units total for this building. One unit labeled 105-C was vacant. Doors were locked (Robert did not have access) to units 105-C, 111-F (Liberty Tax) and rear Riser Room. I was not able to access or visually inspect these units/areas.
13 Page 13 of 46 I. Item 1(Picture) Could not access I. Item 2(Picture) I. Item 3(Picture) I. Item 4(Picture) I. Item 5(Picture) I. Item 6(Picture) Could not access
14 Page 14 of 46 I. Item 7(Picture) I. Item 8(Picture) I. Item 9(Picture) Could not access I. Item 10(Picture) I. Item 11(Picture) I. Item 12(Picture) Styles & Materials General Topography: Flat and Sloped Access and Egress: Paved Driveway Paving Curbing Parking: Asphalt Parking Lot
15 Page 15 of Utilities Items A. Water Inspected The water source is the public utility company. B. Electricity Inspected The source for electricity is the public utility company. C. Natural gas Inspected The fuel source is natural gas and is supplied by the public utility company. C. Item 1(Picture) C. Item 2(Picture) D. Sanitary Sewer Inspected Sanitary waste discharges into the municipal sewer at the street. Styles & Materials Water Source: Public Utility Sanitary Sewer: Public sewer system Electric source: Power company Public Utility Gas supply: Natural Gas Out of Scope Issues: Utilities: Operating conditions of any systems or accessing manholes or utility pits.
16 Page 16 of Structural Frame and Building Envelope Items A. Foundation Inspected Building foundation appeared visually in good condition at time of inspection. B. Building Frame Masonry block at rear left of building had cracking/failing expansion joint sealant. Recommend repair areas to prevent further damage. B. Item 1(Picture) B. Item 2(Picture) C. B. Item 3(Picture)
17 Page 17 of 46 Sidewall System (exterior wall cladding and components) Stucco cladding in area of unit 113-G had crack/damage. Recommend repair area to prevent further damage. C. Item 1(Picture) D. Fenestration System (i.e. windows, openings, doors etc.) Inspected E. Parapets (protective wall barriers at balcony, roof etc.) Not Inspected Roof parapet wall flashing cap sealant and screws were loose or failing/cracked. Recommend repair areas for preventative maintenance and present leaking.
18 Page 18 of 46 E. Item 1(Picture) E. Item 2(Picture) E. Item 3(Picture) E. Item 4(Picture)
19 Page 19 of 46 E. Item 5(Picture) E. Item 6(Picture) E. Item 7(Picture) E. Item 8(Picture) F. Roofing Inspected (1) Roof covering consisted of what appears to be TPO type. Covering overall appeared in good normal condition for its age at this time.
20 Page 20 of 46 F. Item 1(Picture) F. Item 2(Picture) F. Item 3(Picture) F. Item 4(Picture) (2) Evidence of standing water near rear roof edge. Standing water is caused from condensation run-off for HVAC units. Recommend running condensation piping into the gutters to prevent this issue. Recommend evaluate roof by roof contractor to see if repairs are needed to prevent standing water.
21 Page 21 of 46 F. Item 5(Picture) F. Item 6(Picture) F. Item 7(Picture) G. Gutters and downspouts Inspected Styles & Materials Foundation: Masonry Roof Structure: Steel trusses Ventilation: None found Siding Style: Cement stucco Masonry Block Viewed roof covering from: Ground Ladder Walked roof Building Type: Masonry Block Method used to observe attic: No attic access Exterior Entry Doors: Insulated glass Siding Material: Masonry Roof-Type: Flat Attic Insulation: None Window Types: Thermal/Insulated Roof Covering: TPO
22 Page 22 of Mechanical and Electrical System Items A. Plumbing water supply and Distribution and Fixtures (1) Unit 115H had toilet that ran continuously. Recommend repair to prevent further damage or energy waste. A. Item 1(Picture) (2) Unit 113G had water pipe used for water heater that was not properly installed. This could cause leaking or damage. Recommend install proper piping by qualified plumber. A. Item 2(Picture) B. Plumbing Drain, Waste and Vent Systems (1) Unit 109C (Firehouse subs) had kitchen utility sink drain pipe leak. Recommend repair by qualified plumber.
23 Page 23 of 46 B. Item 2(Picture) B. Item 1(Picture) (2) Unit 103B had loose sink mount at rear bathroom. Recommend repair to prevent damage or injury. B. Item 3(Picture) B. Item 4(Picture) C. Domestic hot water production Inspected All water heating devices and tanks were functional at time of inspection for the units.
24 Page 24 of 46 C. Item 1(Picture) C. Item 2(Picture) C. Item 3(Picture) D. Heating and AC Equipment (1) There were total 11 roof HVAC package units installed. All were approximately 5 years old. No major visible issues were noted at time of inspection and all units were functional. If units have not had service by licensed HVAC contractor in past 12 months, I recommend service/cleaning.
25 Page 25 of 46 D. Item 1(Picture) D. Item 2(Picture) D. Item 3(Picture) D. Item 4(Picture) D. Item 5(Picture) D. Item 6(Picture)
26 Page 26 of 46 D. Item 7(Picture) D. Item 8(Picture) D. Item 9(Picture) D. Item 10(Picture) D. Item 11(Picture) (2) A few of the HVAC coil fins were damaged. One at far left corner had what appears to be hail damage. This sometimes can effect the performance of the unit, therefore recommend evaluate by licensed HVAC contractor.
27 Page 27 of 46 D. Item 12(Picture) Evidence of hail damage D. Item 13(Picture) Common damage (3) Condensation piping for all 11 units at roof discharged directly next to units on roof. Recommend installing piping and extending so that it drains direct into the gutter system. D. Item 14(Picture) D. Item 15(Picture) E. Heating & Air conditioning - Ventilation Equipment There was evidence of condensation leaking/drips at HVAC duct pipes at most units (with HVAC units installed). Evidence of condensation stains at drop ceiling tiles. I recommend having the individual units have HVAC contractors service/repair duct piping to prevent further leakage or stains.
28 Page 28 of 46 E. Item 1(Picture) E. Item 2(Picture) E. Item 3(Picture) E. Item 4(Picture)
29 Page 29 of 46 E. Item 5(Picture) E. Item 6(Picture) E. Item 7(Picture) F. Electric Service and Meter Inspected, (1) Main electrical service system consisted of three 400 amp service and eight 200 amp services. All were 3 phase 4 wire 208/120v systems. Each unit had its own main electrical service panel. There was one HP (house panel) located near unit 101A that operated the ground electrical such as irrigation, sign lighting or exterior lighting.
30 Page 30 of 46 F. Item 1(Picture) F. Item 2(Picture) F. Item 3(Picture) F. Item 4(Picture)
31 Page 31 of 46 F. Item 5(Picture) F. Item 6(Picture) F. Item 7(Picture) F. Item 8(Picture)
32 Page 32 of 46 F. Item 9(Picture) F. Item 10(Picture) F. Item 11(Picture) F. Item 12(Picture) (2) Unit 119J electric service main panel had bottom breaker knock-out missing. Recommend install cap.
33 Page 33 of 46 F. Item 13(Picture) G. Electric Distribution Unit 115H had rear damaged or disconnected ceiling light fixture. Recommend repair as needed. G. Item 1(Picture) H. Exhaust, Vents (1) Bathroom exhaust vent fan for unit 107D appears to be causing moisture damage. Evidence of water stains and small mold growth at ceiling tiles. Recommend repair exhaust vent/fan. Recommend remove mold tile.
34 Page 34 of 46 H. Item 1(Picture) H. Item 2(Picture) (2) Restaurant exhaust vent had grease discharge on roof covering. Recommend clean exhaust and roof to prevent damage. H. Item 3(Picture)
35 Page 35 of 46 Styles & Materials Plumbing Water Supply (into building): Not visible Water Heater Power Source: Electric Gas (quick recovery) Number of Heat Systems (excluding wood): Eleven total Ductwork: Insulated and Non-insulated Central Air Manufacturer: LENNOX TRANE Units individually metered (Electrical): Yes Plumbing Water Distribution (inside building): Copper CPVC Water Heater Capacity: Three units Energy Source for Heat: Natural gas Cooling Equipment Type: Air conditioner unit Number of AC Only Units: Eleven units Panel Type: Circuit breakers Plumbing Waste: PVC Heat Type: Forced Air Heat System Brand: LENNOX TRANE Cooling Equipment Energy Source: Electricity Electrical Service Conductors: Below ground Aluminum 3 Phase 208 Volts Out of Scope Issues: Plumbing: Determining adequate pressure and flow rate, fixture-unit values and counts, verifying pipe sizes, or verifying the point of discharge for underground systems. Observation of flue connections, interiors of chimneys, flues or boiler stacks, or tenant owned or maintained equipment. Removing of electrical panel and device covers, except if removed by building staff, EMF issues, electrical testing, or operating of any electrical devices, or opining on process related equipment or tenant owned equipment. Examining of cables, sheaves, controllers, motors, inspection tags, or entering elevator/escalator pits or shafts.
36 Page 36 of Interior Elements (Tenants) Items A. Ceiling, Walls, Floors (1) Units 113 & 103 had evidence of settlement cracks, multiple tiles. Due to type of cracks and spanning several feet, I recommend evaluate by qualified foundation contractor. Recommend repair/seal cracks to prevent further damage or injury. A. Item 1(Picture) Unit 113 A. Item 2(Picture) Unit 113 A. Item 4(Picture) Unit 103 A. Item 3(Picture) Unit 103
37 Page 37 of 46 A. Item 5(Picture) Unit 103 A. Item 6(Picture) Unit 103 A. Item 7(Picture) Unit 103 (2) There was evidence of moisture stains at ceiling tiles in front service rooms at units 109, 113, 103 and 101. These were likely caused from failing exterior cladding/ or roof sealant issues. Recommend evaluate by qualified contractor and repair as needed.
38 Page 38 of 46 A. Item 8(Picture) Unit 109 A. Item 9(Picture) Unit 103 (3) Unit 101 had evidence of moisture stains and water damage at interior wall. Tenant stated this was caused from his personal equipment which is no longer used and a small roof leak back in No current moisture noted. Recommend repair stains as needed or desired. A. Item 10(Picture) A. Item 11(Picture) A. Item 12(Picture)
39 Page 39 of 46 (4) Unit 101 had evidence of water stains at ceiling tiles under the main water supply pipe. No current leaking noted, however recommend evaluate by qualified plumber and repair as needed. A. Item 13(Picture) A. Item 14(Picture) Styles & Materials Ceiling Materials: Suspended ceiling panels Ceiling Tile Wall Material: Sheetrock Paneling Wood Floor Covering(s): Carpet Laminated T&G Tile
40 Page 40 of Additional Considerations Additional Considerations: There may be additional or conditions at a property that users may wish to assess in connection with commercial real estate that are outside the scope of this guide (Out of Scope considerations). Outside Standard Practices. Whether or not a user elects to inquire into non-scope considerations in connection with this guide or any other PCA is not required for compliance by this guide. Other standards or protocols for assessment of conditions associated with nonscope conditions may have been developed by governmental entities, professional organizations, or other private entities. Additional Issues: Following are several non-scope considerations that users may want to assess in connection with E 2018 commercial real estate. No implication is intended as to the relative importance of inquiry into such non-scope considerations, and this list of non-scope considerations is not intended to be all-inclusive: Seismic Considerations, Design Consideration for Natural Disasters (Hurricanes, Tornadoes, High Winds, Floods, Snow, etc.), Insect/Rodent Infestation, Environmental Considerations, ADA Requirements, FFHA Requirements, Indoor Air Quality, and Property Security Systems. Items A. Document Review and Interviews Inspected No documents were provided from review. Only interview was with Robert the property manager. Robert knew little about the building as his company just started to manage the building. B. Out of Scope Considerations Inspected Activity Exclusions The activities listed below generally are excluded from or otherwise represent limitations to the scope of a PCA prepared in accordance with this guide. These should not be construed as all-inclusive or imply that any exclusion not specifically identified is a PCA requirement under this guide. Removing or relocating materials, furniture, storage containers, personal effects, debris material or finishes; conducting exploratory probing or testing; dismantling or operation. This should include material life-safety/building code violations. ing of equipment or appliances; or disturbing personal items or property, that obstructs access or visibility. Preparing engineering calculations (civil, structural, mechanical, electrical, etc.) to determine any system s, component s, or equipment s adequacy or compliance with any specific or commonly accepted design requirements or building codes, or preparing designs or specifications to remedy any physical deficiency. Taking measurements or quantities to establish or confirm any information or representations provided by the owner or user, such as size and dimensions of the subject property or subject building; any legal encumbrances, such as easements; dwelling unit count and mix; building property line setbacks or elevations; number and size of parking spaces; etc. Reporting on the presence or absence of pests such as wood damaging organisms, rodents, or insects unless evidence of such presence is readily apparent during the course of the field observer s walk-through survey or such information is provided to the consultant by the owner, user, property manager, etc. The consultant is not required to provide a suggested remedy for treatment or remediation, determine the extent of infestation, nor provide opinions of probable costs for treatment or remediation of any deterioration that may have resulted. Reporting on the condition of subterranean conditions, such as underground utilities, separate sewage disposal systems, wells; systems that are either considered process related or peculiar to a specific tenancy or use; wastewater treatment plants; or items or systems that are not permanently installed. Entering or accessing any area of the premises deemed to pose a threat of dangerous or adverse conditions with respect to the field observer or to perform any procedure, that may damage or impair the physical integrity of the property, any system, or component. Providing an opinion on the condition of any system or component, that is shutdown, or whose operation by the field observer may increase significantly the registered electrical demand-load; however, the consultant is to provide an opinion of its physical condition to the extent reasonably possible considering its age, obvious condition, manufacturer, etc. Evaluating acoustical or insulating characteristics of systems or components. Providing an opinion on matters regarding security of the subject property and protection of its occupants or users from unauthorized access. Operating or
41 Page 41 of 46 witnessing the operation of lighting or other systems typically controlled by time clocks or that are normally operated by the building s operation staff or service companies. Providing an environmental assessment or opinion on the presence of any environmental issues such as asbestos, hazardous wastes, toxic materials, the location and presence of designated wetlands, IAQ, etc. Warranty, Guarantee, and Code Compliance Exclusions: By conducting a PCA and preparing a PCR, the consultant merely is providing an opinion and does not warrant or guarantee the present or future condition of the subject property, nor may the PCA be construed as either a warranty or guarantee of any of the following: Any system s or component s physical condition or use, nor is a PCA to be construed as substituting for any system s or equipment s warranty transfer inspection; Compliance with any federal, state, or local statute, ordinance, rule or regulation including, but not limited to, building codes, safety codes, environmental regulations, health codes or zoning ordinances or compliance with trade/design standards or the standards developed by the insurance industry; however, should there be any conspicuous material present violations observed or reported based upon actual knowledge of the field observer or the PCR reviewer, they should be identified in the PCR; Compliance of any material, equipment, or system with any certification or actuation rate program, vendor s or manufacturer s warranty provisions, or provisions established by any standards that are related to insurance industry acceptance/approval, such as FM, State Board of Fire Underwriters, etc. Additional/General Considerations: Further Inquiry: There may be physical condition issues or certain physical improvements at the subject property that the parties may wish to assess in connection with a commercial real estate transaction that are outside the scope of this guide. Such issues are referred to as non-scope considerations and if included in the PCR, should be identified. Out of Scope Considerations: Whether or not a user elects to inquire into non-scope considerations in connection with this guide is a decision to be made by the user. No assessment of such non-scope considerations is required for a PCA to be conducted in compliance with this guide. Other Standards: There may be standards or protocols for the discovery or assessment of physical deficiencies associated with non-scope considerations developed by government entities, professional organizations, or private entities, or a combination thereof. Additional Issues: No implication is intended as to the relative importance of inquiry into such nonscope considerations,and this list of non-scope considerations is not intended to be all-inclusive: Seismic Considerations, Design Consideration for Natural Disasters (Hurricanes, Tornadoes, High Winds, Floods, Snow, etc.), Insect/Rodent Infestation, Environmental Considerations, ADA Requirements, FFHA Requirements, Indoor Air Quality, and Property Security Systems. C. Exhibits (See attached, if any) Not Inspected There are no attachments to be viewed. D. Opinions of probable costs to remedy physical deficiencies Not Inspected Not provided. Please refer to the inspection proposal. Uncertainty Not Eliminated No PCA can wholly eliminate the uncertainty regarding the presence of physical deficiencies and the performance of a subject property s building systems. Preparation of a PCR in accordance with this guide is intended to reduce, but not eliminate, the uncertainty regarding the potential for component or system failure and to reduce the potential that such component or system may not be initially observed. This guide also recognizes the inherent subjective nature of a consultant s opinions as to such issues as workmanship, quality of original installation, and estimating the RUL of any given component or system. The guide recognizes a consultant s suggested remedy may be determined under time constraints, formed without the aid of engineering calculations, testing, exploratory probing, the removal of materials, or design. Furthermore, there may be other alternate or more appropriate schemes or methods to remedy the physical deficiency. The consultant s opinions generally are formed without detailed knowledge from those familiar with the component s or system s performance. Not Technically Exhaustive Appropriate due diligence according to this guide is not to be construed as technically exhaustive. There is a point at which the cost of information obtained or the time required to conduct the PCA and prepare the PCR may outweigh the usefulness of the information and, in fact, may be a material detriment to the orderly and timely completion of a commercial real estate transaction. It is the intent of this guide to attempt to identify a balance between limiting the costs and time demands inherent in performing a PCA and reducing the uncertainty about unknown physical deficiencies resulting from completing additional inquiry.
Page 1 of 43 Inspection Report Restaurant Property Address: 19 Indian Trail Lilburn Rd Norcross GA South East Building Consultants Ray Thoroman Atlanta GA Page 2 of 43 678-410-3005 Serving Atlanta GA and
Page 1 of 25 Inspection Report Atlanta Strip Mall Property Address: Smyrna GA 30082 Page 2 of 25 South East Building Consultants Ray Thoroman Serving the entire State of Georgia 6 678-410-3005 Page 3 of
Page 1 of 53 Inspection Report Jacksonville Property Address: Jacksonville FL 32204 South East Building Consultants Ray Thoroman Inspecting Jacksonville FL and entire South East Page 2 of 53 Table of Contents
Vision Home Inspection 324 Rams Run Shepherdsville KY 40165-7877 Inspector: James McFadden Property Inspection Report Client(s): Property address: Inspection date: View report summary This report is the
www.citiesinspection.com October 5, 2015 Dear Client, On 9/14/2015, Cities Inspection Service, Inc. completed a building inspection of the property located at 123 Oak Street, Someplace, Minnesota for you.
South Carolina Home Inspector Standards of Practice The following Standards provide guidelines for the Residential Home Inspector and outline what the Residential Home Inspector should observe, identify,
6/ /07 The Inspection of the property listed above must be performed in compliance with the rules of TREC. The inspection is of conditions which are present and visible at the time of the inspection, and
Page 1 of 58 Inspection Report Prepared For: Atlanta Commercial Customer Property Address: Building 5 Marietta, GA 30066 Superior Home Inspections Ray Thoroman 8070 Ivy Shaw Dr. Gainesville,GA 30506 678-410-3005
(850) 297-1998 1716 Monticello Dr Tallahassee, Florida 32303 PROPERTY INSPECTION REPORT THIS INSPECTION IS A DETAILED LISTING OF AREAS VISUALLY INSPECTED AT:, Tallahassee FL Client Tallahassee, FL 32304
CLIENT Inspection Report 271 Front St. Alert Bay, B.C. Island Building Inspections 2013 V ANCOUVER I SLAND B. C. Elevation Photos For the Property at 271 Front Street Alert Bay, BC ELEVATION PICTURES Front
Page 1 of 35 Inspection Report Mr. Happy Property Address: Joseph Poelsterl 450.010220 6334 W. Grace st Chicago Illinois 60634 1-773-454-6700 Page 2 of 35 Table of Contents Cover Page Table of Contents
APPENDIX 9 AFFORDABLE HOUSING PROGRAM INSPECTION CHECKLIST Participating Jurisdiction: Homeowner Name: Assisted Property Address: Date of Physical Inspection of Property: Total Square Footage of Property:
Crawford Inspection Services C.C.B. # 76914 www.crawfordinspections.com Portland Area PO Box 665 West Linn, OR 97068 Ph: (503) 650-6957 Salem Area 5434 River Rd. N; #192 Keizer, OR 97303 Ph: (503) 362-5809
SC Standards of Practice SOUTH CAROLINA RESIDENTIAL BUILDERS COMMISSION HOME INSPECTOR STANDARDS OF PRACTICE Adopted by the Residential Builders Commission May 13, 1998 PURPOSE: The purpose of a residential
Page 1 of 37 Inspection Report Prepared For: Sampath Sample Property Address: Alpharetta, GA 30004 Atlanta Home Inspections Matthew A Thoroman 6625 Hwy. 53 E. Ste. 410-151 Dawsonville Ga 30534 (678)-410-8062
STATE OF SOUTH CAROLINA RESIDENTIAL PROPERTY CONDITION DISCLOSURE STATEMENT The South Carolina Code of Laws (Title 27, Chapter 50, Article 1) requires that an owner of residential real property (single
Inspecton Report Provided by: National Home Inspections Inspector: Bob Smith 456 S Main Denver, CO 46312 (645) 423-3242 firstname.lastname@example.org www.nationalhomeservices.com Property Address: 873
Cover Page Vari Inspection Services Property Inspection Report Inspection prepared for: Sample Real Estate Agent: None - Date of Inspection: 5/13/2015 Inspector: Tony Vari License # HI8047 23110 STRD 54
Due Diligence Report New York, New York Prepared for Mr. On February 8, 2010 P a g e 1 Table of Contents PAGE 3.. GENERAL INFORMATION PAGE 4 FILINGS PERMITS AND ENCUMBRANCES PAGE 6. CORE AND SHELL PAGE
South Carolina Home Inspector Standards of Practice The following Standards provide guidelines for the Residential Home Inspector and outline what the Residential Home Inspector should observe, identify,
A.C.E. Home Inspection Service www.acehomeweb.com St. Peters, MO 63376 (636) 978-9111 Inspector Name: Tim Knight, ASHI Member 202490 Inspection No: 12121212 Inspection Date: 1/1/2012 Client: Address: John
CHRIS CURLES and ASSOCIATES INSPECTION SERVICES Inc. Chris Curles, President www.homeinspectionsatlanta.com email@example.com Office: 770-493-0227 Professional Member Of: GAHI # 93006 ASHI # 211725
Page 1 of 14 Inspection Report Mr. John Homebuyer Property Address: 123 Main Street Houston TX 77007 Front View EDP Consulting Engineers, PLLC Gerald C. Reece, PE TREC #7825 14119 Willowsong Ct Missouri
Report for Dick and Jane Homeowner 1234 Lovers Lane, Houston, Texas 77000 March 17, 2004 I NI NP R Inspection Item I. STRUCTURAL SYSTEMS o o o A. Foundations (If all crawl space areas are not inspected,
Inspection Report Property Address: St. Marks Ave. Brooklyn NY 11213 Five Borough Home Inspection, LLC Derek Lomer NYS Licence Lic # 16000051234 790 Washington Ave., Unit 112 Brooklyn, NY, 11238 917-494-8474
To be used as a first home visit for note taking. Visit www.homeinspectiondirect.com for more tips and information about buying a home and hiring a home inspector. This form in no way replaces a professional
PROPERTY INSPECTION PROFESSIONALS May 5, 2010 Client Client Address Re: Inspection Address, Chicago, Illinois Dear Mr. Client, On May 4, 2010, Tomacor completed a property inspection of the above referenced
Total Home Inspection Checklist Use a checklist like this to make sure that you are looking at all parts of the house. Check off those items that are in good condition and make notes about those that are
Accurate Home Inspection of Illinois 815-260-1727 1213 Norley st. Joliet, illinois 60435 firstname.lastname@example.org We Inspect to Protect!!! Property Inspection Report For Steve & Jenny Hynek 210 W.Chicago Ave.,
The Uniform Building Inspection Report Condensed Single Family Residence:, Scottsdale, AZ Condensed Report Version Prepared for: John Doe Inspection Date: 9/19/2005, 1:00:00 AM Report Number: 091805s Inspection
GUARDIAN HOME 26 EAST MADISON AVENUE CRESSKILL, NEW JERSEY 07626 (201) 568 2783 (201) 568 8117 FAX REPORT NUMBER: 2007/01/01/100 PROPERTY LOCATION: 123 Main Street, Cresskill, New Jersey PRESENT OWNERS:
A Residential Owner s Guide to PERMITS CITY OF Elgin PLANNING & NEIGHBORHOOD SERVICES CITY OF Elgin A Residential Owner s Guide Welcome! This booklet has been prepared to provide residential property owners
STATE OF FLORIDA HOME INSPECTION STANDARDS OF PRACTICE: 61-30.801 Standards of Practice, General. (1) Home inspections performed to these Standards of Practice are intended to provide the client with information
A TO Z HOME INSPECTIONS PROFESSIONAL HOME INSPECTION SERVICES FOR HOME BUYERS AND SELLERS Insurance Inspection Report 1234 Main Street Tallahassee, Florida Report Prepared For: Charles Smith Report Prepared
Structure Survey Findings: Visible portions of the following were observed: foundations; structure to walls, columns, floors, roofs, overhang posts, and columns; attached or firmly abutting decks, balconies,
BUILDING DEPARTMENT 8748 W. 82 nd Place - Justice, IL 60458 Phone: (708) 458-2130 Fax: (708) 458-3207 SELF EVALUATION CHECKLIST FOR RESIDENTIAL AND MULTI-FAMILY DWELLING INSPECTIONS The attached checklist
Report# 21009 Page 1 of 24 Home Inspection Report Property Address: 123 Maple Lane, St. Augustine, FL 32092 Prepared For: Mr. Smith Prepared By: EDGE Inspections www.edgeinspections.com PO Box 601055 Jacksonville,
Exterior Visual Health & Safety Issue Allowable Action Site Drainage Exterior grade does not slope 2% within the first 10' Site drainage causing bulk moisture in crawl space or basement Repairs to existing
Edgewood Home Inspections, Inc. 407 W. Smith Valley Rd. #1032 Greenwood, IN 46142 (317) 833-6048 HOME INSPECTION REPORT Indianapolis IN 46000 Inspector's Name: License Number: Scott Kissel HI00800073 TABLE
Walkthrough Inspection Checklist This checklist is to aid during an IAQ Walkthrough of the school. The checklist includes considerations both inside and outside the school building: Instructions: 1. Read
Housing Quality Standards Inspection Checklist To prevent delays, the R.T.A. must be complete and upon submission the unit must be in move in condition or an inspection will not be conducted. A Fair Housing
#1) BEFORE Purchasing Land Here Is A Checklist Of Things You Should Check Zoning laws Deed restrictions on home size, foundation style, roof pitch, etc. Suitability (slope, wetland issues, etc.) Accessibility
PROPERTY INSPECTION OR ASSESSMENT OF DAMAGES ADDRESS: Somewhere, FL CLIENT: GAIA GC ID No: 2015000 DATE: 12/31/2015 INSPECTION OR ASSESSMENT BY: GAIA CONSTRUCTION INC. CGC 1516136 FLORIDA HI-2792 FLORIDA
Division 1 Requirements Design and Construction Quality Campus Master Plans Texas Tech University System Operating and Building Maintenance Project Administration Historically Underutilized Business (HUB)
SM MEDALLION INSPECTIONS helping people make informed decisions Pre-Drywall Inspection Report 5657 Garden Valley Place Milton, Georgia 30024 Prepared for Betsy and Paul Dougherty January12, 2015 Medallion
LIMITED ONE-YEAR WARRANTY SELLER S RESPONSIBILITY Except as covered by a manufacturers limited warranty, the Seller hereby provides a Limited Warranty for the dwelling against defects in the original material
Cover Page Property Inspection Report My street, Anytown GA, 30000 Inspection prepared for: John Doe Inspection Date: 7/18/2011 Time: 5pm Age: 25+ Size: >1500 Weather: Clear This ranch style home is in
HEDDERMAN ENGINEERING, INC. www.heddermanengineering.com Office 281-355-9911, Fax 281-355-9903 email@example.com, 2011 TO: Mr. REF: CONDITION OF PROPERTY SURVEY Dear Mr. : At your request,
UPCS in Pictures The following pictures are not all inclusive nor does it cover every deficiency. The pictures, however are some of the most commonly cited deficiencies on REAC inspections. Erosion The
STATE OF OHIO DEPARTMENT OF COMMERCE 2013 RESIDENTIAL PROPERTY DISCLOSURE FORM Purpose of Disclosure Form: This is a statement of certain conditions and information concerning the property actually known
Four-Point Insurance Inspection Report Date of Inspection: Property address: Property's City, State, Zip Code: Approximate Total Square Feet: Approximate Total Living Area: Actual Year Built: Insured/Applicant
Scope of the Inspection 1111 Sample Dr. home warranty inspection 2/30/2006 Home Warranty Inspection Report 1111 Sample Dr., Detroit, MI 48223 Inspection Date: February 30, 2006 Client: Alfred E. Neumann
CITY OF SEATTLE RENTAL REGISTRATION AND INSPECTION ORDINANCE (RRIO) RRIO Checklist Use of checklist: Property owners will use the RRIO Checklist to confirm that their rental housing properties and units
Cleveland Cuyahoga County Healthy House Project Training Integrating Healthy Housing Considerations into Weatherization Inspections Jim LaRue Joint inspections for housing health hazards Weatherization
COMPREHENSIVE PROPERTY INSPECTIONS Thank you for selecting CPI for your Deficiency Observation. A full home inspection was not performed on this property at the buyers request. This inspection is a limited
Home Inspection Report Report Number: 144 For The Property Located On: 123 Any Street 27587 Prepared For Exclusive Use By: Mr. Sample N/A,,, Report Prepared By: Edward Carapezza; License No.: 3447 Inspector
Los Angeles, CA Project Manual and Specification DIVISION 1 GENERAL CONDITIONS 01 01 10 STATEMENT OF WORK 01 11 00 SUMMARY OF THE WORK 01 14 05 METRO (OWNER) - DIRECTED STOPPAGES 01 20 00 PRICE AND PAYMENT
3.1 SITE 1 Concrete curbs Check for cracks, spalling, growth from joints X 2 Stone curbs Check for cracks, spalling, growth from joints X 3 Concrete walkways Look for uneven surfaces, ponding, growth from
DIVISION 00 - PROCUREMENT AND CONTRACTING REQUIREMENTS NOTICE TO BIDDERS BID FORM INSTRUCTIONS TO BIDDERS CONTRACTOR S BID FOR PUBLIC WORK - FORM 96 MINORITY AND WOMEN S BUSINESS ENTERPRISE PARTICIPATION
Department of Health and Human Services, Division of Public Health Occupational and Environmental Epidemiology Branch 1912 Mail Service Center, Raleigh, North Carolina 27699-1912 BUILDING ASSESSMENT QUESTIONNAIRE
New Jersey Property Inspections LLC NJ State Home Inspector License # 24GI00105100 27 Neshanic Drive, Ringoes NJ 08551 908-642-2112/908-788-0055 PRE-INPECTION AGREEMENT READ THIS DOCUMENT CAREFULLY. IT
Inspection Report Mr. Sample Sample Property Address: 1234 USA Drive Indianapolis IN 12345 1234 USA Drive Morris Home Inspection Group, LLC Cedric Morris HI01200039 Fishers, IN 46037 317-550-6281 Table
Housing Choice Voucher Program H.Q.S. Inspection Checklist 1 2 Housing Authority of the City of Austin Established in 1937 SECTION 8 PROGRAM OWNER'S GUIDE THE HOUSING QUALITY STANDARDS INSPECTION The unit
Inspection Report 95 Old Stage Road East Brunswick NJ Scott Frederick Prepared by: The Inspection Guys www.inspectionguys.com 16 Mt. Bethel Road, Suite 171 Warren, NJ 07059 800-903-0670 Fax: 732-238-7092
DETAILED SCOPE OF WORK FOR THE NETCONG ELEMENTARY SCHOOL The Netcong Board of Education Netcong, Morris County New Jersey Roof Replacement Project Health and Safety Renovation Projects Roof Replacement
Exterior Elevated Elements Inspection Guidelines Planning and Development 1. Guideline Purpose These guidelines are intended to assist practicing professionals in complying with Berkeley Municipal Code
Roof Siding Chimney Doors and Windows Building Maintenance Repair and restoration of interior damage caused by roof leak; repair or replacement of structural supports under the roof decking and sheathing
MINNEAPOLIS TRUTH-IN-SALE OF HOUSING DISCLOSURE REPORT A NOTICE Read Entire Report Carefully This is not a Buyers Inspection! Page of Address Of Evaluated Dwelling: Owner Name: Hm Owner Address: Wk (City,
BOROUGH OF NATIONAL PARK APPLICATION FOR A CERTIFICATE OF OCCUPANCY FOR CHANGE OF OCCUPANCY ADDRESS OF PROPERTY FOR INSPECTION # BLOCK LOT VACANT YES NO CURRENT OWNER NAME ADDRESS TELEPHONE # PROSPECTIVE
PERMIT AUTHORIZATION EL LAGO BUILDING DEPARTMENT PERMIT ISSUANCE PROCEDURES As of February 20, 2013 El Lago ordinances require the issuance of building permits as a method of enforcing code minimums, ensuring
HOMEOWNER S PERMIT GUIDE WHEN IS A PERMIT REQUIRED? Department of Development and Permits 306 Cedar Road, City Hall 2 nd Floor P.O. Box 15225 Chesapeake, VA 23328 Phone: (757) 382-6018 Fax: (757) 382-8448
At Home Inspections Inc. Home Inspection Report 613-267-8979 Inspector's Name Allan Taillefer RHI a member of the Ontario Association of Home Inspectors since 2003. Inspection Number 1505003H Inspection
DATE TIME EAST STROUDSBURG BOROUGH RESIDENTIAL RENTAL INSPECTION CHECK LIST INSPECTOR: LICENSE # ADDRESS: PROPERTY OWNER: SINGLE: DOUBLE: MULTI-UNIT # OF UNITS POINT OF INSPECTION Sanitation IPMC 302.1
THIS FORM APPROVED BY THE LAWRENCE HOME BUILDERS ASSOCIATION [REV. 05/00] WARRANTY ADDENDUM TO RESIDENTIAL CONSTRUCTION SALE CONTRACT [Limited One Year Warranty] SECTION 1 - DEFINITIONS Owner's Name: Street
PLANNING AND COMMUNITY DEVELOPMENT DEPARTMENT Rental Registration and Safety Inspection Program 210 Lottie Street, Bellingham, WA 98225 Telephone: (360) 778-8361 Fax: (360) 778-8302 TTY: (360) 778-8382
NOTICE - Read Entire Report Carefully. This is not a Buyer's Inspection! Current Owner Name: Mpls City Property Atn Cped (p Contact: Mpls City Property Atn Cped (p Business/Relationship: Owner Address:
Infrastructure Facility Condition Summary Weighted Avg Condition Score Facility Components Systems Surveyor/ Date Done Comments G Sitework.9 Site Improvements Parking Pedestrian Paving Site Development
Pa g e 1 o f 1 5 All About Homes, LLC Michelle M. Teague Owner 312-371-7414 Phone 773-508-6209 Fax www.michelleinspects.com firstname.lastname@example.org 1725 W. Granville Ave. Chicago, IL 60660 Printed
Inspection Report Property Address: 1234 Anywhere street Phoenix AZ Veteran Inspection Professionals Mark Mandery 040901 4725 W. Aire Libre Ave Glendale AZ, 85306 480-694-2111 Table of Contents Cover Page...1